DateTime Alarm
has communication mode: S
description: a point representing DPT 265.005: DateTime Alarm
subject: 265.5
subject: 265.005
subject: DateTime Alarm
dpt bit size max: 72
datapoint type major number: 265
is assembled with: type.dpt.field.265.5.i1.Reserved
is assembled with: type.dpt.field.265.5.i2.DateAndTime
is assembled with: type.dpt.field.265.5.i0.BinaryInformation
datapoint type minor number: 5
label: DateTime Alarm
type: NamedIndividual
type: DatapointType

type.dpt.field.230.x.i0
field string schema: raw
field type: A[n]
field index: 0
field size: 64
type: Datapoint Type Field
type: NamedIndividual
description: MBus address

ContrModeSecondary
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: hvacContrMode
interface object type annotation: 399
subject: 106
subject: ContrModeSecondary
subject: 399.106
property identifier annotation: 106
label: ContrModeSecondary

PSUMode
has communication mode: S
datapoint type major number: 20
is assembled with: type.dpt.field.20.8.i0
subject: 20.008
subject: PSUMode
subject: 20.8
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 20.008: PSUMode
label: PSUMode
datapoint type minor number: 8
dpt bit size max: 8

Break = 0
value API: break
value KNX: 0
type: NamedIndividual

Restriction
on property: interface object type
has value: 100

AQRoom
type: Class
subject: AQRoom
subject: 331.51
subject: 51
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air co2concentration room
label: AQRoom
property identifier annotation: 51
interface object type annotation: 331

Invert
has communication mode: S
type: DatapointType
type: NamedIndividual
description: a point representing DPT 1.012: Invert
subject: 1.012
subject: Invert
subject: 1.12
datapoint type major number: 1
dpt bit size max: 1
is assembled with: Invert
datapoint type minor number: 12

DALI Control Gear Diagnostic
has communication mode: S
subject: 237.600
subject: DALI Control Gear Diagnostic
datapoint type major number: 237
comment: a point representing DPT 237.600: DALI Control Gear Diagnostic
is assembled with: type.dpt.field.237.600.i4.BallastFailure
is assembled with: type.dpt.field.237.600.i5.ConvertorError
is assembled with: type.dpt.field.237.600.i6.Reserved
is assembled with: type.dpt.field.237.600.i0.DALIAddress
is assembled with: type.dpt.field.237.600.i3.LampFailure
is assembled with: type.dpt.field.237.600.i2.ReadOrResponse
is assembled with: type.dpt.field.237.600.i1.AddressIndicator
type: NamedIndividual
type: DatapointType
dpt bit size max: 16
datapoint type minor number: 600

Heat/Cool
has communication mode: S
is assembled with: type.dpt.field.1.100.i0
subject: Heat/Cool
subject: 1.100
dpt bit size max: 1
datapoint type minor number: 100
comment: a point representing DPT 1.100: Heat/Cool
type: NamedIndividual
type: DatapointType
datapoint type major number: 1

type.digit.u16 0 20000
range min: 0
type: NamedIndividual
range max: 20000

type.dpt.field.23.102.i0
includes KV pair: type.kvpair.23.102.i0.3
includes KV pair: type.kvpair.23.102.i0.0
includes KV pair: type.kvpair.23.102.i0.2
includes KV pair: type.kvpair.23.102.i0.1
field size: 2
field type: N
type: Datapoint Type Field
type: NamedIndividual
field index: 0

mass flow, 1 kg/h = 83
value API: massFlow,1Kgh
type: NamedIndividual
value KNX: 83

RegionCodeAlpha2 ASCII
has communication mode: S
datapoint type major number: 234
comment: a point representing DPT 234.002: RegionCodeAlpha2 ASCII
type: NamedIndividual
type: DatapointType
label: RegionCodeAlpha2 ASCII
is assembled with: type.dpt.field.234.2.i0.Character2
is assembled with: type.dpt.field.234.2.i1.Character1
dpt bit size max: 16
subject: RegionCodeAlpha2 ASCII
subject: 234.2
subject: 234.002
datapoint type minor number: 2

type.dpt.field.22.103.i2.DewPointStatus
type: NamedIndividual
type: Datapoint Type Field
field size: 1
field name: DewPointStatus
includes KV pair: alarm (RTC locked) = 1
includes KV pair: no alarm = 0
comment: Dew Point Status
field type: B
field index: 2

type.dpt.field.20.105.i0
includes KV pair: Test = 7
includes KV pair: Emergency Cool Mode = 16
includes KV pair: type.kvpair.20.105.i0.15
includes KV pair: type.kvpair.20.105.i0.0
includes KV pair: Free Cool = 10
includes KV pair: type.kvpair.20.105.i0.8
includes KV pair: Heat = 1
includes KV pair: type.kvpair.20.105.i0.20
includes KV pair: type.kvpair.20.105.i0.5
includes KV pair: Night Purge = 4
includes KV pair: type.kvpair.20.105.i0.14
includes KV pair: type.kvpair.20.105.i0.17
includes KV pair: Fan only = 9
includes KV pair: type.kvpair.20.105.i0.12
includes KV pair: type.kvpair.20.105.i0.11
includes KV pair: type.kvpair.20.105.i0.3
includes KV pair: type.kvpair.20.105.i0.2
includes KV pair: type.kvpair.20.105.i0.13
includes KV pair: Off = 6
type: NamedIndividual
type: Datapoint Type Field
field index: 0
comment: HVACContrMode
field type: N
field size: 8

M2
type: Unit
type: NamedIndividual
symbol: m²

type.dpt.field.1.x.i0
description: 1-bit
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field string schema: raw

Breaker/Valve is released = 2
value API: breakerValveIsReleased
type: NamedIndividual
value KNX: 2

type.dpt.field.9.5.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes digit: type.digit.f16 0 670433
field size: 16
field type: F
field resolution: 0.01
unit: M-PER-SEC

type.dpt.field.200.x.i0
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field size: 16
field string schema: raw
comment: 8-Bit Enum with Status/Command

String 8859 1
has communication mode: S
dpt bit size max: 112
subject: 16.1
subject: 16.001
subject: String 8859 1
is assembled with: type.dpt.field.16.1.i0.string88591
type: NamedIndividual
type: DatapointType
datapoint type major number: 16
datapoint type minor number: 1
comment: a point representing DPT 16.001: String 8859 1

type.dpt.field.27.1.i25.MaskBitIOO10
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field index: 25
field type: B
field name: MaskBitIOO10
description: Mask Bit Info On Off Output 10
type: Datapoint Type Field
type: NamedIndividual
field size: 1

type.dpt.field.30.1010.i22.ActivationStateOfChannel23
includes KV pair: type.kvpair.30.1010.i22.1
includes KV pair: The visual effect of channel 23 is inactive = 0
field name: ActivationStateOfChannel23
type: NamedIndividual
type: Datapoint Type Field
field size: 1
field type: B
field index: 22
comment: Activation state of channel 23

type.dpt.field.512.505.i0.ps.SQ ID
field name: SQ_ID
field type: U
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u4
field index: 0
description: Power sequence Id
field size: 4

Colour Relative Control RGBW
type: Class
subject: Colour Relative Control RGBW
subject: RC_RGBW
subject: 423.55
subject: 55
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
interface object type annotation: 423
property identifier annotation: 55

Value Electric Charge
has communication mode: S
label: Value Electric Charge
datapoint type major number: 14
dpt bit size max: 32
subject: 14.018
subject: 14.18
subject: Value Electric Charge
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.14.18.i0
comment: DPT 14.018: Value of electric charge
datapoint type minor number: 18

POP3
type: NamedIndividual
type: Protocol

Downwards Movement
type: State Type
type: NamedIndividual
comment: This state type expresses that an equipment has a movement direction that can be interpreted as 'downwards'. Usually, this is associated with equipments that can be moved by a drive along a vertical axis, such as blinds or slats.

type.dpt.field.8.6.i0
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
includes digit: type.digit.s16
unit: MIN
field size: 16
field resolution: 1.0

Value Electric Current
has communication mode: S
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.14.19.i0
subject: 14.019
subject: 14.19
subject: Value Electric Current
datapoint type minor number: 19
label: Value Electric Current
datapoint type major number: 14
dpt bit size max: 32
comment: DPT 14.019: Value of electric current

type.dpt.field.ec.i0.CQ
description: commodity quantity
includes DPT: emCommodityQuantity
field name: CQ
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 8

Motor
comment: Equipment that converts electrical energy into mechanical energy.
type: EquipmentType
type: NamedIndividual

Restriction
has value: 58
on property: property identifier

ErrorClass System
has communication mode: S
label: ErrorClass System
is assembled with: type.dpt.field.20.11.i0
type: NamedIndividual
type: DatapointType
dpt bit size max: 8
subject: 20.11
subject: ErrorClass System
subject: 20.011
datapoint type major number: 20
description: a point representing DPT 20.011: ErrorClass System
datapoint type minor number: 11

Balcony
type: LocationUsage
type: NamedIndividual
comment: A balcony (from Italian: balcone, 'scaffold') is a platform projecting from the wall of a building, supported by columns or console brackets, and enclosed with a balustrade, usually above the ground floor. Preferably used with an Space.

type.dpt.field.242.600.i5.xaxis
field size: 16
field name: xaxis
field type: U
field resolution: 1.0
unit: NUM
includes digit: type.digit.u16
type: Datapoint Type Field
type: NamedIndividual
comment: x-coordinate of the colour information
field index: 5

Restriction
has value: 57
on property: property identifier

type.dpt.field.30.1010.i1.ActivationStateOfChannel2
field index: 1
comment: Activation state of channel 2
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field name: ActivationStateOfChannel2
includes KV pair: The visual effect of channel 2 is inactive = 0
includes KV pair: type.kvpair.30.1010.i1.1
field type: B

Dim Send Style
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: Dim Send Style
subject: 1.13
subject: 1.013
datapoint type major number: 1
comment: a point representing DPT 1.013: Dim Send Style
dpt bit size max: 1
is assembled with: Dim Send Style
datapoint type minor number: 13
label: Dim Send Style

type.dpt.field.240.800.i3.SlatsPosition
description: Slats Position
field type: U
field name: SlatsPosition
type: Datapoint Type Field
type: NamedIndividual
field resolution: 0.3921566
includes digit: type.digit.u8
unit: PERCENT
field size: 8
field index: 3

type.dpt.field.224.100.i0.HVACEmergMode
description: Actual HVAC Emergency Mode
field name: HVACEmergMode
field size: 8
includes DPT: HVACEmergMode
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.201.102.i1.DHWMode
field index: 1
field name: DHWMode
type: Datapoint Type Field
type: NamedIndividual
comment: DHW operating mode
includes DPT: dhwMode
field size: 8

type.dpt.field.30.1010.i11.ActivationStateOfChannel12
type: NamedIndividual
type: Datapoint Type Field
field name: ActivationStateOfChannel12
field size: 1
field type: B
includes KV pair: type.kvpair.30.1010.i11.1
includes KV pair: The visual effect of channel 12 is inactive = 0
comment: Activation state of channel 12
field index: 11

contains asset
range: Asset
inverse of: isAssetOf
type: ObjectProperty
type: AsymmetricProperty
type: IrreflexiveProperty
comment: To define an asset included in other assets such as several equipment’s/ installations as part of an asset.
domain: Asset

type.dpt.field.523.500.i2.sms.OMF
field type: F
includes digit: type.digit.f16
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field index: 2
description: current factor that will be multiplied with given power range of the operation mode. will be set with a transition instruction
field name: OMF

Garbage = 41
type: NamedIndividual
value API: garbage
value KNX: 41

first: Restriction
  on property: interface object type
  has value: 261
rest: nil

type.dpt.field.30.1010.i5.ActivationStateOfChannel6
field name: ActivationStateOfChannel6
comment: Activation state of channel 6
includes KV pair: type.kvpair.30.1010.i5.1
includes KV pair: type.kvpair.30.1010.i5.0
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 5
field type: B

Wind
comment: Wind is the natural movement of air or other gases relative to a planet's surface. Winds are commonly classified by their spatial scale, their speed and direction, the forces that cause them, the regions in which they occur, and their effect.
type: NamedIndividual
type: Phenomenon

CombinedStatus_HVA_CoolA
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 72
subject: CombinedStatus_HVA_CoolA
subject: 399.72
subject: 72
label: CombinedStatus_HVA_CoolA
interface object type annotation: 399

TempRoomSetpAct
type: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  on property: has datapoint type
  has value: Value Temp
interface object type annotation: 397
property identifier annotation: 55
subject: TempRoomSetpAct
subject: 55
subject: 397.55

first: Restriction
  has value: many
  on property: has cardinality
rest: nil

24.x
has communication mode: S
datapoint type major number: 24
subject: 24.major
subject: 24.x
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.24.x.i0
label: 24.x
dpt bit size max: 312

Control Mode Auto
type: NamedIndividual
type: State Type
comment: This state type expresses that mode 'Auto' is chosen for the HVAC system. Usually, this mode is associated with a local controller selecting the appropriate mode for the HVAC system (e.g. based on sensor data). In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.

type.dpt.field.14.32.i0
field size: 32
field type: F
includes digit: type.digit.f32
field resolution: 1.0
unit: http://qudt.org/vocab/unit/N
type: Datapoint Type Field
type: NamedIndividual
description: force
field index: 0

Restriction
has value: RainAlarm
on property: pointName

type.dpt.field.27.1.i31.MaskBitIOO16
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field name: MaskBitIOO16
field index: 31
field type: B
field size: 1
comment: Mask Bit Info On Off Output 16
type: Datapoint Type Field
type: NamedIndividual

Occ Mode Z
has communication mode: LTE
datapoint type major number: 201
is assembled with: type.dpt.field.201.108.i0.StatusCommand
is assembled with: type.dpt.field.201.108.i1.OccMode
label: Occ Mode Z
datapoint type minor number: 108
comment: a point representing DPT 201.108: Occ Mode Z
type: NamedIndividual
type: DatapointType
subject: Occ Mode Z
subject: 201.108
dpt bit size max: 16

type.dpt.field.22.101.i6.StatusStopOptim
type: Datapoint Type Field
type: NamedIndividual
comment: StatusStopOptim
field index: 6
field name: StatusStopOptim
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field size: 1

Down = 1
is applicable datapoint enum of: Downwards Movement
value KNX: 1
value API: down
type: NamedIndividual

type.dpt.field.207.102.i1.Stage2Control
field index: 1
comment: controls operation of stage 1 or base stage
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field name: Stage2Control
includes DPT: switch

HeatCoolMode
type: Class
subject: HeatCoolMode
subject: 151
subject: 258.151
subclass of: Restriction
  on property: has operation kind
subclass of: Class
property identifier annotation: 151
label: HeatCoolMode
interface object type annotation: 258

TempRoomSetpUserAbs
type: Class
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
interface object type annotation: 397
subject: TempRoomSetpUserAbs
subject: 397.83
subject: 83
property identifier annotation: 83

type.dpt.field.22.103.i5.ControllerInactive
description: Controller inactive
type: NamedIndividual
type: Datapoint Type Field
field size: 1
field name: ControllerInactive
includes KV pair: type.kvpair.22.103.i5.0
includes KV pair: type.kvpair.22.103.i5.1
field index: 5
field type: B

Restriction
has value: one
on property: has cardinality

Blinds Stop Trigger
subclass of: Function Point
type: Class

type.dpt.field.27.1.i22.MaskBitIOO7
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.outputStateNotValid
includes KV pair: type.kvpair.outputStateValid
field name: MaskBitIOO7
field type: B
comment: Mask Bit Info On Off Output 7
field index: 22
field size: 1

type.dpt.field.252.600.i8.StepCodeColourBlue
description: Shall specify the fading step size or to the code to stop the fading of the colour blue
field index: 8
includes digit: type.digit.u3
field resolution: 1.0
field type: U
field size: 3
type: Datapoint Type Field
type: NamedIndividual
field name: StepCodeColourBlue

TempHVACAbsNext
has communication mode: LTE
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.220.100.i1.DelayTime
is assembled with: type.dpt.field.220.100.i0.Temp
subject: TempHVACAbsNext
subject: 220.100
comment: a point representing DPT 220.100: Next Temperature and Time Delay
datapoint type major number: 220
datapoint type minor number: 100

ForceSign
has communication mode: LTE
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.21.100.i5.DHWLegio
is assembled with: type.dpt.field.21.100.i7.RoomHMax
is assembled with: type.dpt.field.21.100.i4.DHWNorm
is assembled with: type.dpt.field.21.100.i0.ForceRequest
is assembled with: type.dpt.field.21.100.i1.Protection
is assembled with: type.dpt.field.21.100.i2.Oversupply
is assembled with: type.dpt.field.21.100.i6.RoomHConf
is assembled with: type.dpt.field.21.100.i3.Overrun
subject: ForceSign
subject: 21.100
dpt bit size max: 8
comment: a point representing DPT 21.100: ForceSign
datapoint type minor number: 100
datapoint type major number: 21

type.dpt.field.20.1203.i0
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: type.kvpair.20.1203.i0.2
includes KV pair: type.kvpair.20.1203.i0.4
includes KV pair: closed = 0
includes KV pair: open on overheat with a current value under the maximum switching current value = 6
includes KV pair: open on overheat with a current value over the maximum switching current value = 5
includes KV pair: type.kvpair.20.1203.i0.1
includes KV pair: type.kvpair.20.1203.i0.3
field index: 0
field type: N
field size: 8

is comprised by
domain: FunctionalBlock
type: ObjectProperty
range: Channel

User HVAC Display
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: TempOutside
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: HVACModeEff
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on class: TempRoom
  on property: isComposedByInput
subclass of: Class
  intersection of: FunctionalBlock
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
is incomplete: true
type: Class
interface object type annotation: 390
label: User HVAC Display
subject: UHD
subject: User HVAC Display
subject: 390

HVAC absolute Temperature
has communication mode: LTE
subject: HVAC absolute Temperature
subject: 205.100
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 205.100: TempHVACAbs_Z
datapoint type major number: 205
dpt bit size max: 24
is assembled with: type.dpt.field.205.100.i1.Temp
is assembled with: type.dpt.field.205.100.i0.StatusCommand
datapoint type minor number: 100

type.dpt.field.207.101.i3.PwrReduction
comment: Requested power reduction
field index: 3
field name: PwrReduction
includes digit: type.digit.u8 0 100
field resolution: 1.0
field type: U
type: Datapoint Type Field
type: NamedIndividual
unit: PERCENT
field size: 8

type.dpt.field.12.100.i0
field type: U
field resolution: 1.0
unit: SEC
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u32
field index: 0
field size: 32

254.x
has communication mode: S
datapoint type major number: 254
type: DatapointType
type: NamedIndividual
subject: 254.major
subject: 254.x
label: 254.x
is assembled with: type.dpt.field.254.x.i0
dpt bit size max: 24

9.x
has communication mode: S
label: 9.x
subject: 9.major
subject: 9.x
type: NamedIndividual
type: DatapointType
datapoint type major number: 9
dpt bit size max: 16
is assembled with: type.dpt.field.9.x.i0

Increasing
type: State Type
type: NamedIndividual
description: This state type expresses that a value is changed relatively in an 'increasing' manner, i.e. the value is raised. This state type is the inverse of the 'Decreasing' state type.

TempRoomSetpAct
type: Class
label: TempRoomSetpAct
interface object type annotation: 258
property identifier annotation: 153
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subject: 258.153
subject: 153
subject: TempRoomSetpAct

Restriction
has value: 52
on property: property identifier

Value Capacitance
has communication mode: S
label: Value Capacitance
type: NamedIndividual
type: DatapointType
subject: 14.011
subject: Value Capacitance
subject: 14.11
description: DPT 14.011: Value of capacitance
datapoint type minor number: 11
datapoint type major number: 14
is assembled with: type.dpt.field.14.11.i0
dpt bit size max: 32

ZWave
type: NamedIndividual
type: Protocol

TempRoomSetpAct
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: HVAC absolute Temperature
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
property identifier annotation: 53
subject: TempRoomSetpAct
subject: 160.53
subject: 53
label: TempRoomSetpAct
interface object type annotation: 160

type.dpt.field.251.600.i2.mG
field name: mG
includes KV pair: valid = 1
includes KV pair: not valid = 0
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field type: B
field index: 2
comment: mG

The visual effect of channel 19 is inactive = 0
value KNX: 0
value API: theVisualEffectOfChannel19IsInactiv
type: NamedIndividual

type.dpt.field.19.1.i16.DayOfWeek
comment: DayOfWeek
field default: 0
includes digit: type.digit.u3
field type: U
field resolution: 1.0
unit: DAY
field index: 16
field size: 3
type: Datapoint Type Field
type: NamedIndividual
field name: DayOfWeek

Staircase Trigger Request
subclass of: Restriction
  has value: Lighting
  on property: operates for trade
subclass of: Function Point
type: Class

Value Volume
has communication mode: S
description: DPT 14.076: Value of volume
datapoint type major number: 14
subject: 14.76
subject: Value Volume
subject: 14.076
dpt bit size max: 32
label: Value Volume
is assembled with: type.dpt.field.14.76.i0
type: NamedIndividual
type: DatapointType
datapoint type minor number: 76

type.dpt.field.14.69.i0
description: temperature (absolute)
unit: http://qudt.org/vocab/unit/K
field size: 32
field type: F
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0

SwitchOn message sent = 2
type: NamedIndividual
value API: switchOnMessageSent
value KNX: 2

rest: nil
first: Restriction
  has value: TempRoomSetpUserAbs
  on property: pointName

type.dpt.field.9.25.i0
type: Datapoint Type Field
type: NamedIndividual
unit: L-PER-HR
includes digit: type.digit.f16
field size: 16
field type: F
field index: 0
field resolution: 0.01

234.x
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: 234.x
subject: 234.major
label: 234.x
dpt bit size max: 16
datapoint type major number: 234
is assembled with: type.dpt.field.234.x.i0

type.dpt.field.14.1.i0
description: acceleration, angular
field type: F
includes digit: type.digit.f32
field resolution: 1.0
unit: RAD-PER-SEC2
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0

3 h = 22
type: NamedIndividual
value KNX: 22
value API: 3H

Value Mol
has communication mode: S
datapoint type major number: 14
subject: 14.004
subject: Value Mol
subject: 14.4
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
comment: DPT 14.004: Value of the amount of substance (mol)
datapoint type minor number: 4
is assembled with: type.dpt.field.14.4.i0

Blinds Move Up Down
subclass of: Function Point
type: Class

Day / Night
includes KV pair: type.kvpair.1.24.i0.0
includes KV pair: Night = 1
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
label: Day / Night
field type: B

dehumidification = 2
value KNX: 2
type: NamedIndividual
value API: dehumidification

Restriction
on property: has cardinality
has value: one

LongDeltaTimeSec
has communication mode: S
label: LongDeltaTimeSec
subject: LongDeltaTimeSec
subject: 13.100
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.13.100.i0
datapoint type major number: 13
comment: a point representing DPT 13.100: LongDeltaTimeSec
datapoint type minor number: 100

type.dpt.field.ombc.om.i0.ID
type: NamedIndividual
type: Datapoint Type Field
description: identifier of the operation mode
field size: 4
includes digit: type.digit.u4 1 15
field type: U
field name: ID
field index: 0

ActTargetPos
type: Class
property identifier annotation: 50
subject: 50
subject: 400.50
subject: ActTargetPos
interface object type annotation: 400

type.dpt.field.251.600.i6.W
field index: 6
type: NamedIndividual
type: Datapoint Type Field
includes digit: type.digit.u8
unit: PERCENT
field name: W
comment: Colour Level White
field type: U
field size: 8
field resolution: 0.3921566

type.dpt.field.20.500.i0.cq.ID
includes KV pair: Electric Power L3
includes KV pair: type.kvpair.cqNaturalGasFlowRate
includes KV pair: type.kvpair.cqElectricPowerL2
includes KV pair: type.kvpair.cqHeatThermalPower
includes KV pair: type.kvpair.cqHeatFlowRate
includes KV pair: type.kvpair.cqElectricPowerL1
includes KV pair: type.kvpair.cqOilFlowRate
includes KV pair: type.kvpair.cqHydrogenFlowRate
type: Datapoint Type Field
type: NamedIndividual
description: commodity quantity
field name: ID
field index: 0
field size: 8
field type: N

Scene Recall
type: NamedIndividual
type: State Type
comment: This state type expresses that a scene is activated in scene-controlled instrumentations by restoring a previously learnt value. This covers both activating a scene based on a scene number (e.g. 0-63) or by choosing between two scenes (e.g. Scene A or Scene B).

Enable
includes DPT: enable
field name: enable
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1

Restriction
has value: 61
on property: property identifier

Standard single-phase = 3
value KNX: 3
type: NamedIndividual
value API: standardSingle-phase

has cardinality
comment: Used to indicate the cardinality of a point. This is part of a point's access type in the specification Vol 7 and can be 'one' (1 -> this for inputs or this -> 1 for outputs) or 'many' (N -> this for inputs or this -> N for outputs).
domain: Point
type: DatatypeProperty

Scaling Step Time
has communication mode: S
subject: Scaling Step Time
subject: 225.002
subject: 225.2
is assembled with: type.dpt.field.225.2.i1.TimePeriod
is assembled with: type.dpt.field.225.2.i0.Percent
datapoint type major number: 225
comment: a point representing DPT 225.002: Scaling Step Time
type: NamedIndividual
type: DatapointType
datapoint type minor number: 2
label: Scaling Step Time
dpt bit size max: 24

Restriction
on property: interface object type
has value: 423

Sunshiny = 2
value API: sunshiny
value KNX: 2
type: NamedIndividual

Sun
comment: Relating to energy from the sun.
type: NamedIndividual
type: Phenomenon

Restriction
has value: one
on property: has cardinality

power, 1 kJ/h = 51
value KNX: 51
value API: power,1KJh
type: NamedIndividual

type.dpt.field.256.1.i0.StopDateTime
field size: 64
type: Datapoint Type Field
type: NamedIndividual
field name: StopDateTime
field index: 0
includes DPT: DateTime
comment: Stop Date Time

EnableHeatEff
type: Class
subclass of: Restriction
  has value: enable
  on property: has datapoint type
subject: 399.107
subject: 107
subject: EnableHeatEff
label: EnableHeatEff
property identifier annotation: 107
interface object type annotation: 399

NumberedSceneControl
type: Class
subject: NSC
subject: 73
subject: 417.73
subject: NumberedSceneControl
interface object type annotation: 417
property identifier annotation: 73

Channel Activation 8
has communication mode: S
subject: 21.1010
subject: Channel Activation 8
is assembled with: type.dpt.field.21.1010.i1.ActivationStateOfChannel2
is assembled with: type.dpt.field.21.1010.i6.ActivationStateOfChannel7
is assembled with: type.dpt.field.21.1010.i3.ActivationStateOfChannel4
is assembled with: type.dpt.field.21.1010.i2.ActivationStateOfChannel3
is assembled with: type.dpt.field.21.1010.i0.ActivationStateOfChannel1
is assembled with: type.dpt.field.21.1010.i5.ActivationStateOfChannel6
is assembled with: type.dpt.field.21.1010.i4.ActivationStateOfChannel5
is assembled with: type.dpt.field.21.1010.i7.ActivationStateOfChannel8
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 21.1010: Channel Activation 8
datapoint type major number: 21
datapoint type minor number: 1010
dpt bit size max: 8

DeltaTimeSec
has communication mode: S
is assembled with: type.dpt.field.8.5.i0
label: DeltaTimeSec
subject: DeltaTimeSec
subject: 8.5
subject: 8.005
datapoint type minor number: 5
type: NamedIndividual
type: DatapointType
datapoint type major number: 8
comment: a point representing DPT 8.005: DeltaTimeSec
dpt bit size max: 16

TempRoomSetpSetHeat
type: Class
property identifier annotation: 58
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has datapoint type
  has value: Room Temperature Setpoint
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
subject: 398.58
subject: TempRoomSetpSetHeat
subject: 58
interface object type annotation: 398

StartSynchronization
has communication mode: S
type: NamedIndividual
type: DatapointType
datapoint type minor number: 122
datapoint type major number: 20
dpt bit size max: 8
subject: StartSynchronization
subject: 20.122
label: StartSynchronization
is assembled with: type.dpt.field.20.122.i0
comment: a point representing DPT 20.122: StartSynchronization

type.dpt.field.15.0.i0.Index
field index: 0
comment: Index of access identification code
field size: 4
field type: U
field resolution: 1.0
field name: Index
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual

Value Area
has communication mode: S
subject: 14.10
subject: 14.010
subject: Value Area
description: DPT 14.010: Value of an area
label: Value Area
is assembled with: type.dpt.field.14.10.i0
datapoint type minor number: 10
datapoint type major number: 14
dpt bit size max: 32
type: NamedIndividual
type: DatapointType

two push buttons/binary inputs mode = 4
value KNX: 4
value API: twoPushButtonsbinaryInputsMode
type: NamedIndividual

Historical single-phase = 1
type: NamedIndividual
value KNX: 1
value API: historicalSingle-phase

ActuatorErrorInfo
type: Class
subject: ActuatorErrorInfo
subject: 417.55
subject: 55
label: ActuatorErrorInfo
interface object type annotation: 417
property identifier annotation: 55
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.521.500.i3.ts.R
includes KV pair: no = 0
includes KV pair: type.kvpair.yes
field index: 3
field type: B
field size: 1
field name: R
field default: 0
description: flat that is set to true when the timer is currently running
type: Datapoint Type Field
type: NamedIndividual

Shading Control
subclass of: Restriction
  on property: operates for trade
  has value: shading
subclass of: ApplicationFunction
type: Class
comment: A specific Application Function category that controls the solar irradiance by means of motorized sun protection. Very often there are protection functions that interfere with the sun protection. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.

Restriction
on property: has cardinality
has value: one

type.dpt.field.frbc.ome
field type: D<n>
field index: 0
includes DPT field: type.dpt.field.frbc.ome.i2.FLR
includes DPT field: type.dpt.field.frbc.ome.i0.PR
includes DPT field: type.dpt.field.frbc.ome.i1.FR
description: operation mode element
type: Datapoint Type Field
type: NamedIndividual

Standby = 1
value API: standby
type: NamedIndividual
value KNX: 1

TempRoomSetpUserOffsetEff
type: Class
subject: 86
subject: TempRoomSetpUserOffsetEff
subject: 398.86
subclass of: Restriction
  on property: has datapoint type
  has value: Value Temp D
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
property identifier annotation: 86
label: TempRoomSetpUserOffsetEff
interface object type annotation: 398

TempRoomSetpSetCool
type: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air temperature room
subclass of: Restriction
  has value: Room Temperature Setpoint
  on property: has datapoint type
subject: TempRoomSetpSetCool
subject: 59
subject: 398.59
property identifier annotation: 59
interface object type annotation: 398

type.dpt.field.20.1202.i0
includes KV pair: type.kvpair.20.1202.i0.0
includes KV pair: at base condition = 2
includes KV pair: type.kvpair.20.1202.i0.1
includes KV pair: at measurement condition = 3
field type: N
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.525.500.i7.fv.Upper Limit
type: Datapoint Type Field
type: NamedIndividual
field index: 7
includes DPT: Power
field name: Upper_Limit
field size: 16
description: The upper boundary of the range with 100 % certainty the power value is in it

Software
subclass of: Asset
comment: A software represents a collection of data or instructions that are installed (hosted) on a Device or Computer and tell it how to work. Software is a generic term used to refer to applications, scripts and programs that run on a Device.
type: Class

type.dpt.field.517.500.i2.lr.LT
field type: N
includes KV pair: type.kvpair.UpperLimit
includes KV pair: type.kvpair.LowerLimit
field name: LT
type: Datapoint Type Field
type: NamedIndividual
field index: 2
description: limit type
field size: 4

Heat Stage B Actuator Status
subclass of: Restriction
  on property: has operation kind
  qualified cardinality: 1
  on class: Class
subclass of: Restriction
  has value: Combined Status HVA
  on property: has datapoint type
subclass of: Restriction
  on property: has operation kind
  qualified cardinality: 1
subclass of: Restriction
  on property: has operation kind
  qualified cardinality: 1
subclass of: Function Point
subclass of: Restriction
  on property: has operation kind
  qualified cardinality: 1
type: Class

type.dpt.field.lb.lbe.i0.LR
type: NamedIndividual
type: Datapoint Type Field
description: the leakage rate for the given FLR
field index: 0
field size: 16
field name: LR
includes DPT: emFillLevelLeakageRate

Humidification Mode Inactive
description: This state type expresses that the ventilation system is inactive, i.e. performing neither humidification nor dehumidification tasks.
type: State Type
type: NamedIndividual

2 min = 13
value API: 2Min
value KNX: 13
type: NamedIndividual

type.dpt.field.30.1010.i6.ActivationStateOfChannel7
field name: ActivationStateOfChannel7
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: The visual effect of channel 7 is inactive = 0
includes KV pair: type.kvpair.30.1010.i6.1
field index: 6
field size: 1
field type: B
comment: Activation state of channel 7

AlarmInfo
has communication mode: S
is assembled with: type.dpt.field.219.1.i8.Reserved
is assembled with: type.dpt.field.219.1.i1.AlarmUnAck
is assembled with: type.dpt.field.219.1.i4.Ack Sup
is assembled with: type.dpt.field.219.1.i7.ErrorCode Sup
is assembled with: type.dpt.field.219.1.i5.TimeStamp Sup
is assembled with: type.dpt.field.219.1.i12.LogNumber
is assembled with: type.dpt.field.219.1.i3.Reserved
is assembled with: type.dpt.field.219.1.i2.Locked
is assembled with: type.dpt.field.219.1.i9.ErrorClass
is assembled with: type.dpt.field.219.1.i6.AlarmText Sup
is assembled with: type.dpt.field.219.1.i10.ApplicationArea
is assembled with: type.dpt.field.219.1.i11.AlarmPriority
is assembled with: type.dpt.field.219.1.i0.InAlarm
subject: AlarmInfo
subject: 219.001
subject: 219.1
comment: a point representing DPT 219.001: AlarmInfo
type: NamedIndividual
type: DatapointType
datapoint type major number: 219
datapoint type minor number: 1
dpt bit size max: 48
label: AlarmInfo

failure = 1
value KNX: 1
value API: failure
type: NamedIndividual

LockDevice
type: Class
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: has operation kind
subject: LockDevice
subject: 418.69
subject: 69
interface object type annotation: 418
property identifier annotation: 69

type.dpt.field.250.x.i0
field size: 24
field string schema: raw
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
description: status
field index: 0

Started
value KNX: 3
type: NamedIndividual
value API: Started

Building not used = 1
value API: buildingNotUsed
type: NamedIndividual
value KNX: 1

Cool Stage A Actuator Overridden
subclass of: Function Point
type: Class

Type TIC Channel
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
description: a point representing DPT 20.1209: Type TIC Channel
subject: 20.1209
subject: Type TIC Channel
datapoint type minor number: 1209
is assembled with: type.dpt.field.20.1209.i0
dpt bit size max: 8

Restriction
on property: interface object type
has value: 398

The visual effect of channel 16 is inactive = 0
value KNX: 0
type: NamedIndividual
value API: theVisualEffectOfChannel16IsInactiv

is point operation of
sub property of: isTagOf
type: InverseFunctionalProperty
type: ObjectProperty
domain: Point Operation
range: Operation Kind

type.dpt.field.20.1.i0
field index: 0
includes KV pair: type.kvpair.20.1.i0.0
includes KV pair: type.kvpair.20.1.i0.1
includes KV pair: master = 2
comment: SCLOMode
type: Datapoint Type Field
type: NamedIndividual
field type: N
field size: 8

type.dpt.field.21.101.i1.Reserved
field index: 1
field type: r
type: Datapoint Type Field
type: NamedIndividual
field size: 7
includes reserved bit: type.bit.reserved
field name: Reserved

Level 7 = 7
value API: level7
type: NamedIndividual
value KNX: 7

type.dpt.field.243.600.i6.TimePeriod
type: NamedIndividual
type: Datapoint Type Field
field name: TimePeriod
field index: 6
field size: 16
description: Unsigned time-value for calculating fading time.
includes DPT: TimePeriod100MSec

Restriction
has value: HVACModeUser
on property: pointName

type.dpt.field.252.600.i15.cR
field size: 1
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
field index: 15
type: Datapoint Type Field
type: NamedIndividual
comment: Shall specify whether the colour component red shall be increased or decreased.
field type: B
field name: cR

Value Electromotive Force
has communication mode: S
type: NamedIndividual
type: DatapointType
comment: DPT 14.030: Value of electromotive force
label: Value Electromotive Force
is assembled with: type.dpt.field.14.30.i0
subject: 14.030
subject: 14.30
subject: Value Electromotive Force
datapoint type minor number: 30
datapoint type major number: 14
dpt bit size max: 32

energy, 0,001 kJ = 8
value KNX: 8
type: NamedIndividual
value API: energy,0,001KJ

type.dpt.field.207.100.i2.StatusStage1
field name: StatusStage1
field size: 1
comment: stage 1 or base stage active
type: Datapoint Type Field
type: NamedIndividual
field index: 2
includes DPT: switch

type.dpt.field.207.105.i3.ValveKick
type: NamedIndividual
type: Datapoint Type Field
field size: 1
comment: valve is currently executing a valve kick
field index: 3
includes DPT: State
field name: ValveKick

249.x
has communication mode: S
dpt bit size max: 48
label: 249.x
type: DatapointType
type: NamedIndividual
subject: 249.x
subject: 249.major
datapoint type major number: 249
is assembled with: type.dpt.field.249.x.i0

231.x
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 231.x
subject: 231.major
label: 231.x
datapoint type major number: 231
dpt bit size max: 32
is assembled with: type.dpt.field.231.x.i0

Phase L2
description: Refers to the second phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.
type: Locality
type: NamedIndividual

energy, 1 MWh = 129
value KNX: 129
value API: energy,1MWh
type: NamedIndividual

TempReturnAir
type: Class
property identifier annotation: 51
subject: 51
subject: 323.51
subject: TempReturnAir
interface object type annotation: 323

type.dpt.field.20.3.i0
description: OccMode
includes KV pair: occupied = 0
includes KV pair: type.kvpair.20.3.i0.2
includes KV pair: standby = 1
field type: N
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

activation of priority = 0
type: NamedIndividual
value KNX: 0
value API: activationOfPriority

type.dpt.field.22.100.i5.SolarEnergyOnly
field type: B
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field size: 1
field name: SolarEnergyOnly
type: Datapoint Type Field
type: NamedIndividual
description: SolarEnergyOnly
field index: 5

type.dpt.field.13.13.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 32
unit: KiloW-HR
field resolution: 1.0
includes digit: type.digit.s32
field type: V

Binary Value Control
has communication mode: S
type: DatapointType
type: NamedIndividual
dpt bit size max: 2
subject: Binary Value Control
subject: 2.006
subject: 2.6
label: Binary Value Control
datapoint type major number: 2
description: a point representing DPT 2.006: Binary Value Control
is assembled with: c
is assembled with: Binary Value
datapoint type minor number: 6

Value Common Temperature
has communication mode: S
datapoint type minor number: 68
type: DatapointType
type: NamedIndividual
description: DPT 14.068: Value of common temperature
is assembled with: type.dpt.field.14.68.i0
datapoint type major number: 14
subject: Value Common Temperature
subject: 14.68
subject: 14.068
label: Value Common Temperature
dpt bit size max: 32

type.dpt.field.213.101.i0.TempSetpOffFrostProtect
unit: DEG C
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767
field index: 0
field size: 16
description: DHW temperature setpoint for Off/FrostProtect operating mode
field name: TempSetpOffFrostProtect

type.dpt.field.209.102.i1.NoCoolAvailable
description: temporarily no cooling in the production segment available
type: Datapoint Type Field
type: NamedIndividual
field name: NoCoolAvailable
includes DPT: Bool
field index: 3
field size: 1

StatusSDHWC
has communication mode: LTE
datapoint type major number: 21
is assembled with: type.dpt.field.21.103.i2.SolarLoadSufficient
is assembled with: type.dpt.field.21.103.i1.SDHWLoadActive
is assembled with: type.dpt.field.21.103.i3.Reserved
is assembled with: type.dpt.field.21.103.i0.Fault
subject: StatusSDHWC
subject: 21.103
type: NamedIndividual
type: DatapointType
dpt bit size max: 8
datapoint type minor number: 103
label: StatusSDHWC
comment: a point representing DPT 21.103: StatusSDHWC

Value Electric FieldStrength
has communication mode: S
label: Value Electric FieldStrength
is assembled with: type.dpt.field.14.23.i0
datapoint type major number: 14
subject: 14.023
subject: Value Electric FieldStrength
subject: 14.23
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
comment: DPT 14.023: Value of electric field strength
datapoint type minor number: 23

type.digit.charISO 8859 1
range max: 255
type: NamedIndividual
range min: 0

type.dpt.field.20.602.i0
includes KV pair: 64,0 s = 14
includes KV pair: type.kvpair.20.602.i0.4
includes KV pair: type.kvpair.20.602.i0.1
includes KV pair: type.kvpair.20.602.i0.7
includes KV pair: type.kvpair.20.602.i0.3
includes KV pair: 22,6 s = 11
includes KV pair: type.kvpair.20.602.i0.2
includes KV pair: type.kvpair.20.602.i0.9
includes KV pair: type.kvpair.20.602.i0.12
includes KV pair: type.kvpair.20.602.i0.0
includes KV pair: type.kvpair.20.602.i0.6
includes KV pair: type.kvpair.20.602.i0.5
includes KV pair: type.kvpair.20.602.i0.10
includes KV pair: 8,0 s = 8
includes KV pair: 90,5 s = 15
includes KV pair: type.kvpair.20.602.i0.13
comment: FadeTime
field index: 0
type: Datapoint Type Field
type: NamedIndividual
field type: N
field size: 8

type.dpt.field.30.1010.i0.ActivationStateOfChannel1
includes KV pair: type.kvpair.30.1010.i0.0
includes KV pair: type.kvpair.30.1010.i0.1
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 0
field type: B
field name: ActivationStateOfChannel1
comment: Activation state of channel 1

volume, 10 l = 20
value API: volume,10L
value KNX: 20
type: NamedIndividual

Staircase Switch Request
subclass of: Function Point
type: Class

Value Activation Energy
has communication mode: S
description: DPT 14.002: Value of activation energy
is assembled with: type.dpt.field.14.2.i0
datapoint type major number: 14
dpt bit size max: 32
subject: 14.2
subject: 14.002
subject: Value Activation Energy
type: NamedIndividual
type: DatapointType
datapoint type minor number: 2

type.dpt.field.207.102.i0.Stage1Control
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes DPT: switch
field size: 1
comment: controls stage 2 for two stage burner
field name: Stage1Control

Restriction
has value: Switch On Off
on property: pointName

Room Temperature Setpoint Manager
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: Class
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: Class
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
  on class: TempRoomSetpUserOffset
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
  on class: TempRoomSetpSetCoolShift
subclass of: Restriction
  on class: dpa.398.84
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: ComfortProlongEff
subclass of: Restriction
  on class: HVACModeUserEff
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on class: TempRoomSetpSetHeat
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: HVACModeEffNext
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
  on class: HVACModeUser
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: TempRoomSetpUserOffsetEff
subclass of: Restriction
  on property: isComposedByOutput
  on class: HVACModeEff
  qualified cardinality: 1
subclass of: Restriction
  on class: TempRoomSetpCoolEff
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: TempRoomSetpSetHeatShift
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
  on class: dpa.398.55
subclass of: Restriction
  on class: PresenceStatus
  on property: isComposedByInput
  max qualified cardinality: 1
type: Class
subject: RTSM
subject: 398
subject: Room Temperature Setpoint Manager
label: Room Temperature Setpoint Manager
interface object type annotation: 398

type.dpt.field.27.1.i6.IOO7
includes KV pair: output state is Off = 0
includes KV pair: output state is On = 1
field type: B
description: Info On Off Output 7
type: Datapoint Type Field
type: NamedIndividual
field name: IOO7
field index: 6
field size: 1

type.dpt.field.20.611.i0
field size: 8
includes KV pair: type.kvpair.20.611.i0.2
includes KV pair: type.kvpair.20.611.i0.1
includes KV pair: type.kvpair.20.611.i0.6
includes KV pair: type.kvpair.20.611.i0.3
includes KV pair: Reset Function Test Done Flag = 5
includes KV pair: Stop Test = 4
field type: N
type: Datapoint Type Field
type: NamedIndividual
description: LoadTypeDetected
field index: 0

Restriction
qualified cardinality: 1
on class: Light Absolute Setvalue Request
on property: has function point

Standard = 1
value KNX: 1
type: NamedIndividual
value API: standard

energy, 0,01 kJ = 9
value API: energy,0,01KJ
type: NamedIndividual
value KNX: 9

Restriction
has value: 400
on property: interface object type

Start
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1
field name: start
includes DPT: start

Level 4 = 4
value API: level4
value KNX: 4
type: NamedIndividual

type.dpt.field.238.600.i0.DeviceAddress
comment: Device Address
includes digit: type.digit.u6
field name: DeviceAddress
field type: U
type: Datapoint Type Field
type: NamedIndividual
field size: 6
field index: 0
field resolution: 1.0

Blinds Slat Position Percentage
subclass of: Function Point
subclass of: Restriction
  on property: has datapoint type
  has value: scaling
type: Class

type.dpt.field.21.1.i2.Overridden
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 2
field name: Overridden
comment: corresponding Datapoint Main value is overridden
type: Datapoint Type Field
type: NamedIndividual
field size: 1

is actionpoint of
sub property of: isPointOf
domain: Actionpoint
type: ObjectProperty

HVACModeAct
type: Class
subject: 160.52
subject: HVACModeAct
subject: 52
property identifier annotation: 52
interface object type annotation: 160

Volume Flux ls
has communication mode: S
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.14.1201.i0
subject: 14.1201
subject: Volume Flux ls
datapoint type minor number: 1201
label: Volume Flux ls
dpt bit size max: 32
description: DPT 14.1201: Value of volume flux (in litres per second)
datapoint type major number: 14

type.dpt.field.9.10.i0
field index: 0
field type: F
includes digit: type.digit.f16
field size: 16
field resolution: 0.01
unit: SEC
type: Datapoint Type Field
type: NamedIndividual

Free Cool = 10
value API: freeCool
type: NamedIndividual
value KNX: 10

type.dpt.field.220.100.i1.DelayTime
type: Datapoint Type Field
type: NamedIndividual
includes DPT: TimePeriodMin
comment: Time delay
field index: 1
field name: DelayTime
field size: 16

type.dpt.field.ec.i0
includes DPT field: type.dpt.field.ec.i1.AVR
includes DPT field: type.dpt.field.ec.i5.Reserved
includes DPT field: type.dpt.field.ec.i3.FROM
includes DPT field: type.dpt.field.ec.i0.CQ
includes DPT field: type.dpt.field.ec.i2.UNTIL
includes DPT field: type.dpt.field.ec.i4.ID
field type: D<n>
field index: 0
type: NamedIndividual
type: Datapoint Type Field
description: energy constraint

Overridden
type: Class
comment: This DPA refers to the actuator being manually overridden. In contrast to the Z8 general status fields, in this case the Overridden status information refers to the actual manual operation (and not to an overridden state due to maintenance as does the Z8 field). The overridden state refers to the actual position of the valve (and thus to the specific property Position Vector), which is why the QualityKind is used at this point.
label: Overridden
subject: 400.71
subject: 71
subject: Overridden
property identifier annotation: 71
subclass of: Restriction
  some values from: Class
    intersection of: Operation Kind
  on property: has operation kind
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
interface object type annotation: 400

The visual effect of channel 13 is inactive = 0
value API: theVisualEffectOfChannel13IsInactiv
type: NamedIndividual
value KNX: 0

Invert Control
has communication mode: S
subject: 2.012
subject: Invert Control
subject: 2.12
label: Invert Control
type: NamedIndividual
type: DatapointType
description: a point representing DPT 2.012: Invert Control
is assembled with: c
is assembled with: type.dpt.field.2.12.i0.invert
datapoint type minor number: 12
datapoint type major number: 2
dpt bit size max: 2

Up Down
has communication mode: S
datapoint type major number: 1
label: Up Down
type: DatapointType
type: NamedIndividual
subject: 1.008
subject: Up Down
subject: 1.8
dpt bit size max: 1
comment: a point representing DPT 1.008: Up Down
datapoint type minor number: 8
is assembled with: Up / Down

TimePeriod10MSec
has communication mode: S
subject: TimePeriod10MSec
subject: 7.3
subject: 7.003
datapoint type minor number: 3
type: NamedIndividual
type: DatapointType
label: TimePeriod10MSec
dpt bit size max: 16
comment: a point representing DPT 7.003: TimePeriod10MSec
is assembled with: type.dpt.field.7.3.i0
datapoint type major number: 7

FanSpeedUser
type: Class
property identifier annotation: 74
subject: 74
subject: FanSpeedUser
subject: 399.74
interface object type annotation: 399

TempRoomSetpAct
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has datapoint type
  has value: HVAC absolute Temperature
subject: 257.153
subject: 153
subject: TempRoomSetpAct
property identifier annotation: 153
interface object type annotation: 257

type.dpt.field.522.500.i3.si.SID
field size: 4
includes digit: type.digit.u4 1 15
field type: U
description: sequence ID
type: Datapoint Type Field
type: NamedIndividual
field name: SID
field index: 3

Device Address = 0
value API: deviceAddress
type: NamedIndividual
value KNX: 0

rest: nil
first: Restriction
  on property: interface object type
  has value: 110

Stop Test = 4
value API: stopTest
type: NamedIndividual
value KNX: 4

Power
has communication mode: S
comment: a point representing DPT 9.024: Power
subject: Power
subject: 9.24
subject: 9.024
is assembled with: type.dpt.field.9.24.i0
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
datapoint type major number: 9
datapoint type minor number: 24
label: Power

range min
type: DatatypeProperty
range: Literal
comment: Limits a numerical datapoint type value to a minimum (range min) as a literal, to express float and integer values. May be used from several concepts, such as a DPT. The range is used to limit it for signed/unsigned integers and float values.

is meta data of
type: ObjectProperty
type: AsymmetricProperty
type: IrreflexiveProperty
sub property of: isReferencedBy
domain: Datapoint
comment: to express a “metadata to runtime” relation between different datapoints. Datapoints may provide further information about other datapoints but not including to manipulate their actual value at runtime.
range: Datapoint

Water meter = 7
value API: waterMeter
value KNX: 7
type: NamedIndividual

SwitchOnOff
type: Class
subject: SwitchOnOff
subject: SOO
subject: 52
subject: 417.52
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq luminaire dimmlevel
interface object type annotation: 417
property identifier annotation: 52

no change = 2
value KNX: 2
type: NamedIndividual
value API: noChange

Actual Dimming Value White
type: Class
subject: ASV_W
subject: 86
subject: Actual Dimming Value White
subject: 423.86
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
property identifier annotation: 86
interface object type annotation: 423

15.x
has communication mode: S
subject: 15.x
subject: 15.major
label: 15.x
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.15.x.i0
datapoint type major number: 15

Light
description: Electromagnetic radiation in the visible spectrum
type: NamedIndividual
type: Phenomenon

error = 1
type: NamedIndividual
value API: error
value KNX: 1

Restriction
max qualified cardinality: 1
on class: Protocol
on property: operates on protocol

HVACModeEffNext
type: Class
subject: 399.51
subject: 51
subject: HVACModeEffNext
subclass of: Restriction
  some values from: Class
    intersection of: Operation Kind
  on property: has operation kind
interface object type annotation: 399
property identifier annotation: 51

Step Control
has communication mode: S
datapoint type major number: 2
dpt bit size max: 2
subject: 2.007
subject: 2.7
subject: Step Control
label: Step Control
datapoint type minor number: 7
type: NamedIndividual
type: DatapointType
is assembled with: c
is assembled with: Step
comment: a point representing DPT 2.007: Step Control

type.dpt.field.9.21.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 16
field type: F
includes digit: type.digit.f16
field resolution: 0.01
unit: MilliA

RelSetvalueControl
type: Class
subclass of: Restriction
  on property: has operation kind
label: RelSetvalueControl
interface object type annotation: 418
subject: RelSetvalueControl
subject: 418.68
subject: 68
property identifier annotation: 68

DHW Mode Z
has communication mode: LTE
comment: a point representing DPT 201.102: DHW Mode Z
type: NamedIndividual
type: DatapointType
datapoint type minor number: 102
is assembled with: type.dpt.field.201.102.i1.DHWMode
is assembled with: type.dpt.field.201.102.i0.StatusCommand
label: DHW Mode Z
dpt bit size max: 16
datapoint type major number: 201
subject: 201.102
subject: DHW Mode Z

Relative Control RGBW
has communication mode: S
description: a point representing DPT 252.600: Relative Control RGBW
is assembled with: type.dpt.field.252.600.i15.cR
is assembled with: type.dpt.field.252.600.i14.StepCodeColourRed
is assembled with: type.dpt.field.252.600.i5.StepCodeColourWhite
is assembled with: type.dpt.field.252.600.i0.MaskCW
is assembled with: type.dpt.field.252.600.i1.MaskCB
is assembled with: type.dpt.field.252.600.i16.Reserved
is assembled with: type.dpt.field.252.600.i6.cW
is assembled with: type.dpt.field.252.600.i3.MaskCR
is assembled with: type.dpt.field.252.600.i7.Reserved
is assembled with: type.dpt.field.252.600.i2.MaskCG
is assembled with: type.dpt.field.252.600.i4.Reserved
is assembled with: type.dpt.field.252.600.i12.cG
is assembled with: type.dpt.field.252.600.i13.Reserved
is assembled with: type.dpt.field.252.600.i11.StepCodeColourGreen
is assembled with: type.dpt.field.252.600.i8.StepCodeColourBlue
is assembled with: type.dpt.field.252.600.i9.cB
is assembled with: type.dpt.field.252.600.i10.Reserved
dpt bit size max: 40
type: DatapointType
type: NamedIndividual
datapoint type minor number: 600
label: Relative Control RGBW
subject: 252.600
subject: Relative Control RGBW
datapoint type major number: 252

Restriction
has value: TempRoomSetpCoolEff
on property: pointName

TempRoomSetpSetCoolShift
type: Class
label: TempRoomSetpSetCoolShift
subclass of: Restriction
  on property: has datapoint type
  has value: tempRoomSetpSetShiftF16 a4a
subclass of: Restriction
  on property: has operation kind
subject: 61
subject: TempRoomSetpSetCoolShift
subject: 398.61
interface object type annotation: 398
property identifier annotation: 61

type.dpt.field.14.43.i0
includes digit: type.digit.f32
type: Datapoint Type Field
type: NamedIndividual
unit: CD
field index: 0
comment: luminous intensity
field resolution: 1.0
field size: 32
field type: F

type.dpt.field.22.102.i7.LockedPosition
type: Datapoint Type Field
type: NamedIndividual
description: Locked Position
includes KV pair: not locked = 0
includes KV pair: type.kvpair.22.102.i7.1
field size: 1
field index: 7
field type: B
field name: LockedPosition

TempRoom
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: Value Temp
subject: 399.56
subject: 56
subject: TempRoom
label: TempRoom
interface object type annotation: 399
property identifier annotation: 56

Restriction
has value: 151
on property: property identifier

Group Address Table is not sorted = 15
value API: groupAddressTableIsNotSorted
type: NamedIndividual
value KNX: 15

open on overheat with a current value under the maximum switching current value = 6
value API: openOnOverheatWithACurrentValueUnde
type: NamedIndividual
value KNX: 6

Brightness External
type: Class
label: Brightness External
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Value Lux
  on property: has datapoint type
subject: BE
subject: 414.62
subject: 62
subject: Brightness External
interface object type annotation: 414
property identifier annotation: 62

Restriction
has value: 399
on property: interface object type

type.dpt.field.241.800.i10.Failure
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 10
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field name: Failure
comment: General failure of the actuator or the drive

type.dpt.field.22.1010.i1.ActivationStateOfChannel2
includes KV pair: The visual effect of channel 2 is active = 1
includes KV pair: The visual effect of channel 2 is inactive = 0
field type: B
field index: 1
field name: ActivationStateOfChannel2
comment: Activation state of channel 2
type: Datapoint Type Field
type: NamedIndividual
field size: 1

Restriction
on property: interface object type
has value: 399

type.dpt.field.238.600.i2.BallastFailure
includes KV pair: no error = 0
includes KV pair: error = 1
type: Datapoint Type Field
type: NamedIndividual
description: Ballast Failure
field type: B
field index: 2
field name: BallastFailure
field size: 1

Sun Intensity Z
has communication mode: LTE
type: NamedIndividual
type: DatapointType
subject: Sun Intensity Z
subject: 203.102
datapoint type major number: 203
datapoint type minor number: 102
dpt bit size max: 24
is assembled with: type.dpt.field.203.102.i1.SunIntensity
is assembled with: type.dpt.field.203.102.i0.StatusCommand
comment: a point representing DPT 203.102: Sun Intensity Z

Site
label: Liegenschaft @de
subclass of: Location
comment: A site represents a collection of buildings and grounds that belong to a given institution. A site is usually at the top of a location or rather building hierarchy. The concept can be mapped to a IfcSite.
type: Class

Restriction
on property: interface object type
has value: 257

type.dpt.field.255.1.i1.Longitude
field type: F
field name: Longitude
comment: Longitude information
field index: 1
includes digit: type.digit.f32
unit: DEG
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field size: 32

Relative Set Value Control Blue
type: Class
label: Relative Set Value Control Blue
subclass of: Restriction
  on property: has datapoint type
  has value: Control Dimming
subject: 423.63
subject: Relative Set Value Control Blue
subject: 63
subject: RSC_B
property identifier annotation: 63
interface object type annotation: 423

Restriction
on property: has cardinality
has value: many

State
field index: 0
field size: 1
field type: B
type: Datapoint Type Field
type: NamedIndividual
label: State
includes KV pair: Inactive = 0
includes KV pair: type.kvpair.active

type.dpt.field.19.1.i4.NT
field index: 4
field name: NT
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.19.1.i4.1
includes KV pair: Hour of day, Minutes and Seconds field valid = 0
field size: 1
field type: B
description: No Time
field default: 0

mass flow, 0,01 kg/h = 81
type: NamedIndividual
value KNX: 81
value API: massFlow,0,01Kgh

type.dpt.field.fltp.pe
includes DPT field: type.dpt.field.fltp.pe.i1.DUR
includes DPT field: type.dpt.field.fltp.pe.i0.FLR
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
description: fill level target profile element
field index: 0

Step
field index: 0
label: Step
field type: B
field size: 1
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.249.600.i2.validityOfTimePeriod
field type: B
description: validity of the Time Period
field name: validityOfTimePeriod
field index: 2
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
field size: 1

Value AirQuality
has communication mode: S
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
subject: 9.008
subject: Value AirQuality
subject: 9.8
is assembled with: type.dpt.field.9.8.i0
label: Value AirQuality
comment: a point representing DPT 9.008: Value AirQuality
datapoint type minor number: 8
datapoint type major number: 9

groups
type: ObjectProperty
domain: Aspect
range: Point
comment: To define a relation to a point from an aspect. Aspects without any points is possible.
inverse of: is grouped by

Origin
comment: The tag category contains individuals that describe a specific application data source of a point, used in cases where the input of an point is affected from a superordinated application control (instead of the common control loop).
subclass of: Tag
type: Class

type.dpt.field.22.101.i1.StatusEcoH
field size: 1
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field index: 1
comment: StatusEcoH
type: Datapoint Type Field
type: NamedIndividual
field name: StatusEcoH

TempRoomSetpSetShift[4]
has communication mode: LTE
datapoint type major number: 213
datapoint type minor number: 102
subject: TempRoomSetpSetShift[4]
subject: 213.102
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.213.102.i2.TempSetpShiftStdby
is assembled with: type.dpt.field.213.102.i0.TempSetpShiftBProt
is assembled with: type.dpt.field.213.102.i1.TempSetpShiftEco
is assembled with: type.dpt.field.213.102.i3.TempSetpShiftComf
comment: a point representing DPT 213.102: TempRoomSetpSetShift[4]
dpt bit size max: 64

has operation kind
inverse of: isOperationKindOf
comment: To define an operation kind that hosts a pedefined set of tags.
range: Operation Kind
sub property of: hasTagSet
type: ObjectProperty

type.dpt.field.205.100.i1.Temp
field index: 1
field size: 16
field name: Temp
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C
field resolution: 0.02
comment: temperature absolute value °C

type.dpt.field.13.1201.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 32
unit: M3
field resolution: 1.0
includes digit: type.digit.s32
field type: V

MBus BreakerValve State
has communication mode: S
datapoint type major number: 20
description: a point representing DPT 20.1200: MBus BreakerValve State
subject: MBus BreakerValve State
subject: 20.1200
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.20.1200.i0
datapoint type minor number: 1200
dpt bit size max: 8

Up / Down
field type: B
includes KV pair: type.kvpair.1.8.i0.0
includes KV pair: Down = 1
field size: 1
label: Up / Down
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.19.1.i8.NWD
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: type.kvpair.19.1.i8.1
includes KV pair: WD field valid = 0
field default: 1
field type: B
field name: NWD
field index: 8
comment: No WD

Cool Stage B Actuator Fault
subclass of: Function Point
subclass of: Restriction
  on property: has datapoint type
  has value: Bool
type: Class

Off/FrostProtection = 4
value KNX: 4
type: NamedIndividual
value API: offFrostProtection

Restriction
has value: 418
on property: interface object type

type.dpt.field.209.100.i2.SummerMode
field name: SummerMode
includes DPT: Bool
comment: boiler sequence switched off due to local summer/winter mode (mainly used for monitoring)
field index: 2
type: Datapoint Type Field
type: NamedIndividual
field size: 1

Restriction
on property: isComposedByOutput
qualified cardinality: 1

type.dpt.field.ddbc.om.i4.OME
field name: OME
field index: 4
includes DPT field: type.dpt.field.ddbc.ome
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
description: list of operation mode elements
includes counter: type.dpt.field.ddbc.om.i2.OME CNT

Cooling Tower
type: EquipmentType
type: NamedIndividual
description: Equipment to transfer waste heat into the atmosphere. A cooling tower is a device that rejects waste heat to the atmosphere through the cooling of a coolant stream, usually a water stream to a lower temperature.

HVAC Valve Actuator
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Class
subclass of: Restriction
  on class: Overridden
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: ForcedPosition
  on property: isComposedByInput
type: Class
interface object type annotation: 400
subject: HVA
subject: 400
subject: HVAC Valve Actuator

type.dpt.field.19.1.i7.NY
type: Datapoint Type Field
type: NamedIndividual
comment: No Year
field size: 1
field index: 7
field type: B
field name: NY
includes KV pair: Year field not valid = 1
includes KV pair: type.kvpair.19.1.i7.0
field default: 0

StatusWTC
has communication mode: LTE
is assembled with: type.dpt.field.209.103.i0.TempWaterValid
is assembled with: type.dpt.field.209.103.i4.TempWater
is assembled with: type.dpt.field.209.103.i3.Reserved
is assembled with: type.dpt.field.209.103.i1.Fault
is assembled with: type.dpt.field.209.103.i2.CtrlStatus
dpt bit size max: 24
comment: a point representing DPT 209.103: StatusWTC
datapoint type major number: 209
type: DatapointType
type: NamedIndividual
subject: 209.103
subject: StatusWTC
label: StatusWTC
datapoint type minor number: 103

type.dpt.field.225.2.i0.Percent
description: percent
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field name: Percent
field index: 0
includes DPT: scaling

type.dpt.field.251.600.i9.R
field size: 8
comment: Colour Level Red
field index: 9
field type: U
field name: R
type: Datapoint Type Field
type: NamedIndividual
field resolution: 0.3921566
unit: PERCENT
includes digit: type.digit.u8

Restriction
has value: 372
on property: interface object type

is quality kind of
sub property of: is tag set of
domain: QualityKind
type: ObjectProperty

Operation Mode Based Control
subclass of: smartGridCtrl
comment: Application functions for 'operation mode based control'. A facility has various stages in its process cycle that include powering up, regular functioning, transitions, maintenance, and other similar stages. Operation Mode Based Control provides the monitoring actions related to each of these stages.
type: Class

TempRoomSetpSetHeatEff
type: Class
subject: 399.54
subject: 54
subject: TempRoomSetpSetHeatEff
label: TempRoomSetpSetHeatEff
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: has datapoint type
  has value: Room Temperature Setpoint
interface object type annotation: 399
property identifier annotation: 54

type.dpt.field.20.608.i0
type: Datapoint Type Field
type: NamedIndividual
comment: SwitchOnMode
field index: 0
includes KV pair: type.kvpair.20.608.i0.0
includes KV pair: type.kvpair.20.608.i0.2
includes KV pair: type.kvpair.20.608.i0.1
field type: N
field size: 8

Value Volt
has communication mode: S
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
subject: 9.020
subject: 9.20
subject: Value Volt
datapoint type minor number: 20
comment: a point representing DPT 9.020: Value Volt
is assembled with: type.dpt.field.9.20.i0
datapoint type major number: 9

type.dpt.field.14.63.i0
includes digit: type.digit.f32
field resolution: 1.0
description: solid angle
type: Datapoint Type Field
type: NamedIndividual
unit: SR
field index: 0
field size: 32
field type: F

type.dpt.field.pc.i0
includes DPT field: type.dpt.field.pc.i0.ID
includes DPT field: type.dpt.field.pc.i3.LR CNT
includes DPT field: type.dpt.field.pc.i1.CT
includes DPT field: type.dpt.field.pc.i2.START
includes DPT field: type.dpt.field.pc.i4.LR
description: power constraint
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
field index: 0

Converter Test Info
has communication mode: S
description: a point representing DPT 249.600: Converter Test Info
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.249.600.i3.Reserved
is assembled with: type.dpt.field.249.600.i6.TimePeriod
is assembled with: type.dpt.field.249.600.i1.validityOfAbsoluteColourTemperature
is assembled with: type.dpt.field.249.600.i2.validityOfTimePeriod
is assembled with: type.dpt.field.249.600.i4.AbsoluteBrightness
is assembled with: type.dpt.field.249.600.i5.AbsoluteColorTemperature
is assembled with: type.dpt.field.249.600.i0.validityOfAbsoluteBrightness
datapoint type major number: 249
label: Converter Test Info
subject: 249.600
subject: Converter Test Info
datapoint type minor number: 600
dpt bit size max: 48

DeltaTimeMsec
has communication mode: S
subject: DeltaTimeMsec
subject: 8.002
subject: 8.2
type: NamedIndividual
type: DatapointType
label: DeltaTimeMsec
description: a point representing DPT 8.002: DeltaTimeMsec
dpt bit size max: 16
datapoint type minor number: 2
datapoint type major number: 8
is assembled with: type.dpt.field.8.2.i0

type.dpt.field.230.1000.i0.Medium
includes KV pair: Other = 0
includes KV pair: type.kvpair.230.1000.i0.6
includes KV pair: type.kvpair.230.1000.i0.12
includes KV pair: type.kvpair.230.1000.i0.55
includes KV pair: type.kvpair.230.1000.i0.8
includes KV pair: Electricity meter = 2
includes KV pair: type.kvpair.230.1000.i0.33
includes KV pair: type.kvpair.230.1000.i0.40
includes KV pair: type.kvpair.230.1000.i0.13
includes KV pair: type.kvpair.230.1000.i0.1
includes KV pair: Heat meter = 4
includes KV pair: Bus/System = 14
includes KV pair: type.kvpair.230.1000.i0.9
includes KV pair: type.kvpair.230.1000.i0.5
includes KV pair: Cooling Load meter (outlet) = 11
includes KV pair: Garbage = 41
includes KV pair: Unknown Device type = 15
includes KV pair: Gas meter = 3
includes KV pair: type.kvpair.230.1000.i0.10
includes KV pair: Breaker (electricity) = 32
includes KV pair: Water meter = 7
field name: Medium
comment: Medium
field type: N
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.19.1.i9.WD
comment: Working Day
includes KV pair: Working day = 1
includes KV pair: Bank Holiday (No working day) = 0
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field type: B
field name: WD
field index: 9
field default: 0

type.dpt.field.20.1200.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
includes KV pair: type.kvpair.20.1200.i0.3
includes KV pair: Breaker/Valve is released = 2
includes KV pair: type.kvpair.20.1200.i0.1
includes KV pair: Breaker/Valve is closed = 0
field size: 8
field type: N

Restriction
on property: property identifier
has value: 84

output state is On = 1
type: NamedIndividual
value API: outputStateIsOn
value KNX: 1

contains equipment
domain: Location
type: IrreflexiveProperty
type: ObjectProperty
type: AsymmetricProperty
comment: An OP relationship to express a relation to an equipment from a location. This allows to define the presence of a (tangible) equipment, such as a device as part of a location. Mainly it expresses the “assembly place” of an equipment. The here meant location (domain) is the "installation location" of the equipment, also a device. To retrieve the "place of action" of a device it is needed to traverse from a device/datapoint -> functionPoint/application function/../location.
inverse of: isEquipmentOf
range: Equipment

Binary Value
includes KV pair: type.kvpair.1.6.i0.1
includes KV pair: type.kvpair.1.6.i0.0
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: B
label: Binary Value

Battery Info
has communication mode: S
datapoint type major number: 246
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.246.600.i4.Reserved
is assembled with: type.dpt.field.246.600.i1.BatteryFailure
is assembled with: type.dpt.field.246.600.i3.BatteryFullyCharged
is assembled with: type.dpt.field.246.600.i0.BatteryChargeLevel
is assembled with: type.dpt.field.246.600.i2.BatteryDurationFailure
subject: 246.600
subject: Battery Info
description: a point representing DPT 246.600: Battery Info
dpt bit size max: 16
datapoint type minor number: 600

comfort prolongation User not active = 0
value KNX: 0
value API: comfortProlongationUserNotActive
type: NamedIndividual

LightActuatorErrorInfo
has communication mode: S
datapoint type major number: 21
is assembled with: type.dpt.field.21.601.i0.LoadDetectionError
is assembled with: type.dpt.field.21.601.i6.Overheat
is assembled with: type.dpt.field.21.601.i2.Overcurrent
is assembled with: type.dpt.field.21.601.i3.Underload
is assembled with: type.dpt.field.21.601.i4.DefectiveLoad
is assembled with: type.dpt.field.21.601.i7.Reserved
is assembled with: type.dpt.field.21.601.i5.LampFailure
is assembled with: type.dpt.field.21.601.i1.Undervoltage
type: NamedIndividual
type: DatapointType
label: LightActuatorErrorInfo
subject: 21.601
subject: LightActuatorErrorInfo
dpt bit size max: 8
comment: a point representing DPT 21.601: LightActuatorErrorInfo
datapoint type minor number: 601

Lighting
type: Trade
type: NamedIndividual
comment: Lighting or illumination is the deliberate application of light to achieve some aesthetic or practical effect. Lighting includes use of both artificial light sources such as lamps and natural illumination of interiors from daylight.

Setpoint Manager Relative Humidity
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  on class: HumDehumMode
  max qualified cardinality: 1
subclass of: Restriction
  on class: HumRelSetpDehumEff
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Class
is incomplete: true
type: Class
subject: Setpoint Manager Relative Humidity
subject: 103
subject: SMRH
interface object type annotation: 103

rest:
  rest: nil
  first: Restriction
    has value: 100
    on property: interface object type

type.dpt.field.242.600.i1.C
field type: B
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
field size: 1
comment: This field shall indicate whether the colour infor-mation in the fields x-axis and y-axis is valid or not.
type: Datapoint Type Field
type: NamedIndividual
field index: 1
field name: C

WindowStatus
type: Class
interface object type annotation: 398
subclass of: Restriction
  on property: has operation kind
  some values from: Class
subclass of: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq window positionvector room
subject: 398.62
subject: WindowStatus
subject: 62
property identifier annotation: 62

type.dpt.field.207.600.i4.StaircaseLightingFunction
field name: StaircaseLightingFunction
includes DPT: Bool
field index: 4
comment: true = staircase lighting function is active, e.g. via input TimedStartStop.
type: Datapoint Type Field
type: NamedIndividual
field size: 1

type.dpt.field.237.600.i0.DALIAddress
field type: U
field size: 6
comment: DALI Device Address or DALI Group Address
field name: DALIAddress
field index: 0
field resolution: 1.0
includes digit: type.digit.u6
type: Datapoint Type Field
type: NamedIndividual

Door Lock
description: A door lock is a way to secure a door. A lock is a mechanical or electronic fastening device that is released by a physical object such as a key, keycard, fingerprint, RFID card, security token or coin.
type: EquipmentType
type: NamedIndividual

type.dpt.field.14.34.i0
unit: RAD-PER-SEC
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field size: 32
field index: 0
field type: F
comment: frequency, angular (pulsatance)

volume flow, 10 l/min = 69
type: NamedIndividual
value API: volumeFlow,10Lmin
value KNX: 69

Ventilation
comment: Ventilation is the intentional introduction of outdoor air into a space. Ventilation is a mechanical system in a building that brings in fresh outdoor air and removes the contaminated indoor air.
type: NamedIndividual
type: Trade

TempRoomSetpSetCoolShift
type: Class
subject: 63
subject: TempRoomSetpSetCoolShift
subject: 115.63
subclass of: Restriction
  has value: TempRoomSetpSetShift[3]
  on property: has datapoint type
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
  some values from: Class
interface object type annotation: 115
property identifier annotation: 63

Site Segment
subclass of: Location
label: Liegenschaftsteil @de
comment: A site segment subdivides a site, it is usually occupied by a building.
type: Class

New / Unlock (S-SFK) - Not Associated (G3-PLC) = 0
value API: newUnlock(S-SFK)-NotAssociated(G3-P
type: NamedIndividual
value KNX: 0

Restriction
on property: pointName
has value: Relative Set Value Control White

has product
type: FunctionalProperty
type: ObjectProperty
comment: To define a relation to a product from an equipment.
range: Product
inverse of: is product of
domain: Equipment

Fan Speed Current
subclass of: Function Point
type: Class

Lightly cloudy = 3
value API: lightlyCloudy
type: NamedIndividual
value KNX: 3

type.dpt.field.22.1010.i4.ActivationStateOfChannel5
field type: B
field index: 4
comment: Activation state of channel 5
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: The visual effect of channel 5 is inactive = 0
includes KV pair: type.kvpair.22.1010.i4.1
field size: 1
field name: ActivationStateOfChannel5

energy, 0,1 MWh = 128
value KNX: 128
type: NamedIndividual
value API: energy,0,1MWh

type.dpt.field.213.100.i0.TempSetpBProt
field size: 16
field name: TempSetpBProt
unit: DEG C
comment: room temperature setpoint building protection
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767
field index: 0

type.dpt.field.27.1.i17.MaskBitIOO2
comment: Mask Bit Info On Off Output 2
type: NamedIndividual
type: Datapoint Type Field
field size: 1
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B
field name: MaskBitIOO2
field index: 17

type.dpt.field.21.104.i0.Oil
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field name: Oil
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1
comment: Oil
field type: B

Relative Control RGB
has communication mode: S
description: a point representing DPT 254.600: Relative Control RGB
is assembled with: type.dpt.field.254.600.i1.cB
is assembled with: type.dpt.field.254.600.i8.Reserved
is assembled with: type.dpt.field.254.600.i6.StepCodeColourRed
is assembled with: type.dpt.field.254.600.i3.StepCodeColourGreen
is assembled with: type.dpt.field.254.600.i5.Reserved
is assembled with: type.dpt.field.254.600.i7.cR
is assembled with: type.dpt.field.254.600.i2.Reserved
is assembled with: type.dpt.field.254.600.i4.cG
is assembled with: type.dpt.field.254.600.i0.StepCodeColourBlue
type: DatapointType
type: NamedIndividual
dpt bit size max: 24
datapoint type major number: 254
datapoint type minor number: 600
subject: 254.600
subject: Relative Control RGB
label: Relative Control RGB

Off = 0
type: NamedIndividual
is applicable datapoint enum of: Off State
value API: off
value KNX: 0

StatusRoomSetp
has communication mode: S
type: NamedIndividual
type: DatapointType
label: StatusRoomSetp
dpt bit size max: 8
subject: StatusRoomSetp
subject: 20.113
comment: a point representing DPT 20.113: StatusRoomSetp
is assembled with: type.dpt.field.20.113.i0
datapoint type major number: 20
datapoint type minor number: 113

Value Electric FluxDensity
has communication mode: S
description: DPT 14.025: Value of electric flux density
type: DatapointType
type: NamedIndividual
subject: 14.25
subject: Value Electric FluxDensity
subject: 14.025
datapoint type minor number: 25
datapoint type major number: 14
dpt bit size max: 32
is assembled with: type.dpt.field.14.25.i0
label: Value Electric FluxDensity

Room Setpoint Manager Temperature Driven
type: Class
subclass of: Restriction
  on class: Class
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: Class
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByOutput
  on class: Class
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByInput
  on class: ComfortProlongUser
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: TempRoomSetpTariffShift
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  on class: TempRoomSetpUserAbs
  max qualified cardinality: 1
subclass of: Restriction
  on class: TempRoomSetpAbsNext
  max qualified cardinality: 1
  on property: isComposedByInput
is incomplete: true
label: Room Setpoint Manager Temperature Driven
interface object type annotation: 101
subject: 101
subject: RSMTD
subject: Room Setpoint Manager Temperature Driven

trailing edge (resistive - or capacitive load) = 2
value KNX: 2
type: NamedIndividual
value API: trailingEdge(resistive-OrCapacitive

SSSBMode
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
datapoint type minor number: 803
subject: SSSBMode
subject: 20.803
is assembled with: type.dpt.field.20.803.i0
comment: a point representing DPT 20.803: SSSBMode
dpt bit size max: 8

type.dpt.field.14.27.i0
comment: electric potential
field type: F
includes digit: type.digit.f32
field resolution: 1.0
unit: http://qudt.org/vocab/unit/V
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.6.20.i0.f
type: NamedIndividual
type: Datapoint Type Field
field index: 0
includes KV pair: mode 2 is active = 4
includes KV pair: type.kvpair.6.20.i0.1
includes KV pair: mode 1 is active = 2
field name: f
field type: N
field size: 3

type.dpt.field.232.600.i1.G
field index: 1
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field name: G
includes digit: type.digit.u8
field size: 8
comment: G
unit: NUM

type.dpt.field.14.61.i0
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field size: 32
field index: 0
field type: F
unit: OHM-M
comment: resistivity

Restriction
has value: 393
on property: interface object type

type.dpt.field.21.102.i2.TempFlowLimit
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field name: TempFlowLimit
field index: 2
field size: 1
type: Datapoint Type Field
type: NamedIndividual
description: TempFlowLimit
field type: B

type.dpt.field.250.600.i7.cCT
field name: cCT
comment: Increase or decrease the colour temperature.
includes KV pair: type.kvpair.increase
includes KV pair: Decrease = 0
field index: 7
field type: B
field size: 1
type: Datapoint Type Field
type: NamedIndividual

7.x
has communication mode: S
type: NamedIndividual
type: DatapointType
label: 7.x
subject: 7.major
subject: 7.x
dpt bit size max: 16
is assembled with: type.dpt.field.7.x.i0
datapoint type major number: 7

WindowStatus
type: Class
interface object type annotation: 343
subclass of: Class
  intersection of: Datapoint
property identifier annotation: 51
subject: 343.51
subject: WindowStatus
subject: 51

Restriction
has value: one
on property: has cardinality

Energy
type: Quantity Kind
type: NamedIndividual
description: Energy is the quantity characterizing the ability of a system to do work.

Restriction
on property: has cardinality
has value: one

DayNight
has communication mode: S
label: DayNight
is assembled with: Day / Night
type: NamedIndividual
type: DatapointType
subject: 1.024
subject: 1.24
subject: DayNight
datapoint type minor number: 24
comment: a point representing DPT 1.024: DayNight
datapoint type major number: 1
dpt bit size max: 1

has location
range: Location
comment: A relation to a subclass of a location, e.g. a room as spatial sub-location of a floor.
type: AsymmetricProperty
type: IrreflexiveProperty
type: ObjectProperty
type: InverseFunctionalProperty
domain: Location
sub property of: refers to
inverse of: is location of

type.dpt.field.212.100.i0.TempSetpShiftEco
field size: 16
field resolution: 0.02
description: room temperature setpoint shift economy (delta value)
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
unit: http://qudt.org/vocab/unit/K
includes digit: type.digit.s16
field name: TempSetpShiftEco

253.x
has communication mode: S
label: 253.x
is assembled with: type.dpt.field.253.x.i0
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
subject: 253.major
subject: 253.x
datapoint type major number: 253

type.dpt.field.21.102.i6.StatusStopOptim
description: StatusStopOptim
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field name: StatusStopOptim
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 6
field type: B

Tariff
has communication mode: S
description: a point representing DPT 5.006: Tariff
subject: 5.006
subject: 5.6
subject: Tariff
type: NamedIndividual
type: DatapointType
datapoint type major number: 5
is assembled with: type.dpt.field.5.6.i0
dpt bit size max: 8
datapoint type minor number: 6

Restriction
has value: 420
on property: interface object type

type.dpt.field.14.8.i0
description: angular momentum
field type: F
includes digit: type.digit.f32
unit: J-SEC
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.22.102.i2.Overload
field type: B
field index: 2
field size: 1
comment: Overload
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: No alarm = 0
includes KV pair: type.kvpair.alarm
field name: Overload

Actual Dimming Value Green
type: Class
property identifier annotation: 84
subject: 423.84
subject: ASV_G
subject: Actual Dimming Value Green
subject: 84
subclass of: Class
interface object type annotation: 423

User Blinds Control
type: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq slatsactuator positionvector
subclass of: Shading Control
subclass of: Restriction
  has value: qk ph light illuminance
  on property: hasQualityKind
subject: SAB
subject: SSSB
comment: Application function for 'blinds control'.

Restriction
on property: property identifier
has value: 53

TempRoomSetpSetF16[3]
has communication mode: S
is assembled with: type.dpt.field.222.100.i2.TempSetpComf
is assembled with: type.dpt.field.222.100.i1.TempSetpStdby
is assembled with: type.dpt.field.222.100.i0.TempSetpEco
subject: TempRoomSetpSetF16[3]
subject: 222.100
comment: a point representing DPT 222.100: TempRoomSetpSetF16[3]
datapoint type major number: 222
type: NamedIndividual
type: DatapointType
dpt bit size max: 48
datapoint type minor number: 100

SwitchOnOff
type: Class
property identifier annotation: 62
interface object type annotation: 418
subject: 418.62
subject: 62
subject: SwitchOnOff

type.dpt.field.20.13.i0
includes KV pair: type.kvpair.20.13.i0.15
includes KV pair: type.kvpair.20.13.i0.9
includes KV pair: type.kvpair.20.13.i0.18
includes KV pair: 3 h = 22
includes KV pair: 15 s = 6
includes KV pair: type.kvpair.20.13.i0.2
includes KV pair: type.kvpair.20.13.i0.10
includes KV pair: type.kvpair.20.13.i0.20
includes KV pair: type.kvpair.20.13.i0.7
includes KV pair: 1 s = 1
includes KV pair: type.kvpair.20.13.i0.3
includes KV pair: 5 h = 23
includes KV pair: type.kvpair.20.13.i0.14
includes KV pair: type.kvpair.20.13.i0.4
includes KV pair: type.kvpair.20.13.i0.8
includes KV pair: 30 min = 19
includes KV pair: 5 min = 16
includes KV pair: type.kvpair.20.13.i0.5
includes KV pair: type.kvpair.20.13.i0.11
includes KV pair: type.kvpair.20.13.i0.12
includes KV pair: type.kvpair.20.13.i0.0
includes KV pair: 24 h = 25
includes KV pair: type.kvpair.20.13.i0.21
includes KV pair: type.kvpair.20.13.i0.17
includes KV pair: 12 h = 24
includes KV pair: 2 min = 13
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: TimeDelay
field size: 8
field type: N

type.dpt.field.21.1010.i4.ActivationStateOfChannel5
field size: 1
field type: B
field name: ActivationStateOfChannel5
includes KV pair: The visual effect of channel 5 is inactive = 0
includes KV pair: type.kvpair.21.1010.i4.1
field index: 4
comment: Activation state of channel 5
type: Datapoint Type Field
type: NamedIndividual

first: Restriction
  on property: interface object type
  has value: 397
rest: nil

inactive = 0
type: NamedIndividual
value API: inactive
value KNX: 0

Test pending = 2
type: NamedIndividual
value KNX: 2
value API: testPending

type.dpt.field.207.104.i2.ShiftLoadPriority
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 2
comment: shift load priority
field name: ShiftLoadPriority
includes DPT: Bool

on = 1
type: NamedIndividual
value API: on
value KNX: 1

type.dpt.field.18.x.i0
type: Datapoint Type Field
type: NamedIndividual
comment: scene control
field type: A[n]
field index: 0
field size: 8
field string schema: raw

move Up/Down + StepStop mode (blind) = 1
value KNX: 1
type: NamedIndividual
value API: moveUpDown+StepStopMode(blind)

drive is moving = 0
value API: driveIsMoving
type: NamedIndividual
value KNX: 0

type.digit.u8 1 38
type: NamedIndividual
range max: 38
range min: 1

Room Setpoint Manager HVAC-Mode Driven
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: Class
    intersection of: HVACModeUser
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: ComfortProlongEff
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: TempRoomSetpCoolEff
subclass of: Class
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
  on class: HVACModeUser
subclass of: Restriction
  max qualified cardinality: 1
  on class: ComfortProlongUser
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: HVACModeEffNext
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: TempRoomSetpHeatEff
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: Class
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: Class
is incomplete: true
type: Class
label: Room Setpoint Manager HVAC-Mode Driven
subject: 100
subject: RSMHD
subject: Room Setpoint Manager HVAC-Mode Driven
interface object type annotation: 100

NumberedSceneControl
type: Class
subject: 403.61
subject: NSC
subject: NumberedSceneControl
subject: 61
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
property identifier annotation: 61
interface object type annotation: 403

No Rainfall
comment: This state type expresses the state of no heavy rainfall. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of no heavy rainfall, no protection is required and this equipment might be used for shading purposes as intended. This state type is the inverse of the 'Rainfall State' state type.
type: NamedIndividual
type: State Type

Restriction
has value: one
on property: has cardinality

KiloGM
type: Unit
type: NamedIndividual
symbol: kg

hurricane = 12
type: NamedIndividual
value KNX: 12
value API: hurricane

Load Management = 40
type: NamedIndividual
value API: loadManagement
value KNX: 40

type.dpt.field.218.2.i0.StatusCommand
type: Datapoint Type Field
type: NamedIndividual
field index: 0
description: standard Status/Command
field type: Z8
includes DPT: StatusGen
field name: StatusCommand
field size: 8

Restriction
on property: interface object type
has value: 399

The visual effect of channel 7 is inactive = 0
value API: theVisualEffectOfChannel7IsInactive
type: NamedIndividual
value KNX: 0

type.dpt.field.512.503.i1.pei.AC
field name: AC
includes KV pair: abnormal condition
includes KV pair: type.kvpair.NoAbnormalCondition
type: NamedIndividual
type: Datapoint Type Field
field type: B
field size: 1
description: identification if the power envolope refers to an abnormal condition
field index: 1

Value Temp A
has communication mode: S
datapoint type minor number: 3
type: NamedIndividual
type: DatapointType
label: Value Temp A
is assembled with: type.dpt.field.9.3.i0
datapoint type major number: 9
subject: 9.3
subject: 9.003
subject: Value Temp A
comment: a point representing DPT 9.003: Value Temp A
dpt bit size max: 16

WithoutAcknowledge = 1
type: NamedIndividual
value API: withoutAcknowledge
value KNX: 1

type.dpt.field.14.66.i0
field type: F
includes digit: type.digit.f32
field resolution: 1.0
comment: stress
type: Datapoint Type Field
type: NamedIndividual
unit: PA
field index: 0
field size: 32

type.dpt.field.251.600.i8.G
comment: Colour Level Green
field type: U
type: Datapoint Type Field
type: NamedIndividual
field resolution: 0.3921566
field name: G
unit: PERCENT
includes digit: type.digit.u8
field size: 8
field index: 8

target position is reached = 1
value API: targetPositionIsReached
type: NamedIndividual
value KNX: 1

Fan Stage
has communication mode: S
type: NamedIndividual
type: DatapointType
datapoint type major number: 5
comment: a point representing DPT 5.100: Fan Stage
dpt bit size max: 8
label: Fan Stage
subject: 5.100
subject: Fan Stage
is assembled with: type.dpt.field.5.100.i0
datapoint type minor number: 100

type.dpt.field.20.122.i0
includes KV pair: Position unchanged = 0
includes KV pair: type.kvpair.20.122.i0.1
includes KV pair: type.kvpair.20.122.i0.2
field type: N
description: StartSynchronization
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.265.5.i2.DateAndTime
field index: 2
field size: 64
type: Datapoint Type Field
type: NamedIndividual
includes DPT: DateTime
description: Date and Time
field name: DateAndTime

type.dpt.field.22.101.i10.StatusPreCool
type: NamedIndividual
type: Datapoint Type Field
field name: StatusPreCool
field size: 1
field index: 10
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
description: StatusPreCool
field type: B

Actuator
comment: Used to control a (generic) actuator equipment. Don't care if the (generic functionality) is internally operated from the actuator by a motor or other means.
type: NamedIndividual
type: EquipmentType

type.dpt.field.512.505.i1.ps.SLT CNT
field index: 1
includes digit: type.digit.u4 1 15
field type: U
field name: SLT_CNT
type: Datapoint Type Field
type: NamedIndividual
description: Number of power sequence slots
field size: 4

Version
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: Version
subject: 217.1
subject: 217.001
datapoint type major number: 217
datapoint type minor number: 1
description: a point representing DPT 217.001: Version
label: Version
dpt bit size max: 16
is assembled with: type.dpt.field.217.1.i2.MagicNumber
is assembled with: type.dpt.field.217.1.i0.RevisionNumber
is assembled with: type.dpt.field.217.1.i1.VersionNumber

energy, 1 GJ = 137
value KNX: 137
type: NamedIndividual
value API: energy,1GJ

type.dpt.field.21.104.i2.SolidState
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 2
field size: 1
field name: SolidState
comment: SolidState

Room Temperature Setpoint
has communication mode: S
type: NamedIndividual
type: DatapointType
dpt bit size max: 64
label: Room Temperature Setpoint
subject: 275.100
subject: Room Temperature Setpoint
is assembled with: type.dpt.field.275.100.i2.TempSetpStdby
is assembled with: type.dpt.field.275.100.i3.TempSetpComf
is assembled with: type.dpt.field.275.100.i0.TempSetpBProt
is assembled with: type.dpt.field.275.100.i1.TempSetpEco
datapoint type major number: 275
comment: a point representing DPT 275.100: TempRoomSetpSetF16[4]
datapoint type minor number: 100

Restriction
has value: Absolute Set Value Control Blue
on property: pointName

MicroGM-PER-M3
symbol: μg/m³
type: Unit
type: NamedIndividual

type.dpt.field.219.1.i0.InAlarm
field size: 1
field name: InAlarm
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: B
comment: InAlarm

Restriction
on property: property identifier
has value: 52

emLimitRange
datapoint type major number: 517
is assembled with: type.dpt.field.517.500.i4.lr.Reserved
is assembled with: type.dpt.field.517.500.i0.lr.RANGE
is assembled with: type.dpt.field.517.500.i3.lr.AC
is assembled with: type.dpt.field.517.500.i1.lr.CQ
is assembled with: type.dpt.field.517.500.i2.lr.LT
datapoint type minor number: 500
description: limit range
type: NamedIndividual
type: DatapointType
dpt bit size max: 48

BlinkingWithAcknowledge = 2
value KNX: 2
type: NamedIndividual
value API: blinkingWithAcknowledge

N-M
symbol: N⋅m
type: NamedIndividual
type: Unit

function point data
type: DatatypeProperty
domain: Function Point
comment: A parent data property, used to express any kind of generic data that relates to a function point.

TempRoomSetpUserAbs
type: Class
property identifier annotation: 51
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subject: 384.51
subject: 51
subject: TempRoomSetpUserAbs
label: TempRoomSetpUserAbs
interface object type annotation: 384

type.dpt.field.21.107.i0.WindowStatusEffective
type: Datapoint Type Field
type: NamedIndividual
comment: Effective value of the window status
field index: 0
includes KV pair: at least one window opened = 1
includes KV pair: all windows closed = 0
field type: B
field size: 1
field name: WindowStatusEffective

Restriction
has value: ActCurrPosHeatStageA
on property: pointName

Restriction
on property: property identifier
has value: 51

type.dpt.field.21.100.i4.DHWNorm
type: Datapoint Type Field
type: NamedIndividual
field name: DHWNorm
description: DHWNorm
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 4
field size: 1

HVACModeAct
type: Class
interface object type annotation: 257
subclass of: Restriction
  on property: has operation kind
subject: 152
subject: 257.152
subject: HVACModeAct
property identifier annotation: 152

type.dpt.field.243.x.i0
field size: 64
field string schema: raw
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
comment: colour transition xyY
field index: 0

ShutterBlinds Mode
has communication mode: S
subject: 1.23
subject: 1.023
subject: ShutterBlinds Mode
comment: a point representing DPT 1.023: ShutterBlinds Mode
type: DatapointType
type: NamedIndividual
datapoint type minor number: 23
datapoint type major number: 1
is assembled with: Shutter and Blinds Mode
dpt bit size max: 1

Restriction
on data range: boolean
max qualified cardinality: 1
on property: writable

Value Mass
has communication mode: S
subject: 14.051
subject: Value Mass
subject: 14.51
datapoint type major number: 14
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
datapoint type minor number: 51
is assembled with: type.dpt.field.14.51.i0
label: Value Mass
comment: DPT 14.051: Value of mass

type.dpt.field.250.600.i1.ColourStepValidity
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
type: NamedIndividual
type: Datapoint Type Field
field type: B
field name: ColourStepValidity
comment: CCT and Step Code Colour Validity
field index: 1
field size: 1

TempRoomSetpSet[4]
has communication mode: LTE
subject: 213.100
subject: TempRoomSetpSet[4]
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.213.100.i3.TempSetpComf
is assembled with: type.dpt.field.213.100.i2.TempSetpStdby
is assembled with: type.dpt.field.213.100.i0.TempSetpBProt
is assembled with: type.dpt.field.213.100.i1.TempSetpEco
label: TempRoomSetpSet[4]
datapoint type minor number: 100
dpt bit size max: 64
datapoint type major number: 213
description: a point representing DPT 213.100: TempRoomSetpSet[4]

Value SolidAngle
has communication mode: S
label: Value SolidAngle
type: DatapointType
type: NamedIndividual
subject: Value SolidAngle
subject: 14.063
subject: 14.63
datapoint type minor number: 63
is assembled with: type.dpt.field.14.63.i0
dpt bit size max: 32
comment: DPT 14.063: Value of solid angle
datapoint type major number: 14

StatusGen
has communication mode: S
is assembled with: type.dpt.field.21.1.i2.Overridden
is assembled with: type.dpt.field.21.1.i4.AlarmUnAck
is assembled with: type.dpt.field.21.1.i1.Fault
is assembled with: type.dpt.field.21.1.i3.InAlarm
is assembled with: type.dpt.field.21.1.i5.Reserved
is assembled with: type.dpt.field.21.1.i0.OutOfService
datapoint type major number: 21
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
dpt bit size max: 8
subject: StatusGen
subject: 21.1
subject: 21.001
description: a point representing DPT 21.001: StatusGen
label: StatusGen

type.dpt.field.512.502.i0.pe.ID
type: Datapoint Type Field
type: NamedIndividual
field size: 4
includes digit: type.digit.u4
field index: 0
description: power envelope identifier
field name: ID
field type: U

type.dpt.field.254.600.i4.cG
field name: cG
field type: B
field size: 1
field index: 4
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
comment: Shall specify whether the colour component green shall be increased or decreased.
type: Datapoint Type Field
type: NamedIndividual

Staircase Lighting
subclass of: Restriction
  qualified cardinality: 1
  on class: Staircase Switch Request
  on property: has function point
subclass of: Restriction
  on class: Staircase Trigger Request
  on property: has function point
  qualified cardinality: 1
subclass of: lightingCtrl
comment: A user operated staircase light switch/trigger request including an explicit status.
type: Class
subject: LSAB

Value Resistance
has communication mode: S
subject: Value Resistance
subject: 14.060
subject: 14.60
datapoint type major number: 14
datapoint type minor number: 60
dpt bit size max: 32
comment: DPT 14.060: Value of resistance
type: NamedIndividual
type: DatapointType
label: Value Resistance
is assembled with: type.dpt.field.14.60.i0

type.dpt.field.523.500.i1.sms.ET
field index: 1
field name: ET
field size: 64
type: Datapoint Type Field
type: NamedIndividual
includes DPT: DateTime
description: timestamp when last transition was executed

type.dpt.field.238.1.i2.StorageFunction
comment: The field Storage function shall indicate whether the set value(s) for the scene number SN can be modified at runtime through DPT_SceneControl or not.
field size: 1
field type: B
field name: StorageFunction
includes KV pair: type.kvpair.238.1.i2.1
includes KV pair: enable = 0
field index: 2
type: Datapoint Type Field
type: NamedIndividual

error = 1
value KNX: 1
value API: error
type: NamedIndividual

alternative setpoint = 1
value KNX: 1
value API: alternativeSetpoint
type: NamedIndividual

Speaker
type: EquipmentType
type: NamedIndividual
description: A loudspeaker (commonly referred to as a speaker or speaker driver) is one type of electroacoustic transducer, that is, a device that converts an electrical audio signal into a corresponding sound.

TIC Type
has communication mode: S
comment: a point representing DPT 20.1208: TIC Type
datapoint type major number: 20
subject: TIC Type
subject: 20.1208
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1208
label: TIC Type
dpt bit size max: 8
is assembled with: type.dpt.field.20.1208.i0

type.dpt.field.519.500.i2.tran.FROM
field size: 4
type: NamedIndividual
type: Datapoint Type Field
description: operation mode id the transition starts from
includes digit: type.digit.u4 1 15
field name: FROM
field type: U
field index: 2

Test = 7
value KNX: 7
type: NamedIndividual
value API: test

type.dpt.field.246.600.i1.BatteryFailure
field type: B
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field name: BatteryFailure
field index: 1
comment: Battery Failure
type: Datapoint Type Field
type: NamedIndividual
field size: 1

Switch Current Status
type: Class
subclass of: Function Point
subclass of: Restriction
  on property: has datapoint type
  has value: switch

HumRelSetpUser
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: relValueZ
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air relativehumidity room
interface object type annotation: 388
property identifier annotation: 51
subject: HumRelSetpUser
subject: 51
subject: 388.51

Request Converter Info = 7
type: NamedIndividual
value API: requestConverterInfo
value KNX: 7

Air Humidity Control
type: Class
subclass of: Air Control
comment: Application functions that controls the quantity 'air humidity'.

Frost Sensor
type: Class
subject: 804
subject: FS
subject: Frost Sensor
interface object type annotation: 804

rest:
  first: N
first: F

type.dpt.field.249.600.i3.Reserved
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field index: 3
field size: 5

type.dpt.field.521.500.i1.ts.DUR
type: Datapoint Type Field
type: NamedIndividual
field name: DUR
description: estimated time that the timer needs once it has been started
includes DPT: TimePeriodSec
field index: 1
field size: 16

DimmPBModel
has communication mode: S
description: a point representing DPT 20.607: DimmPBModel
datapoint type minor number: 607
subject: DimmPBModel
subject: 20.607
dpt bit size max: 8
is assembled with: type.dpt.field.20.607.i0
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
label: DimmPBModel

Space
comment: A generic functional subdivison of a location, which represents any physical space that belongs to a building.
type: Locality
type: NamedIndividual

type.dpt.field.22.1010.i12.ActivationStateOfChannel13
field size: 1
field name: ActivationStateOfChannel13
field index: 12
comment: Activation state of channel 13
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: The visual effect of channel 13 is inactive = 0
includes KV pair: The visual effect of channel 13 is active = 1
field type: B

WindAlarm
type: Class
interface object type annotation: 802
subject: 51
subject: WindAlarm
subject: 802.51
label: WindAlarm
property identifier annotation: 51
subclass of: Class

type.dpt.field.241.800.i13.ValidSlatsPos
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field size: 1
field name: ValidSlatsPos
description: Validity slats pos.
type: Datapoint Type Field
type: NamedIndividual
field index: 13
field type: B

LED, trailing = 8
value KNX: 8
value API: lED,Trailing
type: NamedIndividual

Light Relative Dimming Request
subclass of: Function Point
subclass of: Restriction
  on property: has operation kind
  on class: Class
  qualified cardinality: 1
type: Class

Step Code
field type: N
includes KV pair: type.kvpair.stepcode.2
includes KV pair: 100% = 7
includes KV pair: type.kvpair.stepcode.5
includes KV pair: 42% = 3
includes KV pair: type.kvpair.stepcode.1
includes KV pair: type.kvpair.stepcode.6
includes KV pair: 56% = 4
includes KV pair: Break = 0
label: Step Code
type: Datapoint Type Field
type: NamedIndividual
field name: StepCode
comment: The number of intervals into which the range of 0 % … 100 % is subdivided, or the break indication.
field default: 4
field index: 0
field size: 3

Value Pressure
has communication mode: S
subject: 14.058
subject: Value Pressure
subject: 14.58
type: DatapointType
type: NamedIndividual
comment: DPT 14.058: Value of pressure
datapoint type minor number: 58
label: Value Pressure
datapoint type major number: 14
dpt bit size max: 32
is assembled with: type.dpt.field.14.58.i0

The visual effect of channel 16 is active = 1
value API: theVisualEffectOfChannel16IsActive
type: NamedIndividual
value KNX: 1

type.dpt.field.14.11.i0
field index: 0
field size: 32
field type: F
unit: FARAD
comment: capacitance
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.frbc.ome.i0.PR
type: Datapoint Type Field
type: NamedIndividual
includes DPT: emPowerRange
field index: 0
field name: PR
field size: 32
description: power range

Restriction
has value: one
on property: has cardinality

Ramp Control
has communication mode: S
subject: 2.4
subject: Ramp Control
subject: 2.004
type: DatapointType
type: NamedIndividual
description: a point representing DPT 2.004: Ramp Control
label: Ramp Control
datapoint type major number: 2
dpt bit size max: 2
is assembled with: type.dpt.field.2.4.i0.ramp
is assembled with: c
datapoint type minor number: 4

type.dpt.field.234.2.i0.Character2
field name: Character2
includes DPT: Char ASCII
description: second character of RegionCode, ASCII-coded
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

SABExceptBehaviour
has communication mode: S
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
label: SABExceptBehaviour
is assembled with: type.dpt.field.20.801.i0
datapoint type major number: 20
subject: SABExceptBehaviour
subject: 20.801
comment: a point representing DPT 20.801: SABExceptBehaviour
datapoint type minor number: 801

type.dpt.field.9.x.i0
includes digit: type.digit.f16
field size: 16
comment: 2-byte float value
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: F

CombinedInfoOnOff
has communication mode: S
is assembled with: type.dpt.field.27.1.i8.IOO9
is assembled with: type.dpt.field.27.1.i5.IOO6
is assembled with: type.dpt.field.27.1.i15.IOO16
is assembled with: type.dpt.field.27.1.i10.IOO11
is assembled with: type.dpt.field.27.1.i30.MaskBitIOO15
is assembled with: type.dpt.field.27.1.i3.IOO4
is assembled with: type.dpt.field.27.1.i27.MaskBitIOO12
is assembled with: type.dpt.field.27.1.i19.MaskBitIOO4
is assembled with: type.dpt.field.27.1.i28.MaskBitIOO13
is assembled with: type.dpt.field.27.1.i16.MaskBitIOO1
is assembled with: type.dpt.field.27.1.i7.IOO8
is assembled with: type.dpt.field.27.1.i1.IOO2
is assembled with: type.dpt.field.27.1.i14.IOO15
is assembled with: type.dpt.field.27.1.i29.MaskBitIOO14
is assembled with: type.dpt.field.27.1.i23.MaskBitIOO8
is assembled with: type.dpt.field.27.1.i0.IOO1
is assembled with: type.dpt.field.27.1.i12.IOO13
is assembled with: type.dpt.field.27.1.i22.MaskBitIOO7
is assembled with: type.dpt.field.27.1.i31.MaskBitIOO16
is assembled with: type.dpt.field.27.1.i20.MaskBitIOO5
is assembled with: type.dpt.field.27.1.i11.IOO12
is assembled with: type.dpt.field.27.1.i6.IOO7
is assembled with: type.dpt.field.27.1.i4.IOO5
is assembled with: type.dpt.field.27.1.i13.IOO14
is assembled with: type.dpt.field.27.1.i26.MaskBitIOO11
is assembled with: type.dpt.field.27.1.i21.MaskBitIOO6
is assembled with: type.dpt.field.27.1.i17.MaskBitIOO2
is assembled with: type.dpt.field.27.1.i18.MaskBitIOO3
is assembled with: type.dpt.field.27.1.i25.MaskBitIOO10
is assembled with: type.dpt.field.27.1.i24.MaskBitIOO9
is assembled with: type.dpt.field.27.1.i9.IOO10
is assembled with: type.dpt.field.27.1.i2.IOO3
comment: a point representing DPT 27.001: CombinedInfoOnOff
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
label: CombinedInfoOnOff
datapoint type minor number: 1
datapoint type major number: 27
subject: CombinedInfoOnOff
subject: 27.1
subject: 27.001

type.dpt.field.252.600.i12.cG
description: Shall specify whether the colour component green shall be increased or decreased.
field index: 12
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
field name: cG
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field type: B

Restriction
on property: interface object type
has value: 397

type.dpt.field.242.600.i0.B
description: This field shall indicate whether the Brightness information in the field Brightness is valid or not.
field type: B
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
type: Datapoint Type Field
type: NamedIndividual
field name: B
field index: 0
field size: 1

Restriction
has value: 71
on property: property identifier

type.dpt.field.219.1.i8.Reserved
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 4
field index: 8
field type: r

type.dpt.field.512.505.i7.ps.SLT
field type: D<n>
field index: 7
includes DPT: emPowerSequenceSlot
field name: SLT
includes counter: type.dpt.field.512.505.i1.ps.SLT CNT
type: Datapoint Type Field
type: NamedIndividual
description: List of power sequence slots

Colour_Relative Control_RGB
type: Class
subject: 423.53
subject: RC_RGB
subject: 53
subject: Colour_Relative Control_RGB
property identifier annotation: 53
interface object type annotation: 423
label: Colour_Relative Control_RGB

Alarm = 1
value KNX: 1
value API: alarm
type: NamedIndividual

S-PER-M
symbol: S/m
type: NamedIndividual
type: Unit

type.dpt.field.22.101.i2.TempFlowLimit
field index: 2
field size: 1
type: Datapoint Type Field
type: NamedIndividual
comment: TempFlowLimit
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field name: TempFlowLimit

type.dpt.field.256.1.i1.StartDateTime
field index: 1
field name: StartDateTime
type: Datapoint Type Field
type: NamedIndividual
includes DPT: DateTime
comment: Start Date Time
field size: 64

type.dpt.field.213.102.i2.TempSetpShiftStdby
field size: 16
field type: V
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
unit: http://qudt.org/vocab/unit/K
comment: room temperature setpoint shift standby (delta value)
field name: TempSetpShiftStdby
includes digit: type.digit.s16
field index: 2

Cooling Load meter (outlet) = 11
value API: coolingLoadMeter(outlet)
type: NamedIndividual
value KNX: 11

Restriction
on class: Class
on property: has operation kind
qualified cardinality: 1

SwitchHeat
type: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
property identifier annotation: 59
subject: SwitchHeat
subject: 399.59
subject: 59
interface object type annotation: 399

Restriction
on property: property identifier
has value: 52

ChangeOverStatus
type: Class
subject: ChangeOverStatus
subject: 399.64
subject: 64
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph water temperature pipesection supplysection
property identifier annotation: 64
interface object type annotation: 399

SNMP
type: NamedIndividual
type: Protocol

type.dpt.field.206.105.i0.BuildingMode
type: Datapoint Type Field
type: NamedIndividual
field name: BuildingMode
comment: building mode
field index: 0
includes KV pair: type.kvpair.206.105.i0.0
includes KV pair: Building not in use = 1
includes KV pair: Building protected = 2
field type: N
field size: 8

235.x
has communication mode: S
label: 235.x
datapoint type major number: 235
subject: 235.major
subject: 235.x
type: NamedIndividual
type: DatapointType
dpt bit size max: 48
is assembled with: type.dpt.field.235.x.i0

type.dpt.field.206.104.i0.OccMode
includes KV pair: Not occupied = 2
includes KV pair: Standby = 1
includes KV pair: type.kvpair.206.104.i0.0
field index: 0
comment: occupancy mode
field size: 8
field name: OccMode
field type: N
type: Datapoint Type Field
type: NamedIndividual

ControlModeUser
type: Class
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
interface object type annotation: 418
property identifier annotation: 74
subject: 74
subject: ControlModeUser
subject: 418.74

Power Profile Based Control
type: Class
comment: Power profiles are configurations that set the energy consumption levels of equipment and systems to achieve a defined goal. Some examples of power profiles can be “Maximize output”, “Minimize energy consumption” or any custom level of performance.
subclass of: smartGridCtrl

Switch OnOff
type: Class
subject: Switch OnOff
subject: SOO
subject: 414.51
subject: 51
label: Switch OnOff
interface object type annotation: 414
property identifier annotation: 51

Datapoint
subclass of: Restriction
  on property: has communication mode
subclass of: Restriction
  on property: pointName
  all values from: string
subclass of: Point
subclass of: Restriction
  max qualified cardinality: 1
  on property: interface object type
  on data range: unsignedShort
subclass of: Restriction
  all values from: Trade
  on property: operates for trade
comment: A Datapoint exposes an internal state of a device that can be directly accessed (read) and optionally manipulated (write).
type: Class

type.dpt.field.21.106.i3.Cool
comment: Cool
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field index: 3
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: Cool

power, 100 kJ/h = 53
type: NamedIndividual
value API: power,100KJh
value KNX: 53

TempRoomSetpSetCoolEff
type: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air temperature room
subclass of: Restriction
  on property: has datapoint type
  has value: Room Temperature Setpoint
label: TempRoomSetpSetCoolEff
property identifier annotation: 55
subject: 399.55
subject: 55
subject: TempRoomSetpSetCoolEff
interface object type annotation: 399

type.dpt.field.20.610.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes KV pair: type.kvpair.20.610.i0.7
includes KV pair: type.kvpair.20.610.i0.2
includes KV pair: type.kvpair.20.610.i0.5
includes KV pair: type.kvpair.20.610.i0.4
includes KV pair: type.kvpair.20.610.i0.0
includes KV pair: type.kvpair.20.610.i0.1
includes KV pair: type.kvpair.20.610.i0.6
includes KV pair: detection not possible or error = 3
includes KV pair: LED, trailing = 8
field size: 8
field type: N
comment: LoadTypeDetected

type.dpt.field.519.500.i4.tran.ID
type: Datapoint Type Field
type: NamedIndividual
field name: ID
field size: 4
field index: 4
includes digit: type.digit.u4 1 15
field type: U
description: identifier of the transtion

type.dpt.field.525.500.i0.fv.VAL LIM
type: Datapoint Type Field
type: NamedIndividual
field index: 0
description: Limit values are valid
includes KV pair: no = 0
includes KV pair: type.kvpair.yes
field type: B
field size: 1
field name: VAL_LIM

Basement
type: NamedIndividual
type: LocationUsage
comment: A basement or cellar is one or more floors of a building that are completely or partly below the ground floor.

HVAC Contr Mode Z
has communication mode: LTE
subject: 201.104
subject: HVAC Contr Mode Z
is assembled with: type.dpt.field.201.104.i1.HVACContrMode
is assembled with: type.dpt.field.201.104.i0.StatusCommand
type: DatapointType
type: NamedIndividual
label: HVAC Contr Mode Z
datapoint type minor number: 104
datapoint type major number: 201
description: a point representing DPT 201.104: HVAC Contr Mode Z
dpt bit size max: 16

alarm position is UP = 1
type: NamedIndividual
value API: alarmPositionIsUP
value KNX: 1

User HVAC Room Settings
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: Class
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: Class
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Restriction
  on class: TempRoomSetpSetHeat
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on class: ComfortProlongEff
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  on class: WindowStatusEff
  max qualified cardinality: 1
subclass of: Restriction
  on class: TempRoomSetpSetCool
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: dpa.397.63
subclass of: Restriction
  on class: dpa.397.59
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
  on class: HVACModeUserEff
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
  on class: dpa.397.61
type: Class
subject: 397
subject: UHRS
subject: User HVAC Room Settings
label: User HVAC Room Settings
interface object type annotation: 397

Movement Detector for Lighting
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: Class
subclass of: Restriction
  on property: isComposedByInput
  on class: Info OnOff
  max qualified cardinality: 1
type: Class
subject: Movement Detector for Lighting
subject: MDL
subject: 414
interface object type annotation: 414

232.x
has communication mode: S
subject: 232.major
subject: 232.x
type: DatapointType
type: NamedIndividual
dpt bit size max: 24
is assembled with: type.dpt.field.232.x.i0
datapoint type major number: 232

type.dpt.field.14.3.i0
type: NamedIndividual
type: Datapoint Type Field
comment: activity (radioactivity)
field index: 0
field size: 32
unit: PER-SEC
field type: F
includes digit: type.digit.f32
field resolution: 1.0

StatusRHCC
has communication mode: S
comment: a point representing DPT 22.101: StatusRHCC
is assembled with: type.dpt.field.22.101.i9.StatusEcoC
is assembled with: type.dpt.field.22.101.i14.OverheatAlarm
is assembled with: type.dpt.field.22.101.i7.HeatingDisabled
is assembled with: type.dpt.field.22.101.i8.HeatCoolMode
is assembled with: type.dpt.field.22.101.i15.Reserved
is assembled with: type.dpt.field.22.101.i6.StatusStopOptim
is assembled with: type.dpt.field.22.101.i3.TempReturnLimit
is assembled with: type.dpt.field.22.101.i1.StatusEcoH
is assembled with: type.dpt.field.22.101.i5.StatusStartOptim
is assembled with: type.dpt.field.22.101.i2.TempFlowLimit
is assembled with: type.dpt.field.22.101.i0.Fault
is assembled with: type.dpt.field.22.101.i11.CoolingDisabled
is assembled with: type.dpt.field.22.101.i4.StatusMorningBoostH
is assembled with: type.dpt.field.22.101.i12.DewPointStatus
is assembled with: type.dpt.field.22.101.i10.StatusPreCool
is assembled with: type.dpt.field.22.101.i13.FrostAlarm
type: NamedIndividual
type: DatapointType
subject: 22.101
subject: StatusRHCC
dpt bit size max: 16
label: StatusRHCC
datapoint type major number: 22
datapoint type minor number: 101

type.dpt.field.22.1000.i2.PL110
field name: PL110
type: Datapoint Type Field
type: NamedIndividual
field size: 1
comment: PL110
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 2

type.dpt.field.14.35.i0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: F
comment: heat capacity
unit: J-PER-K
includes digit: type.digit.f32
field resolution: 1.0

Emission Control
subclass of: energyCtrl
comment: A specific Application Function to optimize different energy consumers. An emissionCtrl is an energy saving Application Functions and routines based on the actual use of a building (space), depending on real user needs, to avoid unnecessary energy use and CO2 emissions.
type: Class

Restriction
on property: interface object type
has value: 388

no failure = 0
value KNX: 0
type: NamedIndividual
value API: noFailure

energy, 1000 Wh = 6
value API: energy,1000Wh
type: NamedIndividual
value KNX: 6

volume flow, 10000 l/h = 63
value KNX: 63
type: NamedIndividual
value API: volumeFlow,10000Lh

ComfortProlongUser
type: Class
subject: ComfortProlongUser
subject: 54
subject: 398.54
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 398
property identifier annotation: 54

Blinds Actuator
type: NamedIndividual
type: EquipmentType
description: Used to control an actuator equipment to regulate the light incidence (blinds or shutter position). Don't care if the blinds position is internally operated from the actuator by a motor or other means.

type.dpt.field.201.104.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: StatusCommand
field type: Z8
field size: 8
comment: standard Status/Command
includes DPT: StatusGen

56% = 4
value API: 56%
value KNX: 4
type: NamedIndividual

emDemandRateRange
dpt bit size max: 32
is assembled with: type.dpt.field.516.501.i0.drr.LV
is assembled with: type.dpt.field.516.501.i1.drr.UV
description: demand rate range
datapoint type major number: 516
type: NamedIndividual
type: DatapointType
datapoint type minor number: 501

type.dpt.field.241.800.i15.HeightPosition
comment: Height Position
field type: U
field size: 8
field index: 15
type: Datapoint Type Field
type: NamedIndividual
field resolution: 0.3921566
unit: PERCENT
includes digit: type.digit.u8
field name: HeightPosition

ActCurrPosHeatStageA
type: Class
interface object type annotation: 399
subject: 66
subject: 399.66
subject: ActCurrPosHeatStageA
subclass of: Restriction
  has value: scaling
  on property: has datapoint type
label: ActCurrPosHeatStageA
property identifier annotation: 66

AHU Control
comment: An Air Handling Unit (AHU) is an Application Function that controls equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system. An AHU Application Function has usually subfunctions such as fanCtrl, pumpCtrl etc.
subclass of: equipmentCtrl
type: Class

leading edge (inductive load) = 1
value API: leadingEdge(inductiveLoad)
value KNX: 1
type: NamedIndividual

Bool
label: Bool
includes DPT: Bool
field size: 1
field name: bool
type: Datapoint Type Field
type: NamedIndividual
field index: 0

Value Phase AngleRad
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type minor number: 54
datapoint type major number: 14
label: Value Phase AngleRad
subject: 14.054
subject: 14.54
subject: Value Phase AngleRad
is assembled with: type.dpt.field.14.54.i0
dpt bit size max: 32
comment: DPT 14.054: Value of phase angle (in radiant)

HVAC Mode Z
has communication mode: LTE
subject: HVAC Mode Z
subject: 201.100
datapoint type minor number: 100
is assembled with: type.dpt.field.201.100.i1.HVACMode
is assembled with: type.dpt.field.201.100.i0.StatusCommand
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 201.100: HVAC Mode Z
dpt bit size max: 16
datapoint type major number: 201

Behaviour Bus Power Up Down
has communication mode: S
label: Behaviour Bus Power Up Down
description: a point representing DPT 20.601: Behaviour Bus Power Up Down
type: NamedIndividual
type: DatapointType
datapoint type major number: 20
subject: Behaviour Bus Power Up Down
subject: 20.601
dpt bit size max: 8
is assembled with: type.dpt.field.20.601.i0
datapoint type minor number: 601

Value Weight
has communication mode: S
is assembled with: type.dpt.field.14.78.i0
type: NamedIndividual
type: DatapointType
description: DPT 14.078: Value of weight
subject: Value Weight
subject: 14.078
subject: 14.78
datapoint type minor number: 78
datapoint type major number: 14
dpt bit size max: 32

field resolution
comment: Field resolution, a factor for the value range of a KNX data field as part of an entire datapoint type.
type: DatatypeProperty
type: FunctionalProperty
range: float
sub property of: datapointTypeDataField

Current Colour RGB
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: Colour RGB
  on property: has datapoint type
subject: CC_RGB
subject: 423.81
subject: Current Colour RGB
subject: 81
property identifier annotation: 81
interface object type annotation: 423

type.dpt.field.14.26.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
unit: C-PER-M2
field size: 32
field type: F
comment: electric polarization
includes digit: type.digit.f32
field resolution: 1.0

Heating-Cooling Stages Both
type: State Type
type: NamedIndividual
description: This state type relates to both primary and secondary stages of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.

Value Absolute Temperature
has communication mode: S
datapoint type minor number: 69
type: NamedIndividual
type: DatapointType
subject: 14.69
subject: 14.069
subject: Value Absolute Temperature
comment: DPT 14.069: Value of absolute temperature
is assembled with: type.dpt.field.14.69.i0
datapoint type major number: 14
dpt bit size max: 32

Relative Set Value Control Red
type: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subject: Relative Set Value Control Red
subject: 423.57
subject: 57
subject: RSC_R
interface object type annotation: 423
property identifier annotation: 57

type.dpt.field.245.x.i0
comment: Converter test result
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field size: 48
field string schema: raw

CoAP
type: NamedIndividual
type: Protocol

Value Thermal Capacity
has communication mode: S
datapoint type major number: 14
subject: Value Thermal Capacity
subject: 14.071
subject: 14.71
dpt bit size max: 32
comment: DPT 14.071: Value of thermal capacity
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.14.71.i0
label: Value Thermal Capacity
datapoint type minor number: 71

Restriction
on property: pointName
has value: TimedStartStop

ActiveEnergy V64
has communication mode: S
dpt bit size max: 64
is assembled with: type.dpt.field.29.10.i0
subject: ActiveEnergy V64
subject: 29.10
subject: 29.010
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 29.010: ActiveEnergy V64
datapoint type minor number: 10
datapoint type major number: 29
label: ActiveEnergy V64

Logical Function
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: Logical Function
subject: 1.21
subject: 1.021
comment: a point representing DPT 1.021: Logical Function
dpt bit size max: 1
is assembled with: Logical Function
datapoint type minor number: 21
datapoint type major number: 1
label: Logical Function

BlinkingMode
has communication mode: S
description: a point representing DPT 20.603: BlinkingMode
type: NamedIndividual
type: DatapointType
datapoint type minor number: 603
subject: BlinkingMode
subject: 20.603
dpt bit size max: 8
label: BlinkingMode
datapoint type major number: 20
is assembled with: type.dpt.field.20.603.i0

Off = 6
value KNX: 6
value API: off
type: NamedIndividual

Switch
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: Off = 0
includes KV pair: On = 1
field index: 0
field type: B
field size: 1
label: Switch

first: Restriction
  has value: TempRoomSetpUserOffsetEff
  on property: pointName

http://qudt.org/vocab/unit/T
type: NamedIndividual
type: Unit
symbol: T

HVAC relative Temperature
has communication mode: LTE
is assembled with: type.dpt.field.205.101.i1.Temp
is assembled with: type.dpt.field.205.101.i0.StatusCommand
datapoint type minor number: 101
datapoint type major number: 205
subject: HVAC relative Temperature
subject: 205.101
type: DatapointType
type: NamedIndividual
dpt bit size max: 24
comment: a point representing DPT 205.101: TempHVACRel_Z
label: HVAC relative Temperature

type.dpt.field.209.102.i2.Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 4
field name: Reserved
field index: 4

type.dpt.field.14.38.i0
field size: 32
field type: F
comment: impedance
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
unit: OHM

Geographical Location
has communication mode: S
datapoint type minor number: 1
subject: 255.1
subject: 255.001
subject: Geographical Location
is assembled with: type.dpt.field.255.1.i0.Latitude
is assembled with: type.dpt.field.255.1.i1.Longitude
datapoint type major number: 255
type: NamedIndividual
type: DatapointType
dpt bit size max: 64
label: Geographical Location
comment: a point representing DPT 255.001: Geographical Location

Validity
type: NamedIndividual
type: Point Function
comment: A point representing a validity assessment of a datapoint value.

type.dpt.field.512.503.i5.pei.PC ID
field size: 4
field name: PC_ID
field type: U
field index: 5
description: identifier of power constraint
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual

CombinedStatus_RTC
type: Class
interface object type annotation: 398
subject: 65
subject: 398.65
subject: CombinedStatus_RTC
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 65

type.dpt.field.27.1.i11.IOO12
includes KV pair: output state is Off = 0
includes KV pair: output state is On = 1
field type: B
comment: Info On Off Output 12
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field index: 11
field name: IOO12

Chiller
type: EquipmentType
type: NamedIndividual
description: EquipmentType to remove heat from a liquid.

Restriction
on property: pointName
has value: HVACModeAct

TempRoomSetpSetHeat
type: Class
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 397
label: TempRoomSetpSetHeat
subject: TempRoomSetpSetHeat
subject: 397.85
subject: 85
property identifier annotation: 85

222.x
has communication mode: S
datapoint type major number: 222
subject: 222.major
subject: 222.x
type: NamedIndividual
type: DatapointType
dpt bit size max: 48
is assembled with: type.dpt.field.222.x.i0
label: 222.x

Network Router
type: NamedIndividual
type: EquipmentType
comment: A Router is a network node (Device) that that forwards data packets between computer networks typically between OSI Layers 3. A router does not change application layer content.

type.dpt.field.14.48.i0
field type: F
unit: http://qudt.org/vocab/unit/T
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: magnetic polarization
field size: 32

type.dpt.field.12.x.i0
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u32
field index: 0
field size: 32
comment: 4-byte unsigned value
field type: U

Restriction
has value: 152
on property: property identifier

Heat cost allocator = 8
value KNX: 8
type: NamedIndividual
value API: heatCostAllocator

type.dpt.field.21.601.i0.LoadDetectionError
field type: B
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field size: 1
field name: LoadDetectionError
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: LoadDetectionError

ComfortPushbutton
type: Class
subject: 397.82
subject: 82
subject: ComfortPushbutton
subclass of: Restriction
  on property: has datapoint type
  has value: start
property identifier annotation: 82
interface object type annotation: 397

type.dpt.field.265.11.i0.BinaryInformation
comment: Binary Information
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: BinaryInformation
field size: 1
includes DPT: State

has phenomenon type
type: ObjectProperty
type: FunctionalProperty
comment: A child OP relationship to a list that describes the interest characteristic “type of interest” on what an observation or actuation is made.
range: Phenomenon
inverse of: is phenomenon type of
domain: QualityKind
sub property of: has tag

Night Purge = 4
value API: nightPurge
value KNX: 4
type: NamedIndividual

type.dpt.field.15.0.i8.D4
field name: D4
field index: 8
field size: 4
comment: digit 4 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
field type: U
field resolution: 1.0
includes digit: type.digit.u4 0 9
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.7.x.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 16
comment: 2-byte unsigned value
includes digit: type.digit.u16
field type: U

type.dpt.field.253.600.i10.StepCodeSaturation
type: NamedIndividual
type: Datapoint Type Field
comment: Shall specify the fading step size or to the code to stop the fading of the saturation
field index: 10
field name: StepCodeSaturation
includes digit: type.digit.u3
field type: U
field resolution: 1.0
field size: 3

RF ModeInfo
has communication mode: S
subject: RF ModeInfo
subject: 21.1000
label: RF ModeInfo
comment: a point representing DPT 21.1000: RF ModeInfo
is assembled with: type.dpt.field.21.1000.i2.BiBatSlave
is assembled with: type.dpt.field.21.1000.i1.BiBatMaster
is assembled with: type.dpt.field.21.1000.i3.Reserved
is assembled with: type.dpt.field.21.1000.i0.Asynchronous
type: NamedIndividual
type: DatapointType
dpt bit size max: 8
datapoint type minor number: 1000
datapoint type major number: 21

Apartment
comment: An apartment (American English), or flat (British English, Indian English, South African English), is a self-contained housing unit (a type of residential real estate) that occupies part of a building, generally on a single story. Preferably used with a Building.
type: LocationUsage
type: NamedIndividual

TempRoomSetpSetShift[3]
has communication mode: LTE
dpt bit size max: 48
is assembled with: type.dpt.field.212.100.i1.TempSetpShiftStdby
is assembled with: type.dpt.field.212.100.i2.TempSetpShiftComf
is assembled with: type.dpt.field.212.100.i0.TempSetpShiftEco
subject: TempRoomSetpSetShift[3]
subject: 212.100
type: DatapointType
type: NamedIndividual
label: TempRoomSetpSetShift[3]
comment: a point representing DPT 212.100: TempRoomSetpSetShift[3]
datapoint type minor number: 100
datapoint type major number: 212

type.dpt.field.22.101.i12.DewPointStatus
comment: DewPointStatus
type: Datapoint Type Field
type: NamedIndividual
field name: DewPointStatus
field size: 1
includes KV pair: No alarm = 0
includes KV pair: type.kvpair.alarm
field type: B
field index: 12

TimePeriodMin
has communication mode: S
description: a point representing DPT 7.006: TimePeriodMin
subject: 7.6
subject: 7.006
subject: TimePeriodMin
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
label: TimePeriodMin
datapoint type minor number: 6
datapoint type major number: 7
is assembled with: type.dpt.field.7.6.i0

WindowStatusEff
type: Class
subject: 62
subject: 397.62
subject: WindowStatusEff
subclass of: Restriction
  has value: qk eq window positionvector room
  on property: hasQualityKind
subclass of: Restriction
  on property: has operation kind
label: WindowStatusEff
property identifier annotation: 62
interface object type annotation: 397

type.dpt.field.512.507.i4.smfrbc.OM
description: list of operation modes
includes DPT field: type.dpt.field.frbc.om
includes counter: type.dpt.field.512.507.i1.smfrbc.OM CNT
field index: 4
field name: OM
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>

type.dpt.field.235.1.i0.T
field size: 1
includes KV pair: type.kvpair.235.1.i0.0
includes KV pair: not valid = 1
type: Datapoint Type Field
type: NamedIndividual
field name: T
field index: 0
field type: B
comment: validity of the Tariff data

Value Torque
has communication mode: S
description: DPT 14.075: Value of torque
type: DatapointType
type: NamedIndividual
subject: 14.75
subject: 14.075
subject: Value Torque
datapoint type major number: 14
dpt bit size max: 32
is assembled with: type.dpt.field.14.75.i0
datapoint type minor number: 75

type.dpt.field.254.600.i5.Reserved
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 5
includes reserved bit: type.bit.reserved
field size: 4

PLC Status
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 20.1205
subject: PLC Status
datapoint type major number: 20
is assembled with: type.dpt.field.20.1205.i0
comment: a point representing DPT 20.1205: PLC Status
datapoint type minor number: 1205
dpt bit size max: 8

Application Program
subclass of: Class
subclass of: Software
subclass of: Restriction
  on property: implements
  all values from: Functionality
comment: An application program represents a piece of software that implements a functionality. Moreover, specific confifuration parameters may be used to control how the functionality is operating at Runtime.
disjoint with: Functionality
type: Class

type.dpt.field.21.107.i1.PresenceStatusEffective
comment: Effective value of the presence status
field type: B
includes KV pair: no occupancy from presence detectors = 0
includes KV pair: occupancy at least from one presence detector = 1
field index: 1
field name: PresenceStatusEffective
type: Datapoint Type Field
type: NamedIndividual
field size: 1

Zone Heating Control
comment: The Application Function controls the 'air temperature' of a room or zone (group of rooms or space) individually, thereby maximizing comfort and minimizing energy costs. The control loop often uses the outside temperature or a reference room temperature as a process variable.
type: Class
subclass of: Emission Control

The visual effect of channel 12 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel12IsInactiv

type.dpt.field.30.1010.i9.ActivationStateOfChannel10
field size: 1
includes KV pair: The visual effect of channel 10 is inactive = 0
includes KV pair: The visual effect of channel 10 is active = 1
type: Datapoint Type Field
type: NamedIndividual
field name: ActivationStateOfChannel10
field type: B
field index: 9
comment: Activation state of channel 10

type.dpt.field.17.1.i0.SceneNumber
field type: U
unit: NUM
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
comment: Scene number
field size: 6
field index: 0
field name: SceneNumber
includes digit: type.digit.u6

Value Temp
has communication mode: S
comment: a point representing DPT 9.001: Value Temp
is assembled with: type.dpt.field.9.1.i0
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
subject: 9.1
subject: 9.001
subject: Value Temp
datapoint type major number: 9
dpt bit size max: 16

Gym
type: LocationUsage
type: NamedIndividual
comment: A gym (also known as a fitness club, fitness center, health spa, and health club) is a place that houses exercise equipment for the purpose of physical exercise.

type.dpt.field.22.101.i9.StatusEcoC
field type: B
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field index: 9
comment: StatusEcoC
field size: 1
field name: StatusEcoC
type: Datapoint Type Field
type: NamedIndividual

Window Door
field type: B
includes KV pair: type.kvpair.1.19.i0.1
includes KV pair: closed = 0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1

Restriction
has value: 62
on property: property identifier

type.dpt.field.207.105.i1.ManualOverride
field size: 1
field name: ManualOverride
field index: 1
comment: actuator position is manually overridden
includes DPT: Bool
type: Datapoint Type Field
type: NamedIndividual

Restriction
has value: ActualDimmingValue
on property: pointName

Restriction
on property: interface object type
has value: 400

occupied = 1
value KNX: 1
type: NamedIndividual
value API: occupied

Other Residential
type: LocationUsage
type: NamedIndividual
comment: Preferably used with a Building.

Restriction
on property: fieldDefault
max cardinality: 1

Control Mode Pre-Cool
description: This state type expresses that mode 'Pre-Cool' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system cooling an unoccupied room in a predictive manner in order for the room to be at the desired temperature once the room is scheduled to be used. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
type: State Type
type: NamedIndividual

Room Temperature Controller
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.399.73
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: Class
    intersection of: dpa.399.105
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: dpa.399.109
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: dpa.399.71
subclass of: Restriction
  on property: isComposedByInput
  on class: dpa.399.69
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
  on class: TempRoom
subclass of: Restriction
  on property: isComposedByOutput
  on class: dpa.399.100
  qualified cardinality: 1
subclass of: Restriction
  on class: FanManual
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: SwitchCool
subclass of: Restriction
  on property: isComposedByInput
  on class: ActCurrPosHeatStageA
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  on class: dpa.399.68
  max qualified cardinality: 1
subclass of: Restriction
  on class: ActTargetFanSpeed
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
  on class: dpa.399.50
subclass of: Restriction
  on class: dpa.399.101
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  on class: FanSpeedUser
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Class
subclass of: Restriction
  on class: CombinedStatus_FA
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: CombinedStatus_RTC
subclass of: Restriction
  on class: EnableCoolEff
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: EnableHeatEff
subclass of: Restriction
  max qualified cardinality: 1
  on class: TempRoomSetpSetHeatEff
  on property: isComposedByInput
subclass of: Restriction
  on class: TempRoomSetpSetCoolEff
  on property: isComposedByInput
  max qualified cardinality: 1
type: Class
subject: RTC
subject: Room Temperature Controller
subject: 399
interface object type annotation: 399

type.dpt.field.23.1.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
includes KV pair: type.kvpair.23.1.i0.0
includes KV pair: type.kvpair.23.1.i0.3
includes KV pair: type.kvpair.23.1.i0.1
includes KV pair: type.kvpair.23.1.i0.2
field size: 2
field type: N

The visual effect of channel 2 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel2IsInactive

type.dpt.field.21.601.i6.Overheat
field name: Overheat
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field size: 1
comment: Overheat
type: Datapoint Type Field
type: NamedIndividual
field index: 6

Volume m3
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: Volume m3
subject: 12.1201
dpt bit size max: 32
comment: a point representing DPT 12.1201: Volume M3
datapoint type minor number: 1201
is assembled with: type.dpt.field.12.1201.i0
datapoint type major number: 12

type.dpt.field.22.1000.i0.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
includes reserved bit: type.bit.reserved
field type: r
field name: Reserved

type.dpt.field.ddbc.ome.i0.SRR
includes DPT: emPowerRange
field index: 0
description: supply rate range
field name: SRR
type: Datapoint Type Field
type: NamedIndividual
field size: 32

TempRoomSetpHeatEff
type: Class
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
interface object type annotation: 398
subject: 85
subject: TempRoomSetpHeatEff
subject: 398.85
property identifier annotation: 85

type.dpt.field.237.x.i0
description: configuration/ diagnostics
field size: 16
field string schema: raw
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0

type.dpt.field.9.27.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field type: F
includes digit: type.digit.f16 neg45960 670433
field size: 16
unit: DEG F

BuildingMode
has communication mode: S
subject: 20.002
subject: BuildingMode
subject: 20.2
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 20.002: BuildingMode
datapoint type major number: 20
is assembled with: type.dpt.field.20.2.i0
label: BuildingMode
datapoint type minor number: 2

Window
description: A window is an opening in a wall, door, roof, or vehicle that allows the exchange of light and may also allow the passage of sound and sometimes air.
type: NamedIndividual
type: EquipmentType

The visual effect of channel 5 is inactive = 0
value API: theVisualEffectOfChannel5IsInactive
value KNX: 0
type: NamedIndividual

Channel Activation 16
has communication mode: S
is assembled with: type.dpt.field.22.1010.i14.ActivationStateOfChannel15
is assembled with: type.dpt.field.22.1010.i10.ActivationStateOfChannel11
is assembled with: type.dpt.field.22.1010.i9.ActivationStateOfChannel10
is assembled with: type.dpt.field.22.1010.i15.ActivationStateOfChannel16
is assembled with: type.dpt.field.22.1010.i8.ActivationStateOfChannel9
is assembled with: type.dpt.field.22.1010.i1.ActivationStateOfChannel2
is assembled with: type.dpt.field.22.1010.i5.ActivationStateOfChannel6
is assembled with: type.dpt.field.22.1010.i0.ActivationStateOfChannel1
is assembled with: type.dpt.field.22.1010.i6.ActivationStateOfChannel7
is assembled with: type.dpt.field.22.1010.i4.ActivationStateOfChannel5
is assembled with: type.dpt.field.22.1010.i3.ActivationStateOfChannel4
is assembled with: type.dpt.field.22.1010.i12.ActivationStateOfChannel13
is assembled with: type.dpt.field.22.1010.i7.ActivationStateOfChannel8
is assembled with: type.dpt.field.22.1010.i2.ActivationStateOfChannel3
is assembled with: type.dpt.field.22.1010.i13.ActivationStateOfChannel14
is assembled with: type.dpt.field.22.1010.i11.ActivationStateOfChannel12
comment: a point representing DPT 22.1010: Channel Activation 16
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1010
subject: 22.1010
subject: Channel Activation 16
datapoint type major number: 22
dpt bit size max: 16

Absolute Set Value Control Red
type: Class
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq luminaire dimmlevel
subject: ASV_R
subject: Absolute Set Value Control Red
subject: 58
subject: 423.58
interface object type annotation: 423
property identifier annotation: 58

FanSpeedUser
type: Class
subclass of: Restriction
  on property: has operation kind
  some values from: Class
    intersection of: Operation Kind
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 393
subject: 393.51
subject: FanSpeedUser
subject: 51
label: FanSpeedUser
property identifier annotation: 51

type.dpt.field.265.9.i2.DateAndTime
field index: 2
field name: DateAndTime
type: Datapoint Type Field
type: NamedIndividual
comment: Date and Time
includes DPT: DateTime
field size: 64

type.dpt.field.275.101.i3.TempSetpShiftComf
comment: room temperature setpoint shift comfort
includes digit: type.digit.f16
field size: 16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
unit: http://qudt.org/vocab/unit/K
field index: 3
field type: F
field name: TempSetpShiftComf

HVAC User Mode active (means DP ‘HVACModeUser’ is different from ‘Auto’) = 1
type: NamedIndividual
value KNX: 1
value API: hVACUserModeActive(meansDP‘HVACMode

http://qudt.org/vocab/unit/M
symbol: m
type: NamedIndividual
type: Unit

Alarm
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1
includes KV pair: Alarm = 1
includes KV pair: type.kvpair.1.5.i0.0
field type: B

type.dpt.field.275.101.i1.TempSetpShiftEco
field size: 16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
unit: http://qudt.org/vocab/unit/K
comment: room temperature setpoint shift economy
field type: F
field name: TempSetpShiftEco
includes digit: type.digit.f16
field index: 1

type.dpt.field.519.500.i3.tran.TO
field type: U
field name: TO
type: Datapoint Type Field
type: NamedIndividual
field size: 4
field index: 3
description: operation mode id the transition points to
includes digit: type.digit.u4 1 15

type.dpt.field.224.100.i1.ContrModeAct
includes KV pair: NoDem = 20
includes KV pair: type.kvpair.224.100.i1.2
includes KV pair: Emergency Heat = 8
includes KV pair: type.kvpair.224.100.i1.3
includes KV pair: type.kvpair.224.100.i1.5
includes KV pair: Off = 6
includes KV pair: Heat = 1
includes KV pair: Fan only = 9
includes KV pair: Test = 7
includes KV pair: type.kvpair.224.100.i1.11
includes KV pair: type.kvpair.224.100.i1.4
includes KV pair: type.kvpair.224.100.i1.10
includes KV pair: Auto = 0
field name: ContrModeAct
field index: 1
field type: N
comment: Actual controller Mode
type: Datapoint Type Field
type: NamedIndividual
field size: 8

225.x
has communication mode: S
subject: 225.major
subject: 225.x
datapoint type major number: 225
label: 225.x
type: NamedIndividual
type: DatapointType
dpt bit size max: 24
is assembled with: type.dpt.field.225.x.i0

type.dpt.field.14.67.i0
unit: N-PER-M
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: surface tension
field size: 32
field type: F
includes digit: type.digit.f32
field resolution: 1.0

Restriction
has value: ForcedPositionEnable
on property: pointName

Restriction
has value: 52
on property: property identifier

TempRoomSetpSetHeatShift
type: Class
subject: 398.60
subject: TempRoomSetpSetHeatShift
subject: 60
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 60
interface object type annotation: 398

Fill Rate Based Control
comment: Application functions for "fill rate based control". Fill rate is the percentage of demand that can be met without lagging in supply. By using fill-rate as the basis for determining the energy production, conservation and optimization of energy can be done without failing to satisfy demands.
type: Class
subclass of: smartGridCtrl

No Storm
description: This state type expresses the state of no storm. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of no storm, storm protection is not required and this equipment might be used for shading purposes as intended. This state type is the inverse of the 'Storm State' state type.
type: NamedIndividual
type: State Type

Value Electric Flux
has communication mode: S
datapoint type minor number: 24
comment: DPT 14.024: Value of electric flux
subject: 14.024
subject: 14.24
subject: Value Electric Flux
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
label: Value Electric Flux
datapoint type major number: 14
is assembled with: type.dpt.field.14.24.i0

Value Humidity
has communication mode: S
subject: Value Humidity
subject: 9.007
subject: 9.7
type: DatapointType
type: NamedIndividual
datapoint type minor number: 7
is assembled with: type.dpt.field.9.7.i0
label: Value Humidity
comment: a point representing DPT 9.007: Value Humidity
datapoint type major number: 9
dpt bit size max: 16

Activation
type: NamedIndividual
type: Point Function
description: A point representing an enabling/disabeling of a (sub) functionality.

W-HR
symbol: W⋅hr
type: NamedIndividual
type: Unit

type.dpt.field.19.1.i10.F
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: Normal (no fault) = 0
includes KV pair: Fault = 1
field type: B
comment: Fault
field default: 0
field size: 1
field index: 10
field name: F

type.dpt.field.235.1.i2.Reserved
field index: 2
field type: r
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field name: Reserved
field size: 6

rest: nil
first: Restriction
  on property: interface object type
  has value: 323

The visual effect of channel 4 is inactive = 0
value KNX: 0
type: NamedIndividual
value API: theVisualEffectOfChannel4IsInactive

HVACMode
has communication mode: S
datapoint type minor number: 102
is assembled with: type.dpt.field.20.102.i0
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
label: HVACMode
subject: HVACMode
subject: 20.102
comment: a point representing DPT 20.102: HVACMode
dpt bit size max: 8

type.dpt.field.10.1.i0.Seconds
type: Datapoint Type Field
type: NamedIndividual
comment: Seconds
field name: Seconds
field index: 0
field size: 6
includes digit: type.digit.u6 0 59
field type: U
field resolution: 1.0
unit: SEC

type.digit.f16 neg27300 65534
range max: 65534.0
range min: -27300.0
type: NamedIndividual

type.dpt.field.15.0.i7.D3
field type: U
field resolution: 1.0
includes digit: type.digit.u4 0 9
comment: digit 3 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
type: Datapoint Type Field
type: NamedIndividual
field name: D3
field size: 4
field index: 7

ActCurrFanSpeed
type: Class
subclass of: Restriction
  has value: scaling
  on property: has datapoint type
interface object type annotation: 397
property identifier annotation: 68
label: ActCurrFanSpeed
subject: 68
subject: ActCurrFanSpeed
subject: 397.68

Data Link Layer Busmonitor = 1
value KNX: 1
type: NamedIndividual
value API: dataLinkLayerBusmonitor

ActCurrPos
type: Class
subject: ActCurrPos
subject: 400.60
subject: 60
interface object type annotation: 400
property identifier annotation: 60

type.dpt.field.212.101.i1.TempSetpStdby
field name: TempSetpStdby
type: NamedIndividual
type: Datapoint Type Field
comment: room temperature setpoint standby
field resolution: 0.02
field index: 1
unit: DEG C
field size: 16
field type: V
includes digit: type.digit.s16 neg13650 32767

type.dpt.field.20.801.i0
type: NamedIndividual
type: Datapoint Type Field
description: SABExceptBehaviour
field index: 0
includes KV pair: type.kvpair.20.801.i0.3
includes KV pair: no change = 2
includes KV pair: type.kvpair.20.801.i0.1
includes KV pair: stop = 4
includes KV pair: type.kvpair.20.801.i0.0
field type: N
field size: 8

volume, 100 l = 21
value KNX: 21
value API: volume,100L
type: NamedIndividual

CombinedStatus_FA
type: Class
subclass of: Restriction
  on property: has operation kind
  some values from: Class
    intersection of: Operation Kind
subclass of: Restriction
  some values from: Class
  on property: has operation kind
subject: 399.78
subject: CombinedStatus_FA
subject: 78
property identifier annotation: 78
interface object type annotation: 399

Media
has communication mode: S
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 22.1000: Media
is assembled with: type.dpt.field.22.1000.i6.Reserved
is assembled with: type.dpt.field.22.1000.i4.RF
is assembled with: type.dpt.field.22.1000.i0.Reserved
is assembled with: type.dpt.field.22.1000.i2.PL110
is assembled with: type.dpt.field.22.1000.i3.Reserved
is assembled with: type.dpt.field.22.1000.i5.KNXIP
is assembled with: type.dpt.field.22.1000.i1.TP1
dpt bit size max: 16
datapoint type minor number: 1000
subject: 22.1000
subject: Media
label: Media
datapoint type major number: 22

Restriction
on property: property identifier
has value: 91

Pipe Section
type: Locality
type: NamedIndividual
description: A section of piping that refers to those parts of distribution systems in buildings that are pipes, mostly for transporting water.

type.dpt.field.512.500.i0.pc.CE CNT
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: CE_CNT
field size: 8
description: Number of power contraint elements
field type: U
includes digit: type.digit.u8 0 15

Shutter and Blinds Mode
field index: 0
field size: 1
label: Shutter and Blinds Mode
field type: B
includes KV pair: type.kvpair.1.23.i0.0
includes KV pair: move Up/Down + StepStop mode (blind) = 1
type: Datapoint Type Field
type: NamedIndividual

emForecastValue
is assembled with: type.dpt.field.525.500.i3.fv.Lower 95PPR
is assembled with: type.dpt.field.525.500.i0.fv.VAL LIM
is assembled with: type.dpt.field.525.500.i9.fv.Expected
is assembled with: type.dpt.field.525.500.i1.fv.VAL PPR
is assembled with: type.dpt.field.525.500.i2.fv.Reserved
is assembled with: type.dpt.field.525.500.i4.fv.Lower 68PPR
is assembled with: type.dpt.field.525.500.i8.fv.Lower Limit
is assembled with: type.dpt.field.525.500.i6.fv.Upper 95PPR
is assembled with: type.dpt.field.525.500.i7.fv.Upper Limit
is assembled with: type.dpt.field.525.500.i5.fv.Upper 68PPR
dpt bit size max: 120
description: Power forecast value
type: NamedIndividual
type: DatapointType
datapoint type major number: 525
datapoint type minor number: 500

enable stage A = 1
value KNX: 1
value API: enableStageA
type: NamedIndividual

PropDataType
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 7.10
subject: PropDataType
subject: 7.010
datapoint type minor number: 10
is assembled with: type.dpt.field.7.10.i0
datapoint type major number: 7
label: PropDataType
comment: a point representing DPT 7.010: PropDataType
dpt bit size max: 16

type.dpt.field.21.601.i1.Undervoltage
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
description: Undervoltage
field index: 1
field name: Undervoltage
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field type: B

type.dpt.field.252.600.i6.cW
comment: Shall specify whether the colour component white shall be increased or decreased.
field name: cW
field size: 1
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
type: Datapoint Type Field
type: NamedIndividual
field index: 6
field type: B

type.dpt.field.217.1.i1.VersionNumber
field index: 1
field type: U
field resolution: 1.0
unit: NUM
field name: VersionNumber
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u5
field size: 5
comment: Version Number

Terrace
comment: A terrace is an external, raised, open, flat area in either a landscape (such as a park or garden) near a building, or as a roof terrace on a flat roof. Preferably used with an Space.
type: LocationUsage
type: NamedIndividual

not valid = 0
type: NamedIndividual
value KNX: 0
value API: notValid

type.dpt.field.22.100.i7.TempOptimShiftActive
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
comment: TempOptimShiftActive
field size: 1
field name: TempOptimShiftActive
type: Datapoint Type Field
type: NamedIndividual
field index: 7
field type: B

Request Converter DT Info = 5
value KNX: 5
value API: requestConverterDTInfo
type: NamedIndividual

type.dpt.field.20.21.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
includes KV pair: type.kvpair.20.21.i0.4
includes KV pair: Very cloudy = 6
includes KV pair: Cloudy = 5
includes KV pair: Cloudless = 0
includes KV pair: type.kvpair.20.21.i0.9
includes KV pair: type.kvpair.20.21.i0.7
includes KV pair: Sunny = 1
includes KV pair: Sunshiny = 2
includes KV pair: Overcast = 8
includes KV pair: Lightly cloudy = 3
field size: 8
field type: N
comment: CloudCover

N-SEC
type: NamedIndividual
type: Unit
symbol: N⋅s

type.dpt.field.21.2.i0.UserStopped
type: NamedIndividual
type: Datapoint Type Field
field size: 1
field index: 0
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field name: UserStopped
description: The user application is stopped

Operational State Maintenance
type: State Type
type: NamedIndividual
description: This state type expresses that a device is currently in maintenance mode, i.e. it cannot be expected to fulfill its usual functionality until it is fully operational once again. Specific examples include ‘service mode’ or the ‘valve kick’ of valve actuators.

Value AngleDeg
has communication mode: S
subject: Value AngleDeg
subject: 14.007
subject: 14.7
type: DatapointType
type: NamedIndividual
datapoint type major number: 14
datapoint type minor number: 7
dpt bit size max: 32
is assembled with: type.dpt.field.14.7.i0
description: DPT 14.007: Value of an angle (in degrees)
label: Value AngleDeg

Restriction
on property: interface object type
has value: 403

UCount Value 8 Z
has communication mode: LTE
subject: 202.2
subject: UCount Value 8 Z
subject: 202.002
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.202.2.i0.StatusCommand
is assembled with: type.dpt.field.202.2.i1.CounterValue
datapoint type major number: 202
datapoint type minor number: 2
comment: a point representing DPT 202.2: UCount Value 8 Z
dpt bit size max: 16

type.dpt.field.219.1.i9.ErrorClass
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: configuration fault = 3
includes KV pair: type.kvpair.219.1.i9.5
includes KV pair: HW fault = 4
includes KV pair: general device fault (e.g. RAM, EEPROM, UI, Watchdog, ...) = 1
includes KV pair: type.kvpair.219.1.i9.2
includes KV pair: no fault = 0
description: Error Class
field index: 9
field name: ErrorClass
field type: N
field size: 8

Restriction
on property: interface object type
has value: 399

type.dpt.field.14.41.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
comment: luminance
field size: 32
field type: F
unit: CD-PER-M2
includes digit: type.digit.f32

Value Electric PotentialDifference
has communication mode: S
subject: Value Electric PotentialDifference
subject: 14.028
subject: 14.28
description: DPT 14.028: Value of electric potential difference
datapoint type major number: 14
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.14.28.i0
dpt bit size max: 32
datapoint type minor number: 28

The visual effect of channel 23 is inactive = 0
value API: theVisualEffectOfChannel23IsInactiv
type: NamedIndividual
value KNX: 0

MaC room
comment: By a MaC (ETS) allowed location usages for a room.
type: Class

Value Heat Capacity
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: Value Heat Capacity
subject: 14.035
subject: 14.35
comment: DPT 14.035: Value of heat capacity
is assembled with: type.dpt.field.14.35.i0
datapoint type major number: 14
datapoint type minor number: 35
dpt bit size max: 32

power, 0,01 kJ/h = 49
type: NamedIndividual
value KNX: 49
value API: power,0,01KJh

type.dpt.field.512.503.i3.pei.Reserved
description: reserved bits
field index: 3
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field type: r
field name: RESERVED
field size: 3

DateTime
has communication mode: S
is assembled with: type.dpt.field.19.1.i1.SRC
is assembled with: type.dpt.field.19.1.i6.ND
is assembled with: type.dpt.field.19.1.i21.Year
is assembled with: type.dpt.field.19.1.i15.HourOfDay
is assembled with: type.dpt.field.19.1.i12.Reserved
is assembled with: type.dpt.field.19.1.i3.SUTI
is assembled with: type.dpt.field.19.1.i7.NY
is assembled with: type.dpt.field.19.1.i11.Seconds
is assembled with: type.dpt.field.19.1.i18.Reserved
is assembled with: type.dpt.field.19.1.i5.NDOW
is assembled with: type.dpt.field.19.1.i8.NWD
is assembled with: type.dpt.field.19.1.i9.WD
is assembled with: type.dpt.field.19.1.i16.DayOfWeek
is assembled with: type.dpt.field.19.1.i14.Reserved
is assembled with: type.dpt.field.19.1.i13.Minutes
is assembled with: type.dpt.field.19.1.i19.Month
is assembled with: type.dpt.field.19.1.i20.Reserved
is assembled with: type.dpt.field.19.1.i0.Reserved
is assembled with: type.dpt.field.19.1.i17.DayOfMonth
is assembled with: type.dpt.field.19.1.i2.CLQ
is assembled with: type.dpt.field.19.1.i4.NT
is assembled with: type.dpt.field.19.1.i10.F
subject: 19.1
subject: DateTime
subject: 19.001
label: DateTime
datapoint type minor number: 1
type: DatapointType
type: NamedIndividual
datapoint type major number: 19
comment: a point representing DPT 19.001: DateTime
dpt bit size max: 64

FlowRate m3/h Z
has communication mode: LTE
is assembled with: type.dpt.field.218.2.i0.StatusCommand
is assembled with: type.dpt.field.218.2.i1.FlowRate
type: NamedIndividual
type: DatapointType
label: FlowRate m3/h Z
subject: FlowRate m3/h Z
subject: 218.2
subject: 218.002
dpt bit size max: 40
comment: a point representing DPT 218.002: Flow Rate in m3/h Z
datapoint type major number: 218
datapoint type minor number: 2

Shutter Position Percentage
subclass of: Restriction
  has value: scaling
  on property: has datapoint type
subclass of: Function Point
type: Class

Rain Amount
has communication mode: S
subject: 9.026
subject: Rain Amount
subject: 9.26
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
label: Rain Amount
is assembled with: type.dpt.field.9.26.i0
comment: a point representing DPT 9.026: Rain Amount
datapoint type minor number: 26
datapoint type major number: 9

Heating-Cooling Stages None
description: This state type expresses that an HVAC system has neither primary nor secondary stage (for its cooling or heating subsystem). In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
type: State Type
type: NamedIndividual

type.dpt.field.238.600.i1.LampFailure
includes KV pair: error = 1
includes KV pair: type.kvpair.238.600.i1.0
field size: 1
type: Datapoint Type Field
type: NamedIndividual
comment: Lamp Failure
field name: LampFailure
field type: B
field index: 1

Hardwired Inhibit is inactive = 0
value API: hardwiredInhibitIsInactive
type: NamedIndividual
value KNX: 0

MasterSlaveMode
has communication mode: S
label: MasterSlaveMode
subject: MasterSlaveMode
subject: 20.112
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 20.112: MasterSlaveMode
datapoint type minor number: 112
datapoint type major number: 20
is assembled with: type.dpt.field.20.112.i0
dpt bit size max: 8

type.dpt.field.14.46.i0
field type: F
comment: magnetic flux density
unit: http://qudt.org/vocab/unit/T
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field size: 32
field index: 0

Heat Exchanger
description: Equipment to transfer heat between two working fluids. For example, a coil is a heat exchanger used to heat or cool air.
type: NamedIndividual
type: EquipmentType

type.dpt.field.245.600.i0.LPDTR
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes digit: type.digit.u8
comment: LPDTR
field size: 8
field name: LPDTR
field type: U

Restriction
on property: number
max qualified cardinality: 1
on data range: string

HVACModeAct
type: Class
subject: 53
subject: 397.53
subject: HVACModeAct
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 397
property identifier annotation: 53

Colour Transition
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type minor number: 600
subject: Colour Transition
subject: 243.600
label: Colour Transition
is assembled with: type.dpt.field.243.600.i2.Reserved
is assembled with: type.dpt.field.243.600.i1.C
is assembled with: type.dpt.field.243.600.i5.xaxis
is assembled with: type.dpt.field.243.600.i4.yaxis
is assembled with: type.dpt.field.243.600.i6.TimePeriod
is assembled with: type.dpt.field.243.600.i0.B
is assembled with: type.dpt.field.243.600.i3.Brightness
dpt bit size max: 64
comment: a point representing DPT 243.600: Colour Transition
datapoint type major number: 243

Heat = 1
value KNX: 1
type: NamedIndividual
value API: heat

TempRoomSetpAct
type: Class
property identifier annotation: 55
subject: TempRoomSetpAct
subject: 55
subject: 240.55
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air temperature room
interface object type annotation: 240

type.dpt.field.30.1010.i19.ActivationStateOfChannel20
field size: 1
includes KV pair: type.kvpair.30.1010.i19.1
includes KV pair: type.kvpair.30.1010.i19.0
field index: 19
type: Datapoint Type Field
type: NamedIndividual
comment: Activation state of channel 20
field type: B
field name: ActivationStateOfChannel20

maximal table length exceeded = 13
type: NamedIndividual
value API: maximalTableLengthExceeded
value KNX: 13

type.dpt.field.lb.lbe.i1.FLR
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: FLR
includes DPT: emFillLevelRange
description: the range of the fill level the leakage rate (LR) realtes to

has building
range: Building
inverse of: isBuildingOf
comment: A strong OP relationship to express a relation to building contained in a site.
type: ObjectProperty
sub property of: has location

Group Address = 1
value API: groupAddress
value KNX: 1
type: NamedIndividual

type.dpt.field.252.600.i14.StepCodeColourRed
includes digit: type.digit.u3
field type: U
field resolution: 1.0
field size: 3
type: Datapoint Type Field
type: NamedIndividual
description: Shall specify the fading step size or to the code to stop the fading of the colour red
field name: StepCodeColourRed
field index: 14

Pressure
has communication mode: S
comment: a point representing DPT 9.006: Pressure
type: DatapointType
type: NamedIndividual
label: Pressure
datapoint type minor number: 6
subject: 9.6
subject: 9.006
subject: Pressure
is assembled with: type.dpt.field.9.6.i0
datapoint type major number: 9
dpt bit size max: 16

type.dpt.field.207.104.i3.EmergDem
field name: EmergDem
type: Datapoint Type Field
type: NamedIndividual
field size: 1
comment: emergency demand (heating or cooling) for room frost protection or de-icing
field index: 3
includes DPT: Bool

HeatCoolMode
type: Class
label: HeatCoolMode
interface object type annotation: 257
property identifier annotation: 151
subject: HeatCoolMode
subject: 257.151
subject: 151

Value Density
has communication mode: S
datapoint type major number: 14
subject: Value Density
subject: 14.17
subject: 14.017
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
description: DPT 14.017: Value of density
datapoint type minor number: 17
is assembled with: type.dpt.field.14.17.i0

Light Absolute Setvalue Request
subclass of: Restriction
  has value: qk ph light illuminance
  on property: actsOnPhenomenonQualityKind
subclass of: Function Point
type: Class

type.dpt.field.6.20.i4.b
field index: 4
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.clear
includes KV pair: set = 1
comment: Status B
field type: B
field name: b
field size: 1

inverse value of InfoOnOff is sent = 3
value KNX: 3
type: NamedIndividual
value API: inverseValueOfInfoOnOffIsSent

type.dpt.field.27.1.i29.MaskBitIOO14
type: Datapoint Type Field
type: NamedIndividual
field name: MaskBitIOO14
field index: 29
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B
comment: Mask Bit Info On Off Output 14
field size: 1

HVACModeEffNext
type: Class
property identifier annotation: 52
subclass of: Restriction
  on property: has operation kind
subject: HVACModeEffNext
subject: 52
subject: 100.52
interface object type annotation: 100

Value MassFlux
has communication mode: S
datapoint type minor number: 52
subject: Value MassFlux
subject: 14.052
subject: 14.52
label: Value MassFlux
type: DatapointType
type: NamedIndividual
datapoint type major number: 14
is assembled with: type.dpt.field.14.52.i0
dpt bit size max: 32
comment: DPT 14.052: Value of mass flux

standby = 1
type: NamedIndividual
value API: standby
value KNX: 1

general device fault (e.g. RAM, EEPROM, UI, Watchdog, ...) = 1
value KNX: 1
type: NamedIndividual
value API: generalDeviceFault(e.g.RAM,EEPROM,U

Enable HC Stage
has communication mode: S
type: NamedIndividual
type: DatapointType
dpt bit size max: 8
subject: Enable HC Stage
subject: 20.116
datapoint type minor number: 116
comment: a point representing DPT 20.116: Enable HC Stage
datapoint type major number: 20
is assembled with: type.dpt.field.20.116.i0
label: Enable HC Stage

TempRoomSetpSet[3]
has communication mode: LTE
type: NamedIndividual
type: DatapointType
datapoint type major number: 212
is assembled with: type.dpt.field.212.101.i2.TempSetpComf
is assembled with: type.dpt.field.212.101.i1.TempSetpStdby
is assembled with: type.dpt.field.212.101.i0.TempSetpEco
description: a point representing DPT 212.101: TempRoomSetpSet[3]
subject: 212.101
subject: TempRoomSetpSet[3]
dpt bit size max: 48
datapoint type minor number: 101

power, 100 W = 45
type: NamedIndividual
value KNX: 45
value API: power,100W

Value Amplitude
has communication mode: S
subject: Value Amplitude
subject: 14.5
subject: 14.005
datapoint type major number: 14
comment: DPT 14.005: Value of an amplitude
datapoint type minor number: 5
type: NamedIndividual
type: DatapointType
dpt bit size max: 32
is assembled with: type.dpt.field.14.5.i0

type.dpt.field.202.1.i0.StatusCommand
description: standard Status/Command
field type: Z8
field name: StatusCommand
field size: 8
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0

two PBs/binary inputs mode = 2
value API: twoPBsbinaryInputsMode
type: NamedIndividual
value KNX: 2

type.dpt.field.27.1.i30.MaskBitIOO15
type: Datapoint Type Field
type: NamedIndividual
field index: 30
field size: 1
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
comment: Mask Bit Info On Off Output 15
field type: B
field name: MaskBitIOO15

type.dpt.field.20.609.i0
includes KV pair: type.kvpair.20.609.i0.0
includes KV pair: CFL, leading = 5
includes KV pair: type.kvpair.20.609.i0.3
includes KV pair: leading edge (inductive load) = 1
includes KV pair: type.kvpair.20.609.i0.7
includes KV pair: type.kvpair.20.609.i0.6
includes KV pair: trailing edge (resistive - or capacitive load) = 2
includes KV pair: type.kvpair.20.609.i0.8
includes KV pair: type.kvpair.20.609.i0.4
field type: N
field size: 8
comment: LoadTypeSet
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.207.104.i5.ActPosDemAbs
description: Absolute actuator position demand (setpoint, valve linearized)
field name: ActPosDemAbs
field resolution: 1.0
field index: 5
type: Datapoint Type Field
type: NamedIndividual
unit: PERCENT
includes digit: type.digit.u8 0 100
field type: U
field size: 8

type.dpt.field.8.2.i0
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
field resolution: 1.0
unit: MilliSEC
includes digit: type.digit.s16
field size: 16

TempOutside
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: Value Temp
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subject: 398.64
subject: 64
subject: TempOutside
property identifier annotation: 64
interface object type annotation: 398

last modified
range: dateTime
type: DatatypeProperty
type: FunctionalProperty
comment: Last modified time stamp, usually generated by Mac. May be used from other concepts, therefore no domain is defined.

type.dpt.field.22.1010.i3.ActivationStateOfChannel4
type: Datapoint Type Field
type: NamedIndividual
field size: 1
comment: Activation state of channel 4
field type: B
field index: 3
includes KV pair: The visual effect of channel 4 is inactive = 0
includes KV pair: type.kvpair.22.1010.i3.1
field name: ActivationStateOfChannel4

type.digit.u6 0 59
range min: 0
type: NamedIndividual
range max: 59

type.dpt.field.psc.i3.Reserved
field name: RESERVED
description: Reserved Bits
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field index: 3
field size: 4
field type: r

type.dpt.field.213.101.i3.TempSetpLegioProtect
unit: DEG C
comment: DHW temperature setpoint for LegioProtect operating mode
field type: V
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.s16 neg13650 32767
field size: 16
field index: 3
field name: TempSetpLegioProtect

type.dpt.field.25.x.i0
type: NamedIndividual
type: Datapoint Type Field
field type: A[n]
description: 2-nibble set
field index: 0
field size: 8
field string schema: raw

Value Electrical Conductivity
has communication mode: S
dpt bit size max: 32
subject: 14.016
subject: 14.16
subject: Value Electrical Conductivity
comment: DPT 14.016: Value of electrical conductivity
type: NamedIndividual
type: DatapointType
label: Value Electrical Conductivity
is assembled with: type.dpt.field.14.16.i0
datapoint type minor number: 16
datapoint type major number: 14

Step
has communication mode: S
dpt bit size max: 1
label: Step
comment: a point representing DPT 1.007: Step
subject: 1.7
subject: Step
subject: 1.007
datapoint type minor number: 7
type: NamedIndividual
type: DatapointType
is assembled with: Step
datapoint type major number: 1

ControlModeUser
type: Class
subject: ControlModeUser
subject: 417.74
subject: 74
label: ControlModeUser
property identifier annotation: 74
interface object type annotation: 417

Restriction
on property: property identifier
has value: 153

HumDehumMode
has communication mode: S
datapoint type major number: 20
subject: 20.115
subject: HumDehumMode
is assembled with: type.dpt.field.20.115.i0
description: a point representing DPT 20.115: HumDehumMode
type: NamedIndividual
type: DatapointType
dpt bit size max: 8
datapoint type minor number: 115

not locked = 0
type: NamedIndividual
value KNX: 0
value API: notLocked

type.dpt.field.20.22.i0
includes KV pair: type.kvpair.20.22.i0.0
includes KV pair: send always = 1
includes KV pair: send if value changed during powerdown = 2
field type: N
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: power return mode
field size: 8

type.dpt.field.lb.lbe
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
field index: 0
description: leakage behaviour element
includes DPT field: type.dpt.field.lb.lbe.i0.LR
includes DPT field: type.dpt.field.lb.lbe.i1.FLR

type.dpt.field.238.1.i1.SceneActivation
type: NamedIndividual
type: Datapoint Type Field
field index: 1
description: The field Scent Activation shall indicate whether the scene with scene number SN is active or not.
field type: B
includes KV pair: inactive = 1
includes KV pair: type.kvpair.238.1.i1.0
field name: SceneActivation
field size: 1

type.dpt.field.241.800.i12.ValidHeightPos
type: NamedIndividual
type: Datapoint Type Field
field size: 1
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
comment: Validity height pos.
field index: 12
field name: ValidHeightPos

Char ASCII
has communication mode: S
is assembled with: type.dpt.field.4.1.i0
label: Char ASCII
subject: 4.1
subject: 4.001
subject: Char ASCII
datapoint type major number: 4
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 4.001: Char ASCII
datapoint type minor number: 1
dpt bit size max: 8

mode 1 is active = 2
value API: mode1IsActive
value KNX: 2
type: NamedIndividual

type.dpt.field.20.600.i0
field type: N
includes KV pair: type.kvpair.20.600.i0.2
includes KV pair: type.kvpair.20.600.i0.5
includes KV pair: type.kvpair.20.600.i0.0
includes KV pair: memory function value = 4
includes KV pair: value before locking = 6
includes KV pair: on = 1
includes KV pair: value according additional parameter = 3
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 8
comment: Behaviour_Lock_Unlock

type.dpt.field.6.10.i0
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
field size: 8
includes digit: type.digit.s8
unit: NUM

Power
type: Quantity Kind
type: NamedIndividual
comment: Power is the rate at which work is performed or energy is transmitted, or the amount of energy required or expended for a given unit of time. As a rate of change of work done or the energy of a subsystem, power is work divided by time.

Current Colour RGBW
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: has datapoint type
  has value: Converter Info
subject: 423.82
subject: Current Colour RGBW
subject: CC_RGBW
subject: 82
interface object type annotation: 423
property identifier annotation: 82

Value SelfInductance
has communication mode: S
subject: 14.62
subject: 14.062
subject: Value SelfInductance
datapoint type major number: 14
is assembled with: type.dpt.field.14.62.i0
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
datapoint type minor number: 62
label: Value SelfInductance
comment: DPT 14.062: Value of self inductance

type.dpt.field.22.1010.i0.ActivationStateOfChannel1
field name: ActivationStateOfChannel1
field type: B
includes KV pair: The visual effect of channel 1 is active = 1
includes KV pair: type.kvpair.22.1010.i0.0
comment: Activation state of channel 1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1

OccModeNext
has communication mode: LTE
type: DatapointType
type: NamedIndividual
datapoint type minor number: 104
label: OccModeNext
comment: a point representing DPT 206.104: OccModeNext
datapoint type major number: 206
subject: 206.104
subject: OccModeNext
is assembled with: type.dpt.field.206.104.i1.Time
is assembled with: type.dpt.field.206.104.i0.OccMode
dpt bit size max: 24

Alarm Control
has communication mode: S
is assembled with: c
is assembled with: type.dpt.field.2.5.i0.alarm
description: a point representing DPT 2.005: Alarm Control
subject: 2.5
subject: Alarm Control
subject: 2.005
datapoint type minor number: 5
type: DatapointType
type: NamedIndividual
dpt bit size max: 2
datapoint type major number: 2

Percent V8
has communication mode: S
subject: 6.1
subject: 6.001
subject: Percent V8
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
label: Percent V8
dpt bit size max: 8
datapoint type major number: 6
is assembled with: type.dpt.field.6.1.i0
comment: a point representing DPT 6.001: Percent V8

set = 1
value KNX: 1
value API: set
type: NamedIndividual

Restriction
on property: pointName
has value: TempRoomSetpUserAbsEff

Gateway
type: Class
subclass of: Device
comment: A Gateway is a network node (Device) that connects two networks with different transmission protocols and data formats typically between OSI Layers 4-5 (e.g. KNX and BACnet).

type.dpt.field.14.23.i0
includes digit: type.digit.f32
field resolution: 1.0
comment: electric field strength
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 32
unit: V-PER-M
field type: F

minimum
type: DatatypeProperty
type: FunctionalProperty
comment: Limits a numerical datapoint value in its applicative behavior to a minimum. Represents an external definition, hence it is also used from other concepts, therefore no domain is defined (merged ontologies -> intersection problems). The range xsd:decimal covers also numerical values with a fraction such as 12.34 or -13.56.
range: decimal

type.dpt.field.201.109.i0.StatusCommand
field name: StatusCommand
field size: 8
field index: 0
description: standard Status/Command
field type: Z8
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen

type.dpt.field.19.1.i19.Month
unit: MO
field type: U
field resolution: 1.0
field index: 19
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u4 1 12
comment: Month
field size: 4
field name: Month

type.dpt.field.frbc.om
includes DPT field: type.dpt.field.frbc.om.i4.OME
includes DPT field: type.dpt.field.frbc.om.i0.ID
includes DPT field: type.dpt.field.frbc.om.i2.OME CNT
includes DPT field: type.dpt.field.frbc.om.i3.CQ
includes DPT field: type.dpt.field.frbc.om.i1.AC
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
field index: 0

light breeze = 2
type: NamedIndividual
value API: lightBreeze
value KNX: 2

Value Charge DensityVolume
has communication mode: S
datapoint type major number: 14
datapoint type minor number: 13
label: Value Charge DensityVolume
type: DatapointType
type: NamedIndividual
subject: 14.13
subject: Value Charge DensityVolume
subject: 14.013
is assembled with: type.dpt.field.14.13.i0
dpt bit size max: 32
description: DPT 14.013: Value of volume charge density

type.dpt.field.21.1000.i3.Reserved
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field index: 3
field size: 5

type.dpt.field.10.1.i5.Day
field size: 3
includes KV pair: Saturday = 6
includes KV pair: type.kvpair.10.1.i5.2
includes KV pair: type.kvpair.10.1.i5.4
includes KV pair: Monday = 1
includes KV pair: no day = 0
includes KV pair: Sunday = 7
includes KV pair: type.kvpair.10.1.i5.3
includes KV pair: Friday = 5
field type: N
type: Datapoint Type Field
type: NamedIndividual
field name: Day
description: Day
field index: 5

DeltaTime10MSec
has communication mode: S
label: DeltaTime10MSec
subject: DeltaTime10MSec
subject: 8.003
subject: 8.3
is assembled with: type.dpt.field.8.3.i0
type: NamedIndividual
type: DatapointType
datapoint type minor number: 3
datapoint type major number: 8
dpt bit size max: 16
comment: a point representing DPT 8.003: DeltaTime10MSec

Access Data
has communication mode: S
is assembled with: type.dpt.field.15.0.i3.P
is assembled with: type.dpt.field.15.0.i6.D2
is assembled with: type.dpt.field.15.0.i10.D6
is assembled with: type.dpt.field.15.0.i8.D4
is assembled with: type.dpt.field.15.0.i2.D
is assembled with: type.dpt.field.15.0.i5.D1
is assembled with: type.dpt.field.15.0.i1.C
is assembled with: type.dpt.field.15.0.i9.D5
is assembled with: type.dpt.field.15.0.i4.E
is assembled with: type.dpt.field.15.0.i7.D3
is assembled with: type.dpt.field.15.0.i0.Index
comment: a point representing DPT 15.000: Access Data
subject: Access Data
subject: 15.000
subject: 15.0
datapoint type major number: 15
type: DatapointType
type: NamedIndividual
datapoint type minor number: 0
dpt bit size max: 32

volume flow, 0,01 l/min = 66
value KNX: 66
type: NamedIndividual
value API: volumeFlow,0,01Lmin

Colour Actuator RGB(W)
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: Combined Switch On Off
  on property: isComposedByInput
  qualified cardinality: 1
subclass of: Restriction
  on class: Actual Dimming Value Blue
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on class: Absolute Set Value Control Green
  qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Current Colour RGBW
  on property: isComposedByOutput
type: Class
label: Colour Actuator RGB(W)
subject: Colour Actuator RGB(W)
subject: 423
subject: CARGB
interface object type annotation: 423

type.dpt.field.14.57.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
unit: UNITLESS
field size: 32
field type: F
comment: power factor
includes digit: type.digit.f32
field resolution: 1.0

type.dpt.field.9.2.i0
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
field index: 0
unit: http://qudt.org/vocab/unit/K
field size: 16
field type: F
includes digit: type.digit.f16

Restriction
has value: one
on property: has cardinality

Value Magnetic Flux
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 14.045
subject: Value Magnetic Flux
subject: 14.45
comment: DPT 14.045: Value of magnetic flux
datapoint type major number: 14
datapoint type minor number: 45
dpt bit size max: 32
is assembled with: type.dpt.field.14.45.i0

Heat Stage B Actuator Overridden
type: Class
subclass of: Function Point

255.x
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 255.major
subject: 255.x
datapoint type major number: 255
is assembled with: type.dpt.field.255.x.i0
dpt bit size max: 64
label: 255.x

type.dpt.field.230.1000.i1.Version
field type: U
field size: 8
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u8
description: Version
field name: Version
field index: 1

StatusGO
type: Class
subject: StatusGO
subject: 52
subject: 320.52
interface object type annotation: 320
comment: This DPA represents a generic Status (Z8), as described in KNX Vol 3/7/2, section 4.1.2. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring to the device: Bit 0) OutOfService (modeled by the state type tag:operationalStateOutOfService); Bit 1) Fault (modeled by the state type tag:operationalStateFaulty); Bit 2) Overridden (device being in maintenance mode, modeled by the state type tag:operationalStateMaintenance); Bit 3) InAlarm (modeled by the state type tag:operationalStateInAlarm); Bit 4) AlarmUnAck (modeled by the state type tag:operationalStateAlarmPending)
property identifier annotation: 52

type.dpt.field.7.12.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 16
includes digit: type.digit.u16
field type: U
field resolution: 1.0
unit: MilliA

Room
comment: A room is a space in a building that is delimited by walls/windows, ceilings, floors and has a door or a passage to enter the room, it can be subdivided into locations of type room segment.
label: Raum @de
type: Class
subclass of: Space
disjoint with: Room Segment

type.dpt.field.13.12.i0
includes digit: type.digit.s32
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
unit: V-A Reactive-HR
field resolution: 1.0
field size: 32

type.dpt.field.14.33.i0
description: frequency
field type: F
type: NamedIndividual
type: Datapoint Type Field
includes digit: type.digit.f32
field index: 0
field resolution: 1.0
unit: HZ
field size: 32

Ceiling
type: Locality
type: NamedIndividual
comment: A ceiling is an overhead interior surface that covers the upper limits of a room.

no control = 0
type: NamedIndividual
value KNX: 0
value API: noControl

The visual effect of channel 8 is active = 1
value KNX: 1
type: NamedIndividual
value API: theVisualEffectOfChannel8IsActive

Restriction
on property: pointName
has value: ActTargetPos

Restriction
on property: pointName
has value: TempRoomSetpUserOffset

LongTimePeriod Sec
has communication mode: S
dpt bit size max: 32
is assembled with: type.dpt.field.12.100.i0
comment: a point representing DPT 12.100: LongTimePeriod Sec
type: NamedIndividual
type: DatapointType
subject: 12.100
subject: LongTimePeriod Sec
datapoint type major number: 12
datapoint type minor number: 100

type.dpt.field.ec.i2.UNTIL
field name: UNTIL
field size: 64
field index: 2
type: Datapoint Type Field
type: NamedIndividual
description: timestamp when this constraint will be invalid
includes DPT: DateTime

Light Dimming Sensor Basic
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: InfoOnOff
subclass of: Restriction
  qualified cardinality: 1
  on class: SwitchOnOff
  on property: isComposedByOutput
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
  on class: ControlModeEff
type: Class
subject: 420
subject: Light Dimming Sensor Basic
subject: LDSB
interface object type annotation: 420

11.x
has communication mode: S
label: 11.x
datapoint type major number: 11
type: NamedIndividual
type: DatapointType
subject: 11.x
subject: 11.major
dpt bit size max: 24
is assembled with: type.dpt.field.11.x.i0

type.dpt.field.25.1000.i1.Busy
comment: Busy
field size: 4
field index: 1
unit: NUM
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field name: Busy
includes digit: type.digit.u4 0 3

EnableCoolEff
type: Class
label: EnableCoolEff
subject: 399.108
subject: 108
subject: EnableCoolEff
interface object type annotation: 399
property identifier annotation: 108

Response or spontaneous sending = 0
value API: responseOrSpontaneousSending
type: NamedIndividual
value KNX: 0

Info OnOff
type: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subject: 414.60
subject: Info OnOff
subject: IOO
subject: 60
interface object type annotation: 414
property identifier annotation: 60

The visual effect of channel 7 is inactive = 0
value API: theVisualEffectOfChannel7IsInactive
type: NamedIndividual
value KNX: 0

oil = 1
type: NamedIndividual
value API: oil
value KNX: 1

BlindsControlMode
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: BlindsControlMode
subject: 20.804
comment: a point representing DPT 20.804: BlindsControlMode
dpt bit size max: 8
label: BlindsControlMode
is assembled with: type.dpt.field.20.804.i0
datapoint type minor number: 804
datapoint type major number: 20

ControlModeUser
type: Class
subclass of: Class
label: ControlModeUser
property identifier annotation: 64
subject: 421.64
subject: 64
subject: ControlModeUser
interface object type annotation: 421

type.dpt.field.517.500.i4.lr.Reserved
description: reserved bits
includes reserved bit: type.bit.reserved
field type: r
field index: 4
field name: RESERVED
type: Datapoint Type Field
type: NamedIndividual
field size: 3

type.dpt.field.30.1010.i7.ActivationStateOfChannel8
description: Activation state of channel 8
field name: ActivationStateOfChannel8
field index: 7
field type: B
includes KV pair: type.kvpair.30.1010.i7.1
includes KV pair: type.kvpair.30.1010.i7.0
type: Datapoint Type Field
type: NamedIndividual
field size: 1

Meeting Room
comment: A meeting room, conference room, or conference hall is a room provided for singular events such as business conferences and meetings. Preferably used with an Room.
type: LocationUsage
type: NamedIndividual

TempRoomSetpUserOffsetEff
type: Class
subject: 100.58
subject: 58
subject: TempRoomSetpUserOffsetEff
property identifier annotation: 58
interface object type annotation: 100

type.dpt.field.213.100.i2.TempSetpStdby
field size: 16
field name: TempSetpStdby
field index: 2
unit: DEG C
comment: room temperature setpoint standby
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767

Restriction
on property: pointName
has value: TempRoomSetpUserAbs

Restriction
on property: has operation kind
qualified cardinality: 1

HVACModeUser
type: Class
subject: 80
subject: 397.80
subject: HVACModeUser
subclass of: Restriction
  on property: has datapoint type
  has value: HVACMode
subclass of: Class
  intersection of: Datapoint
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
interface object type annotation: 397
property identifier annotation: 80

Value Angular Momentum
has communication mode: S
subject: 14.008
subject: Value Angular Momentum
subject: 14.8
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
label: Value Angular Momentum
datapoint type minor number: 8
description: DPT 14.008: Value of angular momentum
datapoint type major number: 14
is assembled with: type.dpt.field.14.8.i0

LongTimePeriod Hrs
has communication mode: S
subject: LongTimePeriod Hrs
subject: 12.102
datapoint type major number: 12
datapoint type minor number: 102
type: DatapointType
type: NamedIndividual
description: a point representing DPT 12.102: LongTimePeriod Hrs
dpt bit size max: 32
is assembled with: type.dpt.field.12.102.i0

first: Restriction
  has value: 804
  on property: interface object type
rest: nil

type.dpt.field.245.600.i2.Reserved
includes reserved bit: type.bit.reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 2
field name: Reserved
field size: 2
field type: r

Off State
description: This state type expresses that an equipment, such as a luminaire, is switched off. This state type is the inverse of the 'On State' state type.
type: State Type
type: NamedIndividual

Value 1 Count
has communication mode: S
datapoint type minor number: 10
subject: 6.10
subject: 6.010
subject: Value 1 Count
is assembled with: type.dpt.field.6.10.i0
type: NamedIndividual
type: DatapointType
label: Value 1 Count
comment: a point representing DPT 6.010: Value 1 Count
dpt bit size max: 8
datapoint type major number: 6

219.x
has communication mode: S
datapoint type major number: 219
is assembled with: type.dpt.field.219.x.i0
dpt bit size max: 48
label: 219.x
type: DatapointType
type: NamedIndividual
subject: 219.major
subject: 219.x

Actual Dimming Value Red
type: Class
subclass of: Class
subclass of: Restriction
  on property: has datapoint type
  has value: scaling
subject: Actual Dimming Value Red
subject: 423.83
subject: 83
subject: ASV_R
property identifier annotation: 83
interface object type annotation: 423

Unknown Device type = 15
value API: unknownDeviceType
type: NamedIndividual
value KNX: 15

Electricity, AC
description: Alternating current electricity
type: NamedIndividual
type: Phenomenon

Scene Control
type: Class
subclass of: ApplicationFunction
comment: A specific Application Function category that controls a customized setting of different trades for an activity or situation. Scene controllers are intelligent pre-configured settings that orchestrate multiple devices and settings with a single touch of a button or a simple voice command. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.

at base condition = 2
value API: atBaseCondition
value KNX: 2
type: NamedIndividual

5.x
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.5.x.i0
datapoint type major number: 5
label: 5.x
dpt bit size max: 8
subject: 5.x
subject: 5.major

Value Curr
has communication mode: S
subject: Value Curr
subject: 9.21
subject: 9.021
comment: a point representing DPT 9.021: Value Curr
datapoint type major number: 9
dpt bit size max: 16
label: Value Curr
datapoint type minor number: 21
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.9.21.i0

type.dpt.field.20.1001.i0
comment: AddInfoType
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes KV pair: type.kvpair.20.1001.i0.3
includes KV pair: type.kvpair.20.1001.i0.7
includes KV pair: type.kvpair.20.1001.i0.1
includes KV pair: type.kvpair.20.1001.i0.5
includes KV pair: type.kvpair.20.1001.i0.2
includes KV pair: type.kvpair.20.1001.i0.6
includes KV pair: Relative timestamp = 4
field size: 8
field type: N

volume flow, 0,001 l/min = 65
value KNX: 65
type: NamedIndividual
value API: volumeFlow,0,001Lmin

type.dpt.field.20.106.i0
includes KV pair: type.kvpair.20.106.i0.5
includes KV pair: EmergPressure = 1
includes KV pair: EmergDepressure = 2
includes KV pair: EmergShutdown = 4
includes KV pair: type.kvpair.20.106.i0.0
includes KV pair: type.kvpair.20.106.i0.3
field type: N
type: Datapoint Type Field
type: NamedIndividual
field index: 0
description: HVACEmergMode
field size: 8

fresh breeze = 5
value KNX: 5
value API: freshBreeze
type: NamedIndividual

type.dpt.field.218.1.i1.VolumeLiter
includes digit: type.digit.s32
type: Datapoint Type Field
type: NamedIndividual
field type: V
field name: VolumeLiter
field size: 32
field index: 1
comment: volume in liter
field resolution: 1.0
unit: http://qudt.org/vocab/unit/L

Audio Control
comment: A specific Application Function category that controls the audio system. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: ApplicationFunction
type: Class

type.dpt.field.8.x.i0
comment: 2-byte signed value
field index: 0
includes digit: type.digit.s16
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field type: V

Fault = 1
value API: fault
value KNX: 1
type: NamedIndividual

Converter Info
has communication mode: S
datapoint type major number: 251
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.251.600.i3.mR
is assembled with: type.dpt.field.251.600.i8.G
is assembled with: type.dpt.field.251.600.i5.Reserved
is assembled with: type.dpt.field.251.600.i1.mB
is assembled with: type.dpt.field.251.600.i7.B
is assembled with: type.dpt.field.251.600.i4.Reserved
is assembled with: type.dpt.field.251.600.i9.R
is assembled with: type.dpt.field.251.600.i6.W
is assembled with: type.dpt.field.251.600.i0.mW
is assembled with: type.dpt.field.251.600.i2.mG
description: a point representing DPT 251.600: Converter Info
subject: 251.600
subject: Converter Info
dpt bit size max: 48
datapoint type minor number: 600

type.dpt.field.22.103.i6.AdditionalHeatingCoolingStage
field type: B
field size: 1
includes KV pair: Inactive = 0
includes KV pair: type.kvpair.active
field name: AdditionalHeatingCoolingStage
type: Datapoint Type Field
type: NamedIndividual
comment: Additional heating/cooling stage (2. Stage)
field index: 6

at measurement condition = 3
value API: atMeasurementCondition
type: NamedIndividual
value KNX: 3

229.x
has communication mode: S
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.229.x.i0
subject: 229.x
subject: 229.major
label: 229.x
datapoint type major number: 229
dpt bit size max: 48

Hour of day, Minutes and Seconds field valid = 0
value API: hourOfDay,MinutesAndSecondsFieldVal
type: NamedIndividual
value KNX: 0

type.dpt.field.ec.i4.ID
field index: 4
description: id of the energy constraint
field type: U
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual
field size: 4
field name: ID

type.dpt.field.21.1.i4.AlarmUnAck
field name: AlarmUnAck
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
type: Datapoint Type Field
type: NamedIndividual
comment: alarm status of corresponding Datapoint is not acknowledged
field index: 4
field size: 1

SwitchOnOffControlCmd
type: Class
label: SwitchOnOffControlCmd
interface object type annotation: 417
subject: 417.60
subject: SwitchOnOffControlCmd
subject: 60
property identifier annotation: 60
subclass of: Restriction
  on property: has operation kind

is status of
range: Function Point
type: AsymmetricProperty
type: IrreflexiveProperty
type: ObjectProperty
sub property of: isReferencedBy
comment: An OP relationship to express the control/status relation, separated in KNX by using different function points (GAs) for each. A function point relates to another function point, with the specific meaning of FP x represents the status value of the (setpoint/comand value) of FP y.
domain: Function Point

type.dpt.field.209.103.i2.CtrlStatus
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: CtrlStatus
comment: Controller status. on: controller is working (default if not supported). off: controller is stopped; no control of water temperature
includes DPT: Bool
field index: 2

value according additional parameter = 3
type: NamedIndividual
value KNX: 3
value API: valueAccordingAdditionalParameter

25.x
has communication mode: S
subject: 25.x
subject: 25.major
type: NamedIndividual
type: DatapointType
label: 25.x
dpt bit size max: 8
datapoint type major number: 25
is assembled with: type.dpt.field.25.x.i0

Restriction
on data range: string
on property: mac version
max qualified cardinality: 1

FanStep
type: Class
subject: 372.56
subject: 56
subject: FanStep
label: FanStep
property identifier annotation: 56
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  has value: UCount Value 8 Z
  on property: has datapoint type
interface object type annotation: 372

Monitoring
type: Class
subclass of: ApplicationFunction
comment: A specific Application Function category for 'monitoring' a zone, equipment or energy consumption (metering). The category is derived from parent concepts that are specified as part of the EN 50090-6-2.

type.dpt.field.20.114.i0
includes KV pair: type.kvpair.20.114.i0.11
includes KV pair: Gas device = 3
includes KV pair: Heat cost allocator = 8
includes KV pair: type.kvpair.20.114.i0.10
includes KV pair: type.kvpair.20.114.i0.6
includes KV pair: Electricity meter = 2
includes KV pair: type.kvpair.20.114.i0.0
includes KV pair: type.kvpair.20.114.i0.40
includes KV pair: type.kvpair.20.114.i0.7
includes KV pair: breaker (electricity) = 32
includes KV pair: type.kvpair.20.114.i0.13
includes KV pair: type.kvpair.20.114.i0.4
includes KV pair: Steam meter = 5
includes KV pair: void device type = 255
includes KV pair: type.kvpair.20.114.i0.12
includes KV pair: Oil meter = 1
includes KV pair: type.kvpair.20.114.i0.33
includes KV pair: garbage = 41
field size: 8
comment: MeteringDeviceType
field type: N
type: Datapoint Type Field
type: NamedIndividual
field index: 0

13.x
has communication mode: S
datapoint type major number: 13
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
label: 13.x
subject: 13.major
subject: 13.x
is assembled with: type.dpt.field.13.x.i0

Underfloor Heating
type: EquipmentType
type: NamedIndividual
description: Heats a space using pipes or cables embedded beneath floor. The most common kind of radiant heating is underfloor heating. There are three types of underfloor heating: hot air systems, hot water systems and electric systems.

type.dpt.field.22.101.i14.OverheatAlarm
type: Datapoint Type Field
type: NamedIndividual
comment: OverheatAlarm
includes KV pair: No alarm = 0
includes KV pair: type.kvpair.alarm
field type: B
field index: 14
field size: 1
field name: OverheatAlarm

Restriction
on class: Class
qualified cardinality: 1
on property: has operation kind

type.dpt.field.244.600.i5.HSswitch
type: Datapoint Type Field
type: NamedIndividual
description: HS - Hardwired switch
field size: 1
field index: 5
field type: B
includes KV pair: type.kvpair.244.600.i5.0
includes KV pair: type.kvpair.244.600.i5.1
field name: HS switch

type.dpt.field.207.600.i2.Forced
field size: 1
field name: Forced
type: Datapoint Type Field
type: NamedIndividual
comment: true = forced on/off control is active, e.g., via input SwitchedOnOffForced
includes DPT: Bool
field index: 2

ControlModeEff
type: Class
property identifier annotation: 54
interface object type annotation: 421
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subject: ControlModeEff
subject: 54
subject: 421.54

type.dpt.field.20.4.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: Priority
field size: 8
includes KV pair: Medium = 1
includes KV pair: type.kvpair.20.4.i0.0
includes KV pair: Low = 2
includes KV pair: type.kvpair.20.4.i0.3
field type: N

type.dpt.field.255.1.i0.Latitude
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: F
includes digit: type.digit.f32
comment: Latitude information
unit: DEG
field resolution: 1.0
field name: Latitude
field size: 32

type.dpt.field.231.1.i1.Language
comment: Language as in DPT_Language-CodeAlpha2_ASCII (234.001) this is ISO 639-1 alpha-2
field name: Language
includes DPT: LanguageCodeAlpha2 ASCII
field index: 1
type: Datapoint Type Field
type: NamedIndividual
field size: 16

Value Speed
has communication mode: S
subject: 14.65
subject: 14.065
subject: Value Speed
type: NamedIndividual
type: DatapointType
datapoint type major number: 14
is assembled with: type.dpt.field.14.65.i0
label: Value Speed
comment: DPT 14.065: Value of speed
datapoint type minor number: 65
dpt bit size max: 32

type.dpt.field.220.100.i0.Temp
field size: 16
field resolution: 0.02
field name: Temp
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767
field index: 0
comment: absolute temperature value
unit: DEG C

energy, 10000 kJ = 15
type: NamedIndividual
value API: energy,10000KJ
value KNX: 15

Building Mode Z
has communication mode: LTE
subject: Building Mode Z
subject: 201.107
is assembled with: type.dpt.field.201.107.i0.StatusCommand
is assembled with: type.dpt.field.201.107.i1.BuildingMode
dpt bit size max: 16
description: a point representing DPT 201.107: Building Mode Z
datapoint type minor number: 107
type: NamedIndividual
type: DatapointType
datapoint type major number: 201

type.dpt.field.219.1.i6.AlarmText Sup
field index: 6
field size: 1
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field name: AlarmText_Sup
field type: B
type: Datapoint Type Field
type: NamedIndividual
description: AlarmText_Sup

no day = 0
value KNX: 0
type: NamedIndividual
value API: noDay

type.dpt.field.20.1208.i0
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes KV pair: Standard = 1
includes KV pair: type.kvpair.20.1208.i0.0
field type: N

type.dpt.field.19.1.i15.HourOfDay
field size: 5
unit: HR
description: HourOfDay
field name: HourOfDay
field type: U
field resolution: 1.0
field index: 15
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u5 0 24

field size
comment: Field size, used to define the actual size in bits of a KNX data field as part of an entire datapoint type. The size may be not present, in case of an inluded datapoint type (DPT).
type: DatatypeProperty
type: FunctionalProperty
sub property of: datapointTypeDataField
range: nonNegativeInteger

first: Restriction
  has value: Info OnOff
  on property: pointName
rest:
  rest: nil

Value Acceleration Angular
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 14.1
subject: Value Acceleration Angular
subject: 14.001
label: Value Acceleration Angular
datapoint type major number: 14
description: DPT 14.001: Value of angular acceleration
dpt bit size max: 32
is assembled with: type.dpt.field.14.1.i0
datapoint type minor number: 1

Restriction
has value: 60
on property: property identifier

type.dpt.field.218.2.i1.FlowRate
description: Flow Rate in m³/h with high resolution
type: NamedIndividual
type: Datapoint Type Field
field resolution: 0.0001
field name: FlowRate
unit: M3-PER-HR
field index: 1
field size: 32
includes digit: type.digit.s32
field type: V

type.dpt.field.225.3.i0.Tariff
field size: 8
comment: The next active Tariff after expiration of the delay time
field name: Tariff
includes DPT: Tariff
type: Datapoint Type Field
type: NamedIndividual
field index: 0

22,6 s = 11
value KNX: 11
type: NamedIndividual
value API: 22,6S

type.dpt.field.20.1002.i0
type: Datapoint Type Field
type: NamedIndividual
comment: ModeSelect
field type: N
includes KV pair: type.kvpair.20.1002.i0.1
includes KV pair: asynchronous + BiBat Slave = 2
includes KV pair: asynchronous = 0
field size: 8
field index: 0

type.dpt.field.243.600.i0.B
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field type: B
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
field name: B
field size: 1
comment: This field shall indicate whether the Brightness information in the field Brightness is valid or not.

certfication status
type: DatatypeProperty
type: FunctionalProperty
comment: Certfication status of an application program.

DALI Diagnostics
has communication mode: S
subject: DALI Diagnostics
subject: 238.600
type: DatapointType
type: NamedIndividual
datapoint type minor number: 600
is assembled with: type.dpt.field.238.600.i0.DeviceAddress
is assembled with: type.dpt.field.238.600.i2.BallastFailure
is assembled with: type.dpt.field.238.600.i1.LampFailure
datapoint type major number: 238
comment: a point representing DPT 238.600: DALI Diagnostics
dpt bit size max: 8

Phenomenon
type: Class
comment: The tag category contains individuals that describe a phenomonom (including substances) that can only be indirectly observed or actuated upon as part of the building control system. The tag category does not describe concrete existing things, for example the person John Smith.
subclass of: Tag

type.dpt.field.244.600.i0.CF
field size: 2
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: CF
includes KV pair: type.kvpair.244.600.i0.2
includes KV pair: type.kvpair.244.600.i0.1
includes KV pair: type.kvpair.244.600.i0.0
comment: Converter Failure
field type: N

type.dpt.field.22.101.i15.Reserved
field index: 15
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 1
field name: Reserved
field type: r

DewPointStatus
type: Class
subclass of: Class
subject: 344.51
subject: 51
subject: DewPointStatus
interface object type annotation: 344
property identifier annotation: 51

Registered (S-FSK) - reserved (G3-PLC) = 2
value KNX: 2
type: NamedIndividual
value API: registered(S-FSK)-Reserved(G3-PLC)

Cool Stage B Actuator Status
subclass of: Function Point
subclass of: Restriction
  qualified cardinality: 1
  on property: has operation kind
subclass of: Restriction
  qualified cardinality: 1
  on property: has operation kind
type: Class

type.dpt.field.256.x.i0
type: Datapoint Type Field
type: NamedIndividual
field string schema: raw
field type: A[n]
field index: 0
field size: 128

type.dpt.field.252.600.i3.MaskCR
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
type: Datapoint Type Field
type: NamedIndividual
field name: MaskCR
field type: B
field index: 3
field size: 1
comment: validity of the fields CR and Step Code Colour Red.

trigger (0) = 0
type: NamedIndividual
value KNX: 0
value API: trigger(0)

Programmable Controller
description: A programmable logic controller (PLC) or programmable controller is an industrial computer that has been ruggedized and adapted for the control of manufacturing processes, such as assembly lines, machines, robotic devices, or any activity that requires high reliability, ease of programming, and process fault diagnosis.
type: NamedIndividual
type: EquipmentType

None = 0
type: NamedIndividual
value KNX: 0
value API: none

HVACModeEff
type: Class
property identifier annotation: 80
interface object type annotation: 398
label: HVACModeEff
subclass of: Restriction
  on property: has datapoint type
  has value: HVACMode
subject: 80
subject: 398.80
subject: HVACModeEff

type.dpt.field.20.109.i0
comment: DamperMode
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.20.109.i0.3
includes KV pair: Extract air, e.g. for VAV = 4
includes KV pair: Supply air, e.g. for VAV = 2
includes KV pair: type.kvpair.20.109.i0.1
field index: 0
field size: 8
field type: N

first: Restriction
  has value: one
  on property: has cardinality
rest: nil

FanStepUser
type: Class
interface object type annotation: 399
subject: 75
subject: 399.75
subject: FanStepUser
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Class
property identifier annotation: 75

238.x
has communication mode: S
label: 238.x
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.238.x.i0
subject: 238.x
subject: 238.major
datapoint type major number: 238

type.dpt.field.8.5.i0
includes digit: type.digit.s16
field size: 16
field resolution: 1.0
unit: SEC
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0

Pool
description: A swimming pool, swimming bath, wading pool, paddling pool, or simply pool, is a structure designed to hold water to enable swimming or other leisure activities. Preferably used with an Space.
type: LocationUsage
type: NamedIndividual

Restriction
has value: many
on property: has cardinality

Outside
type: Class
comment: Expresses if an location is outside in perspective of a Building. A Space, Site or SiteSegment can be outside of a Building.
disjoint with: Room Segment
disjoint with: Room
label: Außenbereich @de
subclass of: Location

type.dpt.field.14.7.i0
field index: 0
field size: 32
field type: F
comment: angle, degree
unit: DEG
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual

Restriction
on property: interface object type
has value: 399

DateTime OpenClose
has communication mode: S
is assembled with: type.dpt.field.265.9.i2.DateAndTime
is assembled with: type.dpt.field.265.9.i0.BinaryInformation
is assembled with: type.dpt.field.265.9.i1.Reserved
datapoint type minor number: 9
type: NamedIndividual
type: DatapointType
label: DateTime OpenClose
comment: a point representing DPT 265.009: DateTime OpenClose
subject: DateTime OpenClose
subject: 265.009
subject: 265.9
dpt bit size max: 72
datapoint type major number: 265

type.dpt.field.246.600.i2.BatteryDurationFailure
field name: BatteryDurationFailure
comment: Battery Duration Failure
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field index: 2
field type: B
field size: 1

type.dpt.field.209.103.i1.Fault
field size: 1
comment: some failure in the water temperature controller
type: Datapoint Type Field
type: NamedIndividual
field index: 1
field name: Fault
includes DPT: Bool

type.dpt.field.21.x.i0
description: 8-bit set
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field string schema: raw
field size: 8

memory function value = 4
value KNX: 4
type: NamedIndividual
value API: memoryFunctionValue

type.dpt.field.275.x.i0
field size: 64
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
description: F16F16F16F16
field string schema: raw

DateTime Switch
has communication mode: S
is assembled with: type.dpt.field.265.1.i1.Reserved
is assembled with: type.dpt.field.265.1.i2.DateAndTime
is assembled with: type.dpt.field.265.1.i0.BinaryInformation
datapoint type major number: 265
description: a point representing DPT 265.001: DateTime Switch
label: DateTime Switch
subject: DateTime Switch
subject: 265.1
subject: 265.001
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
dpt bit size max: 72

TimePeriodHrs
has communication mode: S
type: DatapointType
type: NamedIndividual
label: TimePeriodHrs
comment: a point representing DPT 7.007: TimePeriodHrs
datapoint type minor number: 7
subject: 7.007
subject: TimePeriodHrs
subject: 7.7
datapoint type major number: 7
is assembled with: type.dpt.field.7.7.i0
dpt bit size max: 16

Value ThermoelectricPower
has communication mode: S
datapoint type major number: 14
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.14.73.i0
subject: 14.073
subject: 14.73
subject: Value ThermoelectricPower
datapoint type minor number: 73
description: DPT 14.073: Value of thermoelectric power

type.dpt.field.212.x.i0
comment: S16S16S16
field size: 48
field string schema: raw
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0

type.dpt.field.10.x.i0
field index: 0
field size: 24
field string schema: raw
comment: time
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]

type.dpt.field.27.1.i14.IOO15
includes KV pair: output state is Off = 0
includes KV pair: output state is On = 1
field type: B
field index: 14
field size: 1
field name: IOO15
type: Datapoint Type Field
type: NamedIndividual
comment: Info On Off Output 15

type.dpt.field.525.500.i2.fv.Reserved
includes reserved bit: type.bit.reserved
field type: r
description: Reserved bits
field name: RESERVED
type: Datapoint Type Field
type: NamedIndividual
field index: 2
field size: 6

Light Switch Request
subclass of: Restriction
  has value: Lighting
  on property: operates for trade
subclass of: Function Point
type: Class

Units for HCA = 110
value API: unitsForHCA
value KNX: 110
type: NamedIndividual

type.dpt.field.27.1.i27.MaskBitIOO12
comment: Mask Bit Info On Off Output 12
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B
field index: 27
field size: 1
field name: MaskBitIOO12

type.dpt.field.20.1209.i0
field type: N
includes KV pair: Historical single-phase = 1
includes KV pair: Historical three-phase = 2
includes KV pair: None = 0
includes KV pair: Standard three-phase = 4
includes KV pair: Standard single-phase = 3
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 8

Combined Status RTSM
has communication mode: S
datapoint type major number: 21
is assembled with: type.dpt.field.21.107.i0.WindowStatusEffective
is assembled with: type.dpt.field.21.107.i2.ComfortPushButtonEffective
is assembled with: type.dpt.field.21.107.i5.Reserved
is assembled with: type.dpt.field.21.107.i4.HVACModeUserModeStatus
is assembled with: type.dpt.field.21.107.i1.PresenceStatusEffective
is assembled with: type.dpt.field.21.107.i3.ComfortProlongationUserStatus
subject: Combined Status RTSM
subject: 21.107
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 21.107: Combined Status RTSM
label: Combined Status RTSM
dpt bit size max: 8
datapoint type minor number: 107

type.dpt.field.252.600.i9.cB
field index: 9
description: Shall specify whether the colour component blue shall be increased or decreased.
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
field name: cB
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field type: B

17.x
has communication mode: S
label: 17.x
type: NamedIndividual
type: DatapointType
subject: 17.major
subject: 17.x
dpt bit size max: 8
datapoint type major number: 17
is assembled with: type.dpt.field.17.x.i0

one PB/binary input, Off / DimDown message sent = 3
value KNX: 3
value API: onePBbinaryInput,OffDimDownMessageS
type: NamedIndividual

Individual Room Control
subclass of: Emission Control
comment: The Application Function controls the air temperature of an single room, thereby maximizing comfort and minimizing energy costs.
type: Class

Oil meter = 1
value API: oilMeter
type: NamedIndividual
value KNX: 1

type.dpt.field.207.600.i6.LocalOverride
comment: true = actuator setvalue is locally overridden, e.g. via a local user interface
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 6
field name: LocalOverride
includes DPT: Bool

The visual effect of channel 18 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel18IsActive
value KNX: 1

type.dpt.field.15.0.i3.P
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.15.0.i3.1
includes KV pair: not accepted = 0
field name: P
field size: 1
field type: B
comment: Permission (informs about the access decision made by the controlling device)
field index: 3

type.dpt.field.14.12.i0
includes digit: type.digit.f32
unit: C-PER-M2
type: Datapoint Type Field
type: NamedIndividual
comment: charge density (surface)
field index: 0
field resolution: 1.0
field size: 32
field type: F

Water Difference Pressure Control
type: Class
subclass of: Water Control
comment: Application Functions that controls the quantity 'water pressure'.

SwitchOnOffForced
type: Class
subject: 417.61
subject: 61
subject: SwitchOnOffForced
subclass of: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has datapoint type
  has value: Switch Control
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
interface object type annotation: 417
property identifier annotation: 61

has tag
inverse of: isTagOf
type: ObjectProperty
range: Tag
comment: A parent OP relationship to express a general relation to a tag. The relationship specifies the OWL range class :Tag, allowing to express any relation to one of the individuals as part of the sub classes of :Tag. As it is also just a generic top OP of specialized (sub) OP relationship predicates, only the latter SHOULD be used.

type.dpt.field.3.x.i0
comment: 3-bit controlled
field string schema: raw
field size: 4
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0

Restriction
has value: 51
on property: property identifier

type.dpt.field.20.102.i0
field index: 0
includes KV pair: type.kvpair.20.102.i0.0
includes KV pair: type.kvpair.20.102.i0.1
includes KV pair: Building Protection = 4
includes KV pair: Standby = 2
includes KV pair: type.kvpair.20.102.i0.3
field size: 8
field type: N
comment: HVACMode
type: Datapoint Type Field
type: NamedIndividual

Restriction
on property: pointName
has value: PresenceStatus

mass, 0,001 kg = 24
type: NamedIndividual
value API: mass,0,001Kg
value KNX: 24

Circuit, AC
description: Electrical circuits for alternative currents. This is a specialization of the tag "Circuit".
type: Locality
type: NamedIndividual

type.dpt.field.209.100.i1.Fault
comment: some failure in boiler sequence: HPM itself or boiler(s) have a failure (mainly used for monitoring)
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes DPT: Bool
field name: Fault
field index: 1

DeltaTimeHrs
has communication mode: S
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
subject: 8.007
subject: 8.7
subject: DeltaTimeHrs
comment: a point representing DPT 8.007: DeltaTimeHrs
label: DeltaTimeHrs
datapoint type minor number: 7
datapoint type major number: 8
is assembled with: type.dpt.field.8.7.i0

filtering by Domain Address and by Serial number table = 3
value KNX: 3
value API: filteringByDomainAddressAndBySerial
type: NamedIndividual

is point interface of
type: ObjectProperty
range: Datapoint
domain: PointInterface
sub property of: isTagOf

type.dpt.field.20.8.i0
description: PSUMode
field size: 8
includes KV pair: enabled (PSU/DPSU fixed on) = 1
includes KV pair: type.kvpair.20.8.i0.2
includes KV pair: type.kvpair.20.8.i0.0
field type: N
type: Datapoint Type Field
type: NamedIndividual
field index: 0

first: iso-8859-1

The visual effect of channel 17 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel17IsActive
value KNX: 1

HVACMode
type: Class
label: HVACMode
subject: 398.51
subject: HVACMode
subject: 51
interface object type annotation: 398
property identifier annotation: 51

Light Current Dimming Value
subclass of: Restriction
  has value: Lighting
  on property: operates for trade
subclass of: Restriction
  on property: is status of
subclass of: Function Point
subclass of: Restriction
  has value: qk ph light illuminance
  on property: observesPhenomenonQualityKind
subclass of: Restriction
  qualified cardinality: 1
  on property: has operation kind
type: Class

type.dpt.field.21.103.i0.Fault
field type: B
field name: Fault
includes KV pair: type.kvpair.21.103.i0.0
includes KV pair: fault = 1
comment: Fault
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1

rest: nil
first: Restriction
  on property: interface object type
  has value: 321

rest: nil
first: Restriction
  has value: 802
  on property: interface object type

Restriction
has value: one
on property: has cardinality

ForcedPosition
type: Class
interface object type annotation: 400
label: ForcedPosition
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subject: 400.51
subject: 51
subject: ForcedPosition
property identifier annotation: 51

Individual Address
sub property of: deviceData
type: FunctionalProperty
type: DatatypeProperty
comment: From MaC assigend individual address (IA).
range: string

1 stage = 1
value KNX: 1
value API: 1Stage
type: NamedIndividual

type.dpt.field.520.500.i1.ss.SLT
field index: 1
field type: U
field size: 4
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual
field name: SLT
description: current running slot

Pressure
type: NamedIndividual
type: Quantity Kind
comment: Pressure is an effect which occurs when a force is applied on a surface. Pressure is the amount of force acting on a unit area. Pressure is distinct from stress, as the former is the ratio of the component of force normal to a surface to the surface area. Stress is a tensor that relates the vector force to the vector area.

Percent V16 Z
has communication mode: LTE
type: NamedIndividual
type: DatapointType
datapoint type major number: 205
is assembled with: type.dpt.field.205.17.i1.RelSignedValue
is assembled with: type.dpt.field.205.17.i0.StatusCommand
datapoint type minor number: 17
subject: 205.17
subject: 205.017
subject: Percent V16 Z
dpt bit size max: 24
comment: a point representing DPT 205.017: Percent_V16_Z
label: Percent V16 Z

Direction 2
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
includes DPT: Open Close
field name: direction2

Dew Point Status Sensor
type: Class
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Class
subject: Dew Point Status Sensor
subject: DPS
subject: 344
interface object type annotation: 344

Restriction
on property: writable
max qualified cardinality: 1
on data range: boolean

Close = 1
type: NamedIndividual
is applicable datapoint enum of: closed
value API: close
value KNX: 1

Alarm
has communication mode: S
subject: Alarm
subject: 1.5
subject: 1.005
datapoint type major number: 1
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 1.005: Alarm
datapoint type minor number: 5
dpt bit size max: 1
is assembled with: Alarm

Light Dimming Actuator Basic
subclass of: Restriction
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByOutput
subclass of: Restriction
  on class: Class
    intersection of: FadeToControlCmd
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  qualified cardinality: 1
subclass of: Class
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: ControlModeEff
subclass of: Restriction
  on class: NightMode
  on property: isComposedByInput
  max qualified cardinality: 1
subclass of: Restriction
  on class: dpa.418.73
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  on class: OverloadDetection
  max qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByInput
  on class: dpa.418.64
  qualified cardinality: 1
type: Class
subject: Light Dimming Actuator Basic
subject: 418
subject: LDAB
interface object type annotation: 418

type.dpt.field.20.115.i0
comment: HumDehumMode
field type: N
includes KV pair: type.kvpair.20.115.i0.1
includes KV pair: dehumidification = 2
includes KV pair: inactive = 0
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

presence simulation = 1
value API: presenceSimulation
type: NamedIndividual
value KNX: 1

209.x
has communication mode: LTE
datapoint type major number: 209
subject: 209.major
subject: 209.x
is assembled with: type.dpt.field.209.x.i0
type: NamedIndividual
type: DatapointType
dpt bit size max: 24
label: 209.x

Restriction
on property: has operation kind
qualified cardinality: 1

type.dpt.field.254.600.i6.StepCodeColourRed
field type: U
field resolution: 1.0
field size: 3
type: Datapoint Type Field
type: NamedIndividual
field index: 6
comment: Shall specify the fading step size or to the code to stop the fading of the colour red
field name: StepCodeColourRed
includes digit: type.digit.u3

type.dpt.field.241.800.i0.UpperEndPos
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field name: UpperEndPos
type: Datapoint Type Field
type: NamedIndividual
comment: Upper end pos. reached
field index: 0
field size: 1

Breaker Status
has communication mode: S
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
label: Breaker Status
comment: a point representing DPT 20.1203: Breaker Status
is assembled with: type.dpt.field.20.1203.i0
datapoint type major number: 20
subject: 20.1203
subject: Breaker Status
datapoint type minor number: 1203

No alarm = 0
value API: noAlarm
value KNX: 0
type: NamedIndividual

Restriction
has value: one
on property: has cardinality

ApparantEnergy
has communication mode: S
label: ApparantEnergy
type: NamedIndividual
type: DatapointType
subject: 13.11
subject: ApparantEnergy
subject: 13.011
datapoint type major number: 13
datapoint type minor number: 11
comment: a point representing DPT 13.011: ApparantEnergy
is assembled with: type.dpt.field.13.11.i0
dpt bit size max: 32

TempRoomSetpHeatEff
type: Class
subject: TempRoomSetpHeatEff
subject: 100.55
subject: 55
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: has datapoint type
subclass of: Restriction
  on property: has operation kind
label: TempRoomSetpHeatEff
property identifier annotation: 55
interface object type annotation: 100

InfoOnOff
type: Class
subject: IOO
subject: InfoOnOff
subject: 51
subject: 417.51
property identifier annotation: 51
interface object type annotation: 417

ComfortProlongUser
type: Class
interface object type annotation: 384
label: ComfortProlongUser
subclass of: Restriction
  on property: has datapoint type
  has value: Trigger
subject: 53
subject: 384.53
subject: ComfortProlongUser
property identifier annotation: 53
comment: This DPA changes the activation state of the comfort prolongation. Thus, it defines the two states tag:active and tag:inactive, which relate to the comfort level (represented as the state type tag:hvacModeComfort).

no change = 2
value KNX: 2
type: NamedIndividual
value API: noChange

The visual effect of channel 3 is inactive = 0
value API: theVisualEffectOfChannel3IsInactive
type: NamedIndividual
value KNX: 0

Switch On Off White
type: Class
subclass of: Restriction
  on property: has operation kind
  some values from: Class
    intersection of: Operation Kind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
interface object type annotation: 423
subject: Switch On Off White
subject: SOO_W
subject: 423.65
subject: 65
property identifier annotation: 65

type.dpt.field.243.600.i5.xaxis
unit: NUM
includes digit: type.digit.u16
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
comment: x-coordinate of the colour information
field size: 16
field name: xaxis
field index: 5

closed = 0
value API: closed
type: NamedIndividual
value KNX: 0

FanManual
type: Class
subject: 76
subject: FanManual
subject: 399.76
label: FanManual
property identifier annotation: 76
interface object type annotation: 399

Fan Speed Target
subclass of: Function Point
type: Class

Store Room
type: LocationUsage
type: NamedIndividual
comment: A store room is a room within a house where equipment not used in day-to-day activities is kept.

TimePeriod100MSec
has communication mode: S
subject: 7.004
subject: 7.4
subject: TimePeriod100MSec
is assembled with: type.dpt.field.7.4.i0
datapoint type major number: 7
comment: a point representing DPT 7.004: TimePeriod100MSec
type: NamedIndividual
type: DatapointType
datapoint type minor number: 4
dpt bit size max: 16

Scene Sensor
type: Class
subclass of: Restriction
  qualified cardinality: 1
  on class: NumberedSceneControl
  on property: isComposedByOutput
subclass of: Restriction
  on class: dpa.403.63
  on property: isComposedByOutput
  max qualified cardinality: 1
is incomplete: true
subject: 403
subject: Scene Sensor
subject: SCS
label: Scene Sensor
interface object type annotation: 403

Value Lux
has communication mode: S
subject: 9.4
subject: Value Lux
subject: 9.004
type: NamedIndividual
type: DatapointType
label: Value Lux
is assembled with: type.dpt.field.9.4.i0
datapoint type minor number: 4
datapoint type major number: 9
comment: a point representing DPT 9.004: Value Lux
dpt bit size max: 16

type.digit.u4 1 15
type: NamedIndividual
range min: 1
range max: 15

AbsSetvalueControlCmd
type: Class
subclass of: Restriction
  on property: has operation kind
label: AbsSetvalueControlCmd
subject: 65
subject: AbsSetvalueControlCmd
subject: 418.65
interface object type annotation: 418
property identifier annotation: 65

type.dpt.field.10.1.i4.Hour
field type: U
field resolution: 1.0
includes digit: type.digit.u5 0 23
type: Datapoint Type Field
type: NamedIndividual
description: Hour
field name: Hour
field size: 5
unit: HR
field index: 4

analog input -> 0% to 100% = 3
type: NamedIndividual
value KNX: 3
value API: analogInput->0%To100%

StatusSAB
has communication mode: S
is assembled with: type.dpt.field.241.800.i1.LowerEndPos
is assembled with: type.dpt.field.241.800.i3.DriveState
is assembled with: type.dpt.field.241.800.i13.ValidSlatsPos
is assembled with: type.dpt.field.241.800.i8.Locked
is assembled with: type.dpt.field.241.800.i9.LocalOverride
is assembled with: type.dpt.field.241.800.i2.LowerPredefPos
is assembled with: type.dpt.field.241.800.i11.Reserved
is assembled with: type.dpt.field.241.800.i4.TargetHPosRestrict
is assembled with: type.dpt.field.241.800.i0.UpperEndPos
is assembled with: type.dpt.field.241.800.i12.ValidHeightPos
is assembled with: type.dpt.field.241.800.i15.HeightPosition
is assembled with: type.dpt.field.241.800.i14.SlatsPosition
is assembled with: type.dpt.field.241.800.i7.Forced
is assembled with: type.dpt.field.241.800.i10.Failure
is assembled with: type.dpt.field.241.800.i5.TargetSPosRestrict
is assembled with: type.dpt.field.241.800.i6.WeatherAlarm
type: DatapointType
type: NamedIndividual
datapoint type minor number: 800
subject: StatusSAB
subject: 241.800
comment: a point representing DPT 241.800: StatusSAB
dpt bit size max: 32
datapoint type major number: 241

Value Work
has communication mode: S
type: NamedIndividual
type: DatapointType
comment: DPT 14.079: Value of work
label: Value Work
subject: Value Work
subject: 14.79
subject: 14.079
datapoint type major number: 14
dpt bit size max: 32
is assembled with: type.dpt.field.14.79.i0
datapoint type minor number: 79

type.dpt.field.7.600.i0
unit: http://qudt.org/vocab/unit/K
includes digit: type.digit.u16
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 16

Other = 0
type: NamedIndividual
value KNX: 0
value API: other

not accepted = 0
type: NamedIndividual
value KNX: 0
value API: notAccepted

Trigger
has communication mode: S
subject: 1.017
subject: 1.17
subject: Trigger
datapoint type major number: 1
dpt bit size max: 1
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 1.017: Trigger
datapoint type minor number: 17
is assembled with: Trigger

Status Lighting Actuator
has communication mode: S
subject: Status Lighting Actuator
subject: 207.600
label: Status Lighting Actuator
comment: a point representing DPT 207.600: Status Lighting Actuator
is assembled with: type.dpt.field.207.600.i6.LocalOverride
is assembled with: type.dpt.field.207.600.i5.Dimming
is assembled with: type.dpt.field.207.600.i0.ValidActualValue
is assembled with: type.dpt.field.207.600.i8.ActualValue
is assembled with: type.dpt.field.207.600.i2.Forced
is assembled with: type.dpt.field.207.600.i1.Locked
is assembled with: type.dpt.field.207.600.i4.StaircaseLightingFunction
is assembled with: type.dpt.field.207.600.i3.NightModeActive
is assembled with: type.dpt.field.207.600.i7.Failure
type: NamedIndividual
type: DatapointType
dpt bit size max: 16
datapoint type minor number: 600
datapoint type major number: 207

Asset
subclass of: Thing
subclass of: Restriction
  on property: contains asset
  all values from: Asset
type: Class
comment: A container for objects in an installation which have a sort of economic value and is owned and managed by an entity, e.g. a service organization.

NoDem = 20
type: NamedIndividual
value API: noDem
value KNX: 20

type.dpt.field.22.101.i8.HeatCoolMode
field name: HeatCoolMode
field index: 8
field size: 1
comment: HeatCoolMode
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.22.101.i8.0
includes KV pair: type.kvpair.22.101.i8.1
field type: B

Friday = 5
value API: friday
value KNX: 5
type: NamedIndividual

TimeOfDay
has communication mode: S
datapoint type minor number: 1
is assembled with: type.dpt.field.10.1.i4.Hour
is assembled with: type.dpt.field.10.1.i2.Minutes
is assembled with: type.dpt.field.10.1.i5.Day
is assembled with: type.dpt.field.10.1.i3.Reserved
is assembled with: type.dpt.field.10.1.i1.Reserved
is assembled with: type.dpt.field.10.1.i0.Seconds
dpt bit size max: 24
label: TimeOfDay
description: a point representing DPT 10.001: TimeOfDay
type: DatapointType
type: NamedIndividual
datapoint type major number: 10
subject: 10.001
subject: 10.1
subject: TimeOfDay

StatusRCC
has communication mode: LTE
comment: a point representing DPT 21.105: StatusRCC
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
datapoint type major number: 21
is assembled with: type.dpt.field.21.105.i0.Fault
is assembled with: type.dpt.field.21.105.i1.Reserved
subject: StatusRCC
subject: 21.105
datapoint type minor number: 105
label: StatusRCC

ErrorClass HVAC
has communication mode: S
subject: ErrorClass HVAC
subject: 20.12
subject: 20.012
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
label: ErrorClass HVAC
description: a point representing DPT 20.012: ErrorClass HVAC
datapoint type minor number: 12
is assembled with: type.dpt.field.20.12.i0
dpt bit size max: 8

Rotation Angle
has communication mode: S
datapoint type minor number: 11
label: Rotation Angle
subject: Rotation Angle
subject: 8.011
subject: 8.11
comment: a point representing DPT 8.011: Rotation Angle
type: NamedIndividual
type: DatapointType
datapoint type major number: 8
dpt bit size max: 16
is assembled with: type.dpt.field.8.11.i0

Value Time 2
has communication mode: S
label: Value Time 2
type: NamedIndividual
type: DatapointType
subject: 9.011
subject: Value Time 2
subject: 9.11
datapoint type major number: 9
comment: a point representing DPT 9.011: Value Time 2
dpt bit size max: 16
is assembled with: type.dpt.field.9.11.i0
datapoint type minor number: 11

type.dpt.field.19.1.i17.DayOfMonth
includes digit: type.digit.u5 1 31
field size: 5
field resolution: 1.0
field index: 17
field type: U
comment: DayOfMonth
unit: DAY
type: Datapoint Type Field
type: NamedIndividual
field name: DayOfMonth

volume flow, 1 l/h = 59
type: NamedIndividual
value KNX: 59
value API: volumeFlow,1Lh

type.dpt.field.21.601.i4.DefectiveLoad
field name: DefectiveLoad
field size: 1
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
type: Datapoint Type Field
type: NamedIndividual
comment: DefectiveLoad
field index: 4

type.dpt.field.206.100.i0.HVACmode
comment: HVAC mode
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes KV pair: Standby = 2
includes KV pair: type.kvpair.206.100.i0.1
includes KV pair: Undefined = 0
includes KV pair: Building Protection = 4
includes KV pair: type.kvpair.206.100.i0.3
field name: HVACmode
field type: N
field size: 8

Bar
type: LocationUsage
type: NamedIndividual
description: A bar, also known as a saloon, a tavern or tippling house, or sometimes as a pub or club, is a retail business establishment that serves alcoholic beverages, such as beer, wine, liquor, cocktails, and other beverages such as mineral water and soft drinks.

volume, 0,01 l = 17
type: NamedIndividual
value KNX: 17
value API: volume,0,01L

Value Electric Polarization
has communication mode: S
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.14.26.i0
comment: DPT 14.026: Value of electric polarization
subject: Value Electric Polarization
subject: 14.26
subject: 14.026
datapoint type minor number: 26
dpt bit size max: 32
label: Value Electric Polarization
datapoint type major number: 14

type.dpt.field.9.9.i0
unit: M3-PER-HR
field type: F
field size: 16
includes digit: type.digit.f16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
field index: 0

KNX
type: NamedIndividual
type: Protocol

Restriction
on property: property identifier
has value: 53

type.dpt.field.23.2.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
includes KV pair: type.kvpair.23.2.i0.0
includes KV pair: alarm position is DOWN = 2
includes KV pair: alarm position is UP = 1
field type: N
field size: 2

Restriction
on property: pointName
has value: CombinedStatus_RTSM

type.dpt.field.22.101.i11.CoolingDisabled
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field size: 1
field index: 11
type: Datapoint Type Field
type: NamedIndividual
field type: B
description: CoolingDisabled
field name: CoolingDisabled

type.dpt.field.245.600.i5.SF
field index: 5
field name: SF
field type: N
type: Datapoint Type Field
type: NamedIndividual
field size: 2
description: SF
includes KV pair: type.kvpair.startMethodGateway
includes KV pair: type.kvpair.startMethodUnknown
includes KV pair: type.kvpair.startMethodAuto

Circuit
comment: Electrical circuit and its associated components such as breakers.
type: NamedIndividual
type: Locality

modulating = 3
value KNX: 3
type: NamedIndividual
value API: modulating

Fire Safety
description: Fire safety deals with preventive actions against fire events (incidents, accidents, and other unwanted conditions) caused by unintentional, human error and/or technical deficiencies, and with the limitation or control of such incidents.
type: NamedIndividual
type: Trade

type.dpt.field.21.103.i2.SolarLoadSufficient
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field index: 2
field size: 1
comment: SolarLoadSufficient
type: Datapoint Type Field
type: NamedIndividual
field name: SolarLoadSufficient

The visual effect of channel 2 is active = 1
value KNX: 1
type: NamedIndividual
value API: theVisualEffectOfChannel2IsActive

type.dpt.field.516.500.i0.pr.LV
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field index: 0
description: lower value
field type: F
includes digit: type.digit.f16
field name: LV

The visual effect of channel 24 is active = 1
value API: theVisualEffectOfChannel24IsActive
type: NamedIndividual
value KNX: 1

power, 10000 kJ/h = 55
type: NamedIndividual
value KNX: 55
value API: power,10000KJh

Test = 7
value KNX: 7
value API: test
type: NamedIndividual

type.dpt.field.241.800.i1.LowerEndPos
type: Datapoint Type Field
type: NamedIndividual
field size: 1
description: Lower end pos. reached
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field name: LowerEndPos
field index: 1

type.dpt.field.243.600.i1.C
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
field size: 1
field type: B
field index: 1
comment: This field shall indicate whether the colour infor-mation in the fields x-axis and y-axis is valid or not.
field name: C

type.dpt.field.19.1.i3.SUTI
includes KV pair: type.kvpair.19.1.i3.0
includes KV pair: Time = UT+X+1 = 1
description: Standard Summer Time
field type: B
field index: 3
field default: 0
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field name: SUTI

actuator fault = 3
type: NamedIndividual
value KNX: 3
value API: actuatorFault

type.dpt.field.206.104.i1.Time
type: NamedIndividual
type: Datapoint Type Field
includes DPT: TimePeriodMin
field name: Time
field index: 1
field size: 16
comment: delay time (min)

type.dpt.field.22.1010.i14.ActivationStateOfChannel15
field name: ActivationStateOfChannel15
field index: 14
comment: Activation state of channel 15
field type: B
includes KV pair: The visual effect of channel 15 is active = 1
includes KV pair: The visual effect of channel 15 is inactive = 0
field size: 1
type: Datapoint Type Field
type: NamedIndividual

217.x
has communication mode: S
is assembled with: type.dpt.field.217.x.i0
label: 217.x
subject: 217.major
subject: 217.x
type: NamedIndividual
type: DatapointType
datapoint type major number: 217
dpt bit size max: 16

TempRoomSetpUserAbsEff
type: Class
subject: 397.56
subject: TempRoomSetpUserAbsEff
subject: 56
interface object type annotation: 397
label: TempRoomSetpUserAbsEff
property identifier annotation: 56

Restriction
on property: pointName
has value: HumRelSetpDehumEff

type.dpt.field.243.600.i4.yaxis
type: NamedIndividual
type: Datapoint Type Field
comment: y-coordinate of the colour information
field index: 4
includes digit: type.digit.u16
field size: 16
field type: U
unit: NUM
field resolution: 1.0
field name: yaxis

type.dpt.field.19.1.i13.Minutes
field resolution: 1.0
field index: 13
field name: Minutes
unit: MIN
includes digit: type.digit.u6 0 59
field type: U
description: Minutes
type: Datapoint Type Field
type: NamedIndividual
field size: 6

no fault = 0
value KNX: 0
type: NamedIndividual
value API: noFault

ControlModeUser
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has datapoint type
  has value: lightControlMode
subject: ControlModeUser
subject: 64
subject: 420.64
interface object type annotation: 420
label: ControlModeUser
property identifier annotation: 64

Network Gateway
type: NamedIndividual
type: EquipmentType
description: A Gateway is a network node (Device) that connects two networks with different transmission protocols and data formats typically between OSI Layers 4-5 (e.g. KNX and BACnet).

one push button/binary input = 1
value KNX: 1
type: NamedIndividual
value API: onePushButtonbinaryInput

FanStepUser
type: Class
subject: 397.88
subject: FanStepUser
subject: 88
interface object type annotation: 397
property identifier annotation: 88
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq fanmotor angularvelocity room

TempRoomSetpCoolEffNext
type: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph temporal delay
subclass of: Restriction
  some values from: Class
  on property: has operation kind
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
property identifier annotation: 54
subject: 101.54
subject: TempRoomSetpCoolEffNext
subject: 54
interface object type annotation: 101

type.dpt.field.513.500.i3.rol.Reserved
field size: 2
field type: r
field name: RESERVED
description: reserved bits
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field index: 3

Restriction
on property: property identifier
has value: 55

State Type
subclass of: Tag
type: Class
comment: The tag category contains individuals that describe specific state types in the control loop of an Application Function. An individual state type is the result of an interpretation of process variables or other states in the control loop. Each state type has a semantically predefined, discrete meaning that can only be figured out together with other context knowledge from the domain of building control. A state type is not assigned with a specific Runtime value, moreover, at least two state types are required to form the set of applicable options, used in the control loop.

type.dpt.field.22.1010.i6.ActivationStateOfChannel7
includes KV pair: type.kvpair.22.1010.i6.1
includes KV pair: The visual effect of channel 7 is inactive = 0
type: Datapoint Type Field
type: NamedIndividual
field type: B
comment: Activation state of channel 7
field name: ActivationStateOfChannel7
field index: 6
field size: 1

inactive = 1
value KNX: 1
type: NamedIndividual
value API: inactive

Request Converter Status = 1
value KNX: 1
type: NamedIndividual
value API: requestConverterStatus

The visual effect of channel 5 is inactive = 0
value API: theVisualEffectOfChannel5IsInactive
type: NamedIndividual
value KNX: 0

communication fault = 2
value KNX: 2
type: NamedIndividual
value API: communicationFault

type.dpt.field.234.2.i1.Character1
field index: 1
description: first character of RegionCode, ASCII-coded
field size: 8
type: Datapoint Type Field
type: NamedIndividual
includes DPT: Char ASCII
field name: Character1

type.dpt.field.24.x.i0
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field size: 312
field index: 0
field string schema: raw

type.dpt.field.8.11.i0
field size: 16
includes digit: type.digit.s16
unit: DEG
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0

Step
label: Step
includes DPT: Step
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: step

Restriction
has value: 399
on property: interface object type

type.dpt.field.8.1.i0
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
field size: 16
includes digit: type.digit.s16
unit: NUM
field resolution: 1.0

TempRoomSetpSetCoolEff
type: Class
interface object type annotation: 100
subject: 100.54
subject: 54
subject: TempRoomSetpSetCoolEff
property identifier annotation: 54

Restriction
on property: interface object type
has value: 399

type.dpt.field.242.600.i3.Brightness
includes digit: type.digit.u8
comment: Brightness of the colour
unit: PERCENT
field index: 3
field resolution: 0.3921566
field type: U
field size: 8
field name: Brightness
type: Datapoint Type Field
type: NamedIndividual

Light Switching Actuator Basic
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: ActuatorErrorInfo
  on property: isComposedByOutput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.417.56
  on property: isComposedByInput
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: ActuatorStatus
subclass of: Restriction
  on class: LockDevice
  max qualified cardinality: 1
  on property: isComposedByInput
subclass of: Class
type: Class
subject: LSAB
subject: Light Switching Actuator Basic
subject: 417
interface object type annotation: 417

Test manually stopped = 5
value KNX: 5
type: NamedIndividual
value API: testManuallyStopped

State
has communication mode: S
datapoint type major number: 1
comment: a point representing DPT 1.011: State
is assembled with: State
datapoint type minor number: 11
dpt bit size max: 1
subject: 1.011
subject: State
subject: 1.11
type: NamedIndividual
type: DatapointType
label: State

type.dpt.field.518.500.i1.rmd.CT
type: NamedIndividual
type: Datapoint Type Field
description: supported control types
field index: 1
includes DPT: emSupportedControlTypes
field size: 8
field name: CT

type.dpt.field.30.1010.i13.ActivationStateOfChannel14
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 13
field type: B
comment: Activation state of channel 14
field name: ActivationStateOfChannel14
includes KV pair: type.kvpair.30.1010.i13.0
includes KV pair: type.kvpair.30.1010.i13.1

type.dpt.field.251.600.i1.mB
comment: mB
includes KV pair: valid = 1
includes KV pair: not valid = 0
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field type: B
field name: mB
field index: 1

HVACModeNext
type: Class
property identifier annotation: 52
interface object type annotation: 398
subject: HVACModeNext
subject: 52
subject: 398.52

TempOutside
type: Class
subject: 60
subject: 397.60
subject: TempOutside
subclass of: Restriction
  has value: Value Temp
  on property: has datapoint type
label: TempOutside
property identifier annotation: 60
interface object type annotation: 397

Value Length
has communication mode: S
type: NamedIndividual
type: DatapointType
datapoint type major number: 14
subject: 14.39
subject: 14.039
subject: Value Length
datapoint type minor number: 39
is assembled with: type.dpt.field.14.39.i0
label: Value Length
comment: DPT 14.039: Value of length
dpt bit size max: 32

Bus/System = 14
type: NamedIndividual
value KNX: 14
value API: busSystem

Euridis Communication Interface Status
has communication mode: S
comment: a point representing DPT 20.1204: Euridis Communication Interface Status
is assembled with: type.dpt.field.20.1204.i0
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
label: Euridis Communication Interface Status
subject: Euridis Communication Interface Status
subject: 20.1204
datapoint type minor number: 1204

Alarm Reaction
has communication mode: S
datapoint type major number: 23
description: a point representing DPT 23.002: Alarm Reaction
label: Alarm Reaction
subject: Alarm Reaction
subject: 23.002
subject: 23.2
type: NamedIndividual
type: DatapointType
datapoint type minor number: 2
dpt bit size max: 2
is assembled with: type.dpt.field.23.2.i0

Request Battery Info = 3
value API: requestBatteryInfo
type: NamedIndividual
value KNX: 3

not running = 0
type: NamedIndividual
value KNX: 0
value API: notRunning

type.dpt.field.205.101.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field type: Z8
field name: StatusCommand
comment: standard Status/Command
field size: 8
includes DPT: StatusGen

TempRoomSetpHeatEff
type: Class
property identifier annotation: 51
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: has datapoint type
subject: 51
subject: 101.51
subject: TempRoomSetpHeatEff
interface object type annotation: 101

HVACModeUser
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: HVAC Mode Z
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
interface object type annotation: 384
subject: HVACModeUser
subject: 384.55
subject: 55
property identifier annotation: 55

Decrease = 0
type: NamedIndividual
is applicable datapoint enum of: Decreasing
value KNX: 0
value API: decrease

type.dpt.field.253.600.i3.Reserved
field index: 3
field size: 5
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved

type.dpt.field.207.101.i2.Reserved
type: NamedIndividual
type: Datapoint Type Field
includes reserved bit: type.bit.reserved
field size: 6
field index: 2
field name: Reserved

type.dpt.field.519.500.i1.tran.START TIMERS
field index: 1
field name: START_TIMERS
includes digit: type.digit.u16
field type: U
field size: 16
type: Datapoint Type Field
type: NamedIndividual
description: defines wich timers will start when executing this transition . each of the 16 timers could be referenced by setting the bits 0-15 to 0 (not starting) or 1 (starting)

Restriction
has value: 423
on property: interface object type

installation data
domain: Installation
comment: A parent data property, used to express any kind of generic data that relates to an installation.
type: DatatypeProperty

type.dpt.field.207.100.i3.StatusStage2
field index: 3
includes DPT: switch
field name: StatusStage2
type: Datapoint Type Field
type: NamedIndividual
comment: stage 2 / modulation active
field size: 1

HVACModeUserEff
type: Class
label: HVACModeUserEff
interface object type annotation: 398
subject: 398.81
subject: 81
subject: HVACModeUserEff
property identifier annotation: 81

18.x
has communication mode: S
datapoint type major number: 18
type: NamedIndividual
type: DatapointType
subject: 18.x
subject: 18.major
is assembled with: type.dpt.field.18.x.i0
dpt bit size max: 8

type.dpt.field.6.20.i2.d
type: NamedIndividual
type: Datapoint Type Field
field index: 2
includes KV pair: type.kvpair.clear
includes KV pair: set = 1
field name: d
field size: 1
comment: Status D
field type: B

type.dpt.field.22.100.i4.OtherEnergySourceActive
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
comment: OtherEnergySourceActive
field name: OtherEnergySourceActive
field index: 4
type: Datapoint Type Field
type: NamedIndividual
field size: 1

230.x
has communication mode: S
dpt bit size max: 64
is assembled with: type.dpt.field.230.x.i0
type: NamedIndividual
type: DatapointType
datapoint type major number: 230
subject: 230.x
subject: 230.major
label: 230.x

cEMI Transport Layer = 6
type: NamedIndividual
value API: cEMITransportLayer
value KNX: 6

HVAC Air Flow Absolute Z
has communication mode: LTE
datapoint type major number: 203
dpt bit size max: 24
subject: 203.104
subject: HVAC Air Flow Absolute Z
comment: a point representing DPT 203.104: HVAC Air Flow Absolute Z
label: HVAC Air Flow Absolute Z
type: DatapointType
type: NamedIndividual
datapoint type minor number: 104
is assembled with: type.dpt.field.203.104.i0.StatusCommand
is assembled with: type.dpt.field.203.104.i1.HVACAirFlow

On State
description: This state type expresses that an equipment, such as a luminaire, is switched on. This state type is the inverse of the 'Off State' state type.
type: NamedIndividual
type: State Type

type.dpt.field.11.1.i4.Day
type: NamedIndividual
type: Datapoint Type Field
includes digit: type.digit.u5 1 31
field name: Day
field size: 5
field type: U
field index: 4
field resolution: 1.0
unit: DAY

not valid = 1
type: NamedIndividual
value API: notValid
value KNX: 1

type.dpt.field.20.121.i0
field index: 0
comment: BackupMode
includes KV pair: type.kvpair.20.121.i0.1
includes KV pair: type.kvpair.20.121.i0.0
field type: N
field size: 8
type: Datapoint Type Field
type: NamedIndividual

Start/stop = 0
value API: startstop
type: NamedIndividual
value KNX: 0

HVAC Emerg Mode Z
has communication mode: LTE
datapoint type minor number: 109
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
datapoint type major number: 201
label: HVAC Emerg Mode Z
subject: 201.109
subject: HVAC Emerg Mode Z
is assembled with: type.dpt.field.201.109.i1.HVACEmergMode
is assembled with: type.dpt.field.201.109.i0.StatusCommand
comment: a point representing DPT 201.109: HVAC Emerg Mode Z

type.dpt.field.207.100.i5.PrelBurner
field name: PrelBurner
type: NamedIndividual
type: Datapoint Type Field
unit: PERCENT
field size: 8
field index: 5
includes digit: type.digit.u8 0 100
field resolution: 1.0
comment: Actual relative power %

FanManual
type: Class
interface object type annotation: 397
subclass of: Restriction
  has value: enable
  on property: has datapoint type
subclass of: Restriction
  on property: has operation kind
subject: 89
subject: 397.89
subject: FanManual
property identifier annotation: 89

Restriction
on property: has operation kind
qualified cardinality: 1

ComfortProlongEff
type: Class
interface object type annotation: 100
property identifier annotation: 60
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: State
  on property: has datapoint type
label: ComfortProlongEff
subject: 100.60
subject: 60
subject: ComfortProlongEff

Security = 30
value KNX: 30
value API: security
type: NamedIndividual

Restriction
has value: 399
on property: interface object type

type.dpt.field.27.1.i12.IOO13
type: Datapoint Type Field
type: NamedIndividual
field name: IOO13
field size: 1
includes KV pair: output state is On = 1
includes KV pair: output state is Off = 0
field type: B
description: Info On Off Output 13
field index: 12

AbsSetvalueControl
type: Class
subject: 70
subject: AbsSetvalueControl
subject: 418.70
interface object type annotation: 418
property identifier annotation: 70

type.dpt.field.14.71.i0
includes digit: type.digit.f32
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 32
field type: F
comment: thermal capacity
unit: J-PER-K

Character
label: Character
field size: 8
field type: A
includes digit: type.digit.charISO 8859 1
type: Datapoint Type Field
type: NamedIndividual
unit: UNITLESS
field index: 0
comment: Represents a ISO 8859-1 character. Encoding according to the character set ISO-8859-1 (Western Europe)
field string schema: iso-8859-1

Value 2 Ucount
has communication mode: S
datapoint type minor number: 1
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
label: Value 2 Ucount
comment: a point representing DPT 7.001: Value 2 Ucount
subject: Value 2 Ucount
subject: 7.1
subject: 7.001
datapoint type major number: 7
is assembled with: type.dpt.field.7.1.i0

type.dpt.field.16.x.i0
field string schema: raw
type: Datapoint Type Field
type: NamedIndividual
field type: A
field size: 112
description: character string
field index: 0

no action (dummy) = 0
value KNX: 0
type: NamedIndividual
value API: noAction(dummy)

type.dpt.field.229.1.i1.ValInfField
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: mass flow, 0,1 kg/h = 82
includes KV pair: mass flow, 10 kg/h = 84
includes KV pair: type.kvpair.229.1.i1.23
includes KV pair: power, 0,01 kJ/h = 49
includes KV pair: mass, 10000 kg = 31
includes KV pair: volume flow, 0,01 l/h = 57
includes KV pair: energy, 0,001 Wh = 0
includes KV pair: type.kvpair.229.1.i1.19
includes KV pair: energy, 1000 Wh = 6
includes KV pair: power, 0,1 kJ/h = 50
includes KV pair: power, 1 MW = 169
includes KV pair: volume flow, 10000 l/h = 63
includes KV pair: type.kvpair.229.1.i1.46
includes KV pair: power, 10000 W = 47
includes KV pair: type.kvpair.229.1.i1.176
includes KV pair: volume flow, 100 ml/s = 77
includes KV pair: type.kvpair.229.1.i1.80
includes KV pair: volume flow, 1000 l/min = 71
includes KV pair: type.kvpair.229.1.i1.2
includes KV pair: energy, 0,01 kJ = 9
includes KV pair: power, 1 kJ/h = 51
includes KV pair: volume flow, 0,001 l/min = 65
includes KV pair: energy, 100 Wh = 5
includes KV pair: volume flow, 100 l/min = 70
includes KV pair: type.kvpair.229.1.i1.3
includes KV pair: type.kvpair.229.1.i1.73
includes KV pair: type.kvpair.229.1.i1.42
includes KV pair: type.kvpair.229.1.i1.64
includes KV pair: type.kvpair.229.1.i1.41
includes KV pair: type.kvpair.229.1.i1.29
includes KV pair: volume flow, 0,001 l/h = 56
includes KV pair: power, 10 W = 44
includes KV pair: volume flow, 1000 ml/s = 78
includes KV pair: type.kvpair.229.1.i1.13
includes KV pair: mass, 0,1 kg = 26
includes KV pair: volume, 10 l = 20
includes KV pair: type.kvpair.229.1.i1.28
includes KV pair: energy, 10000 Wh = 7
includes KV pair: type.kvpair.229.1.i1.14
includes KV pair: type.kvpair.229.1.i1.48
includes KV pair: mass, 0,001 kg = 24
includes KV pair: volume flow, 10000 ml/s = 79
includes KV pair: type.kvpair.229.1.i1.30
includes KV pair: type.kvpair.229.1.i1.62
includes KV pair: energy, 1 MWh = 129
includes KV pair: volume flow, 0,01 l/min = 66
includes KV pair: type.kvpair.229.1.i1.4
includes KV pair: power, 10000 kJ/h = 55
includes KV pair: type.kvpair.229.1.i1.87
includes KV pair: volume flow, 10 ml/s = 76
includes KV pair: volume flow, 1 l/h = 59
includes KV pair: energy, 10000 kJ = 15
includes KV pair: energy, 1 GJ = 137
includes KV pair: type.kvpair.229.1.i1.72
includes KV pair: power, 1000 kJ/h = 54
includes KV pair: type.kvpair.229.1.i1.60
includes KV pair: type.kvpair.229.1.i1.136
includes KV pair: volume, 0,001 l = 16
includes KV pair: type.kvpair.229.1.i1.22
includes KV pair: type.kvpair.229.1.i1.11
includes KV pair: type.kvpair.229.1.i1.61
includes KV pair: volume flow, 10 l/min = 69
includes KV pair: type.kvpair.229.1.i1.27
includes KV pair: type.kvpair.229.1.i1.10
includes KV pair: energy, 0,1 MWh = 128
includes KV pair: power, 100 W = 45
includes KV pair: type.kvpair.229.1.i1.12
includes KV pair: type.kvpair.229.1.i1.75
includes KV pair: volume, 0,01 l = 17
includes KV pair: type.kvpair.229.1.i1.86
includes KV pair: power, 10 kJ/h = 52
includes KV pair: volume flow, 0,1 l/min = 67
includes KV pair: mass flow, 100 kg/h = 85
includes KV pair: type.kvpair.229.1.i1.18
includes KV pair: mass flow, 0,01 kg/h = 81
includes KV pair: volume flow, 0,1 l/h = 58
includes KV pair: type.kvpair.229.1.i1.177
includes KV pair: energy, 0,001 kJ = 8

Auto = 0
value API: auto
type: NamedIndividual
value KNX: 0

ReactiveEnergy
has communication mode: S
datapoint type minor number: 12
datapoint type major number: 13
type: DatapointType
type: NamedIndividual
label: ReactiveEnergy
subject: ReactiveEnergy
subject: 13.12
subject: 13.012
description: a point representing DPT 13.012: ReactiveEnergy
is assembled with: type.dpt.field.13.12.i0
dpt bit size max: 32

MBus Address
has communication mode: S
datapoint type minor number: 1000
is assembled with: type.dpt.field.230.1000.i0.Medium
is assembled with: type.dpt.field.230.1000.i3.ManufactID
is assembled with: type.dpt.field.230.1000.i1.Version
is assembled with: type.dpt.field.230.1000.i2.IdentNumber
subject: 230.1000
subject: MBus Address
dpt bit size max: 64
type: NamedIndividual
type: DatapointType
label: MBus Address
datapoint type major number: 230
comment: a point representing DPT 230.1000: MBus Address

power, 10 kJ/h = 52
type: NamedIndividual
value KNX: 52
value API: power,10KJh

Value Luminous Intensity
has communication mode: S
subject: 14.43
subject: Value Luminous Intensity
subject: 14.043
is assembled with: type.dpt.field.14.43.i0
comment: DPT 14.043: Value of luminous intensity
label: Value Luminous Intensity
type: DatapointType
type: NamedIndividual
datapoint type minor number: 43
datapoint type major number: 14
dpt bit size max: 32

type.dpt.field.21.101.i0.ForceRequest
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field name: ForceRequest
field type: B
type: Datapoint Type Field
type: NamedIndividual
description: ForceRequest
field size: 1
field index: 0

type.dpt.field.27.1.i18.MaskBitIOO3
field size: 1
field index: 18
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B
field name: MaskBitIOO3
comment: Mask Bit Info On Off Output 3

emRoles
is assembled with: type.dpt.field.513.500.i2.rol.C2
is assembled with: type.dpt.field.513.500.i3.rol.Reserved
is assembled with: type.dpt.field.513.500.i1.rol.C1
is assembled with: type.dpt.field.513.500.i0.rol.C0
dpt bit size max: 8
type: NamedIndividual
type: DatapointType
datapoint type major number: 513
datapoint type minor number: 500

type.dpt.field.ddbc.om.i1.AC
field size: 1
field type: B
field index: 1
description: abnormal condition
field name: AC
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: abnormal condition
includes KV pair: type.kvpair.NoAbnormalCondition

type.dpt.field.26.1.i1.B
field name: B
type: NamedIndividual
type: Datapoint Type Field
field size: 1
includes KV pair: type.kvpair.26.1.i1.1
includes KV pair: type.kvpair.26.1.i1.0
field type: B
field index: 1

Restriction
on property: property identifier
has value: 63

type.dpt.field.236.1.i1.p
includes KV pair: type.kvpair.236.1.i1.5
includes KV pair: type.kvpair.236.1.i1.6
includes KV pair: type.kvpair.236.1.i1.7
includes KV pair: type.kvpair.236.1.i1.3
includes KV pair: type.kvpair.236.1.i1.1
includes KV pair: type.kvpair.236.1.i1.2
includes KV pair: Level 4 = 4
includes KV pair: Level 0 = 0
field name: p
comment: priority level
field index: 1
field type: N
field size: 3
type: Datapoint Type Field
type: NamedIndividual

rest: nil
first: Restriction
  on property: interface object type
  has value: 398

Restriction
on property: interface object type
has value: 398

Restriction
on property: pointName
has value: FanStepUser

type.dpt.field.512.503.i8.pei.PWR ENV
type: NamedIndividual
type: Datapoint Type Field
field type: D<n>
field name: PWR_ENV
description: list of power envelopes
field index: 8
includes DPT: emPowerEnvelope
includes counter: type.dpt.field.512.503.i7.pei.PE CNT

type.dpt.field.521.500.i4.ts.Reserved
field name: RESERVED
field size: 3
field type: r
field index: 4
description: reserved bits
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved

type.dpt.field.14.59.i0
field index: 0
unit: OHM
field type: F
includes digit: type.digit.f32
field resolution: 1.0
field size: 32
comment: reactance
type: Datapoint Type Field
type: NamedIndividual

is trade operated by
domain: Trade
inverse of: operates for trade
sub property of: isTagOf
type: ObjectProperty

Restriction
has value: CombinedStatus_HVA_HeatB
on property: pointName

type.dpt.field.207.102.i2.Reserved
field index: 2
field name: Reserved
field size: 6
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved

energy, 0,01 Wh = 1
value KNX: 1
type: NamedIndividual
value API: energy,0,01Wh

type.dpt.field.20.803.i0
field type: N
includes KV pair: two push buttons/binary inputs mode = 4
includes KV pair: one push button/binary input = 1
includes KV pair: one push button/binary input, MoveDown / StepDown message sent = 3
includes KV pair: type.kvpair.20.803.i0.2
comment: SSSBMode
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

first: Restriction
  on property: has cardinality
  has value: one
rest: nil

type.dpt.field.14.74.i0
includes digit: type.digit.f32
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
unit: SEC
comment: time
field size: 32
field type: F

NightMode
type: Class
subject: 63
subject: NightMode
subject: 417.63
label: NightMode
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
property identifier annotation: 63
interface object type annotation: 417

type.dpt.field.ombc.om.i3.CQ
field size: 8
includes KV pair: type.kvpair.cqNaturalGasFlowRate
includes KV pair: type.kvpair.cqElectricPowerL2
includes KV pair: type.kvpair.cqHeatThermalPower
includes KV pair: type.kvpair.cqElectricPowerL1
includes KV pair: type.kvpair.cqHeatFlowRate
includes KV pair: type.kvpair.cqOilFlowRate
includes KV pair: type.kvpair.cqHydrogenFlowRate
includes KV pair: Electric Power L3
type: Datapoint Type Field
type: NamedIndividual
field name: CQ
field index: 3
description: commodity quantity
field type: U

CombinedStatus_RTC
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air dewpointtemperature room
subject: 110
subject: CombinedStatus_RTC
subject: 399.110
label: CombinedStatus_RTC
property identifier annotation: 110
interface object type annotation: 399

type.dpt.field.14.20.i0
type: NamedIndividual
type: Datapoint Type Field
description: electric current density
field index: 0
field size: 32
field type: F
unit: A-PER-M2
includes digit: type.digit.f32
field resolution: 1.0

PBAction
has communication mode: S
comment: a point representing DPT 20.606: PBAction
subject: 20.606
subject: PBAction
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
is assembled with: type.dpt.field.20.606.i0
label: PBAction
datapoint type minor number: 606

TempOutside
type: Class
subclass of: Restriction
  has value: qk ph air temperature outside
  on property: hasQualityKind
subclass of: Restriction
  on property: has datapoint type
  has value: Value Temp
subject: 57
subject: 399.57
subject: TempOutside
interface object type annotation: 399
property identifier annotation: 57

start sequence
type: NamedIndividual
value API: seqInstrStartInterrupt
value KNX: 1
description: start sequence insterrupt

SwitchOnMode
has communication mode: S
is assembled with: type.dpt.field.20.608.i0
subject: SwitchOnMode
subject: 20.608
type: NamedIndividual
type: DatapointType
label: SwitchOnMode
datapoint type major number: 20
datapoint type minor number: 608
comment: a point representing DPT 20.608: SwitchOnMode
dpt bit size max: 8

FuelTypeSet
has communication mode: LTE
comment: a point representing DPT 21.104: FuelTypeSet
type: DatapointType
type: NamedIndividual
datapoint type minor number: 104
is assembled with: type.dpt.field.21.104.i3.Reserved
is assembled with: type.dpt.field.21.104.i2.SolidState
is assembled with: type.dpt.field.21.104.i0.Oil
is assembled with: type.dpt.field.21.104.i1.Gas
label: FuelTypeSet
subject: 21.104
subject: FuelTypeSet
datapoint type major number: 21
dpt bit size max: 8

Oven
type: NamedIndividual
type: EquipmentType
description: An oven is a tool which is used to expose materials to a hot environment. Ovens contain a hollow chamber and provide a means of heating the chamber in a controlled way. Ovens are often used for cooking (home appliances EN 50523: gas oven or electical oven), where they can be used to heat food to a desired temperature.

Point Function
subclass of: Tag
type: Class
comment: The tag category contains individuals that describe the role of a Point in the control loop of an application function.

Laundry Room
comment: Laundry refers to the washing of clothing and other textiles, and, more broadly, their drying and ironing as well. Preferably used with an Room.
type: NamedIndividual
type: LocationUsage

ControlModeEff
type: Class
subclass of: Restriction
  has value: lightControlMode
  on property: has datapoint type
subject: ControlModeEff
subject: 420.54
subject: 54
label: ControlModeEff
property identifier annotation: 54
interface object type annotation: 420

224.x
has communication mode: LTE
subject: 224.major
subject: 224.x
datapoint type major number: 224
label: 224.x
type: NamedIndividual
type: DatapointType
dpt bit size max: 48
is assembled with: type.dpt.field.224.x.i0

no change = 2
value API: noChange
value KNX: 2
type: NamedIndividual

Restroom
type: NamedIndividual
type: LocationUsage
description: A toilet is a small room used for privately accessing the sanitation fixture (toilet) for urination and defecation. Toilet rooms often include a sink (basin) with soap/handwash for handwashing, as this is important for personal hygiene.

type.dpt.field.19.1.i2.CLQ
field index: 2
comment: Quality of clock
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.19.1.i2.0
includes KV pair: type.kvpair.19.1.i2.1
field size: 1
field default: 1
field type: B
field name: CLQ

emPowerSequence
datapoint type minor number: 505
is assembled with: type.dpt.field.512.505.i3.ps.I
is assembled with: type.dpt.field.512.505.i4.ps.S
is assembled with: type.dpt.field.512.505.i1.ps.SLT CNT
is assembled with: type.dpt.field.512.505.i2.ps.AC
is assembled with: type.dpt.field.512.505.i7.ps.SLT
is assembled with: type.dpt.field.512.505.i5.ps.Reserved
is assembled with: type.dpt.field.512.505.i6.ps.MPB
is assembled with: type.dpt.field.512.505.i0.ps.SQ ID
description: Power sequence
type: NamedIndividual
type: DatapointType
dpt bit size max: 1792
datapoint type major number: 512

type.dpt.field.265.11.i1.Reserved
type: Datapoint Type Field
type: NamedIndividual
field size: 7
includes reserved bit: type.bit.reserved
field name: Reserved
field index: 1
field type: r

type.dpt.field.21.100.i0.ForceRequest
description: ForceRequest
field size: 1
field index: 0
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
type: Datapoint Type Field
type: NamedIndividual
field name: ForceRequest
field type: B

Cool Stage B Actuator Overridden
type: Class
subclass of: Restriction
  on property: measuresEquipmentQualityKind
  has value: qk eq valveactuator positionvector pipesection supplysection
subclass of: Function Point
subclass of: Restriction
  on property: has datapoint type
  has value: Bool

Restriction
on property: has operation kind
qualified cardinality: 1

type.dpt.field.14.75.i0
comment: torque
unit: N-M
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 32
field type: F
includes digit: type.digit.f32

User Fan Speed Setting
is incomplete: true
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByOutput
  on class: Class
type: Class
subject: 393
subject: User Fan Speed Setting
subject: UFS
label: User Fan Speed Setting
interface object type annotation: 393

Shutters and blinds = 50
type: NamedIndividual
value API: shuttersAndBlinds
value KNX: 50

Restriction
has value: Switch OnOff
on property: pointName

type.dpt.field.526.500.i0.p.PWR FCV
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 120
field name: PWR_FCV
includes DPT: emForecastValue
description: The power forecast of a power sequence slot

No Frost
comment: This state type expresses the state of no frost. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case no frost has been detected, no frost protection is required and this equipment might be used as intended. This state type is the inverse of the 'Frost State' state type.
type: State Type
type: NamedIndividual

type.dpt.field.frbc.om.i3.CQ
includes KV pair: type.kvpair.cqNaturalGasFlowRate
includes KV pair: type.kvpair.cqElectricPowerL2
includes KV pair: type.kvpair.cqHeatThermalPower
includes KV pair: type.kvpair.cqHeatFlowRate
includes KV pair: type.kvpair.cqElectricPowerL1
includes KV pair: type.kvpair.cqOilFlowRate
includes KV pair: type.kvpair.cqHydrogenFlowRate
includes KV pair: Electric Power L3
type: NamedIndividual
type: Datapoint Type Field
field name: CQ
field index: 3
field size: 3
field type: U

Open Close
has communication mode: S
is assembled with: Open / Close
type: DatapointType
type: NamedIndividual
subject: 1.009
subject: 1.9
subject: Open Close
datapoint type major number: 1
dpt bit size max: 1
comment: a point representing DPT 1.009: Open Close
datapoint type minor number: 9

notice PE2 in progress = 2
value API: noticePE2InProgress
type: NamedIndividual
value KNX: 2

type.dpt.field.209.100.i0.TempFlowValid
includes DPT: Bool
comment: validity of TempFlowProdSegmH field
type: Datapoint Type Field
type: NamedIndividual
field name: TempFlowValid
field size: 1
field index: 0

Liquid
type: NamedIndividual
type: Phenomenon
comment: Substance with definite volume but takes the shape of its container

ActTargetFanSpeedEff
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: scaling
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subject: ActTargetFanSpeedEff
subject: 66
subject: 397.66
label: ActTargetFanSpeedEff
property identifier annotation: 66
interface object type annotation: 397

Drive
comment: Physical unit used for driving mechanically actuated final controlling elements. Examples of actuating drives are electric, hydraulic or pneumatic actuating drives, diaphragm systems or piston actuators (see IEC 60050-351).
type: NamedIndividual
type: EquipmentType

Length
type: NamedIndividual
type: Quantity Kind
comment: In geometric measurements, length most commonly refers to the estimated dimension of an object. In some contexts, the term "length" is reserved for a certain dimension of an object along which the length is measured.

type.dpt.field.14.55.i0
description: phase angle, degrees
unit: DEG
includes digit: type.digit.f32
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: F

External Address
type: Class
comment: An address is represented by an external ontology object, which has data properties such as country-name, locality (city), street-address.

HVACModeAct
type: Class
subject: 54
subject: HVACModeAct
subject: 167.54
interface object type annotation: 167
property identifier annotation: 54

The visual effect of channel 13 is inactive = 0
value API: theVisualEffectOfChannel13IsInactiv
type: NamedIndividual
value KNX: 0

power, 1000 kJ/h = 54
type: NamedIndividual
value KNX: 54
value API: power,1000KJh

DAY
type: NamedIndividual
type: Unit
symbol: day

ControlModeEff
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: lightControlMode
property identifier annotation: 54
interface object type annotation: 418
subject: ControlModeEff
subject: 54
subject: 418.54

Auto = 0
value API: auto
value KNX: 0
type: NamedIndividual

type.dpt.field.241.800.i11.Reserved
field size: 3
type: Datapoint Type Field
type: NamedIndividual
field index: 11
includes reserved bit: type.bit.reserved
field type: r
field name: Reserved

Humidification Mode
comment: This state type expresses the 'humidification' mode of the ventilation system. Usually, this is related to raising the relative air humidity by adding moist air to a room.
type: State Type
type: NamedIndividual

type.dpt.field.14.17.i0
field index: 0
comment: density
field type: F
includes digit: type.digit.f32
field resolution: 1.0
unit: KiloGM-PER-M3
type: Datapoint Type Field
type: NamedIndividual
field size: 32

Switch On Off Green
type: Class
label: Switch On Off Green
subject: Switch On Off Green
subject: 423.59
subject: 59
subject: SOO_G
subclass of: Restriction
  on property: has datapoint type
  has value: switch
property identifier annotation: 59
interface object type annotation: 423

Intrusion Detection
type: Trade
type: NamedIndividual
description: An intrusion system monitors a building or systems for malicious activity or policy violations.

Chilled Beam
type: NamedIndividual
type: EquipmentType
description: Conditions a space using a heat exchanger integrated into the ceiling. A chilled beam is a type of radiation/convection HVAC system (as is an alternative design known as 'chilled ceiling') designed to heat and cool large buildings.

type.dpt.field.237.600.i5.ConvertorError
field name: ConvertorError
includes KV pair: type.kvpair.237.600.i5.0
includes KV pair: error = 1
type: Datapoint Type Field
type: NamedIndividual
field index: 5
field type: B
description: Convertor error
field size: 1

type.dpt.field.pc.i2.START
description: timestamp when the constraints becomes valid
field name: START
field index: 2
type: Datapoint Type Field
type: NamedIndividual
includes DPT: DateTime
field size: 64

TempRoomSetpAct
type: Class
interface object type annotation: 259
subject: TempRoomSetpAct
subject: 259.153
subject: 153
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
property identifier annotation: 153

has communication mode
type: DatatypeProperty
comment: Used to indicate that a KNX concept implements the KNX communication mode (S-Mode, LTE-Mode). Most likely, this can be assigned to KNX Datapoint Types and to KNX DPAs (i.e. those which are not present in S-Mode implementations of FBs)

DoubleNibble
has communication mode: S
is assembled with: type.dpt.field.25.1000.i0.Nak
is assembled with: type.dpt.field.25.1000.i1.Busy
type: DatapointType
type: NamedIndividual
subject: 25.1000
subject: DoubleNibble
label: DoubleNibble
comment: a point representing DPT 25.1000: DoubleNibble
dpt bit size max: 8
datapoint type minor number: 1000
datapoint type major number: 25

Start = 1
value KNX: 1
type: NamedIndividual
value API: start

Combined Switch On Off
type: Class
subject: 51
subject: Combined Switch On Off
subject: 423.51
subject: CSOO
interface object type annotation: 423
label: Combined Switch On Off
property identifier annotation: 51

has point operation
domain: Operation Kind
sub property of: has tag
type: ObjectProperty
type: FunctionalProperty
range: Point Operation
comment: An OP relationship to a list that describes the runtime interworking operation type of the value of a point. Examples are absolute values, values representing an offset or realtive values.
inverse of: is point operation of

Process Variable
type: NamedIndividual
type: Point Function
description: A Point provides the current (measured) value of a quantity kind or the current (status) value of a state kind.

The visual effect of channel 10 is active = 1
value KNX: 1
value API: theVisualEffectOfChannel10IsActive
type: NamedIndividual

Value Magnetic Moment
has communication mode: S
is assembled with: type.dpt.field.14.47.i0
datapoint type major number: 14
subject: 14.047
subject: Value Magnetic Moment
subject: 14.47
dpt bit size max: 32
comment: DPT 14.047: Value of magnetic moment
type: NamedIndividual
type: DatapointType
datapoint type minor number: 47

Slats Actuator
type: EquipmentType
type: NamedIndividual
comment: Slats are vertical or horizontal pieces of a window blind. Slats actuator is used to control an actuator equipment to regulate the light incidence (slats position/angle). Don't care if the slats position/angle is internally operated from the actuator by a motor or other means.

Bool
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.1.2.i0
datapoint type minor number: 2
subject: 1.2
subject: 1.002
subject: Bool
label: Bool
datapoint type major number: 1
comment: a point representing DPT 1.002: Bool
dpt bit size max: 1

TempRoomSetpAct
type: Class
subject: 256.153
subject: 153
subject: TempRoomSetpAct
interface object type annotation: 256
property identifier annotation: 153

C-M
type: NamedIndividual
type: Unit
symbol: C⋅m

Actual Dimming Value Blue
type: Class
subject: Actual Dimming Value Blue
subject: ASV_B
subject: 85
subject: 423.85
property identifier annotation: 85
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 423

Combined Status RTC
has communication mode: S
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 22.103: Combined Status RTC
datapoint type minor number: 103
is assembled with: type.dpt.field.22.103.i9.Reserved
is assembled with: type.dpt.field.22.103.i5.ControllerInactive
is assembled with: type.dpt.field.22.103.i0.GeneralFailureInformation
is assembled with: type.dpt.field.22.103.i8.CoolingModeEnabled
is assembled with: type.dpt.field.22.103.i3.FrostAlarm
is assembled with: type.dpt.field.22.103.i1.ActiveMode
is assembled with: type.dpt.field.22.103.i7.HeatingModeEnabled
is assembled with: type.dpt.field.22.103.i6.AdditionalHeatingCoolingStage
is assembled with: type.dpt.field.22.103.i4.OverheatAlarm
is assembled with: type.dpt.field.22.103.i2.DewPointStatus
subject: Combined Status RTC
subject: 22.103
datapoint type major number: 22

type.dpt.field.22.100.i2.LegioProtActive
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 2
description: LegioProtActive
field name: LegioProtActive

type.dpt.field.265.9.i1.Reserved
includes reserved bit: type.bit.reserved
type: NamedIndividual
type: Datapoint Type Field
field size: 7
field index: 1
field type: r
field name: Reserved

type.dpt.field.207.105.i2.CalibrationMode
field name: CalibrationMode
field index: 2
comment: actuator is currently in calibration mode
includes DPT: State
type: Datapoint Type Field
type: NamedIndividual
field size: 1

invalid Group Object number (ASAP) = 17
value API: invalidGroupObjectNumber(ASAP)
type: NamedIndividual
value KNX: 17

213.x
has communication mode: LTE
subject: 213.major
subject: 213.x
type: DatapointType
type: NamedIndividual
dpt bit size max: 64
label: 213.x
datapoint type major number: 213
is assembled with: type.dpt.field.213.x.i0

type.dpt.field.230.1000.i3.ManufactID
includes digit: type.digit.u16
field size: 16
field type: U
field name: ManufactID
comment: ManufactID
field index: 3
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.21.102.i5.StatusStartOptim
comment: StatusStartOptim
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field index: 5
field type: B
type: Datapoint Type Field
type: NamedIndividual
field name: StatusStartOptim
field size: 1

Sensor
type: NamedIndividual
type: EquipmentType
comment: Sensor is a Peripheral that measures physical input from its environment and converts it into data that can be interpreted by either a human or a machine.

Outside Temperature Sensor
type: Class
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: StatusGO
label: Outside Temperature Sensor
subject: Outside Temperature Sensor
subject: OTS
subject: 320
interface object type annotation: 320

Value AirFlow
has communication mode: S
subject: Value AirFlow
subject: 9.009
subject: 9.9
label: Value AirFlow
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.9.9.i0
comment: a point representing DPT 9.009: Value AirFlow
datapoint type minor number: 9
datapoint type major number: 9

type.digit.f16 neg27300 670433
range min: -27300.0
range max: 670433.0
type: NamedIndividual

Cabinet
type: LocationUsage
type: NamedIndividual
description: Room or space used for electrical equipment such as switch cabinets, a fuese box etc. Preferably used with an Space.

serial number
range: string
comment: An identifier to specify the (string based) erial number of a device.
sub property of: deviceData
type: DatatypeProperty
type: FunctionalProperty

Combined Info On Off
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: switch
subject: CIOO
subject: 423.80
subject: Combined Info On Off
subject: 80
property identifier annotation: 80
label: Combined Info On Off
interface object type annotation: 423

Negative = 1
type: NamedIndividual
value KNX: 1
value API: negative

HVAC Mode Protection
comment: This state type expresses that the lowest level named 'Protection' is chosen for the HVAC mode. Usually, the 'Protection' level is associated with a focus on building and equipment protection (e.g. against frost damage). This level is used for rooms or buildings, which will not be used for a longer time, such as holidays. Additionally, the 'Protection' level is chosen for a room if windows in this room are opened. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
type: State Type
type: NamedIndividual

power, 1 MW = 169
value KNX: 169
value API: power,1MW
type: NamedIndividual

Value Volume Flux
has communication mode: S
type: NamedIndividual
type: DatapointType
label: Value Volume Flux
subject: Value Volume Flux
subject: 14.77
subject: 14.077
is assembled with: type.dpt.field.14.77.i0
comment: DPT 14.077: Value of volume flux
datapoint type minor number: 77
datapoint type major number: 14
dpt bit size max: 32

29.x
has communication mode: S
datapoint type major number: 29
label: 29.x
subject: 29.major
subject: 29.x
type: NamedIndividual
type: DatapointType
dpt bit size max: 64
is assembled with: type.dpt.field.29.x.i0

number
sub property of: topDataProperty
type: DatatypeProperty
range: string
comment: Used to define the current number of an entity, such as the building number. May be used from other concepets, therefore no domain is defined.

type.dpt.field.512.508.i3.fltp.PE
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
field name: PE
includes DPT field: type.dpt.field.fltp.pe
field index: 3
includes counter: type.dpt.field.512.508.i2.fltp.PE CNT
description: list of fill level target profile element

type.dpt.field.td.i2.Reserved
type: NamedIndividual
type: Datapoint Type Field
includes reserved bit: type.bit.reserved
field name: RESERVED
field type: r
description: reserved bits
field index: 2
field size: 4

type.dpt.field.15.0.i4.E
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: type.kvpair.15.0.i4.0
includes KV pair: reading of access information code was not successful = 1
field name: E
field size: 1
field type: B
comment: Detection error
field index: 4

HVAC Direct Electrical Heating = 12
type: NamedIndividual
value KNX: 12
value API: hVACDirectElectricalHeating

c
includes KV pair: type.kvpair.control
includes KV pair: no control = 0
label: c
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: c
field type: B
field index: 1

The visual effect of channel 11 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel11IsInactiv

User Light Switching
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph light illuminance
subclass of: Restriction
  on class: Light Switch Request
  on property: has function point
  qualified cardinality: 1
subclass of: lightingCtrl
type: Class
comment: A user operated light switch request including an explicit switch status.
subject: LSSB
subject: LSAB

Educational
type: LocationUsage
type: NamedIndividual
description: An educational institution is a place where people of different ages gain an education, including preschools, childcare, primary-elementary schools, secondary-high schools, and universities. They provide a large variety of learning environments and learning spaces. Preferably used with a Building.

Restriction
has value: 398
on property: interface object type

type.dpt.field.22.1000.i6.Reserved
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
field size: 10
includes reserved bit: type.bit.reserved
field index: 6

type.dpt.field.ec.i1.AVR
type: NamedIndividual
type: Datapoint Type Field
includes DPT: emPowerRange
field name: AVR
field index: 1
description: power range the device will operate for the given time period
field size: 32

type.dpt.field.240.800.i1.ValidHeightPos
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 1
field name: ValidHeightPos
comment: Validity Height Position
type: Datapoint Type Field
type: NamedIndividual
field size: 1

is incomplete
range: boolean
comment: Used to indicate that an entity is not yet completely defined and should be excluded from use in MaCs. Note 1: if this property has the value false, it must be treated exactly as if ths property would not be present at all. Note 2: If an entity has been completed for MaC use, this property must be removed from the entity.
type: AnnotationProperty

type.dpt.field.237.600.i3.LampFailure
field size: 1
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.237.600.i3.1
includes KV pair: type.kvpair.237.600.i3.0
comment: Lamp Failure
field name: LampFailure
field type: B
field index: 3

252.x
has communication mode: S
dpt bit size max: 40
label: 252.x
datapoint type major number: 252
is assembled with: type.dpt.field.252.x.i0
type: NamedIndividual
type: DatapointType
subject: 252.x
subject: 252.major

automatic light control = 0
type: NamedIndividual
value API: automaticLightControl
value KNX: 0

SceneControl
has communication mode: S
is assembled with: type.dpt.field.18.1.i0.SceneNumber
is assembled with: type.dpt.field.18.1.i1.Reserved
is assembled with: type.dpt.field.18.1.i2.C
description: a point representing DPT 18.001: SceneControl
datapoint type major number: 18
label: SceneControl
subject: 18.001
subject: SceneControl
subject: 18.1
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
dpt bit size max: 8

emFillLevelTargetProfile
is assembled with: type.dpt.field.512.508.i0.fltp.START
is assembled with: type.dpt.field.512.508.i3.fltp.PE
is assembled with: type.dpt.field.512.508.i2.fltp.PE CNT
is assembled with: type.dpt.field.512.508.i1.fltp.CQ
dpt bit size max: 1792
datapoint type major number: 512
type: DatapointType
type: NamedIndividual
datapoint type minor number: 508

CommMode
has communication mode: S
is assembled with: type.dpt.field.20.1000.i0
datapoint type major number: 20
subject: CommMode
subject: 20.1000
label: CommMode
datapoint type minor number: 1000
comment: a point representing DPT 20.1000: CommMode
type: NamedIndividual
type: DatapointType
dpt bit size max: 8

Control Blinds
has communication mode: S
description: a point representing DPT 3.008: Control Blinds
subject: 3.008
subject: Control Blinds
subject: 3.8
type: NamedIndividual
type: DatapointType
dpt bit size max: 4
label: Control Blinds
is assembled with: c
is assembled with: Step Code
datapoint type minor number: 8
datapoint type major number: 3

Energy Storage Control
type: Class
comment: A specific Application Function to optimize different energy storages.
subclass of: energyCtrl

Restriction
on property: pointName
has value: FanSpeed

Consumer / Producer
field type: B
label: Consumer / Producer
includes KV pair: Consumer = 0
includes KV pair: type.kvpair.1.1200.i0.1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1

type.dpt.field.525.500.i9.fv.Expected
type: Datapoint Type Field
type: NamedIndividual
description: Expected value
includes DPT: Power
field index: 9
field size: 16
field name: Expected

influences
domain: Datapoint
type: IrreflexiveProperty
type: ObjectProperty
type: AsymmetricProperty
comment: To express an “impact to cause” relation between different datapoints. Datapoints may affect other datapoint values, including manipulating their actual value at runtime.
range: Datapoint
sub property of: isReferencedBy

Restriction
on data range: string
on property: Installation Hints
max qualified cardinality: 1

type.dpt.field.20.1003.i0
includes KV pair: type.kvpair.20.1003.i0.1
includes KV pair: type.kvpair.20.1003.i0.0
includes KV pair: filtering by Domain Address and by Serial number table = 3
includes KV pair: filtering by KNX Serial Number table = 2
field type: N
comment: RF_FilterSelect
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.205.102.i1.HVACAirFlow
field type: V
type: NamedIndividual
type: Datapoint Type Field
field size: 16
includes digit: type.digit.s16
unit: M3-PER-HR
field index: 1
field resolution: 1.0
field name: HVACAirFlow

16.x
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: 16.major
subject: 16.x
label: 16.x
is assembled with: type.dpt.field.16.x.i0
datapoint type major number: 16
dpt bit size max: 112

closed = 0
type: NamedIndividual
value KNX: 0
value API: closed

4.x
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 4.major
subject: 4.x
is assembled with: type.dpt.field.4.x.i0
datapoint type major number: 4
dpt bit size max: 8

type.dpt.field.18.1.i2.C
field type: B
field name: C
includes KV pair: type.kvpair.18.1.i2.0
includes KV pair: learn the scene corresponding to the field Scene Number = 1
field index: 2
field size: 1
type: Datapoint Type Field
type: NamedIndividual

Percent V16
has communication mode: S
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.8.10.i0
subject: 8.010
subject: 8.10
subject: Percent V16
datapoint type minor number: 10
description: a point representing DPT 8.010: Percent V16
datapoint type major number: 8

28.x
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 28.x
subject: 28.major
is assembled with: type.dpt.field.28.x.i0
datapoint type major number: 28
dpt bit size max: 312

type.dpt.field.20.6.i0
includes KV pair: HVAC VAC = 14
includes KV pair: type.kvpair.20.6.i0.1
includes KV pair: HVAC Direct Electrical Heating = 12
includes KV pair: type.kvpair.20.6.i0.30
includes KV pair: Lighting = 20
includes KV pair: Load Management = 40
includes KV pair: type.kvpair.20.6.i0.10
includes KV pair: type.kvpair.20.6.i0.13
includes KV pair: type.kvpair.20.6.i0.0
includes KV pair: type.kvpair.20.6.i0.11
includes KV pair: Shutters and blinds = 50
field size: 8
type: Datapoint Type Field
type: NamedIndividual
comment: ApplicationArea
field index: 0
field type: N

type.dpt.field.14.37.i0
unit: http://qudt.org/vocab/unit/J
field index: 0
field size: 32
field type: F
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
description: heat, quantity of

SceneInfo
has communication mode: S
type: NamedIndividual
type: DatapointType
datapoint type major number: 26
is assembled with: type.dpt.field.26.1.i2.Reserved
is assembled with: type.dpt.field.26.1.i1.B
is assembled with: type.dpt.field.26.1.i0.SceneNumber
datapoint type minor number: 1
dpt bit size max: 8
description: a point representing DPT 26.001: SceneInfo
subject: SceneInfo
subject: 26.001
subject: 26.1

TempRoomSetpHeatEff
type: Class
label: TempRoomSetpHeatEff
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subject: TempRoomSetpHeatEff
subject: 399.52
subject: 52
property identifier annotation: 52
interface object type annotation: 399

type.dpt.field.201.104.i1.HVACContrMode
field size: 8
field index: 1
includes DPT: hvacContrMode
field name: HVACContrMode
type: Datapoint Type Field
type: NamedIndividual

Function Point
type: Class
subclass of: Aspect
subclass of: Restriction
  on property: hasTagSet
subclass of: Restriction
  max qualified cardinality: 1
  on data range: string
  on property: ipv6Multicast
subclass of: Class
subclass of: Restriction
  on property: nonKNXmappingAddress
  all values from: integer
subclass of: Restriction
  on property: is status of
  all values from: Function Point
disjoint with: ApplicationFunction
comment: A function point groups typically more than one point needed to express the communication link between all the points. The points provide the input/output data interfaces of the devices in an installation. A function point is derived from parent concepts that are specified as part of the EN 50090-6-2.

type.dpt.field.219.1.i12.LogNumber
includes digit: type.digit.u8
comment: Log Number
field name: LogNumber
unit: NUM
field type: U
field resolution: 1.0
field size: 8
field index: 12
type: Datapoint Type Field
type: NamedIndividual

CombinedPosition
has communication mode: S
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.240.800.i0.ValidSlatsPos
is assembled with: type.dpt.field.240.800.i1.ValidHeightPos
is assembled with: type.dpt.field.240.800.i4.HeightPosition
is assembled with: type.dpt.field.240.800.i3.SlatsPosition
is assembled with: type.dpt.field.240.800.i2.Reserved
datapoint type major number: 240
subject: CombinedPosition
subject: 240.800
datapoint type minor number: 800
label: CombinedPosition
comment: a point representing DPT 240.800: CombinedPosition
dpt bit size max: 24

type.dpt.field.30.1010.i4.ActivationStateOfChannel5
comment: Activation state of channel 5
field type: B
includes KV pair: type.kvpair.30.1010.i4.1
includes KV pair: The visual effect of channel 5 is inactive = 0
field index: 4
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field name: ActivationStateOfChannel5

244.x
has communication mode: S
datapoint type major number: 244
subject: 244.major
subject: 244.x
type: NamedIndividual
type: DatapointType
label: 244.x
dpt bit size max: 16
is assembled with: type.dpt.field.244.x.i0

type.dpt.field.10.1.i1.Reserved
type: NamedIndividual
type: Datapoint Type Field
includes reserved bit: type.bit.reserved
field name: Reserved
field size: 2
field index: 1
field type: r

Steam Oven
type: EquipmentType
type: NamedIndividual
comment: Steam oven (also called combi-steamers, hot-air steamers, combination steam-convection ovens, or simply combi ovens) are cooking appliances (EN 50523) typically used in professional catering or food service operations.

Restriction
on property: interface object type
has value: 399

Restriction
on property: interface object type
has value: 345

Angle
unit: DEG
field type: U
comment: Represents an angle from 0 to 360 degrees.
label: Angle
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes digit: type.digit.u8
field size: 8
field resolution: 1.4117647

type.dpt.field.254.600.i1.cB
includes KV pair: type.kvpair.increase
includes KV pair: Decrease = 0
field size: 1
field type: B
field index: 1
comment: Shall specify whether the colour component blue shall be increased or decreased.
field name: cB
type: Datapoint Type Field
type: NamedIndividual

first: Restriction
  has value: many
  on property: has cardinality
rest: nil

type.dpt.field.207.105.i0.Failure
type: Datapoint Type Field
type: NamedIndividual
comment: actuator has a failure
field index: 0
field name: Failure
includes DPT: Bool
field size: 1

Cool Stage A Actuator Fault
type: Class
subclass of: Function Point
subclass of: Restriction
  on property: has datapoint type
  has value: Bool

BlinkingDisabled = 0
value API: blinkingDisabled
value KNX: 0
type: NamedIndividual

206.x
has communication mode: LTE
type: DatapointType
type: NamedIndividual
label: 206.x
datapoint type major number: 206
subject: 206.major
subject: 206.x
is assembled with: type.dpt.field.206.x.i0
dpt bit size max: 24

StatusTempRoomSetpEff
type: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air temperature room
subclass of: Restriction
  has value: StatusRoomSetp
  on property: has datapoint type
subject: 101.55
subject: 55
subject: StatusTempRoomSetpEff
property identifier annotation: 55
interface object type annotation: 101

type.dpt.field.234.1.i0.Character2
description: second character of LanguageCode, ASCII-coded
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: Character2
includes DPT: Char ASCII
field size: 8

type.dpt.field.20.607.i0
includes KV pair: type.kvpair.20.607.i0.4
includes KV pair: type.kvpair.20.607.i0.1
includes KV pair: type.kvpair.20.607.i0.2
includes KV pair: one PB/binary input, Off / DimDown message sent = 3
field type: N
type: Datapoint Type Field
type: NamedIndividual
comment: LDSBMode
field index: 0
field size: 8

Value Power
has communication mode: S
datapoint type major number: 14
is assembled with: type.dpt.field.14.56.i0
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
description: DPT 14.056: Value of power
subject: Value Power
subject: 14.056
subject: 14.56
datapoint type minor number: 56
label: Value Power

SwitchOnOffControlCmd
type: Class
interface object type annotation: 418
subject: SwitchOnOffControlCmd
subject: 60
subject: 418.60
label: SwitchOnOffControlCmd
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 60

Value Heat FlowRate
has communication mode: S
label: Value Heat FlowRate
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
subject: Value Heat FlowRate
subject: 14.036
subject: 14.36
datapoint type minor number: 36
datapoint type major number: 14
is assembled with: type.dpt.field.14.36.i0
description: DPT 14.036: Value of heat flow rate

Restriction
on property: pointName
has value: HVACModeEff

The visual effect of channel 13 is active = 1
value API: theVisualEffectOfChannel13IsActive
value KNX: 1
type: NamedIndividual

type.dpt.field.523.500.i0.sms.STAT TMR
field index: 0
description: status of all timers wether they are running or not. each bit declares the status of the timer with the id of the bit position. bn = 0 means timer n is not running, bn = 1 means timer n is running
field size: 16
field name: STAT_TMR
type: Datapoint Type Field
type: NamedIndividual
includes DPT: emTimerStatus

Trigger
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1
field type: B
includes KV pair: type.kvpair.1.17.i0.1
includes KV pair: trigger (0) = 0

LongTimePeriod Min
has communication mode: S
datapoint type minor number: 101
datapoint type major number: 12
label: LongTimePeriod Min
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 12.101: LongTimePeriod Min
subject: 12.101
subject: LongTimePeriod Min
is assembled with: type.dpt.field.12.101.i0
dpt bit size max: 32

ActiveEnergy MWh
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: 13.16
subject: 13.016
subject: ActiveEnergy MWh
is assembled with: type.dpt.field.13.16.i0
dpt bit size max: 32
datapoint type major number: 13
label: ActiveEnergy MWh
datapoint type minor number: 16
comment: a point representing DPT 13.016: ActiveEnergy MWh

reading of access information code was not successful = 1
value KNX: 1
value API: readingOfAccessInformationCodeWasNo
type: NamedIndividual

Value Electric DipoleMoment
has communication mode: S
comment: DPT 14.021: Value of electric dipole moment
dpt bit size max: 32
type: DatapointType
type: NamedIndividual
subject: Value Electric DipoleMoment
subject: 14.021
subject: 14.21
datapoint type minor number: 21
datapoint type major number: 14
is assembled with: type.dpt.field.14.21.i0

ValveKick
type: Class
interface object type annotation: 400
subject: 400.73
subject: 73
subject: ValveKick
subclass of: Restriction
  on property: has datapoint type
  has value: Bool
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
property identifier annotation: 73

interface object type
range: unsignedShort
comment: In KNX used (numerical) identifier to address a specific interface object type reflecting a KNX functional block id. The range xsd:unsignedShort supports exactly the KNX value range from 0 to 65535.
type: DatatypeProperty
type: FunctionalProperty

CombinedStatus_RTSM
type: Class
label: CombinedStatus_RTSM
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
  some values from: Class
    intersection of: Operation Kind
subclass of: Restriction
  has value: qk ph person positionvector room
  on property: hasQualityKind
subject: 64
subject: CombinedStatus_RTSM
subject: 397.64
interface object type annotation: 397
property identifier annotation: 64

type.dpt.field.524.500.i3.ti.ET
includes DPT: DateTime
description: time when this instruction will be executed
field name: ET
field size: 64
type: Datapoint Type Field
type: NamedIndividual
field index: 3

type.dpt.field.512.502.i3.pe.LR CNT
includes digit: type.digit.u8 1 38
field name: LR_CNT
field type: U
type: Datapoint Type Field
type: NamedIndividual
field index: 3
description: number of power envelope elements
field size: 8

type.dpt.field.21.107.i4.HVACModeUserModeStatus
field name: HVACModeUserModeStatus
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: HVAC User Mode active (means DP ‘HVACModeUser’ is different from ‘Auto’) = 1
includes KV pair: HVAC User Mode not active = 0
comment: Status of HVAC Mode User
field type: B
field index: 4

Value Temp F
has communication mode: S
type: DatapointType
type: NamedIndividual
description: a point representing DPT 9.027: Value Temp F
is assembled with: type.dpt.field.9.27.i0
subject: 9.027
subject: 9.27
subject: Value Temp F
datapoint type minor number: 27
datapoint type major number: 9
dpt bit size max: 16

error = 1
type: NamedIndividual
value API: error
value KNX: 1

246.x
has communication mode: S
datapoint type major number: 246
is assembled with: type.dpt.field.246.x.i0
type: NamedIndividual
type: DatapointType
dpt bit size max: 16
label: 246.x
subject: 246.major
subject: 246.x

type.dpt.field.7.10.i0
unit: UNITLESS
includes digit: type.digit.u16
field size: 16
field type: U
type: Datapoint Type Field
type: NamedIndividual
field index: 0

ValveMode
has communication mode: S
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
subject: 20.108
subject: ValveMode
datapoint type major number: 20
datapoint type minor number: 108
description: a point representing DPT 20.108: ValveMode
label: ValveMode
is assembled with: type.dpt.field.20.108.i0

TimePeriodSec
has communication mode: S
subject: 7.005
subject: TimePeriodSec
subject: 7.5
description: a point representing DPT 7.005: TimePeriodSec
is assembled with: type.dpt.field.7.5.i0
label: TimePeriodSec
datapoint type major number: 7
datapoint type minor number: 5
type: NamedIndividual
type: DatapointType
dpt bit size max: 16

at least one window opened = 1
value KNX: 1
value API: atLeastOneWindowOpened
type: NamedIndividual

type.dpt.field.14.18.i0
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
comment: electric charge
field index: 0
unit: http://qudt.org/vocab/unit/C
field type: F
includes digit: type.digit.f32

212.x
has communication mode: LTE
type: DatapointType
type: NamedIndividual
subject: 212.x
subject: 212.major
datapoint type major number: 212
label: 212.x
is assembled with: type.dpt.field.212.x.i0
dpt bit size max: 48

first: Restriction
  has value: 423
  on property: interface object type
rest: nil

HVACMode
type: Class
subject: 51
subject: HVACMode
subject: 110.51
subclass of: Restriction
  on property: has datapoint type
  has value: HVAC Mode Z
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 110
property identifier annotation: 51

type.dpt.field.241.800.i8.Locked
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field index: 8
comment: Movement is locked, e.g. by DeviceLocked input
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: Locked
field type: B

type.dpt.field.224.100.i2.TempSetpHeating
unit: DEG C
field size: 16
comment: Supply air temperature heating setpoint
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767
field name: TempSetpHeating
field resolution: 0.02
field index: 2

type.dpt.field.25.1000.i0.Nak
field type: U
unit: NUM
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 4
comment: Nak
includes digit: type.digit.u4 0 3
field name: Nak

Restriction
on property: interface object type
has value: 384

Restriction
has value: one
on property: has cardinality

The visual effect of channel 5 is inactive = 0
value API: theVisualEffectOfChannel5IsInactive
type: NamedIndividual
value KNX: 0

LightApplicationMode
has communication mode: S
type: DatapointType
type: NamedIndividual
label: LightApplicationMode
datapoint type major number: 20
subject: LightApplicationMode
subject: 20.5
subject: 20.005
datapoint type minor number: 5
is assembled with: type.dpt.field.20.5.i0
comment: a point representing DPT 20.005: LightApplicationMode
dpt bit size max: 8

type.dpt.field.27.1.i7.IOO8
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field name: IOO8
includes KV pair: output state is On = 1
includes KV pair: output state is Off = 0
comment: Info On Off Output 8
field index: 7
field type: B

type.dpt.field.249.600.i6.TimePeriod
type: Datapoint Type Field
type: NamedIndividual
field name: TimePeriod
field size: 16
field index: 6
includes DPT: TimePeriod100MSec

type.dpt.field.275.100.i1.TempSetpEco
field name: TempSetpEco
field size: 16
comment: room temperature setpoint economy
includes digit: type.digit.f16 neg27300 65534
unit: DEG C
field resolution: 0.01
field type: F
type: Datapoint Type Field
type: NamedIndividual
field index: 1

AddInfoTypes
has communication mode: S
subject: 20.1001
subject: AddInfoTypes
is assembled with: type.dpt.field.20.1001.i0
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 20.1001: AddInfoTypes
dpt bit size max: 8
datapoint type major number: 20
datapoint type minor number: 1001

Frequency
type: Quantity Kind
type: NamedIndividual
comment: "Frequency" is the number of occurrences of a repeating event per unit time. The repetition of the events may be periodic (that is. the length of time between event repetitions is fixed) or aperiodic (i.e. the length of time between event repetitions varies). Therefore, we distinguish between periodic and aperiodic frequencies. In the SI system, periodic frequency is measured in hertz (Hz) or multiples of hertz, while aperiodic frequency is measured in becquerel (Bq). In spectroscopy, v is mostly used. Light passing through different media keeps its frequency, but not its wavelength or wavenumber.

type.dpt.field.14.56.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
description: power
field type: F
includes digit: type.digit.f32
field resolution: 1.0
field size: 32
unit: http://qudt.org/vocab/unit/W

Not active = 0
value KNX: 0
value API: notActive
type: NamedIndividual

Restriction
on property: pointName
has value: TempRoomSetpSetCool

type.dpt.field.14.16.i0
field type: F
field size: 32
includes digit: type.digit.f32
comment: conductivity, electrical
unit: S-PER-M
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0

type.dpt.field.21.500.i0.sct.CT
includes digit: type.digit.u8
description: supported control types, set bitwise b0 = PEBC b1 = PPBC b2 = OMBC b3 = FRBC b4 = DDBC b5-b7 = reserved
field type: U
type: Datapoint Type Field
type: NamedIndividual
field name: CT
field size: 8
field index: 0

volume, 0,001 l = 16
type: NamedIndividual
value KNX: 16
value API: volume,0,001L

Restriction
has value: AQRoom
on property: pointName

14.x
has communication mode: S
subject: 14.major
subject: 14.x
type: DatapointType
type: NamedIndividual
datapoint type major number: 14
dpt bit size max: 32
is assembled with: type.dpt.field.14.x.i0

has point
range: Point
comment: To define a generic relation from a functionality to several points. A functionality without any points is possible.
inverse of: isPointOf
type: ObjectProperty
domain: Functionality

type.dpt.field.203.102.i1.SunIntensity
type: NamedIndividual
type: Datapoint Type Field
field name: SunIntensity
field size: 16
unit: W-PER-M2
field index: 1
includes digit: type.digit.u16 0 28000
comment: Sun intensity W/m2
field type: U
field resolution: 0.05

type.dpt.field.225.2.i1.TimePeriod
field name: TimePeriod
type: Datapoint Type Field
type: NamedIndividual
description: time period
field size: 16
field index: 1
includes DPT: TimePeriodMsec

HVAC Hot Water Heating = 11
type: NamedIndividual
value KNX: 11
value API: hVACHotWaterHeating

type.dpt.field.219.1.i7.ErrorCode Sup
type: Datapoint Type Field
type: NamedIndividual
field name: ErrorCode_Sup
field size: 1
field index: 7
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
comment: ErrorCode_Sup

Restriction
has value: 400
on property: interface object type

inactive = 0
type: NamedIndividual
value KNX: 0
value API: inactive

Humidity
has communication mode: S
comment: a point representing DPT 9.029: Humidity
subject: 9.29
subject: 9.029
subject: Humidity
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.9.29.i0
datapoint type major number: 9
dpt bit size max: 16
label: Humidity
datapoint type minor number: 29

Operational State Out Of Service
type: State Type
type: NamedIndividual
description: This state type expresses that a datapoint is accessible but out of service, i.e., the main value is void and may contain any value. The device itself is operational. Typical usages are an optional sensor is not connected (out of service, sensor data is invalid) or a configuration parameter is void (function disabled).

first: Restriction
  on property: pointName
  has value: SwitchOnOff

type.dpt.field.252.600.i5.StepCodeColourWhite
field name: StepCodeColourWhite
field index: 5
field size: 3
includes digit: type.digit.u3
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
comment: Shall specify the fading step size or to the code to stop the fading of the colour white

Restriction
on property: property identifier
has value: 54

type.dpt.field.9.4.i0
field resolution: 0.01
unit: LUX
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes digit: type.digit.f16 0 670433
field size: 16
field type: F

Elevator
type: NamedIndividual
type: EquipmentType
comment: Enclosure used to move people between floors. An elevator or lift is a cable-assisted, hydraulic cylinder-assisted, or roller-track assisted machine that vertically transports people or freight between floors, levels, or decks of a building, vessel, or other structure.

EmergDepressure = 2
value KNX: 2
type: NamedIndividual
value API: emergDepressure

datapoint type
comment: A parent data property, used to express any kind of generic data that relates to a datapoint type.
type: DatatypeProperty
domain: DatapointType

type.dpt.field.512.510.i0.smddbc.COM
type: NamedIndividual
type: Datapoint Type Field
includes digit: type.digit.u4
description: supported commodities (b0 = electricity, b1 = gas, b2 = oil, b3 = 0/reserved)
field name: COM
field index: 0
field size: 4
field type: U

type.dpt.field.20.112.i0
field type: N
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes KV pair: type.kvpair.20.112.i0.1
includes KV pair: type.kvpair.20.112.i0.2
includes KV pair: type.kvpair.20.112.i0.0
field size: 8
comment: MasterSlaveMode

Behaviour Lock Unlock
has communication mode: S
subject: 20.600
subject: Behaviour Lock Unlock
label: Behaviour Lock Unlock
type: NamedIndividual
type: DatapointType
dpt bit size max: 8
datapoint type minor number: 600
is assembled with: type.dpt.field.20.600.i0
datapoint type major number: 20
comment: a point representing DPT 20.600: Behaviour Lock Unlock

245.x
has communication mode: S
label: 245.x
type: NamedIndividual
type: DatapointType
datapoint type major number: 245
dpt bit size max: 48
subject: 245.major
subject: 245.x
is assembled with: type.dpt.field.245.x.i0

Restriction
on property: has cardinality
has value: one

Request Converter Info Fix = 8
value API: requestConverterInfoFix
value KNX: 8
type: NamedIndividual

type.dpt.field.237.600.i4.BallastFailure
includes KV pair: type.kvpair.237.600.i4.0
includes KV pair: error = 1
field index: 4
comment: Ballast Failure
field name: BallastFailure
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field type: B

Restriction
on property: interface object type
has value: 328

ActTargetPosCoolStageA
type: Class
label: ActTargetPosCoolStageA
property identifier annotation: 104
subject: ActTargetPosCoolStageA
subject: 399.104
subject: 104
interface object type annotation: 399

type.dpt.field.20.604.i0
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: automatic light control = 0
includes KV pair: manual light control = 1
description: LightControlMode
field index: 0
field size: 8
field type: N

Storm State
type: State Type
type: NamedIndividual
description: This state type expresses the state of storm. Usually, this state is related to the protection of shading equipment such as blinds and slats, which can be damaged due to high wind speeds. In case of storm, this equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Storm' state type.

Restriction
max qualified cardinality: 1
on property: datapoint type minor number
on data range: nonNegativeInteger

Binary Value Z
has communication mode: LTE
subject: 200.101
subject: Binary Value Z
comment: a point representing DPT 200.101: Binary Value Z
label: Binary Value Z
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.200.101.i0.StatusCommand
is assembled with: type.dpt.field.200.101.i1.BinaryValue
datapoint type major number: 200
datapoint type minor number: 101
dpt bit size max: 16

Room Temperature Control
comment: A user operated room temperature control including actual room/outside temperature inputs and valve control outputs.
subclass of: Restriction
  qualified cardinality: 1
  on property: has function point
  on class: Cool Stage B Actuator Status
subclass of: Restriction
  on class: HeatStageBActuatorFault
  on property: has function point
  qualified cardinality: 1
subclass of: Restriction
  on property: has function point
  qualified cardinality: 1
  on class: Outside Temperature
subclass of: Fan Actuator
subclass of: Restriction
  on class: RoomTemperature
  on property: has function point
  qualified cardinality: 1
subclass of: Restriction
  on class: HeatStageAActuatorFault
  on property: has function point
  qualified cardinality: 1
subclass of: Restriction
  on property: has function point
  on class: Heat Stage B Actuator Status
  qualified cardinality: 1
subclass of: Restriction
  on property: has function point
  on class: Cool Stage A Actuator Fault
  qualified cardinality: 1
subclass of: Restriction
  on property: has function point
  qualified cardinality: 1
  on class: Cool Stage A Actuator Calibration Mode
subclass of: Restriction
  qualified cardinality: 1
  on class: CoolStageAActuatorCurrentPosition
  on property: has function point
subclass of: airTemperatureCtrl
subject: RTC
type: Class

WindowSwitch
type: Class
property identifier annotation: 52
subclass of: Restriction
  has value: windowDoor
  on property: has datapoint type
label: WindowSwitch
subject: 343.52
subject: WindowSwitch
subject: 52
interface object type annotation: 343

TempRoomSetpAbsNext
type: Class
interface object type annotation: 113
subclass of: Restriction
  has value: TempHVACAbsNext
  on property: has datapoint type
subject: 113.52
subject: 52
subject: TempRoomSetpAbsNext
label: TempRoomSetpAbsNext
property identifier annotation: 52

composes
inverse of: isComposedBy
sub property of: isDatapointOf
range: FunctionalBlock
type: ObjectProperty
comment: An OP relationship to express a relation from a functional block to datapoints as part of a FB. Such datapoints includes per definition additional semantic information, with this a FB can be composed with its mandatory/optional datapoints.

strong gale = 9
type: NamedIndividual
value KNX: 9
value API: strongGale

EnergyDirection
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type major number: 1
description: a point representing DPT 1.1201: EnergyDirection
dpt bit size max: 1
subject: 1.1201
subject: EnergyDirection
is assembled with: Energy Direction
datapoint type minor number: 1201

type.dpt.field.14.28.i0
field type: F
comment: electric potential difference
field index: 0
field resolution: 1.0
unit: http://qudt.org/vocab/unit/V
type: Datapoint Type Field
type: NamedIndividual
field size: 32
includes digit: type.digit.f32

Night = 1
value KNX: 1
type: NamedIndividual
value API: night

type.dpt.field.249.600.i0.validityOfAbsoluteBrightness
field index: 0
description: validity of the absolute brightness
field type: B
field name: validityOfAbsoluteBrightness
field size: 1
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.20.11.i0
includes KV pair: type.kvpair.20.11.i0.0
includes KV pair: type.kvpair.20.11.i0.1
includes KV pair: maximal table length exceeded = 13
includes KV pair: type.kvpair.20.11.i0.14
includes KV pair: communication fault = 2
includes KV pair: hardware fault = 4
includes KV pair: type.kvpair.20.11.i0.10
includes KV pair: type.kvpair.20.11.i0.9
includes KV pair: type.kvpair.20.11.i0.7
includes KV pair: type.kvpair.20.11.i0.16
includes KV pair: type.kvpair.20.11.i0.5
includes KV pair: Group Address Table is not sorted = 15
includes KV pair: type.kvpair.20.11.i0.11
includes KV pair: invalid Group Object number (ASAP) = 17
includes KV pair: type.kvpair.20.11.i0.3
includes KV pair: type.kvpair.20.11.i0.8
includes KV pair: type.kvpair.20.11.i0.18
includes KV pair: insufficient non volatile memory = 6
includes KV pair: type.kvpair.20.11.i0.12
type: Datapoint Type Field
type: NamedIndividual
comment: ErrorClass_System
field type: N
field size: 8
field index: 0

ActuatorStatus
type: Class
subject: 53
subject: ActuatorStatus
subject: 418.53
label: ActuatorStatus
subclass of: Restriction
  has value: Status Lighting Actuator
  on property: has datapoint type
property identifier annotation: 53
interface object type annotation: 418

type.dpt.field.203.100.i0.StatusCommand
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0
field type: Z8
field name: StatusCommand
field size: 8
comment: standard Status/Command

Room Temperature Sensor
type: Class
subject: 321
subject: Room Temperature Sensor
subject: RTS
label: Room Temperature Sensor
interface object type annotation: 321

Value Energy
has communication mode: S
datapoint type major number: 14
datapoint type minor number: 31
subject: Value Energy
subject: 14.31
subject: 14.031
dpt bit size max: 32
label: Value Energy
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.14.31.i0
comment: DPT 14.031: Value of energy

42% = 3
type: NamedIndividual
value KNX: 3
value API: 42%

Steam meter = 5
value API: steamMeter
value KNX: 5
type: NamedIndividual

Restriction
has value: many
on property: has cardinality

Reduced = 3
value API: reduced
type: NamedIndividual
value KNX: 3

Start Control
has communication mode: S
datapoint type minor number: 10
description: a point representing DPT 2.010: Start Control
type: NamedIndividual
type: DatapointType
subject: 2.010
subject: Start Control
subject: 2.10
label: Start Control
is assembled with: c
is assembled with: Start
datapoint type major number: 2
dpt bit size max: 2

SceneNumber
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: 17.1
subject: 17.001
subject: SceneNumber
datapoint type minor number: 1
description: a point representing DPT 17.001: SceneNumber
is assembled with: type.dpt.field.17.1.i1.Reserved
is assembled with: type.dpt.field.17.1.i0.SceneNumber
dpt bit size max: 8
label: SceneNumber
datapoint type major number: 17

On = 1
value API: on
is applicable datapoint enum of: On State
type: NamedIndividual
value KNX: 1

Value Luminous Flux
has communication mode: S
datapoint type major number: 14
is assembled with: type.dpt.field.14.42.i0
datapoint type minor number: 42
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
subject: 14.42
subject: Value Luminous Flux
subject: 14.042
comment: DPT 14.042: Value of luminous flux

Electricity, DC
description: Direct current electricity
type: Phenomenon
type: NamedIndividual

HVACModeNext
type: Class
label: HVACModeNext
subject: HVACModeNext
subject: 52
subject: 104.52
subclass of: Restriction
  on property: has datapoint type
  has value: hvacModeNext
property identifier annotation: 52
interface object type annotation: 104

type.dpt.field.15.0.i10.D6
field size: 4
field name: D6
field type: U
field resolution: 1.0
includes digit: type.digit.u4 0 9
comment: digit 6 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
type: Datapoint Type Field
type: NamedIndividual
field index: 10

TempRoomSetpCoolEff
type: Class
interface object type annotation: 398
subclass of: Restriction
  some values from: Class
  on property: has operation kind
subject: 398.87
subject: 87
subject: TempRoomSetpCoolEff
property identifier annotation: 87

Return Section
type: Locality
type: NamedIndividual
description: Refers to distribution systems used to transport substances (and phenomena) such as water, air, or heat back to the specific centralized plants in a building. The distribution systems interface with the individual rooms at the start of the return part of the distribution system.

type.dpt.field.23.3.i0
includes KV pair: type.kvpair.23.3.i0.1
includes KV pair: type.kvpair.23.3.i0.2
includes KV pair: DownUp = 3
includes KV pair: type.kvpair.23.3.i0.0
field type: N
type: Datapoint Type Field
type: NamedIndividual
field size: 2
field index: 0

Restriction
qualified cardinality: 1
on property: has operation kind

Shutter Stop Step
subclass of: Function Point
subclass of: Restriction
  on property: actsOnPhenomenonQualityKind
  has value: qk ph light illuminance room
type: Class

Scaling
type: Datapoint Type Field
type: NamedIndividual
field resolution: 0.3921566
comment: Represents a percentage value between 0 and 100%.
field index: 0
includes digit: type.digit.u8
unit: PERCENT
field size: 8
label: Scaling
field type: U

Chromaticity Red
description: This state type expresses that the red part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.
type: State Type
type: NamedIndividual

type.dpt.field.10.1.i3.Reserved
includes reserved bit: type.bit.reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 3
field name: Reserved
field type: r
field size: 2

TempRoomSetpSetCoolEff
type: Class
subject: 90
subject: TempRoomSetpSetCoolEff
subject: 398.90
interface object type annotation: 398
property identifier annotation: 90

10.x
has communication mode: S
label: 10.x
subject: 10.x
subject: 10.major
type: NamedIndividual
type: DatapointType
dpt bit size max: 24
is assembled with: type.dpt.field.10.x.i0
datapoint type major number: 10

rest: nil
first: Restriction
  on property: interface object type
  has value: 417

type.dpt.field.212.100.i1.TempSetpShiftStdby
field index: 1
field size: 16
description: room temperature setpoint shift standby (delta value)
type: Datapoint Type Field
type: NamedIndividual
field resolution: 0.02
field type: V
unit: http://qudt.org/vocab/unit/K
field name: TempSetpShiftStdby
includes digit: type.digit.s16

c
field index: 1
includes DPT: Up Down
label: c
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: c
description: Move up or down.

The visual effect of channel 10 is inactive = 0
value API: theVisualEffectOfChannel10IsInactiv
type: NamedIndividual
value KNX: 0

Restriction
has value: many
on property: has cardinality

Restriction
has value: one
on property: has cardinality

Value Acceleration
has communication mode: S
subject: Value Acceleration
subject: 14.000
subject: 14.0
comment: DPT 14.000: Value of acceleration
type: DatapointType
type: NamedIndividual
datapoint type major number: 14
datapoint type minor number: 0
label: Value Acceleration
dpt bit size max: 32
is assembled with: type.dpt.field.14.0.i0

Value Volume Flow
has communication mode: S
is assembled with: type.dpt.field.9.25.i0
dpt bit size max: 16
label: Value Volume Flow
datapoint type major number: 9
subject: Value Volume Flow
subject: 9.25
subject: 9.025
comment: a point representing DPT 9.025: Value Volume Flow
type: DatapointType
type: NamedIndividual
datapoint type minor number: 25

Level 0 = 0
value API: level0
type: NamedIndividual
value KNX: 0

HVACModeAct
type: Class
property identifier annotation: 152
subclass of: Restriction
  on property: has operation kind
  some values from: Class
subclass of: Class
subject: 258.152
subject: 152
subject: HVACModeAct
interface object type annotation: 258

type.dpt.field.522.500.i2.si.Reserved
field size: 7
field name: RESERVED
field type: r
description: reserved bits
type: Datapoint Type Field
type: NamedIndividual
field index: 2
includes reserved bit: type.bit.reserved

ComfortProlongUser
type: Class
subclass of: Restriction
  on property: has operation kind
label: ComfortProlongUser
interface object type annotation: 397
property identifier annotation: 81
subject: 397.81
subject: ComfortProlongUser
subject: 81

type.dpt.field.21.601.i3.Underload
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
description: Underload
field type: B
field index: 3
field name: Underload
field size: 1

Not occupied = 2
value API: notOccupied
value KNX: 2
type: NamedIndividual

type.dpt.field.14.51.i0
field size: 32
field type: F
includes digit: type.digit.f32
unit: KiloGM
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
comment: mass
field index: 0

updated value = 5
value API: updatedValue
type: NamedIndividual
value KNX: 5

type.dpt.field.21.107.i2.ComfortPushButtonEffective
type: NamedIndividual
type: Datapoint Type Field
field size: 1
includes KV pair: no comfort push button is pressed = 0
includes KV pair: at least one comfort push button is pressed = 1
comment: Effective value of the comfort push button
field type: B
field index: 2
field name: ComfortPushButtonEffective

type.dpt.field.512.504.i2.pp.START
includes DPT: DateTime
field size: 64
type: Datapoint Type Field
type: NamedIndividual
field index: 2
field name: START
description: Start of time period that will be covered by the power profile

Restriction
on property: property identifier
has value: 51

type.dpt.field.235.1.i3.Tariff
type: Datapoint Type Field
type: NamedIndividual
field size: 8
description: Tariff
field index: 3
field name: Tariff
includes DPT: Tariff

type.dpt.field.21.100.i5.DHWLegio
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field index: 5
field type: B
description: DHWLegio
field size: 1
field name: DHWLegio
type: Datapoint Type Field
type: NamedIndividual

64,0 s = 14
type: NamedIndividual
value API: 64,0S
value KNX: 14

emTimerStatus
is assembled with: type.dpt.field.521.500.i4.ts.Reserved
is assembled with: type.dpt.field.521.500.i0.ts.FTS
is assembled with: type.dpt.field.521.500.i1.ts.DUR
is assembled with: type.dpt.field.521.500.i2.ts.ID
is assembled with: type.dpt.field.521.500.i3.ts.R
dpt bit size max: 88
type: NamedIndividual
type: DatapointType
datapoint type major number: 521
datapoint type minor number: 500

HVACMode
type: Class
property identifier annotation: 51
subclass of: Class
subject: HVACMode
subject: 51
subject: 104.51
interface object type annotation: 104

is location of
type: AsymmetricProperty
type: IrreflexiveProperty
type: FunctionalProperty
type: ObjectProperty
sub property of: isReferencedBy
domain: Location
range: Location

HW fault = 4
value API: hWFault
value KNX: 4
type: NamedIndividual

Extended emergency mode active = 6
type: NamedIndividual
value KNX: 6
value API: extendedEmergencyModeActive

rest: nil
first: Restriction
  on property: interface object type
  has value: 321

Gas Measurement Condition
has communication mode: S
label: Gas Measurement Condition
comment: a point representing DPT 20.1202: Gas Measurement Condition
type: NamedIndividual
type: DatapointType
subject: 20.1202
subject: Gas Measurement Condition
dpt bit size max: 8
is assembled with: type.dpt.field.20.1202.i0
datapoint type major number: 20
datapoint type minor number: 1202

Enable = 1
value API: enable
value KNX: 1
type: NamedIndividual
is applicable datapoint enum of: enabled

Channel
subclass of: Functionality
comment: A channel is grouping datapoints together, which may linked to a related hardware (such as a terminal) and/or a related application program. It fulfils a certain functionality of the device, which is a collection of datapoints (when available with a standardized semantic meaning as functional block) and the related hardware connections (i.e. input or output terminals). A channel is derived from parent concepts that are specified as part of the EN 50090-6-2.
disjoint with: FunctionalBlock
type: Class

Restriction
on property: pointName
has value: TempRoomSetpTariffShift

type.dpt.field.22.100.i0.Fault
type: Datapoint Type Field
type: NamedIndividual
field name: Fault
field index: 0
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
comment: Fault
field size: 1

8,0 s = 8
value KNX: 8
type: NamedIndividual
value API: 8,0S

type.dpt.field.22.101.i4.StatusMorningBoostH
field size: 1
field index: 4
type: Datapoint Type Field
type: NamedIndividual
field name: StatusMorningBoostH
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
description: StatusMorningBoostH

type.dpt.field.522.500.i6.si.IT
description: instruction type
field type: N
includes KV pair: type.kvpair.seqInstrStopInterrupt
includes KV pair: schedule sequence
includes KV pair: start sequence
includes KV pair: select sequence
field name: IT
field index: 6
type: Datapoint Type Field
type: NamedIndividual
field size: 4

type.dpt.field.212.101.i2.TempSetpComf
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767
field index: 2
field name: TempSetpComf
comment: room temperature setpoint comfort
unit: DEG C
field size: 16

Value Light Quantity
has communication mode: S
label: Value Light Quantity
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.14.40.i0
datapoint type minor number: 40
description: DPT 14.040: Value of light quantity
subject: Value Light Quantity
subject: 14.40
subject: 14.040
datapoint type major number: 14

Storage Tank
type: EquipmentType
type: NamedIndividual
description: Tank used to store a substance for temporary holding. For example, a fuel tank (also called a petrol tank or gas tank) is a safe container for flammable fluids.

Restriction
has value: 399
on property: interface object type

type.dpt.field.229.1.i0.StatusCommand
field name: StatusCommand
comment: standard Status/Command
field size: 8
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0
field type: Z8

Restriction
has value: 400
on property: interface object type

rest:
  first: Restriction
    on property: interface object type
    has value: 101
  rest: nil

TempRoomSetpCoolEff
type: Class
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subject: 101.53
subject: 53
subject: TempRoomSetpCoolEff
interface object type annotation: 101
property identifier annotation: 53

type.dpt.field.22.103.i7.HeatingModeEnabled
comment: Heating Mode Enabled
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 7
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field name: HeatingModeEnabled
field type: B

type.dpt.field.217.1.i0.RevisionNumber
comment: Revision Number
field type: U
field resolution: 1.0
field name: RevisionNumber
type: Datapoint Type Field
type: NamedIndividual
field size: 6
field index: 0
includes digit: type.digit.u6
unit: NUM

Point
subclass of: Thing
comment: A generic concept to represents an interface to data. A point can carry additional meta data, provided by tags and/or feature of interests. To describe a point more precise the class has several subclasses.
type: Class

1 s = 1
value KNX: 1
value API: 1S
type: NamedIndividual

ScalingSpeed
has communication mode: S
subject: ScalingSpeed
subject: 225.1
subject: 225.001
datapoint type minor number: 1
type: DatapointType
type: NamedIndividual
dpt bit size max: 24
comment: a point representing DPT 225.001: ScalingSpeed
is assembled with: type.dpt.field.225.1.i1.TimePeriod
is assembled with: type.dpt.field.225.1.i0.Percent
datapoint type major number: 225

type.dpt.field.11.1.i2.Month
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u4 1 12
field index: 2
field size: 4
unit: MO
field name: Month
field type: U
field resolution: 1.0

ControlModeEff
type: Class
subclass of: Restriction
  has value: lightControlMode
  on property: has datapoint type
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subject: ControlModeEff
subject: 54
subject: 417.54
interface object type annotation: 417
property identifier annotation: 54

DecimalFactor
has communication mode: S
label: DecimalFactor
subject: DecimalFactor
subject: 5.005
subject: 5.5
type: NamedIndividual
type: DatapointType
datapoint type major number: 5
description: a point representing DPT 5.005: DecimalFactor
dpt bit size max: 8
is assembled with: type.dpt.field.5.5.i0
datapoint type minor number: 5

ActTargetPosHeatStageA
type: Class
subject: ActTargetPosHeatStageA
subject: 102
subject: 399.102
label: ActTargetPosHeatStageA
property identifier annotation: 102
interface object type annotation: 399

type.dpt.field.513.500.i2.rol.C2
field size: 2
includes KV pair: type.kvpair.rolConsumerAndProducer
includes KV pair: Consumer
includes KV pair: type.kvpair.rolProducer
includes KV pair: type.kvpair.rolNone
description: roles for commodity OIL
field type: U
type: Datapoint Type Field
type: NamedIndividual
field index: 2
field name: C2

Restriction
on property: property identifier
has value: 51

type.dpt.field.21.1001.i1.KNXSN
field type: B
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
description: KNX SN
field index: 1
field name: KNXSN
type: Datapoint Type Field
type: NamedIndividual
field size: 1

is assembled with
type: ObjectProperty
type: IrreflexiveProperty
range: Datapoint Type Field
domain: DatapointType
comment: At least one DPT field must be present for a datapoint type (DPT).

Position Vector
comment: Represents a (numerical, countable) position, such as %.
type: NamedIndividual
type: Quantity Kind

type.dpt.field.250.600.i8.Reserved
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
field size: 4
field index: 8
includes reserved bit: type.bit.reserved
field type: r

Value Temp D
has communication mode: S
datapoint type major number: 9
dpt bit size max: 16
label: Value Temp D
type: DatapointType
type: NamedIndividual
subject: 9.2
subject: Value Temp D
subject: 9.002
is assembled with: type.dpt.field.9.2.i0
comment: a point representing DPT 9.002: Value Temp D
datapoint type minor number: 2

Status Mode 3
has communication mode: S
dpt bit size max: 8
is assembled with: type.dpt.field.6.20.i2.d
is assembled with: type.dpt.field.6.20.i3.c
is assembled with: type.dpt.field.6.20.i0.f
is assembled with: type.dpt.field.6.20.i4.b
is assembled with: type.dpt.field.6.20.i1.e
is assembled with: type.dpt.field.6.20.i5.a
type: DatapointType
type: NamedIndividual
datapoint type major number: 6
subject: Status Mode 3
subject: 6.020
subject: 6.20
label: Status Mode 3
datapoint type minor number: 20
comment: a point representing DPT 6.020: Status Mode 3

Prioritised Mode Control
has communication mode: S
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.236.1.i1.p
is assembled with: type.dpt.field.236.1.i0.m
is assembled with: type.dpt.field.236.1.i2.d
subject: 236.001
subject: Prioritised Mode Control
subject: 236.1
description: a point representing DPT 236.001: Prioritised Mode Control
datapoint type minor number: 1
datapoint type major number: 236
dpt bit size max: 8
label: Prioritised Mode Control

Restriction
on data range: string
on property: manufacturer
qualified cardinality: 1

90,5 s = 15
value API: 90,5S
value KNX: 15
type: NamedIndividual

StatusBUC
has communication mode: LTE
type: DatapointType
type: NamedIndividual
subject: StatusBUC
subject: 207.100
label: StatusBUC
is assembled with: type.dpt.field.207.100.i0.PrelBurnerValid
is assembled with: type.dpt.field.207.100.i1.Fault
is assembled with: type.dpt.field.207.100.i5.PrelBurner
is assembled with: type.dpt.field.207.100.i2.StatusStage1
is assembled with: type.dpt.field.207.100.i4.Reserved
is assembled with: type.dpt.field.207.100.i3.StatusStage2
datapoint type major number: 207
datapoint type minor number: 100
comment: a point representing DPT 207.100: StatusBUC
dpt bit size max: 16

The visual effect of channel 14 is active = 1
value API: theVisualEffectOfChannel14IsActive
type: NamedIndividual
value KNX: 1

TempRoomSetpUserOffset
type: Class
subclass of: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subject: 398.57
subject: TempRoomSetpUserOffset
subject: 57
label: TempRoomSetpUserOffset
interface object type annotation: 398
property identifier annotation: 57

type.digit.u3
range min: 0
type: NamedIndividual
range max: 7

schedule sequence
description: schedule sequence
value KNX: 0
type: NamedIndividual
value API: seqInstrSchedule

type.dpt.field.207.101.i0.LockRequest
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 0
field name: LockRequest
includes DPT: Bool
comment: indicates if power reduction is necessary (validity of PwrReduction)

Restriction
has value: one
on property: has cardinality

type.dpt.field.253.600.i12.Reserved
field size: 4
field type: r
field name: Reserved
field index: 12
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved

Restriction
has value: many
on property: has cardinality

Dimmer
type: EquipmentType
type: NamedIndividual
comment: A dimmer is a device connected to a light fixture and used to lower the brightness of the light.

type.dpt.field.209.101.i5.TempRoomDem
field type: V
unit: DEG C
includes digit: type.digit.s16 neg13650 32767
field resolution: 0.02
field index: 5
type: Datapoint Type Field
type: NamedIndividual
description: requested room temperature setpoint
field size: 16
field name: TempRoomDem

type.dpt.field.6.1.i0
field resolution: 1.0
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
unit: PERCENT
includes digit: type.digit.s8

type.dpt.field.512.512.i1.uf.FE CNT
field index: 1
field type: U
description: number of usage forecast elements
type: Datapoint Type Field
type: NamedIndividual
field name: FE_CNT
field size: 8
includes digit: type.digit.u8 0 12

HVACModeAct
type: Class
subject: 152
subject: HVACModeAct
subject: 259.152
interface object type annotation: 259
label: HVACModeAct
subclass of: Restriction
  on property: has datapoint type
  has value: HVAC Mode Z
property identifier annotation: 152

configuration fault = 3
value KNX: 3
value API: configurationFault
type: NamedIndividual

type.dpt.field.pc.i1.CT
description: consequence type of the power constraint
field index: 1
field type: U
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual
field size: 4
field name: CT

type.dpt.field.245.600.i4.SD
field size: 2
field type: N
field index: 4
description: SD
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.startMethodGateway
includes KV pair: type.kvpair.startMethodUnknown
includes KV pair: type.kvpair.startMethodAuto
field name: SD

Value 1 U Count
type: NamedIndividual
type: Datapoint Type Field
field index: 0
includes digit: type.digit.u8
label: Value 1 U Count
field type: U
unit: NUM
comment: Represents values for counting from 0 to 255 counter pulses.
field resolution: 1.0
field size: 8

Garden
description: A garden is a planned space, usually outdoors, set aside for the cultivation, display, and enjoyment of plants and other forms of nature. Preferably used with an outside Location or Space.
type: LocationUsage
type: NamedIndividual

energy, 0,001 Wh = 0
type: NamedIndividual
value API: energy,0,001Wh
value KNX: 0

HVAC Mode Economy
comment: This state type expresses that the second-lowest level named 'Economy' is chosen for the HVAC mode. Usually, the 'Economy' level is associated with a room that is unoccupied for longer periods in time (e.g. during the night). In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
type: State Type
type: NamedIndividual

Value Surface Tension
has communication mode: S
dpt bit size max: 32
subject: 14.067
subject: 14.67
subject: Value Surface Tension
is assembled with: type.dpt.field.14.67.i0
type: NamedIndividual
type: DatapointType
description: DPT 14.067: Value of surface tension
datapoint type major number: 14
datapoint type minor number: 67

type.dpt.field.30.1010.i2.ActivationStateOfChannel3
field type: B
includes KV pair: The visual effect of channel 3 is inactive = 0
includes KV pair: The visual effect of channel 3 is active = 1
field index: 2
field size: 1
field name: ActivationStateOfChannel3
type: Datapoint Type Field
type: NamedIndividual
comment: Activation state of channel 3

type.dpt.field.27.1.i21.MaskBitIOO6
field size: 1
comment: Mask Bit Info On Off Output 6
field name: MaskBitIOO6
field index: 21
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B

Hardwired Inhibit is active = 1
type: NamedIndividual
value API: hardwiredInhibitIsActive
value KNX: 1

ComfortProlongEff
type: Class
label: ComfortProlongEff
property identifier annotation: 54
subject: ComfortProlongEff
subject: 54
subject: 397.54
interface object type annotation: 397

Restriction
on property: interface object type
has value: 398

RF FilterInfo
has communication mode: S
is assembled with: type.dpt.field.21.1001.i2.DoAandKNXSN
is assembled with: type.dpt.field.21.1001.i3.Reserved
is assembled with: type.dpt.field.21.1001.i1.KNXSN
is assembled with: type.dpt.field.21.1001.i0.DoA
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
label: RF FilterInfo
comment: a point representing DPT 21.1001: RF FilterInfo
subject: RF FilterInfo
subject: 21.1001
datapoint type minor number: 1001
datapoint type major number: 21

type.dpt.field.27.1.i16.MaskBitIOO1
type: NamedIndividual
type: Datapoint Type Field
field size: 1
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
comment: Mask Bit Info On Off Output 1
field type: B
field index: 16
field name: MaskBitIOO1

LoadTypeSet
has communication mode: S
is assembled with: type.dpt.field.20.609.i0
datapoint type minor number: 609
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
label: LoadTypeSet
comment: a point representing DPT 20.609: LoadTypeSet
datapoint type major number: 20
subject: 20.609
subject: LoadTypeSet

HVACModeUser
type: Class
subject: 398.53
subject: 53
subject: HVACModeUser
subclass of: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
property identifier annotation: 53
interface object type annotation: 398

type.dpt.field.245.600.i8.LTRD
includes KV pair: Failed, test executed in time = 3
includes KV pair: type.kvpair.testResultPassedInTime
includes KV pair: Test manually stopped = 5
includes KV pair: type.kvpair.testResultPassedExceeded
includes KV pair: type.kvpair.testResultUnknown
includes KV pair: Failed, max delay exceeded = 4
field name: LTRD
field index: 8
description: LTRD
field size: 4
field type: N
type: Datapoint Type Field
type: NamedIndividual

203.x
has communication mode: LTE
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.203.x.i0
subject: 203.x
subject: 203.major
datapoint type major number: 203
dpt bit size max: 24

Boiler
type: NamedIndividual
type: EquipmentType
description: A boiler is a closed vessel in which fluid (generally water) is heated. Equipment to generate hot water or steam for heating.

error = 1
value API: error
value KNX: 1
type: NamedIndividual

Restriction
on property: has cardinality
has value: one

volume flow, 0,01 l/h = 57
type: NamedIndividual
value API: volumeFlow,0,01Lh
value KNX: 57

Restriction
has value: 400
on property: interface object type

type.dpt.field.22.103.i3.FrostAlarm
includes KV pair: No alarm = 0
includes KV pair: type.kvpair.alarm
field type: B
field index: 3
comment: Frost Alarm
field name: FrostAlarm
type: Datapoint Type Field
type: NamedIndividual
field size: 1

HVACModeEffNext
type: Class
subject: 398.82
subject: 82
subject: HVACModeEffNext
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 398
property identifier annotation: 82

21.x
has communication mode: S
subject: 21.x
subject: 21.major
is assembled with: type.dpt.field.21.x.i0
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
label: 21.x
datapoint type major number: 21

emPowerConstraints
dpt bit size max: 1792
is assembled with: type.dpt.field.512.500.i1.pc.CE
is assembled with: type.dpt.field.512.500.i0.pc.CE CNT
datapoint type major number: 512
datapoint type minor number: 500
description: Power Constraints
type: DatapointType
type: NamedIndividual

The visual effect of channel 4 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel4IsInactive

type.dpt.field.250.600.i5.Reserved
field name: Reserved
field index: 5
field type: r
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 4

Value Electric Displacement
has communication mode: S
datapoint type minor number: 22
label: Value Electric Displacement
subject: 14.22
subject: 14.022
subject: Value Electric Displacement
is assembled with: type.dpt.field.14.22.i0
type: DatapointType
type: NamedIndividual
comment: DPT 14.022: Value of electric displacement
datapoint type major number: 14
dpt bit size max: 32

type.dpt.field.514.500.i0.flr.LV
type: Datapoint Type Field
type: NamedIndividual
field size: 8
field index: 0
description: lower value
field name: LV
includes digit: type.digit.f16
field type: U

SCLOMode
has communication mode: S
label: SCLOMode
description: a point representing DPT 20.001: SCLOMode
subject: 20.1
subject: 20.001
subject: SCLOMode
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.20.1.i0
datapoint type minor number: 1
dpt bit size max: 8
datapoint type major number: 20

LockSign
has communication mode: LTE
is assembled with: type.dpt.field.207.101.i0.LockRequest
is assembled with: type.dpt.field.207.101.i2.Reserved
is assembled with: type.dpt.field.207.101.i1.Type
is assembled with: type.dpt.field.207.101.i3.PwrReduction
subject: LockSign
subject: 207.101
datapoint type minor number: 101
label: LockSign
type: NamedIndividual
type: DatapointType
datapoint type major number: 207
dpt bit size max: 16
comment: a point representing DPT 207.101: LockSign

Value Reactance
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type major number: 14
description: DPT 14.059: Value of reactance
subject: 14.59
subject: Value Reactance
subject: 14.059
dpt bit size max: 32
is assembled with: type.dpt.field.14.59.i0
datapoint type minor number: 59
label: Value Reactance

HumRelSetpDehumEff
type: Class
subclass of: Class
subject: HumRelSetpDehumEff
subject: 52
subject: 103.52
interface object type annotation: 103
property identifier annotation: 52

Date
has communication mode: S
comment: a point representing DPT 11.001: Date
type: DatapointType
type: NamedIndividual
subject: Date
subject: 11.001
subject: 11.1
dpt bit size max: 24
label: Date
is assembled with: type.dpt.field.11.1.i2.Month
is assembled with: type.dpt.field.11.1.i5.Reserved
is assembled with: type.dpt.field.11.1.i0.Year
is assembled with: type.dpt.field.11.1.i4.Day
is assembled with: type.dpt.field.11.1.i1.Reserved
is assembled with: type.dpt.field.11.1.i3.Reserved
datapoint type major number: 11
datapoint type minor number: 1

Switch
label: Switch
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 0
includes DPT: switch
field name: switch

5 h = 23
value KNX: 23
type: NamedIndividual
value API: 5H

Logical Function
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: logical function AND = 1
includes KV pair: type.kvpair.1.21.i0.0
field type: B
field index: 0
field size: 1

23.x
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: 23.x
subject: 23.major
is assembled with: type.dpt.field.23.x.i0
dpt bit size max: 2
label: 23.x
datapoint type major number: 23

type.dpt.field.245.600.i1.LDTR
includes digit: type.digit.u16 0 510
unit: MIN
field index: 1
field size: 16
field type: U
field resolution: 1.0
field name: LDTR
type: Datapoint Type Field
type: NamedIndividual
comment: LDTR

Time Delay
has communication mode: S
subject: 20.013
subject: 20.13
subject: Time Delay
datapoint type major number: 20
label: Time Delay
comment: a point representing DPT 20.013: Time Delay
datapoint type minor number: 13
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.20.13.i0
dpt bit size max: 8

type.dpt.field.9.6.i0
type: Datapoint Type Field
type: NamedIndividual
unit: PA
field index: 0
includes digit: type.digit.f16 0 670433
field size: 16
field type: F
field resolution: 0.01

Brightness
has communication mode: S
comment: a point representing DPT 7.013: Brightness
label: Brightness
datapoint type minor number: 13
subject: 7.13
subject: 7.013
subject: Brightness
datapoint type major number: 7
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.7.13.i0
dpt bit size max: 16

type.dpt.field.8.3.i0
field type: V
field index: 0
includes digit: type.digit.s16
type: Datapoint Type Field
type: NamedIndividual
unit: MilliSEC
field resolution: 10.0
field size: 16

asynchronous = 0
value API: asynchronous
type: NamedIndividual
value KNX: 0

205.x
has communication mode: LTE
datapoint type major number: 205
type: DatapointType
type: NamedIndividual
dpt bit size max: 24
label: 205.x
is assembled with: type.dpt.field.205.x.i0
subject: 205.major
subject: 205.x

type.dpt.field.13.100.i0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
field resolution: 1.0
includes digit: type.digit.s32
unit: SEC

Blinds Stop Step
subclass of: Restriction
  on property: actsOnPhenomenonQualityKind
  has value: qk ph light illuminance room
subclass of: Restriction
  on property: has operation kind
  qualified cardinality: 1
subclass of: Function Point
type: Class

Dali
type: Protocol
type: NamedIndividual

Accepted
type: NamedIndividual
value KNX: 0
value API: Accepted

rest: nil
first: Restriction
  has value: one
  on property: has cardinality

type.dpt.field.525.500.i6.fv.Upper 95PPR
field index: 6
includes DPT: Power
description: The upper boundary of the range with 95 % certainty the power value is in it
field name: Upper_95PPR
field size: 16
type: Datapoint Type Field
type: NamedIndividual

HumDehumMode
type: Class
subclass of: Restriction
  has value: qk ph air relativehumidity room
  on property: hasQualityKind
interface object type annotation: 103
subject: 103.54
subject: HumDehumMode
subject: 54
property identifier annotation: 54

ActTargetPosHeatStageB
type: Class
subclass of: Restriction
  on property: has operation kind
  some values from: Class
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
label: ActTargetPosHeatStageB
subject: 103
subject: ActTargetPosHeatStageB
subject: 399.103
property identifier annotation: 103
interface object type annotation: 399

type.dpt.field.516.501.i1.drr.UV
field name: UV
field type: F
includes digit: type.digit.f16
field index: 1
description: upper value of the range
field size: 16
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.253.600.i2.MaskCS
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: type.kvpair.invalid
includes KV pair: valid = 1
field type: B
field index: 2
field name: MaskCS
field size: 1
comment: validity of the fields CS and Step Code Saturation.

type.dpt.field.8.7.i0
field index: 0
includes digit: type.digit.s16
unit: HR
field size: 16
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field type: V

The visual effect of channel 2 is inactive = 0
value API: theVisualEffectOfChannel2IsInactive
type: NamedIndividual
value KNX: 0

Restriction
on property: property identifier
has value: 67

Heat Stage B Actuator Valve Kick
subclass of: Restriction
  on property: has operation kind
  qualified cardinality: 1
subclass of: Function Point
type: Class

Heat = 1
value API: heat
type: NamedIndividual
value KNX: 1

The visual effect of channel 4 is active = 1
value API: theVisualEffectOfChannel4IsActive
value KNX: 1
type: NamedIndividual

UTF-8
has communication mode: S
is assembled with: type.dpt.field.28.1.i0
subject: UTF-8
subject: 28.1
subject: 28.001
dpt bit size max: 312
type: NamedIndividual
type: DatapointType
datapoint type major number: 28
datapoint type minor number: 1
description: a point representing DPT 28.001: UTF-8

type.dpt.field.245.600.i3.SP
description: SP
type: Datapoint Type Field
type: NamedIndividual
field size: 2
includes KV pair: type.kvpair.startMethodGateway
includes KV pair: type.kvpair.startMethodAuto
includes KV pair: type.kvpair.startMethodUnknown
field name: SP
field index: 3
field type: N

12 h = 24
type: NamedIndividual
value KNX: 24
value API: 12H

Position unchanged = 0
type: NamedIndividual
value KNX: 0
value API: positionUnchanged

type.dpt.field.22.1010.i13.ActivationStateOfChannel14
includes KV pair: The visual effect of channel 14 is inactive = 0
includes KV pair: The visual effect of channel 14 is active = 1
field name: ActivationStateOfChannel14
description: Activation state of channel 14
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 13
field type: B

Air Control
comment: A specific Application Function category that controls a quantity (e.g., temperature, pressure) of the phenomenon air. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: ApplicationFunction
type: Class

type.dpt.field.21.1010.i2.ActivationStateOfChannel3
includes KV pair: The visual effect of channel 3 is inactive = 0
includes KV pair: type.kvpair.21.1010.i2.1
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: ActivationStateOfChannel3
field type: B
description: Activation state of channel 3
field index: 2

type.dpt.field.13.15.i0
field type: V
type: NamedIndividual
type: Datapoint Type Field
field index: 0
unit: KiloV-A Reactive-HR
field resolution: 1.0
includes digit: type.digit.s32
field size: 32

Value AngleRad
has communication mode: S
description: DPT 14.006: Value of an angle (in radiant)
dpt bit size max: 32
is assembled with: type.dpt.field.14.6.i0
type: NamedIndividual
type: DatapointType
subject: 14.6
subject: 14.006
subject: Value AngleRad
datapoint type minor number: 6
datapoint type major number: 14

HVAC Air Quality Relative Value
has communication mode: LTE
is assembled with: type.dpt.field.205.103.i1.HVACAirQuality
is assembled with: type.dpt.field.205.103.i0.StatusCommand
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 205.103: HVACAirQualRel_Z
datapoint type major number: 205
subject: HVAC Air Quality Relative Value
subject: 205.103
dpt bit size max: 24
datapoint type minor number: 103
label: HVAC Air Quality Relative Value

type.dpt.field.209.100.i4.NoHeatAvailable
includes DPT: Bool
field index: 4
description: boiler sequence is temporary not producing heat
field name: NoHeatAvailable
type: Datapoint Type Field
type: NamedIndividual
field size: 1

ActuatorConnectType
has communication mode: S
label: ActuatorConnectType
is assembled with: type.dpt.field.20.20.i0
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
dpt bit size max: 8
description: a point representing DPT 20.020: ActuatorConnectType
datapoint type minor number: 20
subject: 20.020
subject: ActuatorConnectType
subject: 20.20

ActuatorErrorInfo
type: Class
subject: 55
subject: 418.55
subject: ActuatorErrorInfo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
property identifier annotation: 55
interface object type annotation: 418

unreliable synchronisation source (mains, local quartz) = 0
type: NamedIndividual
value KNX: 0
value API: unreliableSynchronisationSource(mai

Extract air, e.g. for VAV = 4
value KNX: 4
type: NamedIndividual
value API: extractAir,E.g.ForVAV

The visual effect of channel 15 is active = 1
type: NamedIndividual
value KNX: 1
value API: theVisualEffectOfChannel15IsActive

Colour RGB
has communication mode: S
is assembled with: type.dpt.field.232.600.i0.B
is assembled with: type.dpt.field.232.600.i1.G
is assembled with: type.dpt.field.232.600.i2.R
datapoint type major number: 232
type: NamedIndividual
type: DatapointType
dpt bit size max: 24
label: Colour RGB
subject: Colour RGB
subject: 232.600
datapoint type minor number: 600
description: a point representing DPT 232.600: Colour RGB

type.dpt.field.21.2.i2.VerifyMode
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
comment: Verify Mode is on
field index: 2
field name: VerifyMode
type: Datapoint Type Field
type: NamedIndividual
field size: 1

Restriction
on property: has operation kind
on class: Class
qualified cardinality: 1

Colour Set RGB
type: Class
subject: CS_RGB
subject: 423.52
subject: 52
subject: Colour Set RGB
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 52
interface object type annotation: 423

Value ElectromagneticMoment
has communication mode: S
datapoint type minor number: 29
is assembled with: type.dpt.field.14.29.i0
datapoint type major number: 14
dpt bit size max: 32
subject: 14.029
subject: 14.29
subject: Value ElectromagneticMoment
comment: DPT 14.029: Value of electromagnetic moment
type: NamedIndividual
type: DatapointType
label: Value ElectromagneticMoment

type.dpt.field.241.800.i3.DriveState
field name: DriveState
type: Datapoint Type Field
type: NamedIndividual
description: Indicated whether the target position is reached of the drive is moving
field type: B
field index: 3
includes KV pair: drive is moving = 0
includes KV pair: target position is reached = 1
field size: 1

type.dpt.field.22.1010.i7.ActivationStateOfChannel8
field name: ActivationStateOfChannel8
includes KV pair: The visual effect of channel 8 is active = 1
includes KV pair: type.kvpair.22.1010.i7.0
type: Datapoint Type Field
type: NamedIndividual
field index: 7
field type: B
field size: 1
description: Activation state of channel 8

type.dpt.field.524.500.i0.ti.AC
field index: 0
field type: B
field name: AC
description: defines whether this is an abnormal condition or not
includes KV pair: type.kvpair.NoAbnormalCondition
includes KV pair: abnormal condition
field size: 1
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.13.1200.i0
field resolution: 1.0
unit: http://qudt.org/vocab/unit/L
includes digit: type.digit.s32
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
field size: 32

Restriction
has value: 101
on property: interface object type

type.dpt.field.17.1.i1.Reserved
field type: r
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field name: Reserved
field size: 2
field index: 1

SMTP
type: Protocol
type: NamedIndividual

type.dpt.field.18.1.i0.SceneNumber
includes digit: type.digit.u6
unit: NUM
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
comment: Scene number
field size: 6
field index: 0
field name: SceneNumber

has part
domain: Equipment
inverse of: is part of
comment: To define the presence of a (tangible) equipment, such as a device as part of a cabinet (that is also an equipment).
type: AsymmetricProperty
type: IrreflexiveProperty
type: InverseFunctionalProperty
type: ObjectProperty
range: Equipment

Restriction
qualified cardinality: 1
on property: has operation kind

relates to state type
comment: This OP relationship allows to refine the applicative semantics of a datapoint, classified with a state type.
range: State Type
domain: Operation Kind
type: ObjectProperty

is phenomenon type of
type: ObjectProperty
range: QualityKind
sub property of: isTagOf
domain: Phenomenon

Cool Stage A Actuator Valve Kick
subclass of: Restriction
  qualified cardinality: 1
  on property: has operation kind
subclass of: Function Point
type: Class

Location
subclass of: Thing
comment: A location is a physical named geographical place that is used to identify a point, an area or room, inside or outside of a building. This generic location root node simplifies the replacement of the entire location model.
type: Class

L-PER-HR
symbol: L/hr
type: NamedIndividual
type: Unit

Restriction
on property: interface object type
has value: 104

Colour xyY
has communication mode: S
datapoint type major number: 242
is assembled with: type.dpt.field.242.600.i4.yaxis
is assembled with: type.dpt.field.242.600.i2.Reserved
is assembled with: type.dpt.field.242.600.i5.xaxis
is assembled with: type.dpt.field.242.600.i3.Brightness
is assembled with: type.dpt.field.242.600.i0.B
is assembled with: type.dpt.field.242.600.i1.C
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 242.600: Colour xyY
dpt bit size max: 48
datapoint type minor number: 600
subject: 242.600
subject: Colour xyY

TempRoomSetpAct
type: Class
label: TempRoomSetpAct
interface object type annotation: 167
subject: 53
subject: 167.53
subject: TempRoomSetpAct
property identifier annotation: 53

Energy Direction
includes KV pair: Negative = 1
includes KV pair: type.kvpair.1.1201.i0.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1
field type: B

TempRoomSetpLoadShedShift
type: Class
subject: TempRoomSetpLoadShedShift
subject: 52
subject: 121.52
property identifier annotation: 52
interface object type annotation: 121

Floor
disjoint with: Outside
type: Class
subclass of: Location
subclass of: Restriction
  all values from: Floor
  on property: has lower floor
subclass of: Restriction
  all values from: Room
  on property: hasRoom
subclass of: Restriction
  on property: hasSpace
  all values from: Space
label: Etage @de
comment: A floor is a level or plane concept in a building, it is separating a building into horizontal spaces. A floor can have spaces assigned, in particular a room. The concept can be mapped to a IfcBuildingStorey.

learn the scene corresponding to the field Scene Number = 1
value API: learnTheSceneCorrespondingToTheFiel
value KNX: 1
type: NamedIndividual

type.dpt.field.14.x.i0
comment: 4-byte float value
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 32
field type: F
includes digit: type.digit.f32

SwitchOnOffForced
type: Class
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: Switch Control
  on property: has datapoint type
property identifier annotation: 61
subject: 61
subject: SwitchOnOffForced
subject: 418.61
interface object type annotation: 418

TempRoomSetpSetHeatEff
type: Class
subclass of: Restriction
  on property: has operation kind
subject: 89
subject: 398.89
subject: TempRoomSetpSetHeatEff
interface object type annotation: 398
property identifier annotation: 89

Restriction
on property: interface object type
has value: 423

type.dpt.field.213.100.i1.TempSetpEco
field name: TempSetpEco
field size: 16
comment: room temperature setpoint economy
type: Datapoint Type Field
type: NamedIndividual
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C
field resolution: 0.02
field index: 1

Air Quality Control
comment: Application functions that controls the quantity 'air quality'.
subclass of: Air Control
type: Class

identifier
comment: Used to represents an URN.
type: AnnotationProperty

up = 0
type: NamedIndividual
value API: up
value KNX: 0

Normal (no fault) = 0
type: NamedIndividual
value KNX: 0
value API: normal(noFault)

Fan only = 9
type: NamedIndividual
value KNX: 9
value API: fanOnly

HVACModeEff
type: Class
subject: 51
subject: 100.51
subject: HVACModeEff
interface object type annotation: 100
property identifier annotation: 51

type.dpt.field.201.105.i0.StatusCommand
field name: StatusCommand
field size: 8
comment: standard Status/Command
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0
field type: Z8

type.dpt.field.253.600.i11.cS
type: Datapoint Type Field
type: NamedIndividual
field index: 11
field size: 1
includes KV pair: type.kvpair.increase
includes KV pair: Decrease = 0
field name: cS
comment: Shall specify whether the saturation of the colour shall be increased or decreased.
field type: B

Breaker/Valve is closed = 0
type: NamedIndividual
value KNX: 0
value API: breakerValveIsClosed

System Clock
type: Class
subclass of: Restriction
  qualified cardinality: 1
  on class: CurrentDateAndTime
  on property: has function point
subclass of: Restriction
  on property: has function point
  qualified cardinality: 1
  on class: CurrentDate
subclass of: timeSynchronization
subject: SCLO
comment: Application function to provide a 'system clock' for the system.

type.dpt.field.16.0.i0.stringascii
field index: 0
unit: UNITLESS
includes DPT: Char ASCII
field string schema: us-ascii
field size: 112
field name: stringascii
type: Datapoint Type Field
type: NamedIndividual
field type: A

Diameter
type: NamedIndividual
type: Quantity Kind
comment: In classical geometry, the "Diameter" of a circle is any straight line segment that passes through the center of the circle and whose endpoints lie on the circle.

UserChangeOverMode
type: Class
subject: 51
subject: 392.51
subject: UserChangeOverMode
property identifier annotation: 51
interface object type annotation: 392

type.dpt.field.212.100.i2.TempSetpShiftComf
field type: V
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
comment: room temperature setpoint shift comfort (delta value)
unit: http://qudt.org/vocab/unit/K
includes digit: type.digit.s16
field name: TempSetpShiftComf
field index: 2
field size: 16

CombinedStatus_HVA
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 400
comment: This DPA represents a combined status of a Heating Valve Actuator. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring (mostly) to the device, which are modeled by the respective tag:operationalStateXYZ tags, if not otherwise stated: Bit 0) Current Valve Position (referring to the property PositionVector, modeled by the state types tag:opened and tag:closed); Bit 1) Short Circuit; Bit 2) Overload; Bit 3) Valve kick (very specific for valves, abstractly modeled by the state type tag:operationalStateMaintenance); Bit 4) Service Mode (modeled by the state type tag:operationalStateMaintenance as well); Bit 5) Manual operation (overridden) - in this case the Overridden status information refers to the actual manual operation (similar to DPA 400.71 the overridden state refers to the actual position of the valve (and thus to the specific property Position Vector), which is why the QualityKind is used at this point; Bit 6) Forced Position (modeled by tag:forced); Bit 7) Locked Position (modeled by tag:locked); and Bit 8) Calibration Mode.
subject: CombinedStatus_HVA
subject: 74
subject: 400.74
property identifier annotation: 74

type.dpt.field.9.1.i0
unit: DEG C
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes digit: type.digit.f16 neg27300 670433
field size: 16
field type: F

TempRoom
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: Value Temp
subject: TempRoom
subject: 51
subject: 321.51
property identifier annotation: 51
interface object type annotation: 321

ActuatorStatus
type: Class
property identifier annotation: 53
interface object type annotation: 417
subject: 53
subject: ActuatorStatus
subject: 417.53

SceneConfig
has communication mode: S
description: a point representing DPT 238.001: SceneConfig
datapoint type minor number: 1
subject: 238.001
subject: SceneConfig
subject: 238.1
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
label: SceneConfig
is assembled with: type.dpt.field.238.1.i1.SceneActivation
is assembled with: type.dpt.field.238.1.i0.SceneNumber
is assembled with: type.dpt.field.238.1.i2.StorageFunction
datapoint type major number: 238

User Presence Switch
type: Class
interface object type annotation: 391
subject: UPS
subject: User Presence Switch
subject: 391

Condensate
type: NamedIndividual
type: Phenomenon
description: Liquid phase produced by the condensation of steam or other gas

Outside
description: The relation is meant to be outside a building (outdoor is the same).
type: Locality
type: NamedIndividual

DamperMode
has communication mode: S
label: DamperMode
comment: a point representing DPT 20.109: DamperMode
is assembled with: type.dpt.field.20.109.i0
type: NamedIndividual
type: DatapointType
datapoint type minor number: 109
subject: DamperMode
subject: 20.109
dpt bit size max: 8
datapoint type major number: 20

is tag set of
domain: TagSet
type: ObjectProperty

type.dpt.field.14.22.i0
unit: C-PER-M2
field size: 32
comment: electric displacement
field type: F
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0

TempRoomSetpUserAbsEff
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: HVAC absolute Temperature
property identifier annotation: 59
subject: 100.59
subject: 59
subject: TempRoomSetpUserAbsEff
label: TempRoomSetpUserAbsEff
interface object type annotation: 100

Room Relative Humidity Sensor
is incomplete: true
type: Class
subclass of: Class
label: Room Relative Humidity Sensor
subject: RRHS
subject: 337
subject: Room Relative Humidity Sensor
interface object type annotation: 337

rest:
  first: Restriction
    has value: 423
    on property: interface object type
  rest: nil

Restriction
has value: many
on property: has cardinality

Kitchen
type: LocationUsage
type: NamedIndividual
description: A kitchen is a room or part of a room used for cooking and food preparation in a dwelling or in a commercial establishment. Preferably used with an Room.

type.dpt.field.512.508.i1.fltp.CQ
includes KV pair: type.kvpair.cqNaturalGasFlowRate
includes KV pair: type.kvpair.cqElectricPowerL2
includes KV pair: type.kvpair.cqHeatThermalPower
includes KV pair: type.kvpair.cqHeatFlowRate
includes KV pair: type.kvpair.cqElectricPowerL1
includes KV pair: type.kvpair.cqOilFlowRate
includes KV pair: type.kvpair.cqHydrogenFlowRate
includes KV pair: Electric Power L3
field size: 8
type: Datapoint Type Field
type: NamedIndividual
field name: CQ
description: commodity quantity
field index: 1
field type: U

type.dpt.field.249.600.i1.validityOfAbsoluteColourTemperature
field index: 1
field name: validityOfAbsoluteColourTemperature
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
type: Datapoint Type Field
type: NamedIndividual
comment: validity of the Absolute Colour Temperature
field size: 1
field type: B

FT in progress = 7
value API: fTInProgress
value KNX: 7
type: NamedIndividual

Device
type: NamedIndividual
type: EquipmentType
description: A Device can be any electronic equipment with some computing ability that has a firmware or supports the installation of software. Examples are pumps, dampers, valves, sensors, detectors, limit switches, remote/local switches or automation devices.

TempRoomSetpCoolEff
type: Class
interface object type annotation: 399
property identifier annotation: 53
subject: 53
subject: TempRoomSetpCoolEff
subject: 399.53

first: LTE

mac version
comment: Used to represent the current version of the content for the MaC.
range: positiveInteger
type: AnnotationProperty

type.dpt.field.203.100.i1.HVACAirQual
field name: HVACAirQual
field resolution: 1.0
unit: PPM
type: Datapoint Type Field
type: NamedIndividual
field index: 1
includes digit: type.digit.u16
field size: 16
field type: U

A-PER-M2
type: NamedIndividual
type: Unit
symbol: A/m²

Monday = 1
value KNX: 1
type: NamedIndividual
value API: monday

Off = 6
type: NamedIndividual
value KNX: 6
value API: off

PowerDensity
has communication mode: S
datapoint type minor number: 22
datapoint type major number: 9
dpt bit size max: 16
is assembled with: type.dpt.field.9.22.i0
type: DatapointType
type: NamedIndividual
subject: 9.022
subject: 9.22
subject: PowerDensity
comment: a point representing DPT 9.022: PowerDensity
label: PowerDensity

type.dpt.field.21.1001.i0.DoA
field name: DoA
description: DoA
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 0

type.dpt.field.519.500.i5.tran.AC
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field type: B
description: abnormal condition
field index: 5
includes KV pair: abnormal condition
includes KV pair: type.kvpair.NoAbnormalCondition
field name: AC

type.dpt.field.19.1.i5.NDOW
field index: 5
field type: B
comment: No Day of Week
includes KV pair: Day of week field valid = 0
includes KV pair: type.kvpair.19.1.i5.1
field name: NDOW
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field default: 1

Building
subclass of: Restriction
  all values from: Room
  on property: hasRoom
subclass of: Location
subclass of: Restriction
  all values from: Space
  on property: hasSpace
label: Gebäude @de
type: Class
comment: A building represents a whole building that hosts several other elements such as stacked floors or spaces or rooms. The concept can be mapped to a IfcBuilding.
disjoint with: Outside

Automatic
type: NamedIndividual
type: Origin
description: Refers to information that originates from algorithms, i.e. usually computed by a controller device.

type.dpt.field.222.101.i1.TempSetpShiftStdby
field name: TempSetpShiftStdby
field type: F
field index: 1
includes digit: type.digit.f16
field size: 16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
description: TempSetpShiftStdby
unit: http://qudt.org/vocab/unit/K

type.dpt.field.205.100.i0.StatusCommand
comment: standard Status/Command
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0
field type: Z8
field name: StatusCommand
field size: 8

type.dpt.field.20.116.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes KV pair: type.kvpair.20.116.i0.3
includes KV pair: enable stage B = 2
includes KV pair: type.kvpair.20.116.i0.0
includes KV pair: enable stage A = 1
comment: EnableH/CStage
field type: N
field size: 8

The visual effect of channel 3 is active = 1
type: NamedIndividual
value KNX: 1
value API: theVisualEffectOfChannel3IsActive

type.dpt.field.14.76.i0
unit: M3
field index: 0
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
description: volume
field type: F
includes digit: type.digit.f32

Cooling
description: A cooling system keeps air cool and dry within a home, office, or other buildings. Refrigration is the cooling of a space or substance below the environmental temperature.
type: NamedIndividual
type: Trade

type.dpt.field.14.19.i0
includes digit: type.digit.f32
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
comment: electric current
field index: 0
unit: http://qudt.org/vocab/unit/A
field type: F

LockDevice
type: Class
property identifier annotation: 69
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  on property: has operation kind
subject: 69
subject: 417.69
subject: LD
subject: LockDevice
interface object type annotation: 417

J-PER-K
symbol: J/K
type: NamedIndividual
type: Unit

DeltaTimeMin
has communication mode: S
is assembled with: type.dpt.field.8.6.i0
subject: 8.006
subject: DeltaTimeMin
subject: 8.6
type: NamedIndividual
type: DatapointType
datapoint type major number: 8
dpt bit size max: 16
description: a point representing DPT 8.006: DeltaTimeMin
datapoint type minor number: 6

Switch Control
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type major number: 2
label: Switch Control
subject: Switch Control
subject: 2.001
subject: 2.1
is assembled with: Switch
is assembled with: c
dpt bit size max: 2
comment: a point representing DPT 2.001: Switch Control
datapoint type minor number: 1

8.x
has communication mode: S
subject: 8.major
subject: 8.x
datapoint type major number: 8
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
label: 8.x
is assembled with: type.dpt.field.8.x.i0

Value Stress
has communication mode: S
datapoint type minor number: 66
label: Value Stress
subject: Value Stress
subject: 14.066
subject: 14.66
type: DatapointType
type: NamedIndividual
comment: DPT 14.066: Value of stress
is assembled with: type.dpt.field.14.66.i0
datapoint type major number: 14
dpt bit size max: 32

Cool Stage B Actuator Valve Kick
subclass of: Function Point
type: Class

http://qudt.org/vocab/unit/S
type: Unit
type: NamedIndividual
symbol: S

Time = UT+X+1 = 1
value KNX: 1
value API: time=UT+X+1
type: NamedIndividual

select sequence
type: NamedIndividual
value KNX: 3
description: select sequence
value API: seqInstrSeqSel

Value Charge DensitySurface
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 14.12
subject: Value Charge DensitySurface
subject: 14.012
datapoint type major number: 14
comment: DPT 14.012: Value of surface charge density
dpt bit size max: 32
is assembled with: type.dpt.field.14.12.i0
datapoint type minor number: 12

Restriction
has value: TempRoomSetpAct
on property: pointName

SceneNumber
type: Class
subject: 72
subject: SceneNumber
subject: 417.72
subject: SN
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 72
interface object type annotation: 417

emTransitionInstruction
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.524.500.i1.ti.Reserved
is assembled with: type.dpt.field.524.500.i4.ti.ID
is assembled with: type.dpt.field.524.500.i2.ti.OMF
is assembled with: type.dpt.field.524.500.i0.ti.AC
is assembled with: type.dpt.field.524.500.i3.ti.ET
datapoint type minor number: 500
description: Instruction to force the state machine switching from one operation mode to another or just set a new new value of the operation mode factor
dpt bit size max: 104
datapoint type major number: 524

strong breeze = 6
value API: strongBreeze
type: NamedIndividual
value KNX: 6

type.dpt.field.27.1.i1.IOO2
field index: 1
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: output state is On = 1
includes KV pair: output state is Off = 0
field name: IOO2
field type: B
description: Info On Off Output 2

power, 0,1 MW = 168
value API: power,0,1MW
type: NamedIndividual
value KNX: 168

no fault = 0
type: NamedIndividual
value KNX: 0
value API: noFault

not forced = 0
value API: notForced
type: NamedIndividual
value KNX: 0

Building Protection = 4
value API: buildingProtection
value KNX: 4
type: NamedIndividual
is applicable datapoint enum of: HVAC Mode Protection

History values
type: NamedIndividual
type: Point Function
comment: A Point representing history/ trend data with a log of timestamp/value pairs. Only this tag value is allowed to be used together with other tags from this category, such as to define a Datapoint expressing a history log of process values.

type.dpt.field.29.10.i0
field size: 64
field resolution: 1.0
includes digit: type.digit.s64
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
unit: W-HR

Restriction
has value: ValveKick
on property: pointName

Living Room
type: LocationUsage
type: NamedIndividual
description: In Western architecture, a living room, also called a lounge room (Australian English), lounge (British English), sitting room (British English), or drawing room, is a room for relaxing and socializing in a residential house or apartment. Preferably used with an Room.

filtering by KNX Serial Number table = 2
value API: filteringByKNXSerialNumberTable
value KNX: 2
type: NamedIndividual

MBus
type: Protocol
type: NamedIndividual

Restriction
on property: pointName
has value: WindowSwitch

HVAC Air Flow Relative Value
has communication mode: LTE
type: NamedIndividual
type: DatapointType
subject: HVAC Air Flow Relative Value
subject: 205.102
comment: a point representing DPT 205.102: HVACAirFlowRel_Z
datapoint type major number: 205
datapoint type minor number: 102
dpt bit size max: 24
is assembled with: type.dpt.field.205.102.i1.HVACAirFlow
is assembled with: type.dpt.field.205.102.i0.StatusCommand

type.dpt.field.207.104.i0.PrelBurnerValid
includes DPT: Bool
description: Validity of ActPosDem. ‘false’ means also ‘no demand’
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field name: PrelBurnerValid
field index: 0

Height
description: "Height" is the measurement of vertical distance, but has two meanings in common use. It can either indicate how "tall" something is, or how "high up" it is.
type: NamedIndividual
type: Quantity Kind

type.dpt.field.212.101.i0.TempSetpEco
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.s16 neg13650 32767
field resolution: 0.02
field type: V
field index: 0
comment: room temperature setpoint economy
field name: TempSetpEco
unit: DEG C
field size: 16

User Shutter Control
subclass of: Restriction
  qualified cardinality: 1
  on property: has function point
  on class: ShutterMoveUpDown
subclass of: Shading Control
subject: SSSB
subject: SAB
comment: Application function for 'shutter control'.
type: Class

is protocol operated by
domain: Protocol
type: ObjectProperty
inverse of: operates on protocol
sub property of: isTagOf

Value Power Factor
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.14.57.i0
datapoint type minor number: 57
label: Value Power Factor
subject: Value Power Factor
subject: 14.57
subject: 14.057
datapoint type major number: 14
comment: DPT 14.057: Value of power factor
dpt bit size max: 32

CombinedStatus_RTC
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: Combined Status RTC
  on property: has datapoint type
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air dewpointtemperature room
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  some values from: Class
  on property: has operation kind
subject: 65
subject: CombinedStatus_RTC
subject: 397.65
label: CombinedStatus_RTC
interface object type annotation: 397
property identifier annotation: 65

Electric Power 3 Phase Symmetric
type: NamedIndividual
value API: ElectricPower3PhaseSymmetric
value KNX: 4

Site
comment: A functional subdivison of a location, consisting of one or several usually adjoining buildings.
type: Locality
type: NamedIndividual

type.dpt.field.14.60.i0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0
unit: OHM
field type: F
includes digit: type.digit.f32
comment: resistance
field resolution: 1.0

Invert
includes KV pair: Inverted = 1
includes KV pair: type.kvpair.1.12.i0.0
label: Invert
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1
field type: B

type.dpt.field.27.1.i28.MaskBitIOO13
type: Datapoint Type Field
type: NamedIndividual
comment: Mask Bit Info On Off Output 13
field size: 1
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field name: MaskBitIOO13
field type: B
field index: 28

type.dpt.field.521.500.i0.ts.FTS
field index: 0
includes DPT: DateTime
description: time when timer will be finished
field size: 64
type: Datapoint Type Field
type: NamedIndividual
field name: FTS

Restriction
max qualified cardinality: 1
on property: unit
on class: Unit

Temporal
comment: Indicator for time related type of interests, more granular defined with a quantity kind
type: NamedIndividual
type: Phenomenon

Emergency mode active = 5
value KNX: 5
value API: emergencyModeActive
type: NamedIndividual

type.dpt.field.30.1010.i12.ActivationStateOfChannel13
field type: B
description: Activation state of channel 13
type: Datapoint Type Field
type: NamedIndividual
field index: 12
includes KV pair: The visual effect of channel 13 is active = 1
includes KV pair: The visual effect of channel 13 is inactive = 0
field size: 1
field name: ActivationStateOfChannel13

type.dpt.field.9.22.i0
unit: W-PER-M2
field type: F
includes digit: type.digit.f16
field size: 16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
field index: 0

Cloud Cover
has communication mode: S
comment: a point representing DPT 20.021: Cloud Cover
subject: Cloud Cover
subject: 20.21
subject: 20.021
type: NamedIndividual
type: DatapointType
label: Cloud Cover
dpt bit size max: 8
datapoint type minor number: 21
is assembled with: type.dpt.field.20.21.i0
datapoint type major number: 20

type.dpt.field.9.11.i0
includes digit: type.digit.f16
field size: 16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
unit: MilliSEC
field index: 0
field type: F

type.dpt.field.6.x.i0
includes digit: type.digit.s8
field size: 8
field type: V
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: 8-bit signed value

type.dpt.field.15.x.i0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field string schema: raw
description: entrance access

scene A = 0
value API: sceneA
type: NamedIndividual
value KNX: 0

Refrigerator
type: NamedIndividual
type: EquipmentType
comment: A washing machine (laundry machine, clothes washer, washer, or simply wash) is a home appliance (EN 50523) used to wash laundry.

Restriction
has value: StatusGO
on property: pointName

SwitchCool
type: Class
subject: SwitchCool
subject: 399.60
subject: 60
label: SwitchCool
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  on property: has datapoint type
  has value: enable
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 60
    on property: property identifier
property identifier annotation: 60
interface object type annotation: 399

ApplicationArea
has communication mode: S
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 20.006: ApplicationArea
datapoint type major number: 20
datapoint type minor number: 6
is assembled with: type.dpt.field.20.6.i0
subject: 20.6
subject: ApplicationArea
subject: 20.006
dpt bit size max: 8

Hallway
type: LocationUsage
type: NamedIndividual
comment: A hallway or corridor is an interior space in a building that is used to connect other rooms. Preferably used with an Room.

Input Source
field size: 1
includes KV pair: Calculated = 1
includes KV pair: Fixed = 0
type: Datapoint Type Field
type: NamedIndividual
label: Input Source
field index: 0
field type: B

type.dpt.field.13.10.i0
field resolution: 1.0
field size: 32
includes digit: type.digit.s32
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
unit: W-HR

Active Energy
has communication mode: S
label: Active Energy
datapoint type major number: 13
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.13.10.i0
comment: a point representing DPT 13.010: ActiveEnergy
datapoint type minor number: 10
subject: Active Energy
subject: 13.10
subject: 13.010
dpt bit size max: 32

type.dpt.field.202.1.i1.RelValue
type: NamedIndividual
type: Datapoint Type Field
comment: Unsigned relative value
field name: RelValue
includes DPT: Percent U8
field index: 1
field size: 8

TempRoomSetpAct
type: Class
subclass of: Restriction
  on property: has datapoint type
  has value: HVAC absolute Temperature
label: TempRoomSetpAct
interface object type annotation: 260
subject: 260.153
subject: 153
subject: TempRoomSetpAct
property identifier annotation: 153

no peak event = 0
value API: noPeakEvent
type: NamedIndividual
value KNX: 0

Electricity
description: Associated with electricity or with electrical force, power, or energy.
type: NamedIndividual
type: Phenomenon

type.dpt.field.205.103.i1.HVACAirQuality
type: NamedIndividual
type: Datapoint Type Field
field type: V
comment: Relative air quality value
field size: 16
includes digit: type.digit.s16
field index: 1
field resolution: 1.0
unit: PPM
field name: HVACAirQuality

218.x
has communication mode: LTE
type: DatapointType
type: NamedIndividual
dpt bit size max: 40
subject: 218.x
subject: 218.major
is assembled with: type.dpt.field.218.x.i0
datapoint type major number: 218

TempRoomSetpSetHeatEff
type: Class
interface object type annotation: 100
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 53
subject: TempRoomSetpSetHeatEff
subject: 53
subject: 100.53

type.dpt.field.24.1.i0
field string schema: iso-8859-1
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
unit: UNITLESS
field size: 312
includes DPT: char88591
field index: 0

type.dpt.field.11.1.i5.Reserved
field type: r
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field name: Reserved
field index: 5
field size: 3

Nursery
comment: A nursery is usually, in American connotations, a bedroom within a house or other dwelling set aside for an infant or toddler. Preferably used with an Room.
type: LocationUsage
type: NamedIndividual

Building protected = 2
type: NamedIndividual
value API: buildingProtected
value KNX: 2

type.dpt.field.14.31.i0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
unit: http://qudt.org/vocab/unit/J
field index: 0
field type: F
comment: energy
includes digit: type.digit.f32
field resolution: 1.0

Failed, max delay exceeded = 4
value API: failed,MaxDelayExceeded
value KNX: 4
type: NamedIndividual

Concentration, VOC
comment: Refers to the concentration of volatile organic compounds (TVOC) in the air, measured in ppm. This is a specialization of quantitykind:Concentration.
type: Quantity Kind
type: NamedIndividual

type.dpt.field.252.600.i1.MaskCB
field index: 1
field size: 1
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
field name: MaskCB
comment: validity of the fields CB and Step Code Colour Blue.
field type: B

type.dpt.field.203.101.i1.WindSpeed
field size: 16
description: wind speed absolute value m/s
field index: 1
field type: U
field name: WindSpeed
field resolution: 0.01
unit: M-PER-SEC
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u16 0 20000

Converter Test Control
has communication mode: S
label: Converter Test Control
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.20.611.i0
datapoint type major number: 20
subject: 20.611
subject: Converter Test Control
datapoint type minor number: 611
description: a point representing DPT 20.611: Converter Test Control
dpt bit size max: 8

type.dpt.field.19.1.i20.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 20
includes reserved bit: type.bit.reserved
field size: 4
field type: r
field name: Reserved

Restriction
on property: has cardinality
has value: many

Restriction
on property: has cardinality
has value: one

type.dpt.field.201.109.i1.HVACEmergMode
type: Datapoint Type Field
type: NamedIndividual
field index: 1
includes DPT: HVACEmergMode
field name: HVACEmergMode
field size: 8

type.dpt.field.512.500.i1.pc.CE
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
description: Power Constraint Element
includes DPT field: type.dpt.field.pc.i0
field index: 1
includes counter: type.dpt.field.512.500.i0.pc.CE CNT

Restriction
on property: has cardinality
has value: many

Panel
type: EquipmentType
type: NamedIndividual
comment: Enclosure for electrical and control equipment.

type.dpt.field.uf.i1.DUR
field index: 1
description: duration
field name: DUR
type: Datapoint Type Field
type: NamedIndividual
includes DPT: TimePeriodSec
field size: 16

Percent U8
unit: PERCENT
field type: U
field size: 8
type: Datapoint Type Field
type: NamedIndividual
description: Represents a percentage value with 1% resolution for 0 to 255%.
field index: 0
field resolution: 1.0
includes digit: type.digit.u8

ADAType
has communication mode: S
datapoint type minor number: 120
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 20.120: ADAType
dpt bit size max: 8
subject: ADAType
subject: 20.120
datapoint type major number: 20
is assembled with: type.dpt.field.20.120.i0

VAV = 2
value API: vAV
value KNX: 2
type: NamedIndividual

Combined Status HVA
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.22.102.i3.ValveKick
is assembled with: type.dpt.field.22.102.i8.CalibrationMode
is assembled with: type.dpt.field.22.102.i0.CurrentValvePosition
is assembled with: type.dpt.field.22.102.i5.ManualOperation
is assembled with: type.dpt.field.22.102.i4.ServiceMode
is assembled with: type.dpt.field.22.102.i7.LockedPosition
is assembled with: type.dpt.field.22.102.i2.Overload
is assembled with: type.dpt.field.22.102.i6.ForcedPosition
is assembled with: type.dpt.field.22.102.i9.Reserved
is assembled with: type.dpt.field.22.102.i1.ShortCircuit
subject: 22.102
subject: Combined Status HVA
label: Combined Status HVA
datapoint type major number: 22
datapoint type minor number: 102
dpt bit size max: 16
comment: a point representing DPT 22.102: Combined Status HVA

enabled (PSU/DPSU fixed on) = 1
value KNX: 1
type: NamedIndividual
value API: enabled(PSUDPSUFixedOn)

Start
field index: 0
includes KV pair: Start = 1
includes KV pair: type.kvpair.1.10.i0.0
label: Start
field type: B
field size: 1
type: Datapoint Type Field
type: NamedIndividual

SwitchOnOff
type: Class
label: SwitchOnOff
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subject: SwitchOnOff
subject: 420.61
subject: 61
interface object type annotation: 420
property identifier annotation: 61

Very cloudy = 6
value API: veryCloudy
type: NamedIndividual
value KNX: 6

Operational State Alarm Pending
type: NamedIndividual
type: State Type
description: This state type expresses that the alarm status of a datapoint is not yet acknowledged by an operator. No assumption about the validity of the datapoint’s value can be made.

Atrium
type: NamedIndividual
type: LocationUsage
description: An atrium is a large open-air or skylight-covered space surrounded by a building.

BinarySceneRecall
type: Class
subject: BinarySceneRecall
subject: SABA
subject: 403.62
subject: 62
property identifier annotation: 62
subclass of: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
interface object type annotation: 403
label: BinarySceneRecall

type.dpt.field.523.500.i4.sms.PID
field size: 4
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual
field name: PID
description: identifier of previous operation mode that was active before the state machine switched to the current one. CT=0 no previous operation mode declared
field index: 4
field type: U

Info On Off
type: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq luminaire dimmlevel
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  on property: has operation kind
  some values from: Class
    intersection of: Operation Kind
property identifier annotation: 53
interface object type annotation: 421
subject: IOO
subject: Info On Off
subject: 421.53
subject: 53

Other Commercial
comment: Preferably used with a Building.
type: LocationUsage
type: NamedIndividual

Value Electric Potential
has communication mode: S
subject: 14.027
subject: Value Electric Potential
subject: 14.27
description: DPT 14.027: Value of electric potential
datapoint type minor number: 27
dpt bit size max: 32
is assembled with: type.dpt.field.14.27.i0
type: NamedIndividual
type: DatapointType
datapoint type major number: 14

Gas device = 3
value KNX: 3
type: NamedIndividual
value API: gasDevice

type.dpt.field.21.1000.i1.BiBatMaster
type: Datapoint Type Field
type: NamedIndividual
comment: BiBat Master
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field name: BiBatMaster
field index: 1
field size: 1

EnableHCStage Z
has communication mode: LTE
description: a point representing DPT 201.105: EnableHCStage Z
is assembled with: type.dpt.field.201.105.i0.StatusCommand
is assembled with: type.dpt.field.201.105.i1.EnableHCStage
dpt bit size max: 16
subject: EnableHCStage Z
subject: 201.105
datapoint type minor number: 105
type: DatapointType
type: NamedIndividual
datapoint type major number: 201
label: EnableHCStage Z

type.dpt.field.8.12.i0
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
unit: http://qudt.org/vocab/unit/M
includes digit: type.digit.s16
field size: 16
field resolution: 1.0

Location
label: Ort @de
subclass of: Restriction
  on property: has adjacent location
  all values from: Location
subclass of: Restriction
  on property: hasAddress
  all values from: External Address
subclass of: Restriction
  all values from: string
  on property: comment
subclass of: Location
subclass of: Restriction
  all values from: Outside
  on property: has outside
type: Class
comment: To represent a location, used to express a spatial location structure. The defined location model class/subclass structure does not reflect the hierarchy of a real world spatial building, such as a site/building with floors, rooms and/or spaces.

Priority
has communication mode: S
datapoint type minor number: 4
is assembled with: type.dpt.field.20.4.i0
label: Priority
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
subject: 20.4
subject: 20.004
subject: Priority
datapoint type major number: 20
description: a point representing DPT 20.004: Priority

ComfortPushbutton
type: Class
interface object type annotation: 384
subject: ComfortPushbutton
subject: 384.54
subject: 54
property identifier annotation: 54
comment: This DPA switches the comfort level to Comfort. Thus it is represented as a trigger point, that relates to the Comfort level (represented by the state type tag:hvacModeComfort)

Electrical
type: NamedIndividual
type: Trade
description: An electrical installation is a group of items of electrical equipment that are permanently electrically connected together and can be supplied with electricity from the works of an electricity entity or from a generating source. An electrical installation contains the electrical wiring of buildings, transmission lines, stationary machines, fuses, and related equipment.

Disable = 0
type: NamedIndividual
value KNX: 0
value API: disable
is applicable datapoint enum of: disabled

KiloV-A-HR
type: NamedIndividual
type: Unit
symbol: kV⋅A/hr

type.dpt.field.231.x.i0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
comment: Locale information
field string schema: raw

Day of week field valid = 0
type: NamedIndividual
value KNX: 0
value API: dayOfWeekFieldValid

Supply air, e.g. for VAV = 2
value API: supplyAir,E.g.ForVAV
type: NamedIndividual
value KNX: 2

TempRoomSetpTariffShift
type: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subject: 51
subject: TempRoomSetpTariffShift
subject: 121.51
interface object type annotation: 121
property identifier annotation: 51

PER-SEC
type: NamedIndividual
type: Unit
symbol: /s

send always = 1
value KNX: 1
type: NamedIndividual
value API: sendAlways

Inverted = 1
value KNX: 1
type: NamedIndividual
value API: inverted

type.dpt.field.512.502.i1.pe.Reserved
field index: 1
field name: RESERVED
type: Datapoint Type Field
type: NamedIndividual
description: reserved bits
field size: 4
includes reserved bit: type.bit.reserved
field type: r

EnableHeat
type: Class
subject: 399.61
subject: 61
subject: EnableHeat
interface object type annotation: 399
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
property identifier annotation: 61

Dining Room
comment: A dining room is a room for consuming food. Preferably used with an Room.
type: LocationUsage
type: NamedIndividual

type.dpt.field.524.500.i4.ti.ID
field size: 16
field name: ID
includes digit: type.digit.u16
field index: 4
field type: U
type: Datapoint Type Field
type: NamedIndividual
description: identifier of this instruction. value shall be unique. Old IDs will be reused.

Level 8 = 8
value API: level8
value KNX: 8
type: NamedIndividual

no fault = 0
value API: noFault
type: NamedIndividual
value KNX: 0

InfoOnOff
type: Class
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subject: 420.53
subject: InfoOnOff
subject: 53
interface object type annotation: 420
property identifier annotation: 53

unit
comment: Hosts the unit of a datapoint (if applicable). A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
range: Unit
type: ObjectProperty

first: Restriction
  has value: one
  on property: has cardinality
rest: nil

no comfort push button is pressed = 0
value API: noComfortPushButtonIsPressed
type: NamedIndividual
value KNX: 0

TempRoomSetpAbs
type: Class
property identifier annotation: 51
label: TempRoomSetpAbs
subject: 51
subject: TempRoomSetpAbs
subject: 113.51
interface object type annotation: 113

Control Mode Emergency Cool
comment: This state type expresses that mode 'Emergency Cooling' is chosen for the HVAC system. Usually, this mode indicates whether emergency cooling demand is requested for the HVAC system, e.g. for heat protection of a room. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
type: State Type
type: NamedIndividual

Dim Send Style
field type: B
field size: 1
includes KV pair: Start/stop = 0
includes KV pair: type.kvpair.1.13.i0.1
label: Dim Send Style
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.20.111.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: FanMode
field size: 8
includes KV pair: permanently running = 1
includes KV pair: not running = 0
includes KV pair: type.kvpair.20.111.i0.2
field type: N

type.dpt.field.241.800.i2.LowerPredefPos
type: Datapoint Type Field
type: NamedIndividual
field size: 1
comment: Lower predef. pos. reached, typ. height 100 %, slats-angle < 100 %
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 2
field name: LowerPredefPos

type.dpt.field.253.600.i8.cC
field index: 8
field size: 1
field name: cC
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
type: Datapoint Type Field
type: NamedIndividual
field type: B
description: Shall specify whether the colour shall be increased or decreased.

ActualDimming-Value
type: Class
property identifier annotation: 55
subclass of: Restriction
  on property: has operation kind
subject: 55
subject: ActualDimming-Value
subject: 420.55
interface object type annotation: 420

at least one comfort push button is pressed = 1
value KNX: 1
value API: atLeastOneComfortPushButtonIsPresse
type: NamedIndividual

mode 2 is active = 4
value KNX: 4
type: NamedIndividual
value API: mode2IsActive

Equipment Quality Kind
subclass of: QualityKind
disjoint with: PhenomenonQualityKind
type: Class

type.dpt.field.14.53.i0
includes digit: type.digit.f32
field resolution: 1.0
comment: momentum
type: Datapoint Type Field
type: NamedIndividual
unit: N-SEC
field index: 0
field size: 32
field type: F

first: Auto

enable = 0
value KNX: 0
type: NamedIndividual
value API: enable

Gas meter = 3
type: NamedIndividual
value KNX: 3
value API: gasMeter

type.dpt.field.205.17.i1.RelSignedValue
type: Datapoint Type Field
type: NamedIndividual
field type: V
comment: Relative air quality value
unit: PERCENT
field size: 16
includes digit: type.digit.s16
field name: RelSignedValue
field index: 1
field resolution: 0.01

CalibrationMode
type: Class
subject: 72
subject: 400.72
subject: CalibrationMode
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 72
interface object type annotation: 400

type.dpt.field.22.103.i4.OverheatAlarm
field index: 4
field size: 1
field name: OverheatAlarm
type: Datapoint Type Field
type: NamedIndividual
comment: Overheat-Alarm
includes KV pair: No alarm = 0
includes KV pair: type.kvpair.alarm
field type: B

Restriction
on property: pointName
has value: InfoOnOff

type.dpt.field.241.800.i5.TargetSPosRestrict
field index: 5
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field size: 1
comment: Restriction of slats height pos., pos. can not be reached
field name: TargetSPosRestrict
type: Datapoint Type Field
type: NamedIndividual

Medium = 1
value API: medium
value KNX: 1
type: NamedIndividual

Displacement
type: Quantity Kind
type: NamedIndividual
description: "Displacement" is the shortest distance from the initial to the final position of a point P.

one push button/binary input, MoveDown / StepDown message sent = 3
value API: onePushButtonbinaryInput,MoveDownSt
type: NamedIndividual
value KNX: 3

type.dpt.field.16.1.i0.string88591
type: Datapoint Type Field
type: NamedIndividual
field type: A
field size: 112
includes DPT: char88591
field index: 0
unit: UNITLESS
field name: string88591
field string schema: iso-8859-1

has lower floor
type: ObjectProperty
type: InverseFunctionalProperty
type: FunctionalProperty
domain: Floor
sub property of: refers to
comment: A relation from one floor to the next floor.
inverse of: hasUpperFloor
range: Floor

type.digit.u4 0 9
range min: 0
range max: 9
type: NamedIndividual

refers to
type: ObjectProperty
type: TransitiveProperty
comment: To define a general relation between different concepts. With the child properties a relation with a specific semantic meaning can be expressed (such as between locations). Due to the usage from several concepts the domain and range is not specified for this OP.

200.x
has communication mode: LTE
dpt bit size max: 16
subject: 200.major
subject: 200.x
type: DatapointType
type: NamedIndividual
label: 200.x
is assembled with: type.dpt.field.200.x.i0
datapoint type major number: 200

RelDimmingSpeed
type: Class
subject: 67
subject: RelDimmingSpeed
subject: 418.67
subclass of: Restriction
  on property: has datapoint type
  has value: TimePeriod100MSec
interface object type annotation: 418
property identifier annotation: 67

Sunny = 1
type: NamedIndividual
value API: sunny
value KNX: 1

type.dpt.field.516.500.i1.pr.UV
field index: 1
includes digit: type.digit.f16
description: upper value
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field name: UV
field type: F

type.dpt.field.21.1.i5.Reserved
field index: 5
field name: Reserved
field size: 3
field type: r
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved

WD field valid = 0
value API: wDFieldValid
type: NamedIndividual
value KNX: 0

Light Colour Temperature
comment: Color temperature is the color of light emitted by an idealized opaque, non-reflective body at a particular temperature measured in kelvins. The color temperature scale is used to categorize the color of light emitted by other light sources regardless of their temperature. Color temperatures over 5000 K are called "cool colors" (bluish), while lower color temperatures (2700–3000 K) are called "warm colors" (yellowish).
type: NamedIndividual
type: Quantity Kind

Fan Actuator
subclass of: fanCtrl
subclass of: Restriction
  on class: Fan Speed Target
  on property: has function point
  qualified cardinality: 1
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq fanmotor angularvelocity
subject: FA
type: Class
comment: A fan actuator.

Restriction
on property: property identifier
has value: 54

Active Energy kWh
has communication mode: S
comment: a point representing DPT 13.013: ActiveEnergy kWh
datapoint type minor number: 13
is assembled with: type.dpt.field.13.13.i0
subject: 13.013
subject: 13.13
subject: Active Energy kWh
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
label: Active Energy kWh
datapoint type major number: 13

Trend
type: Class
comment: A trend application function monitors live and historical, time-indexed, quantitative etc. data, for example, for visuaization.
subclass of: Monitoring

ComfortProlongEff
type: Class
subclass of: Restriction
  on property: operates on protocol
  has value: KNX
subclass of: Restriction
  on property: has operation kind
subject: 398.83
subject: 83
subject: ComfortProlongEff
interface object type annotation: 398
property identifier annotation: 83

Restriction
has value: 73
on property: property identifier

StatusAHU
has communication mode: LTE
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.21.106.i2.Heat
is assembled with: type.dpt.field.21.106.i1.FanActive
is assembled with: type.dpt.field.21.106.i4.Reserved
is assembled with: type.dpt.field.21.106.i3.Cool
is assembled with: type.dpt.field.21.106.i0.Fault
label: StatusAHU
datapoint type major number: 21
subject: StatusAHU
subject: 21.106
datapoint type minor number: 106
comment: a point representing DPT 21.106: StatusAHU
dpt bit size max: 8

Value Wsp kmh
has communication mode: S
subject: 9.28
subject: Value Wsp kmh
subject: 9.028
type: NamedIndividual
type: DatapointType
description: a point representing DPT 9.028: Value Wsp kmh
is assembled with: type.dpt.field.9.28.i0
datapoint type major number: 9
dpt bit size max: 16
datapoint type minor number: 28
label: Value Wsp kmh

no notice in progress = 0
value API: noNoticeInProgress
type: NamedIndividual
value KNX: 0

Value 2 Count
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 8.1
subject: Value 2 Count
subject: 8.001
comment: a point representing DPT 8.001: Value 2 Count
is assembled with: type.dpt.field.8.1.i0
datapoint type minor number: 1
datapoint type major number: 8
label: Value 2 Count
dpt bit size max: 16

Undefined = 0
value KNX: 0
value API: undefined
type: NamedIndividual

Restriction
has value: Switch On Off Red
on property: pointName

volume flow, 0,1 ml/s = 74
type: NamedIndividual
value API: volumeFlow,0,1Mls
value KNX: 74

type.dpt.field.14.30.i0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/V
type: Datapoint Type Field
type: NamedIndividual
description: electromotive force
field index: 0
field resolution: 1.0

Electric Power L3
type: NamedIndividual
value API: ElectricPowerL3
value KNX: 2

PresenceStatus
type: Class
interface object type annotation: 391
subject: 51
subject: PresenceStatus
subject: 391.51
property identifier annotation: 51

HVAC VAC = 14
value API: hVACVAC
value KNX: 14
type: NamedIndividual

Electrical Voltage
comment: Voltage, also referred to as Electric Tension, is the difference between electrical potentials of two points. For an irrotational electric field, the voltage is independent of the path between the two points a and b.
type: NamedIndividual
type: Quantity Kind

Restriction
has value: 60
on property: property identifier

type.dpt.field.217.1.i2.MagicNumber
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.u5
field size: 5
field name: MagicNumber
comment: Magic Number
unit: NUM
field index: 2
field type: U
field resolution: 1.0

mac version
type: DatatypeProperty
type: FunctionalProperty
comment: Version identifier that has generated an installation, usually generated by a Mac.
range: string
sub property of: installation data

Battery
type: EquipmentType
type: NamedIndividual
description: Battery used to store electric energy.

Operational State Defect Overload
type: State Type
type: NamedIndividual
description: This state type is a special type of a defect state. It expresses that the actual device hosting the datapoint is not working properly due to an overload. Thus, no valid value is available at the datapoint.

Channel Activation 24
has communication mode: S
is assembled with: type.dpt.field.30.1010.i7.ActivationStateOfChannel8
is assembled with: type.dpt.field.30.1010.i3.ActivationStateOfChannel4
is assembled with: type.dpt.field.30.1010.i5.ActivationStateOfChannel6
is assembled with: type.dpt.field.30.1010.i0.ActivationStateOfChannel1
is assembled with: type.dpt.field.30.1010.i11.ActivationStateOfChannel12
is assembled with: type.dpt.field.30.1010.i21.ActivationStateOfChannel22
is assembled with: type.dpt.field.30.1010.i19.ActivationStateOfChannel20
is assembled with: type.dpt.field.30.1010.i9.ActivationStateOfChannel10
is assembled with: type.dpt.field.30.1010.i16.ActivationStateOfChannel17
is assembled with: type.dpt.field.30.1010.i6.ActivationStateOfChannel7
is assembled with: type.dpt.field.30.1010.i1.ActivationStateOfChannel2
is assembled with: type.dpt.field.30.1010.i18.ActivationStateOfChannel19
is assembled with: type.dpt.field.30.1010.i13.ActivationStateOfChannel14
is assembled with: type.dpt.field.30.1010.i4.ActivationStateOfChannel5
is assembled with: type.dpt.field.30.1010.i8.ActivationStateOfChannel9
is assembled with: type.dpt.field.30.1010.i14.ActivationStateOfChannel15
is assembled with: type.dpt.field.30.1010.i15.ActivationStateOfChannel16
is assembled with: type.dpt.field.30.1010.i10.ActivationStateOfChannel11
is assembled with: type.dpt.field.30.1010.i2.ActivationStateOfChannel3
is assembled with: type.dpt.field.30.1010.i20.ActivationStateOfChannel21
is assembled with: type.dpt.field.30.1010.i17.ActivationStateOfChannel18
is assembled with: type.dpt.field.30.1010.i22.ActivationStateOfChannel23
is assembled with: type.dpt.field.30.1010.i12.ActivationStateOfChannel13
is assembled with: type.dpt.field.30.1010.i23.ActivationStateOfChannel24
datapoint type major number: 30
datapoint type minor number: 1010
type: DatapointType
type: NamedIndividual
dpt bit size max: 24
comment: a point representing DPT 30.1010: Channel Activation 24
label: Channel Activation 24
subject: Channel Activation 24
subject: 30.1010

Restriction
on property: interface object type
has value: 100

Working day = 1
value KNX: 1
value API: workingDay
type: NamedIndividual

rest: nil
first: Unregistered

no occupancy from presence detectors = 0
type: NamedIndividual
value KNX: 0
value API: noOccupancyFromPresenceDetectors

VolumeLiquid Litre
has communication mode: S
subject: 12.1200
subject: VolumeLiquid Litre
is assembled with: type.dpt.field.12.1200.i0
label: VolumeLiquid Litre
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 12.1200: VolumeLiquid Litre
dpt bit size max: 32
datapoint type minor number: 1200
datapoint type major number: 12

HVACModeUserEff
type: Class
subject: 100.57
subject: HVACModeUserEff
subject: 57
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 100
property identifier annotation: 57

type.dpt.field.22.1010.i8.ActivationStateOfChannel9
includes KV pair: The visual effect of channel 9 is inactive = 0
includes KV pair: type.kvpair.22.1010.i8.1
comment: Activation state of channel 9
field name: ActivationStateOfChannel9
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field type: B
field index: 8

Restriction
on property: readable
on data range: boolean
max qualified cardinality: 1

type.dpt.field.241.800.i9.LocalOverride
field type: B
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field index: 9
field size: 1
description: Actuator setvalue is locally overridden, e.g. via a local user interface
type: Datapoint Type Field
type: NamedIndividual
field name: LocalOverride

HVACModeAct
type: Class
label: HVACModeAct
subject: HVACModeAct
subject: 224.54
subject: 54
property identifier annotation: 54
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 224

type.dpt.field.21.102.i1.SatusECO
field size: 1
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field name: SatusECO
comment: SatusECO
field index: 1

type.dpt.field.22.1000.i3.Reserved
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 1
field index: 3

permanently running = 1
value KNX: 1
value API: permanentlyRunning
type: NamedIndividual

Restriction
has value: 398
on property: interface object type

24 h = 25
value API: 24H
type: NamedIndividual
value KNX: 25

rest:
  first: Restriction
    has value: Switch On Off Blue
    on property: pointName
first: Switch On Off Blue

sequence not interruptible
value KNX: 0
value API: seqni
description: Sequence is not interruptible
type: NamedIndividual

type.dpt.field.8.10.i0
includes digit: type.digit.s16
field size: 16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
unit: PERCENT

Converter Data Request
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.20.613.i0
subject: Converter Data Request
subject: 20.613
comment: a point representing DPT 20.613: Converter Data Request
datapoint type minor number: 613
label: Converter Data Request
dpt bit size max: 8
datapoint type major number: 20

LoadPriority
has communication mode: S
description: a point representing DPT 20.104: LoadPriority
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
datapoint type minor number: 104
datapoint type major number: 20
subject: 20.104
subject: LoadPriority
is assembled with: type.dpt.field.20.104.i0

type.dpt.field.27.1.i2.IOO3
type: NamedIndividual
type: Datapoint Type Field
field size: 1
includes KV pair: output state is On = 1
includes KV pair: output state is Off = 0
field type: B
description: Info On Off Output 3
field index: 2
field name: IOO3

TempRoomSetpSetCool
type: Class
interface object type annotation: 397
subject: 86
subject: 397.86
subject: TempRoomSetpSetCool
subclass of: Restriction
  on property: has operation kind
subclass of: Class
label: TempRoomSetpSetCool
property identifier annotation: 86

Value Magnetization
has communication mode: S
is assembled with: type.dpt.field.14.49.i0
datapoint type minor number: 49
label: Value Magnetization
description: DPT 14.049: Value of magnetization
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
subject: Value Magnetization
subject: 14.49
subject: 14.049
datapoint type major number: 14

Direction 2 Control
has communication mode: S
label: Direction 2 Control
datapoint type minor number: 9
type: NamedIndividual
type: DatapointType
description: a point representing DPT 2.009: Direction 2 Control
is assembled with: c
is assembled with: Direction 2
subject: 2.009
subject: Direction 2 Control
subject: 2.9
datapoint type major number: 2
dpt bit size max: 2

type.dpt.field.246.600.i4.Reserved
field index: 4
field size: 5
field name: Reserved
field type: r
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved

Month and Day of Month fields valid = 0
value API: monthAndDayOfMonthFieldsValid
value KNX: 0
type: NamedIndividual

volume flow, 10000 ml/s = 79
value KNX: 79
value API: volumeFlow,10000Mls
type: NamedIndividual

EnableComfort
type: Class
subject: 53
subject: EnableComfort
subject: 104.53
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: enable
  on property: has datapoint type
interface object type annotation: 104
property identifier annotation: 53

type.dpt.field.213.102.i0.TempSetpShiftBProt
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
field name: TempSetpShiftBProt
unit: http://qudt.org/vocab/unit/K
field size: 16
includes digit: type.digit.s16
description: room temperature setpoint shift building protection (delta value)

type.dpt.field.229.1.i2.CountVal
type: Datapoint Type Field
type: NamedIndividual
field type: V
field size: 32
description: CountVal
field name: CountVal
unit: NUM
field index: 2
field resolution: 1.0
includes digit: type.digit.s32

HeatCoolMode
type: Class
property identifier annotation: 151
label: HeatCoolMode
subject: HeatCoolMode
subject: 151
subject: 260.151
interface object type annotation: 260

type.dpt.field.219.x.i0
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field string schema: raw
comment: alarm info
field size: 48

TempOutside
type: Class
subclass of: Restriction
  on property: has operation kind
subject: 51
subject: TempOutside
subject: 320.51
interface object type annotation: 320
property identifier annotation: 51

energy, 10000 Wh = 7
value KNX: 7
type: NamedIndividual
value API: energy,10000Wh

Operational State Faulty
comment: This state type expresses that a datapoint’s main value is corrupted due to failure. The device itself is operational. Typical usages are a sensor value is corrupted due to a hardware problem (data is invalid) or a database value is corrupted (due to loss off backup power, erased EEPROM etc).
type: State Type
type: NamedIndividual

251.x
has communication mode: S
dpt bit size max: 48
type: DatapointType
type: NamedIndividual
subject: 251.major
subject: 251.x
label: 251.x
is assembled with: type.dpt.field.251.x.i0
datapoint type major number: 251

master = 2
value KNX: 2
type: NamedIndividual
value API: master

KelvinPerPercent
has communication mode: S
subject: KelvinPerPercent
subject: 9.023
subject: 9.23
datapoint type major number: 9
label: KelvinPerPercent
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
datapoint type minor number: 23
is assembled with: type.dpt.field.9.23.i0
comment: a point representing DPT 9.023: KelvinPerPercent

manufacturer
comment: The manufacturer of an application program or product (as a note, a device is part of a product).
type: DatatypeProperty
type: FunctionalProperty
range: string

operates on protocol
sub property of: has tag
type: ObjectProperty
comment: An OP relationship to a list that describes the primary protocol that a datapoint uses to send its data.
range: Protocol

Value Angular Velocity
has communication mode: S
is assembled with: type.dpt.field.14.9.i0
label: Value Angular Velocity
subject: Value Angular Velocity
subject: 14.9
subject: 14.009
datapoint type major number: 14
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
datapoint type minor number: 9
comment: DPT 14.009: Value of angular velocity

type.dpt.field.21.107.i5.Reserved
includes reserved bit: type.bit.reserved
field type: r
field name: Reserved
field size: 3
type: Datapoint Type Field
type: NamedIndividual
field index: 5

type.dpt.field.12.102.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes digit: type.digit.u32
field resolution: 1.0
field size: 32
unit: HR
field type: U

type.dpt.field.19.x.i0
field string schema: raw
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field size: 64
description: Date Time

TempSupplyAirSetpSet
has communication mode: LTE
label: TempSupplyAirSetpSet
is assembled with: type.dpt.field.224.100.i0.HVACEmergMode
is assembled with: type.dpt.field.224.100.i3.TempSetpCooling
is assembled with: type.dpt.field.224.100.i1.ContrModeAct
is assembled with: type.dpt.field.224.100.i2.TempSetpHeating
comment: a point representing DPT 224.100: TempSupplyAirSetpSet
datapoint type major number: 224
datapoint type minor number: 100
type: NamedIndividual
type: DatapointType
dpt bit size max: 48
subject: TempSupplyAirSetpSet
subject: 224.100

type.dpt.field.pc.i4.LR
field index: 4
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
description: list of limit ranges
includes DPT: emLimitRange
field name: LR
includes counter: type.dpt.field.pc.i3.LR CNT

Restriction
on property: property identifier
has value: 88

Restriction
qualified cardinality: 1
on property: has operation kind

c
description: Increase or decrease the brightness.
label: c
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: c
includes DPT: Step
field index: 1

Restriction
on property: property identifier
has value: 59

type.dpt.field.275.101.i0.TempSetpShiftBProt
unit: http://qudt.org/vocab/unit/K
field size: 16
field type: F
includes digit: type.digit.f16
field resolution: 0.01
comment: room temperature setpoint shift building protection
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: TempSetpShiftBProt

Water Change Over Status Sensor
is incomplete: true
type: Class
subclass of: Restriction
  on property: isComposedByInput
  on class: dpa.324.51
  max qualified cardinality: 1
subject: WCOS
subject: Water Change Over Status Sensor
subject: 342
interface object type annotation: 342

type.dpt.field.512.501.i1.ec.CE
field index: 1
field name: CE
description: list of energy constraint elements
includes counter: type.dpt.field.512.501.i0.ec.CE CNT
includes DPT field: type.dpt.field.ec.i0
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>

type.dpt.field.244.600.i6.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 6
includes reserved bit: type.bit.reserved
field name: Reserved
field size: 2
field type: r

operates for trade
sub property of: has tag
type: ObjectProperty
range: Trade
comment: An OP relationship to a list that describes the application areas in which a aspect (incl. subclasses) or a datapoint is used. An (parent) entity may inherit all trades from its underlying childs, this is domain/application specific.

Data Link Layer Raw Frames = 2
value KNX: 2
type: NamedIndividual
value API: dataLinkLayerRawFrames

type.dpt.field.209.101.i2.ShiftLoadPriority
type: Datapoint Type Field
type: NamedIndividual
description: shift load priority
field name: ShiftLoadPriority
includes DPT: Bool
field index: 2
field size: 1

Value Time
has communication mode: S
subject: 14.074
subject: 14.74
subject: Value Time
type: DatapointType
type: NamedIndividual
label: Value Time
comment: DPT 14.074: Value of time
is assembled with: type.dpt.field.14.74.i0
datapoint type major number: 14
datapoint type minor number: 74
dpt bit size max: 32

Restriction
has value: 51
on property: property identifier

Step Code
includes KV pair: type.kvpair.stepcode.5
includes KV pair: type.kvpair.stepcode.1
includes KV pair: 56% = 4
includes KV pair: Break = 0
includes KV pair: type.kvpair.stepcode.6
includes KV pair: type.kvpair.stepcode.2
includes KV pair: 100% = 7
includes KV pair: 42% = 3
field type: N
label: Step Code
type: Datapoint Type Field
type: NamedIndividual
field name: StepCode
comment: The number of intervals into which the range of 0 % … 100 % is subdivided, or the break indication.
field index: 0
field default: 4
field size: 3

emInstructionStatus
dpt bit size max: 24
is assembled with: type.dpt.field.515.500.i0.is.STAT
is assembled with: type.dpt.field.515.500.i1.is.INSTR ID
datapoint type major number: 515
type: NamedIndividual
type: DatapointType
datapoint type minor number: 500

Ack
has communication mode: S
description: a point representing DPT 1.016: Ack
subject: Ack
subject: 1.016
subject: 1.16
type: DatapointType
type: NamedIndividual
dpt bit size max: 1
label: Ack
datapoint type minor number: 16
is assembled with: Ack
datapoint type major number: 1

Frost Alarm
subclass of: Function Point
subclass of: Restriction
  on property: has datapoint type
  has value: Alarm
type: Class

SensorSelect
has communication mode: S
subject: SensorSelect
subject: 20.17
subject: 20.017
dpt bit size max: 8
datapoint type minor number: 17
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.20.17.i0
datapoint type major number: 20
comment: a point representing DPT 20.017: SensorSelect

includes
comment: Hosts specific information that depends on the field type.
type: ObjectProperty
domain: Datapoint Type Field

Forced State
type: NamedIndividual
type: State Type
comment: This state type expresses that an equipment is in a forced state, i.e. its current value / position is a result of a command with very high priority. The equipment's normal processing of input commands is bypassed and the high priority input command is executed as-is. This state type is the inverse of the 'Not Forced State' state type.

Value Luminance
has communication mode: S
label: Value Luminance
subject: 14.041
subject: 14.41
subject: Value Luminance
is assembled with: type.dpt.field.14.41.i0
type: DatapointType
type: NamedIndividual
datapoint type major number: 14
comment: DPT 14.041: Value of luminance
datapoint type minor number: 41
dpt bit size max: 32

type.dpt.field.ddbc.ome
type: NamedIndividual
type: Datapoint Type Field
includes DPT field: type.dpt.field.ddbc.ome.i0.SRR
includes DPT field: type.dpt.field.ddbc.ome.i1.PR
description: operation mode element

type.dpt.field.6.20.i5.a
type: Datapoint Type Field
type: NamedIndividual
comment: Status A
field size: 1
field index: 5
field type: B
field name: a
includes KV pair: set = 1
includes KV pair: type.kvpair.clear

type.dpt.field.frbc.om.i1.AC
field name: AC
includes KV pair: abnormal condition
includes KV pair: type.kvpair.NoAbnormalCondition
field size: 1
type: Datapoint Type Field
type: NamedIndividual
description: abnormal condition
field type: B
field index: 1

has proxy
range: Gateway
type: AsymmetricProperty
type: IrreflexiveProperty
type: ObjectProperty
property disjoint with: isProxyFor
domain: Device
comment: To define a representative entry point for datapoints with a gateway. With this datapoints in an installation can be exposed for different purposes, such as all datapoints on a 3rd Party API (gateway).
inverse of: isProxyFor

Multimedia Room
type: NamedIndividual
type: LocationUsage
description: A multimedia room is a space in a building that is used to contain multimedia gadgets such like consoles and entertainment. Preferably used with a Room.

Value Magnetic Polarization
has communication mode: S
label: Value Magnetic Polarization
datapoint type minor number: 48
datapoint type major number: 14
dpt bit size max: 32
subject: 14.48
subject: Value Magnetic Polarization
subject: 14.048
type: NamedIndividual
type: DatapointType
comment: DPT 14.048: Value of magnetic polarization
is assembled with: type.dpt.field.14.48.i0

type.dpt.field.203.104.i1.HVACAirFlow
field name: HVACAirFlow
unit: M3-PER-HR
field index: 1
includes digit: type.digit.u16
field size: 16
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual

type.dpt.field.22.102.i1.ShortCircuit
includes KV pair: type.kvpair.alarm
includes KV pair: No alarm = 0
comment: Short Circuit
field name: ShortCircuit
field index: 1
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field type: B

The visual effect of channel 12 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel12IsActive
value KNX: 1

LoadFailedDetection
type: Class
subject: LoadFailedDetection
subject: 418.58
subject: 58
label: LoadFailedDetection
interface object type annotation: 418
property identifier annotation: 58

type.dpt.field.512.505.i3.ps.I
description: Indicator whether sequence is interruptible or not
type: Datapoint Type Field
type: NamedIndividual
field name: I
field index: 3
field size: 1
field type: B
includes KV pair: type.kvpair.seqInterruptible
includes KV pair: sequence not interruptible

type.dpt.field.265.1.i1.Reserved
type: Datapoint Type Field
type: NamedIndividual
field size: 7
includes reserved bit: type.bit.reserved
field index: 1
field type: r
field name: Reserved

type.dpt.field.207.600.i1.Locked
comment: true = actuator is locked, e.g., via input LockDevice.
field name: Locked
type: Datapoint Type Field
type: NamedIndividual
includes DPT: Bool
field index: 1
field size: 1

power, 10000 W = 47
value KNX: 47
type: NamedIndividual
value API: power,10000W

NightMode
type: Class
subject: 63
subject: NightMode
subject: 418.63
property identifier annotation: 63
interface object type annotation: 418

type.dpt.field.201.x.i0
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field string schema: raw
comment: 8-Bit Enum with Status/Command

Operational State In Alarm
type: NamedIndividual
type: State Type
comment: This state type expresses that some alarm condition for a datapoint occurred. No assumption about the validity of the datapoint’s value can be made.

is grouped by
type: ObjectProperty
domain: Point
range: Aspect

220.x
has communication mode: LTE
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
subject: 220.x
subject: 220.major
is assembled with: type.dpt.field.220.x.i0
datapoint type major number: 220

Heat Stage B Proportional = 3
type: NamedIndividual
value KNX: 3
value API: heatStageBProportional

mass, 0,1 kg = 26
value KNX: 26
value API: mass,0,1Kg
type: NamedIndividual

type.dpt.field.201.102.i0.StatusCommand
field name: StatusCommand
field size: 8
comment: standard Status/Command
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0
field type: Z8

Low = 2
value API: low
type: NamedIndividual
value KNX: 2

Restriction
on property: has product
on class: Product
max qualified cardinality: 1

emTimerDeclaration
datapoint type minor number: 511
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.512.511.i1.td.TIMER
is assembled with: type.dpt.field.512.511.i0.td.TIMER CNT
dpt bit size max: 1792
datapoint type major number: 512

Heat Pump
comment: A heat pump is a device that can heat a building (or part of a building) by transferring thermal energy from the outside using the refrigeration cycle. Many heat pumps can also operate in the opposite direction, cooling the building by removing heat from the enclosed space and ejecting it outside. Units that only provide cooling are called air conditioners.
type: NamedIndividual
type: EquipmentType

Restriction
on property: has cardinality
has value: one

abnormal condition
value KNX: 1
value API: ac
type: NamedIndividual
description: Abnormal condition

Restriction
on property: property identifier
has value: 53

Restriction
has value: many
on property: has cardinality

Switch On Off Blue
type: Class
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 62
subject: SOO_B
subject: 62
subject: 423.62
subject: Switch On Off Blue
interface object type annotation: 423

Presence Occupied
description: This state type expresses that a room is occupied. The actual number of people is not of interest. This state type is the inverse of the 'Presence Unoccupied' state type.
type: NamedIndividual
type: State Type

Water Control
type: Class
subclass of: ApplicationFunction
comment: A specific Application Function category that controls a quantity (e.g. temperature, pressure) of the phenomenon water. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.

The visual effect of channel 2 is active = 1
value KNX: 1
value API: theVisualEffectOfChannel2IsActive
type: NamedIndividual

rest: nil
first: Restriction
  on property: interface object type
  has value: 258

type.dpt.field.22.1010.i15.ActivationStateOfChannel16
field type: B
field name: ActivationStateOfChannel16
includes KV pair: The visual effect of channel 16 is inactive = 0
includes KV pair: The visual effect of channel 16 is active = 1
description: Activation state of channel 16
field index: 15
type: Datapoint Type Field
type: NamedIndividual
field size: 1

HumRelRoom
type: Class
label: HumRelRoom
property identifier annotation: 51
interface object type annotation: 337
subject: 51
subject: HumRelRoom
subject: 337.51

HZ
type: Unit
type: NamedIndividual
symbol: Hz

HVAC User Mode not active = 0
value API: hVACUserModeNotActive
type: NamedIndividual
value KNX: 0

TimedStartStop
type: Class
interface object type annotation: 421
property identifier annotation: 65
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subject: 421.65
subject: TimedStartStop
subject: 65

type.dpt.field.21.1000.i2.BiBatSlave
comment: BiBat Slave
type: Datapoint Type Field
type: NamedIndividual
field name: BiBatSlave
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field index: 2
field size: 1

System & functions of common interest = 1
value KNX: 1
type: NamedIndividual
value API: system&FunctionsOfCommonInterest

type.dpt.field.19.1.i6.ND
includes KV pair: Month and Day of Month fields valid = 0
includes KV pair: type.kvpair.19.1.i6.1
field type: B
field name: ND
description: No Date
field default: 0
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field index: 6

Luminaire
type: NamedIndividual
type: EquipmentType
description: Light fixture using electricity to provide illumination.

VolumeLiter Z
has communication mode: LTE
label: VolumeLiter Z
comment: a point representing DPT 218.001: Volume in Liter
is assembled with: type.dpt.field.218.1.i1.VolumeLiter
is assembled with: type.dpt.field.218.1.i0.StatusCommand
subject: VolumeLiter Z
subject: 218.1
subject: 218.001
type: NamedIndividual
type: DatapointType
datapoint type major number: 218
datapoint type minor number: 1
dpt bit size max: 40

is datapoint type of
type: ObjectProperty
domain: DatapointType

2.x
has communication mode: S
label: 2.x
type: DatapointType
type: NamedIndividual
datapoint type major number: 2
dpt bit size max: 2
is assembled with: type.dpt.field.2.x.i0
subject: 2.major
subject: 2.x

Year field not valid = 1
type: NamedIndividual
value API: yearFieldNotValid
value KNX: 1

type.dpt.field.15.0.i1.C
type: NamedIndividual
type: Datapoint Type Field
description: Encryption of access information
includes KV pair: type.kvpair.yes
includes KV pair: no = 0
field type: B
field name: C
field index: 1
field size: 1

HVAC Mode Comfort
type: State Type
type: NamedIndividual
comment: This state type expresses that the highest level named 'Comfort' is chosen for the HVAC mode. Usually, the 'Comfort' level is associated with an occupied room. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.

The visual effect of channel 3 is inactive = 0
value API: theVisualEffectOfChannel3IsInactive
type: NamedIndividual
value KNX: 0

TempRoomDemAbs
has communication mode: LTE
is assembled with: type.dpt.field.209.101.i4.Reserved
is assembled with: type.dpt.field.209.101.i5.TempRoomDem
is assembled with: type.dpt.field.209.101.i0.DemValid
is assembled with: type.dpt.field.209.101.i3.EmergDem
is assembled with: type.dpt.field.209.101.i2.ShiftLoadPriority
is assembled with: type.dpt.field.209.101.i1.AbsLoadPriority
dpt bit size max: 24
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 209.101: TempRoomDemAbs
subject: TempRoomDemAbs
subject: 209.101
datapoint type major number: 209
label: TempRoomDemAbs
datapoint type minor number: 101

Device
subclass of: Class
subclass of: Equipment
subclass of: Restriction
  on data range: string
  max qualified cardinality: 1
  on property: serial number
subclass of: Restriction
  max qualified cardinality: 1
  on property: last modified
  on data range: dateTime
comment: A Device can be any electronic equipment with some computing ability that has a firmware, optionally with input and output terminals (I/O), an Application Program that provides as set of Points as the interface for the I/O operations, and parameter values controlling the behavior of the I/O operations at Runtime.
type: Class

The visual effect of channel 3 is inactive = 0
value API: theVisualEffectOfChannel3IsInactive
type: NamedIndividual
value KNX: 0

Alert
type: NamedIndividual
type: Point Function
description: A point contains a warning that draws attention to something that usually does not need immediate attention.

Delta Volume Liquid Litre
has communication mode: S
datapoint type major number: 13
subject: Delta Volume Liquid Litre
subject: 13.1200
type: DatapointType
type: NamedIndividual
label: Delta Volume Liquid Litre
dpt bit size max: 32
is assembled with: type.dpt.field.13.1200.i0
comment: a point representing DPT 13.1200: Delta Volume Liquid Litre
datapoint type minor number: 1200

Locked State
comment: This state type expresses that an equipment is in a locked state, which usually indicates that the equipment will not react on new input commands until the locked state is lifted. This state type is the inverse of the 'unlocked' state type.
type: State Type
type: NamedIndividual

Heat Stage A Actuator Calibration Mode
type: Class
subclass of: Function Point

Open / Close
field size: 1
includes KV pair: type.kvpair.1.9.i0.0
includes KV pair: Close = 1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
label: Open / Close
field type: B

has application function
domain: Location
range: ApplicationFunction
type: ObjectProperty
inverse of: isApplicationFunctionOf

Intrusion Alarming
type: Class
comment: Application functions to monitor an 'intrusion alarm'.
subclass of: Monitoring

Restriction
on property: interface object type
has value: 100

type.dpt.field.20.804.i0
field type: N
includes KV pair: type.kvpair.20.804.i0.1
includes KV pair: type.kvpair.20.804.i0.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
comment: BlindsControlMode
field size: 8

Restriction
on property: groupAddress
on data range: positiveInteger
qualified cardinality: 1

type.dpt.field.252.600.i2.MaskCG
field index: 2
field size: 1
comment: validity of the fields CG and Step Code Colour Green.
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
type: Datapoint Type Field
type: NamedIndividual
field type: B
field name: MaskCG

202.x
has communication mode: LTE
is assembled with: type.dpt.field.202.x.i0
label: 202.x
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
subject: 202.x
subject: 202.major
datapoint type major number: 202

type.dpt.field.253.x.i0
field string schema: raw
description: Relative Control xyY
field type: A[n]
field index: 0
field size: 32
type: Datapoint Type Field
type: NamedIndividual

emFillLevelRange
is assembled with: type.dpt.field.514.500.i1.flr.UV
is assembled with: type.dpt.field.514.500.i0.flr.LV
dpt bit size max: 16
datapoint type major number: 514
datapoint type minor number: 500
type: DatapointType
type: NamedIndividual

Heat Stage A Actuator Target Position
subclass of: Restriction
  on property: has operation kind
  qualified cardinality: 1
subclass of: Function Point
type: Class

Restriction
has value: 103
on property: interface object type

type.dpt.field.512.510.i3.smddb.Reserved
field size: 4
field type: r
field name: RESERVED
description: reserved bits
type: Datapoint Type Field
type: NamedIndividual
field index: 3
includes reserved bit: type.bit.reserved

type.dpt.field.22.100.i6.SolarEnergySupport
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field size: 1
type: Datapoint Type Field
type: NamedIndividual
field index: 6
comment: SolarEnergySupport
field name: SolarEnergySupport
field type: B

Restriction
on property: has cardinality
has value: many

Restriction
has value: 398
on property: interface object type

Unknown = 0
value API: unknown
value KNX: 0
type: NamedIndividual

Leisure
description: A leisure centre facility or building may include a swimming pool, large sports hall, squash courts, cafeteria, licensed bar, fitness suite, aerobics studios, outdoor grass and/or artificial pitches for football (soccer), hockey etc., a solarium, sauna and/or steam room. Preferably used with a Building.
type: LocationUsage
type: NamedIndividual

User
comment: Refers to information that originates from user action, e.g. issueing light switching commands or selecting setpoints.
type: NamedIndividual
type: Origin

hardware fault = 4
type: NamedIndividual
value API: hardwareFault
value KNX: 4

HVACEmergMode
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.20.106.i0
label: HVACEmergMode
subject: HVACEmergMode
subject: 20.106
dpt bit size max: 8
datapoint type minor number: 106
comment: a point representing DPT 20.106: HVACEmergMode
datapoint type major number: 20

type.dpt.field.9.24.i0
field index: 0
field resolution: 0.01
unit: KiloW
type: Datapoint Type Field
type: NamedIndividual
field size: 16
includes digit: type.digit.f16
field type: F

Restriction
has value: WindowStatus
on property: pointName

Value Sound Intensity
has communication mode: S
datapoint type minor number: 64
datapoint type major number: 14
dpt bit size max: 32
subject: Value Sound Intensity
subject: 14.64
subject: 14.064
type: NamedIndividual
type: DatapointType
label: Value Sound Intensity
comment: DPT 14.064: Value of sound intensity
is assembled with: type.dpt.field.14.64.i0

Restriction
on data range: positiveInteger
on property: datapoint type major number
qualified cardinality: 1

Restriction
on property: pointName
has value: ActuatorErrorInfo

type.dpt.field.242.x.i0
field string schema: raw
field size: 48
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
description: status
field index: 0

type.dpt.field.265.1.i0.BinaryInformation
type: Datapoint Type Field
type: NamedIndividual
comment: Binary Information
field index: 0
includes DPT: switch
field name: BinaryInformation
field size: 1

Meter
comment: EquipmentType to meter a substance or phenomenon
type: EquipmentType
type: NamedIndividual

OnOff Action
has communication mode: S
is assembled with: type.dpt.field.23.1.i0
comment: a point representing DPT 23.001: OnOff Action
subject: 23.001
subject: 23.1
subject: OnOff Action
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
dpt bit size max: 2
datapoint type major number: 23

Installation Hints
type: FunctionalProperty
type: DatatypeProperty
range: string
comment: From MaC assigend installation hints as part of the project.
sub property of: deviceData

type.digit.s8
range min: -128
range max: 127
type: NamedIndividual

Restriction
has value: ActuatorStatus
on property: pointName

Relation to GMT
subclass of: Restriction
  has value: DeltaTimeMin
  on property: has datapoint type
subclass of: Function Point
type: Class

mass flow, 100 kg/h = 85
type: NamedIndividual
value KNX: 85
value API: massFlow,100Kgh

type.dpt.field.14.68.i0
field size: 32
field type: F
includes digit: type.digit.f32
unit: DEG C
field resolution: 1.0
comment: temperature, common
type: Datapoint Type Field
type: NamedIndividual
field index: 0

type.dpt.field.19.1.i12.Reserved
type: Datapoint Type Field
type: NamedIndividual
field size: 2
includes reserved bit: type.bit.reserved
field type: r
field index: 12
field name: Reserved

type.dpt.field.254.600.i2.Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 4
field index: 2
field type: r
field name: Reserved

Absolut load priority = 2
value KNX: 2
type: NamedIndividual
value API: absolutLoadPriority

type.dpt.field.11.x.i0
type: Datapoint Type Field
type: NamedIndividual
field size: 24
field string schema: raw
comment: date
field type: A[n]
field index: 0

volume flow, 0,001 l/h = 56
value KNX: 56
value API: volumeFlow,0,001Lh
type: NamedIndividual

power, 10 W = 44
type: NamedIndividual
value API: power,10W
value KNX: 44

first: Restriction
  has value: 56
  on property: property identifier

open on overheat with a current value over the maximum switching current value = 5
value KNX: 5
type: NamedIndividual
value API: openOnOverheatWithACurrentValueOver

Operation Kind
comment: An operation kind describes by what means the quantity kind value of a specific 'type of interest' from a QK or the state type value is used. The same OK individual MAY refer to arbitrary QK individuals.
type: Class
subclass of: Restriction
  max qualified cardinality: 1
  on class: Point Operation
  on property: has point operation
subclass of: TagSet
disjoint with: QualityKind

TempRoomSetpUserOffset
type: Class
subclass of: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph air temperature room
subclass of: Restriction
  on property: has operation kind
property identifier annotation: 84
subject: TempRoomSetpUserOffset
subject: 84
subject: 397.84
interface object type annotation: 397

has location usage
type: ObjectProperty
range: LocationUsage
domain: Location
sub property of: has tag
inverse of: is location usage of

Failed, test executed in time = 3
type: NamedIndividual
value KNX: 3
value API: failed,TestExecutedInTime

type.dpt.field.9.20.i0
field type: F
unit: MilliV
field index: 0
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.f16
field size: 16

type.dpt.field.203.104.i0.StatusCommand
comment: standard Status/Command
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0
field type: Z8
field name: StatusCommand
field size: 8

The visual effect of channel 13 is active = 1
value API: theVisualEffectOfChannel13IsActive
value KNX: 1
type: NamedIndividual

type.dpt.field.21.1010.i0.ActivationStateOfChannel1
comment: Activation state of channel 1
includes KV pair: type.kvpair.21.1010.i0.0
includes KV pair: The visual effect of channel 1 is active = 1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1
field type: B
field name: ActivationStateOfChannel1

Cool stage A for normal cooling = 3
type: NamedIndividual
value KNX: 3
value API: coolStageAForNormalCooling

Switch On Off Red
type: Class
label: Switch On Off Red
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: switch
  on property: has datapoint type
subject: 56
subject: SOO_R
subject: Switch On Off Red
subject: 423.56
interface object type annotation: 423
property identifier annotation: 56

26.x
has communication mode: S
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.26.x.i0
subject: 26.major
subject: 26.x
datapoint type major number: 26

240.x
has communication mode: S
type: NamedIndividual
type: DatapointType
label: 240.x
datapoint type major number: 240
dpt bit size max: 24
subject: 240.x
subject: 240.major
is assembled with: type.dpt.field.240.x.i0

Button
description: A device used to operate functions and equipment in a room by pushing. Examples are push buttons used to switch light, indicate presence and similar use cases.
type: NamedIndividual
type: EquipmentType

Water
description: Water (chemical formula H2O) is an inorganic, transparent, tasteless, odorless, and nearly colorless chemical substance, which is the main constituent of Earth's hydrosphere and the fluids of all known living organisms.
type: NamedIndividual
type: Phenomenon

datapoint type major number
sub property of: datapoint type
comment: The leading number of the major datapoint type (DPT) in bits, specified in KNX with a numerical scheme. The major type must be present for sub types and for a major type. The range is used to include 0 (the KNX DPT numbering scheme starts at 0).
type: DatatypeProperty
type: FunctionalProperty
range: positiveInteger

type.dpt.field.14.21.i0
field type: F
comment: electric dipole moment
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field size: 32
field index: 0
unit: C-M

Control Dimming
has communication mode: S
label: Control Dimming
datapoint type minor number: 7
type: NamedIndividual
type: DatapointType
subject: 3.007
subject: 3.7
subject: Control Dimming
description: a point representing DPT 3.007: Control Dimming
dpt bit size max: 4
is assembled with: Step Code
is assembled with: c
datapoint type major number: 3

type.dpt.field.7.4.i0
type: NamedIndividual
type: Datapoint Type Field
unit: MilliSEC
field index: 0
field resolution: 100.0
includes digit: type.digit.u16
field size: 16
field type: U

type.dpt.field.219.1.i10.ApplicationArea
field name: ApplicationArea
field size: 8
includes KV pair: type.kvpair.219.1.i10.12
includes KV pair: type.kvpair.219.1.i10.14
includes KV pair: type.kvpair.219.1.i10.13
includes KV pair: type.kvpair.219.1.i10.20
includes KV pair: System & functions of common interest = 1
includes KV pair: Security = 30
includes KV pair: HVAC Hot Water Heating = 11
includes KV pair: no fault = 0
includes KV pair: type.kvpair.219.1.i10.10
includes KV pair: Load Management = 40
includes KV pair: type.kvpair.219.1.i10.50
comment: Application Area
type: Datapoint Type Field
type: NamedIndividual
field index: 10
field type: N

The visual effect of channel 1 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel1IsActive
value KNX: 1

type.dpt.field.253.600.i7.StepCodeColour
description: Shall specify the fading step size or to the code to stop the fading of the colour
includes digit: type.digit.u3
field type: U
field resolution: 1.0
field size: 3
type: Datapoint Type Field
type: NamedIndividual
field index: 7
field name: StepCodeColour

type.dpt.field.235.1.i4.ActiveElectricalEnergy
field index: 4
comment: ActiveElectricalEnergy
includes DPT: Active Energy
type: Datapoint Type Field
type: NamedIndividual
field size: 32
field name: ActiveElectricalEnergy

HVACModeAct
type: Class
subject: 152
subject: HVACModeAct
subject: 260.152
interface object type annotation: 260
property identifier annotation: 152

Restriction
on property: has cardinality
has value: one

type.dpt.field.10.1.i2.Minutes
unit: MIN
field size: 6
comment: Minutes
field index: 2
includes digit: type.digit.u6 0 59
field type: U
field name: Minutes
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual

Value TemperatureDifference
has communication mode: S
datapoint type major number: 14
label: Value TemperatureDifference
dpt bit size max: 32
subject: Value TemperatureDifference
subject: 14.070
subject: 14.70
is assembled with: type.dpt.field.14.70.i0
datapoint type minor number: 70
comment: DPT 14.070: Value of temperature difference
type: NamedIndividual
type: DatapointType

type.dpt.field.13.1.i0
unit: NUM
field resolution: 1.0
includes digit: type.digit.s32
type: Datapoint Type Field
type: NamedIndividual
field type: V
field index: 0
field size: 32

Rain Sensor
subclass of: Restriction
  on property: isApplicableFunctionalityOf
type: Class
interface object type annotation: 803
subject: 803
subject: RS
subject: Rain Sensor

type.dpt.field.27.1.i23.MaskBitIOO8
comment: Mask Bit Info On Off Output 8
type: NamedIndividual
type: Datapoint Type Field
field name: MaskBitIOO8
field index: 23
field size: 1
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B

Restriction
has value: TempOutside
on property: pointName

Air Volume Control
type: Class
subclass of: Air Control
comment: Application functions that controls the quantity 'air volume'.

Restriction
on property: interface object type
has value: 398

KiloGM-PER-SEC
symbol: kg/s
type: NamedIndividual
type: Unit

Restriction
on property: property identifier
has value: 62

type.dpt.field.240.800.i0.ValidSlatsPos
comment: Validity Slats Position
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field size: 1
field name: ValidSlatsPos
type: Datapoint Type Field
type: NamedIndividual
field index: 0

energy, 100 Wh = 5
type: NamedIndividual
value API: energy,100Wh
value KNX: 5

EnableCool
type: Class
property identifier annotation: 62
subclass of: Restriction
  on property: has datapoint type
  has value: Enable HC Stage
subject: 399.62
subject: 62
subject: EnableCool
interface object type annotation: 399

type.dpt.field.225.3.i1.DelayTime
type: Datapoint Type Field
type: NamedIndividual
includes DPT: TimePeriodMin
comment: Delay time until next change of tariff
field index: 1
field name: DelayTime
field size: 16

emUsageForecast
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.512.512.i1.uf.FE CNT
is assembled with: type.dpt.field.512.512.i2.uf.FE
is assembled with: type.dpt.field.512.512.i0.uf.START
datapoint type major number: 512
description: the usage forecast allow the resource manager to communicate planned usage of a storage for a certain period of time in the future
dpt bit size max: 1792
datapoint type minor number: 512

TempRoomSetpCoolEff
type: Class
subject: 100.56
subject: TempRoomSetpCoolEff
subject: 56
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
property identifier annotation: 56
interface object type annotation: 100

Unknown = 0
type: NamedIndividual
value API: unknown
value KNX: 0

ContrModeAct
type: Class
label: ContrModeAct
subclass of: Restriction
  on property: has datapoint type
  has value: hvacContrMode
subject: ContrModeAct
subject: 399.111
subject: 111
interface object type annotation: 399
property identifier annotation: 111

first: Restriction
  has value: Current Colour RGBW
  on property: pointName

PE2 in progress = 2
type: NamedIndividual
value API: pE2InProgress
value KNX: 2

Heat meter = 4
value API: heatMeter
value KNX: 4
type: NamedIndividual

breaker (electricity) = 32
type: NamedIndividual
value KNX: 32
value API: breaker(electricity)

type.dpt.field.512.510.i5.smddb.TRAN
field index: 5
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
includes DPT: emTransition
description: list of transitions
includes counter: type.dpt.field.512.510.i2.smddb.TRAN CNT

Volume Flux for Meters
has communication mode: S
datapoint type major number: 14
label: Volume Flux for Meters
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1200
subject: Volume Flux for Meters
subject: 14.1200
comment: DPT 14.1200: Value of volume flux (in cubic meters per hour)
is assembled with: type.dpt.field.14.1200.i0

type.dpt.field.241.800.i14.SlatsPosition
field index: 14
description: Slats Position
field type: U
field name: SlatsPosition
type: Datapoint Type Field
type: NamedIndividual
field resolution: 0.3921566
unit: PERCENT
includes digit: type.digit.u8
field size: 8

Limit
type: Point Function
type: NamedIndividual
description: A point representing a dynamic limitation for an essential variable or a process value.

Beaufort Wind Force Scale
has communication mode: S
label: Beaufort Wind Force Scale
dpt bit size max: 8
comment: a point representing DPT 20.014: Beaufort Wind Force Scale
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.20.14.i0
subject: 20.014
subject: Beaufort Wind Force Scale
subject: 20.14
datapoint type minor number: 14
datapoint type major number: 20

simple alarm = 1
type: NamedIndividual
value KNX: 1
value API: simpleAlarm

EmergPressure = 1
value API: emergPressure
value KNX: 1
type: NamedIndividual

building protection setpoint = 2
value API: buildingProtectionSetpoint
type: NamedIndividual
value KNX: 2

Equipment
type: Class
subclass of: Asset
comment: An equipment is often refered to as "Fixed Asset". Via an object property realationship an equipment has a relation to an element in the location, in most cases inside a building, for example, a whiteboard, a chair, a table, a fan or a motor, which one can assign a product category and/or product type.

Electricity meter = 2
type: NamedIndividual
value API: electricityMeter
value KNX: 2

Restriction
on property: property identifier
has value: 52

not occupied = 0
value API: notOccupied
type: NamedIndividual
value KNX: 0

type.dpt.field.fltp.pe.i0.FLR
type: Datapoint Type Field
type: NamedIndividual
field name: FLR
includes DPT: emFillLevelRange
field index: 0
field size: 16
description: the range of the fill level that will be reached in the given time

type.dpt.field.14.1200.i0
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0
unit: M3-PER-HR
field type: F
includes digit: type.digit.f32

Overcast = 8
value KNX: 8
value API: overcast
type: NamedIndividual

Occupancy
has communication mode: S
subject: 1.018
subject: 1.18
subject: Occupancy
datapoint type minor number: 18
type: DatapointType
type: NamedIndividual
is assembled with: Occupancy
datapoint type major number: 1
dpt bit size max: 1
comment: a point representing DPT 1.018: Occupancy

type.digit.u8 0 254
range min: 0
type: NamedIndividual
range max: 254

Bedroom
type: LocationUsage
type: NamedIndividual
comment: A bedroom or bedchamber is a room situated within a residential or accommodation unit characterised by its usage for sleeping. Preferably used with a Room.

ReactiveEnergy V64
has communication mode: S
subject: 29.012
subject: ReactiveEnergy V64
subject: 29.12
dpt bit size max: 64
type: NamedIndividual
type: DatapointType
datapoint type major number: 29
is assembled with: type.dpt.field.29.12.i0
label: ReactiveEnergy V64
description: a point representing DPT 29.012: ReactiveEnergy V64
datapoint type minor number: 12

Shutter Stop Trigger
type: Class
subclass of: Function Point
subclass of: Restriction
  on property: actsOnPhenomenonQualityKind
  has value: qk ph light illuminance room

3.x
has communication mode: S
datapoint type major number: 3
type: DatapointType
type: NamedIndividual
subject: 3.x
subject: 3.major
label: 3.x
is assembled with: type.dpt.field.3.x.i0
dpt bit size max: 4

type.dpt.field.209.101.i3.EmergDem
comment: emergency demand (heating or cooling) for room frost protection or de-icing
type: Datapoint Type Field
type: NamedIndividual
field index: 3
field name: EmergDem
includes DPT: Bool
field size: 1

type.dpt.field.26.x.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 8
field string schema: raw
comment: 8-bit set
field type: A[n]

Luminous Flux
type: Quantity Kind
type: NamedIndividual
comment: Luminous Flux or Luminous Power is the measure of the perceived power of light. It differs from radiant flux, the measure of the total power of light emitted, in that luminous flux is adjusted to reflect the varying sensitivity of the human eye to different wavelengths of light.

type.dpt.field.252.600.i7.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 7
includes reserved bit: type.bit.reserved
field size: 4
field type: r
field name: Reserved

Restriction
on property: has cardinality
has value: one

Restriction
has value: TempRoomSetpUserOffset
on property: pointName

ConsumerProducer
has communication mode: S
is assembled with: Consumer / Producer
datapoint type minor number: 1200
type: DatapointType
type: NamedIndividual
label: ConsumerProducer
datapoint type major number: 1
subject: ConsumerProducer
subject: 1.1200
dpt bit size max: 1
comment: a point representing DPT 1.1200: ConsumerProducer

TempRoomSetpAct
type: Class
property identifier annotation: 153
label: TempRoomSetpAct
subject: 261.153
subject: 153
subject: TempRoomSetpAct
interface object type annotation: 261

Restriction
has value: 60
on property: property identifier

type.dpt.field.207.102.i3.RelBurnerDem
comment: Relative demand %: for modulating burner
unit: PERCENT
field index: 3
includes digit: type.digit.u8 0 100
field type: U
field size: 8
field name: RelBurnerDem
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual

Humidifier
type: EquipmentType
type: NamedIndividual
comment: Equipment which adds moisture to air to increase humidity.

27.x
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type major number: 27
label: 27.x
is assembled with: type.dpt.field.27.x.i0
dpt bit size max: 32
subject: 27.x
subject: 27.major

Relative Control xyY
has communication mode: S
datapoint type major number: 253
is assembled with: type.dpt.field.253.600.i4.StepCodeBrightness
is assembled with: type.dpt.field.253.600.i11.cS
is assembled with: type.dpt.field.253.600.i6.Reserved
is assembled with: type.dpt.field.253.600.i12.Reserved
is assembled with: type.dpt.field.253.600.i0.MaskCB
is assembled with: type.dpt.field.253.600.i8.cC
is assembled with: type.dpt.field.253.600.i3.Reserved
is assembled with: type.dpt.field.253.600.i7.StepCodeColour
is assembled with: type.dpt.field.253.600.i5.cB
is assembled with: type.dpt.field.253.600.i9.Reserved
is assembled with: type.dpt.field.253.600.i2.MaskCS
is assembled with: type.dpt.field.253.600.i1.MaskCC
is assembled with: type.dpt.field.253.600.i10.StepCodeSaturation
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 253.600: Relative Control xyY
datapoint type minor number: 600
subject: 253.600
subject: Relative Control xyY
dpt bit size max: 32

Restriction
on property: has cardinality
has value: one

first: Restriction
  has value: TempRoomSetpCoolEff
  on property: pointName

Point Operation
comment: The tag category contains individuals allowing to express how a point value has to be interpreted (mathematically or logically) in order to affect the behavior of the system.
subclass of: Tag
type: Class

Timed StartStop
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
property identifier annotation: 52
subject: 414.52
subject: TSS
subject: Timed StartStop
subject: 52
interface object type annotation: 414

Restriction
on property: interface object type
has value: 397

first: Restriction
  has value: Timed StartStop
  on property: pointName

MilliSEC
type: NamedIndividual
type: Unit
symbol: ms

on = 1
value KNX: 1
value API: on
type: NamedIndividual

type.dpt.field.224.x.i0
field size: 48
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field string schema: raw

emPowerProfile
is assembled with: type.dpt.field.512.504.i0.pp.ID
is assembled with: type.dpt.field.512.504.i2.pp.START
is assembled with: type.dpt.field.512.504.i3.pp.END
is assembled with: type.dpt.field.512.504.i4.pp.SC
is assembled with: type.dpt.field.512.504.i1.pp.SC CNT
type: DatapointType
type: NamedIndividual
datapoint type minor number: 504
description: Power profile
dpt bit size max: 1792
datapoint type major number: 512

stop = 4
value API: stop
value KNX: 4
type: NamedIndividual

manual light control = 1
value API: manualLightControl
value KNX: 1
type: NamedIndividual

Length m
has communication mode: S
datapoint type major number: 8
datapoint type minor number: 12
dpt bit size max: 16
is assembled with: type.dpt.field.8.12.i0
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 8.012: Length m
subject: 8.12
subject: 8.012
subject: Length m

Value Wsp
has communication mode: S
comment: a point representing DPT 9.005: Value Wsp
datapoint type minor number: 5
type: NamedIndividual
type: DatapointType
label: Value Wsp
subject: Value Wsp
subject: 9.005
subject: 9.5
datapoint type major number: 9
dpt bit size max: 16
is assembled with: type.dpt.field.9.5.i0

type.dpt.field.512.512.i0.uf.START
field size: 64
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: START
includes DPT: DateTime
description: start time of the forecast

Restriction
has value: 399
on property: interface object type

type.dpt.field.9.3.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field type: F
includes digit: type.digit.f16
unit: K-PER-HR
field size: 16
field resolution: 0.01

ChangeoverMode
has communication mode: S
is assembled with: type.dpt.field.20.107.i0
dpt bit size max: 8
label: ChangeoverMode
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 20.107: ChangeoverMode
datapoint type major number: 20
subject: 20.107
subject: ChangeoverMode
datapoint type minor number: 107

DateTime Period
has communication mode: S
description: a point representing DPT 256.001: DateTime Period
label: DateTime Period
dpt bit size max: 128
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.256.1.i1.StartDateTime
is assembled with: type.dpt.field.256.1.i0.StopDateTime
subject: 256.001
subject: DateTime Period
subject: 256.1
datapoint type minor number: 1
datapoint type major number: 256

Sunday = 7
value KNX: 7
type: NamedIndividual
value API: sunday

Occupancy
field type: B
includes KV pair: not occupied = 0
includes KV pair: occupied = 1
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 1

type.dpt.field.250.600.i4.cB
includes KV pair: type.kvpair.increase
includes KV pair: Decrease = 0
field type: B
field index: 4
comment: Increase or decrease the brightness.
field name: cB
type: Datapoint Type Field
type: NamedIndividual
field size: 1

fault = 1
type: NamedIndividual
value KNX: 1
value API: fault

Order Number
comment: An identifier to specify the (string based) order number of a vendor product. The order number scheme is vendor specific.
sub property of: productData
type: DatatypeProperty
type: FunctionalProperty
range: string

Controls panel
type: NamedIndividual
type: EquipmentType
description: Panel housing controllers and networking gear. A control panel is a flat, often vertical, area where control or monitoring instruments are displayed or it is an enclosed unit that is the part of a system that users can access, such as the control panel of a security system (also called control unit).

PresenceStatus
type: Class
property identifier annotation: 51
label: PresenceStatus
subject: 51
subject: 345.51
subject: PresenceStatus
interface object type annotation: 345

Restriction
has value: ControlModeUser
on property: pointName

garbage = 41
value API: garbage
type: NamedIndividual
value KNX: 41

Rainfall State
description: This state type expresses the state of heavy rainfall. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of heavy rainfall, this equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Rainfall' state type.
type: NamedIndividual
type: State Type

type.dpt.field.209.102.i3.TempFlowProdSegmC
unit: DEG C
field type: V
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.s16 neg13650 32767
field index: 5
field size: 16
field name: TempFlowProdSegmC
comment: chilled water flow te

Reset
includes KV pair: type.kvpair.1.15.i0.1
includes KV pair: no action (dummy) = 0
type: Datapoint Type Field
type: NamedIndividual
label: Reset
field index: 0
field type: B
field size: 1

Presence Unoccupied
type: State Type
type: NamedIndividual
description: This state type expresses that a room is unoccupied, i.e. no people are in the room. This state type is the inverse of the 'Presence Occupied' state type.

HVAC Air Qual Z
has communication mode: LTE
datapoint type minor number: 100
is assembled with: type.dpt.field.203.100.i1.HVACAirQual
is assembled with: type.dpt.field.203.100.i0.StatusCommand
description: a point representing DPT 203.100: HVAC Air Qual Z
subject: 203.100
subject: HVAC Air Qual Z
type: NamedIndividual
type: DatapointType
datapoint type major number: 203
dpt bit size max: 24

type.dpt.field.21.2.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field index: 3
field size: 5
field type: r
field name: Reserved

Restriction
has value: many
on property: has cardinality

AbsSetvalueControl
type: Class
subject: 63
subject: AbsSetvalueControl
subject: 420.63
property identifier annotation: 63
subclass of: Restriction
  on property: has operation kind
interface object type annotation: 420

type.dpt.field.207.105.i6.ActPos
includes digit: type.digit.u8 0 100
field name: ActPos
field type: U
field resolution: 1.0
field size: 8
description: actual actuator position
type: Datapoint Type Field
type: NamedIndividual
field index: 6
unit: PERCENT

asynchronous + BiBat Slave = 2
value KNX: 2
type: NamedIndividual
value API: asynchronous+BiBatSlave

Restriction
on property: has operation kind
qualified cardinality: 1

Window Switch
subclass of: Restriction
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
subclass of: Restriction
  qualified cardinality: 1
  on property: isComposedByOutput
  on class: WindowStatus
subclass of: Restriction
  max qualified cardinality: 1
  on property: isComposedByInput
  on class: WindowSwitch
type: Class
interface object type annotation: 343
subject: 343
subject: WOS
subject: Window Switch

Restriction
has value: DewPointStatus
on property: pointName

type.dpt.field.243.600.i3.Brightness
type: Datapoint Type Field
type: NamedIndividual
comment: Brightness of the colour
field index: 3
includes DPT: scaling
field size: 8
field name: Brightness

30 min = 19
type: NamedIndividual
value API: 30Min
value KNX: 19

Level 0 = 0
value API: level0
type: NamedIndividual
value KNX: 0

type.dpt.field.21.100.i3.Overrun
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
comment: Overrun
field type: B
field index: 3
field name: Overrun

emSequenceStatus
is assembled with: type.dpt.field.520.500.i3.ss.CID
is assembled with: type.dpt.field.520.500.i4.ss.PID
is assembled with: type.dpt.field.520.500.i0.ss.ET
is assembled with: type.dpt.field.520.500.i2.ss.SID
is assembled with: type.dpt.field.520.500.i1.ss.SLT
type: DatapointType
type: NamedIndividual
datapoint type minor number: 500
dpt bit size max: 80
description: state of a sequence
datapoint type major number: 520

100% = 7
value API: 100%
value KNX: 7
type: NamedIndividual

Restriction
has value: TempRoomSetpSetCoolEff
on property: pointName

Restriction
has value: 399
on property: interface object type

Facade
type: Locality
type: NamedIndividual
comment: A façade is generally the front part or exterior of a building. Mainly used as a building facade.

no alarm = 0
type: NamedIndividual
value KNX: 0
value API: noAlarm

Restriction
on property: property identifier
has value: 53

Relative Humidity
description: Relative Humidity is the ratio of the partial pressure of water vapor in an air-water mixture to the saturated vapor pressure of water at a prescribed temperature. The relative humidity of air depends not only on temperature but also on the pressure of the system of interest.
type: Quantity Kind
type: NamedIndividual

ApparantEnergy V64
has communication mode: S
description: a point representing DPT 29.011: ApparantEnergy V64
datapoint type minor number: 11
subject: ApparantEnergy V64
subject: 29.011
subject: 29.11
is assembled with: type.dpt.field.29.11.i0
datapoint type major number: 29
dpt bit size max: 64
type: NamedIndividual
type: DatapointType

Converter Test Result
has communication mode: S
is assembled with: type.dpt.field.245.600.i0.LPDTR
is assembled with: type.dpt.field.245.600.i3.SP
is assembled with: type.dpt.field.245.600.i2.Reserved
is assembled with: type.dpt.field.245.600.i6.Reserved
is assembled with: type.dpt.field.245.600.i9.LTRF
is assembled with: type.dpt.field.245.600.i4.SD
is assembled with: type.dpt.field.245.600.i7.LTRP
is assembled with: type.dpt.field.245.600.i1.LDTR
is assembled with: type.dpt.field.245.600.i8.LTRD
is assembled with: type.dpt.field.245.600.i5.SF
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 245.600: Converter Test Result
subject: Converter Test Result
subject: 245.600
datapoint type major number: 245
dpt bit size max: 48
datapoint type minor number: 600

Not Forced State
description: This state type expresses that an equipment is not in a forced state, i.e. no command with very high priority influenced the equipment's current value / position. The equipment's normal processing of input commands is executed. This state type is the inverse of the 'Forced State' state type.
type: NamedIndividual
type: State Type

TempRoomSetpSetHeatShift
type: Class
label: TempRoomSetpSetHeatShift
subclass of: Class
subclass of: Restriction
  some values from: Class
  on property: has operation kind
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subject: 115.62
subject: TempRoomSetpSetHeatShift
subject: 62
interface object type annotation: 115
property identifier annotation: 62

Control Mode Off
type: State Type
type: NamedIndividual
description: This state type expresses that mode 'Off' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system being idle, i.e. neither heating nor cooling functionality being required. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.

type.dpt.field.242.600.i2.Reserved
field index: 2
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
field size: 6
includes reserved bit: type.bit.reserved

alarm (RTC locked) = 1
value API: alarm(RTCLocked)
type: NamedIndividual
value KNX: 1

first: Restriction
  on property: property identifier
  has value: 60

FadeToControlCmd
type: Class
subclass of: Restriction
  some values from: Class
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
  some values from: Class
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph temporal duration
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
property identifier annotation: 66
label: FadeToControlCmd
subject: FadeToControlCmd
subject: 66
subject: 418.66
interface object type annotation: 418

type.dpt.field.27.1.i19.MaskBitIOO4
field index: 19
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B
field name: MaskBitIOO4
comment: Mask Bit Info On Off Output 4

Restriction
has value: many
on property: has cardinality

type.dpt.field.12.1201.i0
includes digit: type.digit.u32
unit: M3
field type: U
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0

5 min = 16
type: NamedIndividual
value KNX: 16
value API: 5Min

Cabinet
disjoint with: Device
subclass of: Restriction
  all values from: string
  on property: comment
subclass of: Equipment
comment: A Cabinet is a physical enclosure for electrical or electronic equipment such as automatic switches, fuses, circuit breakers, control devices, timers and similar.
type: Class

power, 0,1 kJ/h = 50
value KNX: 50
value API: power,0,1KJh
type: NamedIndividual

Value Momentum
has communication mode: S
subject: Value Momentum
subject: 14.53
subject: 14.053
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
description: DPT 14.053: Value of momentum
datapoint type minor number: 53
is assembled with: type.dpt.field.14.53.i0
label: Value Momentum
datapoint type major number: 14

Standby = 2
value KNX: 2
value API: standby
type: NamedIndividual
is applicable datapoint enum of: hvacModeStandby

type.dpt.field.14.39.i0
includes digit: type.digit.f32
field resolution: 1.0
field size: 32
type: Datapoint Type Field
type: NamedIndividual
field index: 0
description: length
unit: http://qudt.org/vocab/unit/M
field type: F

type.dpt.field.512.504.i0.pp.ID
type: Datapoint Type Field
type: NamedIndividual
field size: 4
includes digit: type.digit.u4
field index: 0
field name: ID
description: Power profile id
field type: U

Consumer
value KNX: 1
type: NamedIndividual
value API: roleConsumer

Movement Trigger
type: Class
subclass of: Restriction
  on property: has operation kind
subject: 414.63
subject: 63
subject: Movement Trigger
subject: MT
property identifier annotation: 63
interface object type annotation: 414

Value Electric CurrentDensity
has communication mode: S
datapoint type minor number: 20
subject: 14.20
subject: 14.020
subject: Value Electric CurrentDensity
datapoint type major number: 14
is assembled with: type.dpt.field.14.20.i0
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
label: Value Electric CurrentDensity
description: DPT 14.020: Value of electric current density

Datapoint Type Field
subclass of: Thing
subclass of: Class
type: Class
comment: A generic concept to describe the individual parts of a KNX datapoint type. A datapoint type field is derived from parent concepts that are specified as part of the EN 50090-6-2.

type.dpt.field.213.102.i3.TempSetpShiftComf
field name: TempSetpShiftComf
comment: room temperature setpoint shift comfort (delta value)
field size: 16
field resolution: 0.02
type: Datapoint Type Field
type: NamedIndividual
field type: V
unit: http://qudt.org/vocab/unit/K
includes digit: type.digit.s16
field index: 3

volume flow, 1000 ml/s = 78
value API: volumeFlow,1000Mls
type: NamedIndividual
value KNX: 78

type.dpt.field.22.103.i8.CoolingModeEnabled
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field name: CoolingModeEnabled
field index: 8
field size: 1
description: Cooling Mode Enabled
type: Datapoint Type Field
type: NamedIndividual

volume flow, 0,1 l/h = 58
value KNX: 58
type: NamedIndividual
value API: volumeFlow,0,1Lh

Saturday = 6
type: NamedIndividual
value API: saturday
value KNX: 6

type.dpt.field.207.600.i8.ActualValue
field resolution: 1.0
unit: PERCENT
field index: 8
field name: ActualValue
comment: Current lighting level in %. In case of a switching actuator LSAB the range is limited to the discrete values 0 % and 100 %.
includes digit: type.digit.u8 0 100
field type: U
field size: 8
type: Datapoint Type Field
type: NamedIndividual

is part of
domain: Equipment
type: ObjectProperty
type: AsymmetricProperty
type: IrreflexiveProperty
type: FunctionalProperty
range: Equipment

type.dpt.field.265.9.i0.BinaryInformation
field index: 0
includes DPT: Open Close
field name: BinaryInformation
field size: 1
type: Datapoint Type Field
type: NamedIndividual
comment: Binary Information

type.dpt.field.525.500.i8.fv.Lower Limit
field size: 16
description: The lower boundary of the range with 100 % certainty the power value is in it
field name: Lower_Limit
field index: 8
type: Datapoint Type Field
type: NamedIndividual
includes DPT: Power

enable stage B = 2
value API: enableStageB
value KNX: 2
type: NamedIndividual

rest: nil
first: Restriction
  on property: interface object type
  has value: 397

LegioProtect = 1
value API: legioProtect
type: NamedIndividual
value KNX: 1

Restriction
on property: pointName
has value: StatusGO

265.x
has communication mode: S
datapoint type major number: 265
is assembled with: type.dpt.field.265.x.i0
label: 265.x
type: DatapointType
type: NamedIndividual
dpt bit size max: 72
subject: 265.major
subject: 265.x

emStateMachineDDBC
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.512.510.i2.smddb.TRAN CNT
is assembled with: type.dpt.field.512.510.i0.smddbc.COM
is assembled with: type.dpt.field.512.510.i1.smddbc.OM CNT
is assembled with: type.dpt.field.512.510.i4.smddb.OM
is assembled with: type.dpt.field.512.510.i5.smddb.TRAN
is assembled with: type.dpt.field.512.510.i3.smddb.Reserved
datapoint type minor number: 510
datapoint type major number: 512
dpt bit size max: 1792

type.dpt.field.11.1.i0.Year
type: Datapoint Type Field
type: NamedIndividual
field size: 7
field index: 0
field name: Year
includes digit: type.digit.u7 0 99
unit: YR
field type: U
field resolution: 1.0

Restriction
on property: has operation kind
qualified cardinality: 1

Locale ASCII
has communication mode: S
datapoint type minor number: 1
subject: 231.1
subject: 231.001
subject: Locale ASCII
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.231.1.i1.Language
is assembled with: type.dpt.field.231.1.i0.Region
comment: a point representing DPT 231.001: Locale ASCII
datapoint type major number: 231
dpt bit size max: 32

Radiator
type: NamedIndividual
type: EquipmentType
description: Heats a space using exposed pipes or coils. Radiators are heat exchangers used to transfer thermal energy from one medium to another for the purpose of cooling and heating. The majority of radiators are constructed to function in cars, buildings, and electronics.

The visual effect of channel 14 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel14IsInactiv

LoadTypeDetected
has communication mode: S
label: LoadTypeDetected
is assembled with: type.dpt.field.20.610.i0
subject: 20.610
subject: LoadTypeDetected
type: NamedIndividual
type: DatapointType
datapoint type minor number: 610
dpt bit size max: 8
datapoint type major number: 20
comment: a point representing DPT 20.610: LoadTypeDetected

Restriction
has value: many
on property: has cardinality

type.dpt.field.244.600.i3.FP
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.testNotPending
includes KV pair: Unknown = 0
includes KV pair: Test pending = 2
comment: Function Test Pending
field index: 3
field size: 2
field type: N
field name: FP

Lighting = 20
value KNX: 20
value API: lighting
type: NamedIndividual

Absolute Set Value Control Green
type: Class
subject: 423.61
subject: ASV_G
subject: Absolute Set Value Control Green
subject: 61
label: Absolute Set Value Control Green
property identifier annotation: 61
interface object type annotation: 423

Restriction
has value: 418
on property: interface object type

type.dpt.field.241.800.i6.WeatherAlarm
comment: At least one of the inputs Wind-/Rain-/Frost-Alarm is ‘in alarm’
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 6
field name: WeatherAlarm
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B

Stopped Movement
type: NamedIndividual
type: State Type
description: This state type expresses that the movement of an equipment has stopped. Usually, this is associated with equipments that can be moved by a drive, such as valves, blinds, slats, windows, or doors.

Fixed = 0
type: NamedIndividual
value KNX: 0
value API: fixed

type.dpt.field.14.47.i0
comment: magnetic moment
includes digit: type.digit.f32
type: Datapoint Type Field
type: NamedIndividual
unit: A-M2
field index: 0
field resolution: 1.0
field size: 32
field type: F

Value Thermal Conductivity
has communication mode: S
subject: 14.072
subject: 14.72
subject: Value Thermal Conductivity
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
description: DPT 14.072: Value of thermal conductivity
label: Value Thermal Conductivity
datapoint type minor number: 72
datapoint type major number: 14
is assembled with: type.dpt.field.14.72.i0

type.dpt.field.205.103.i0.StatusCommand
type: Datapoint Type Field
type: NamedIndividual
field index: 0
description: standard Status/Command
field type: Z8
includes DPT: StatusGen
field name: StatusCommand
field size: 8

Wire
description: Cabling used to convey electricity (AC/DC) or data.
type: Locality
type: NamedIndividual

DownUp = 3
type: NamedIndividual
value KNX: 3
value API: downUp

201.x
has communication mode: LTE
label: 201.x
dpt bit size max: 16
subject: 201.major
subject: 201.x
type: DatapointType
type: NamedIndividual
datapoint type major number: 201
is assembled with: type.dpt.field.201.x.i0

implements
range: Functionality
type: InverseFunctionalProperty
type: ObjectProperty
inverse of: is implemented by
domain: Application Program
comment: To define a functionality (=collection of datapoints) as part of an application program.

rest: nil
first: Restriction
  has value: 259
  on property: interface object type

Quantity Kind
type: Class
subclass of: Tag
comment: The tag category contains individuals that describe the numerical quantity of the measurement/adjustment (equipment) or observation/actuation (phenomenon).

type.dpt.field.26.1.i2.Reserved
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 2
includes reserved bit: type.bit.reserved

Restriction
on property: has cardinality
has value: one

Dehumidification Mode
description: This state type expresses the 'dehumidification' mode of the ventilation system. Usually, this is related to lowering the relative air humidity by removing moist air and replacing it with dry air.
type: NamedIndividual
type: State Type

Restriction
max qualified cardinality: 1
on property: has tag

Restriction
on property: pointName
has value: ComfortPushbutton

alarm position is DOWN = 2
value KNX: 2
type: NamedIndividual
value API: alarmPositionIsDOWN

Health Care
type: LocationUsage
type: NamedIndividual
description: A health facility is, in general, any location where healthcare is provided. Health facilities are clinics and doctor's offices or urgent care centers with elaborate emergency rooms. Preferably used with a Building or a Site/Space.

has eventpoint
range: Eventpoint
inverse of: isEventpointOf
type: ObjectProperty
sub property of: has point

Heat/Cool Z
has communication mode: LTE
dpt bit size max: 16
type: DatapointType
type: NamedIndividual
subject: 200.100
subject: Heat/Cool Z
datapoint type minor number: 100
comment: a point representing DPT 200.100: Heat/Cool Z
is assembled with: type.dpt.field.200.100.i1.HeatCool
is assembled with: type.dpt.field.200.100.i0.StatusCommand
datapoint type major number: 200

Restriction
on property: pointName
has value: TempRoomSetpUserOffset

Building not in use = 1
type: NamedIndividual
value API: buildingNotInUse
value KNX: 1

type.digit.u16 0 28000
type: NamedIndividual
range max: 28000
range min: 0

StatusAct
has communication mode: LTE
is assembled with: type.dpt.field.207.105.i0.Failure
is assembled with: type.dpt.field.207.105.i4.SynchronizationMode
is assembled with: type.dpt.field.207.105.i3.ValveKick
is assembled with: type.dpt.field.207.105.i2.CalibrationMode
is assembled with: type.dpt.field.207.105.i1.ManualOverride
is assembled with: type.dpt.field.207.105.i5.Reserved
is assembled with: type.dpt.field.207.105.i6.ActPos
label: StatusAct
type: NamedIndividual
type: DatapointType
subject: StatusAct
subject: 207.105
dpt bit size max: 16
datapoint type minor number: 105
datapoint type major number: 207
description: a point representing DPT 207.105: StatusAct

type.dpt.field.251.x.i0
field size: 48
field string schema: raw
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
comment: Colour RGBW

type.dpt.field.14.15.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: F
description: conductance
includes digit: type.digit.f32
field resolution: 1.0
field size: 32
unit: http://qudt.org/vocab/unit/S

Converter Info Fix
has communication mode: S
datapoint type major number: 250
description: a point representing DPT 250.600: Converter Info Fix
is assembled with: type.dpt.field.250.600.i7.cCT
is assembled with: type.dpt.field.250.600.i4.cB
is assembled with: type.dpt.field.250.600.i8.Reserved
is assembled with: type.dpt.field.250.600.i6.StepCodeColourTemperature
is assembled with: type.dpt.field.250.600.i3.StepCodeBrightness
is assembled with: type.dpt.field.250.600.i0.BrightnessStepValidity
is assembled with: type.dpt.field.250.600.i5.Reserved
is assembled with: type.dpt.field.250.600.i1.ColourStepValidity
is assembled with: type.dpt.field.250.600.i2.Reserved
type: NamedIndividual
type: DatapointType
label: Converter Info Fix
dpt bit size max: 24
subject: Converter Info Fix
subject: 250.600
datapoint type minor number: 600

type.dpt.field.235.x.i0
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
field size: 48
field string schema: raw
comment: Signed value with classification and validity

250.x
has communication mode: S
label: 250.x
datapoint type major number: 250
type: NamedIndividual
type: DatapointType
subject: 250.x
subject: 250.major
is assembled with: type.dpt.field.250.x.i0
dpt bit size max: 24

PERCENT
type: NamedIndividual
type: Unit
symbol: %

UpDown Action
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 23.003
subject: UpDown Action
subject: 23.3
dpt bit size max: 2
datapoint type major number: 23
datapoint type minor number: 3
label: UpDown Action
comment: a point representing DPT 23.003: UpDown Action
is assembled with: type.dpt.field.23.3.i0

type.dpt.field.ombc.om.i1.AC
field size: 1
field type: B
description: abnormal condition
field index: 1
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: abnormal condition
includes KV pair: type.kvpair.NoAbnormalCondition
field name: B

TempRoomSetpHeatEffNext
type: Class
subject: TempRoomSetpHeatEffNext
subject: 52
subject: 101.52
subclass of: Class
subclass of: Restriction
  has value: TempHVACAbsNext
  on property: has datapoint type
subclass of: Restriction
  on property: hasQualityKind
  has value: qk ph temporal delay
interface object type annotation: 101
property identifier annotation: 52

type.dpt.field.275.101.i2.TempSetpShiftStdby
unit: http://qudt.org/vocab/unit/K
field size: 16
field type: F
description: room temperature setpoint shift standby
field index: 2
includes digit: type.digit.f16
field resolution: 0.01
field name: TempSetpShiftStdby
type: Datapoint Type Field
type: NamedIndividual

EmergShutdown = 4
value API: emergShutdown
type: NamedIndividual
value KNX: 4

PresenceStatus
type: Class
label: PresenceStatus
subject: PresenceStatus
subject: 398.63
subject: 63
interface object type annotation: 398
property identifier annotation: 63

type.dpt.field.20.5.i0
field type: N
includes KV pair: presence simulation = 1
includes KV pair: type.kvpair.20.5.i0.2
includes KV pair: type.kvpair.20.5.i0.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 8
comment: Application Mode

State
type: NamedIndividual
type: Datapoint Type Field
field size: 1
field index: 0
field name: state
label: State
includes DPT: State

Demand Driven Based Control
subclass of: smartGridCtrl
comment: Application functions for "demand driven based control" is an approach to dynamically manage energy output based on the demand for energy that arises within the smart grid.
type: Class

type.dpt.field.222.101.i0.TempSetpShiftEco
type: Datapoint Type Field
type: NamedIndividual
field index: 0
unit: http://qudt.org/vocab/unit/K
field type: F
description: TempSetpShiftEco
field name: TempSetpShiftEco
includes digit: type.digit.f16
field size: 16
field resolution: 0.01

TimedStartStop
type: Class
interface object type annotation: 418
subject: TimedStartStop
subject: 418.71
subject: 71
property identifier annotation: 71

has function point
range: Function Point
domain: ApplicationFunction
type: ObjectProperty
comment: To define the existence of several function points as part of an application function. Application functions without any function points are possible but useless (a MaC may not prevent to remove them all).
inverse of: isFunctionPointOf

emPowerEnvelope
dpt bit size max: 1792
is assembled with: type.dpt.field.512.502.i1.pe.Reserved
is assembled with: type.dpt.field.512.502.i2.pe.CQ
is assembled with: type.dpt.field.512.502.i3.pe.LR CNT
is assembled with: type.dpt.field.512.502.i4.pe.LR
is assembled with: type.dpt.field.512.502.i0.pe.ID
datapoint type major number: 512
type: DatapointType
type: NamedIndividual
datapoint type minor number: 502

Breaker (electricity) = 32
type: NamedIndividual
value KNX: 32
value API: breaker(electricity)

Wall
type: NamedIndividual
type: EquipmentType
comment: A wall is a building element that physically separates two or more neighbouring locations (typically rooms).

Reset Function Test Done Flag = 5
value API: resetFunctionTestDoneFlag
type: NamedIndividual
value KNX: 5

Restriction
has value: NumberedSceneControl
on property: pointName

Electricity meter = 2
type: NamedIndividual
value API: electricityMeter
value KNX: 2

type.digit.u5
range max: 31
range min: 0
type: NamedIndividual

volume flow, 1000 l/min = 71
value API: volumeFlow,1000Lmin
type: NamedIndividual
value KNX: 71

Restriction
on property: has operation kind
qualified cardinality: 1

Wellness
description: A wellness room may contain facilities such as a sauna, pool, steam room, or whirlpool. A wellness room provides a variety of services for the purpose of improving health, beauty, and relaxation through personal care treatments such as massages and facials. Preferably used with an Room.
type: LocationUsage
type: NamedIndividual

StatusRHC
has communication mode: LTE
is assembled with: type.dpt.field.21.102.i3.TempReturnLimit
is assembled with: type.dpt.field.21.102.i6.StatusStopOptim
is assembled with: type.dpt.field.21.102.i0.Fault
is assembled with: type.dpt.field.21.102.i5.StatusStartOptim
is assembled with: type.dpt.field.21.102.i4.StatusMorningBoost
is assembled with: type.dpt.field.21.102.i1.SatusECO
is assembled with: type.dpt.field.21.102.i2.TempFlowLimit
is assembled with: type.dpt.field.21.102.i7.SummerMode
comment: a point representing DPT 21.102: StatusRHC
subject: StatusRHC
subject: 21.102
datapoint type major number: 21
type: NamedIndividual
type: DatapointType
datapoint type minor number: 102
dpt bit size max: 8

type.dpt.field.21.100.i6.RoomHConf
includes KV pair: type.kvpair.true
includes KV pair: type.kvpair.false
field name: RoomHConf
comment: RoomHConf
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 6
field type: B

valid = 1
value API: valid
value KNX: 1
type: NamedIndividual

Ack
field size: 1
label: Ack
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: type.kvpair.1.16.i0.1
includes KV pair: no action (dummy) = 0
field index: 0
field type: B

Metering DeviceType
has communication mode: S
type: NamedIndividual
type: DatapointType
label: Metering DeviceType
dpt bit size max: 8
is assembled with: type.dpt.field.20.114.i0
subject: 20.114
subject: Metering DeviceType
datapoint type major number: 20
description: a point representing DPT 20.114: Metering DeviceType
datapoint type minor number: 114

Restriction
on property: property identifier
has value: 100

Public Building
description: Preferably used with a Building.
type: LocationUsage
type: NamedIndividual

The visual effect of channel 15 is inactive = 0
value API: theVisualEffectOfChannel15IsInactiv
value KNX: 0
type: NamedIndividual

MeteringValue
has communication mode: S
dpt bit size max: 48
datapoint type minor number: 1
datapoint type major number: 229
is assembled with: type.dpt.field.229.1.i2.CountVal
is assembled with: type.dpt.field.229.1.i1.ValInfField
is assembled with: type.dpt.field.229.1.i0.StatusCommand
type: DatapointType
type: NamedIndividual
subject: 229.1
subject: 229.001
subject: MeteringValue
description: a point representing DPT 229.001: MeteringValue

Concentration µg/m3
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: 9.30
subject: 9.030
subject: Concentration µg/m3
comment: a point representing DPT 9.030: Concentration µg/m3
is assembled with: type.dpt.field.9.30.i0
datapoint type major number: 9
dpt bit size max: 16
datapoint type minor number: 30
label: Concentration µg/m3

type.dpt.field.11.1.i1.Reserved
field index: 1
field size: 1
field type: r
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field name: Reserved

Door
type: EquipmentType
type: NamedIndividual
comment: A door is a hinged or otherwise movable barrier that allows ingress (entry) into and egress (exit) from an enclosure.

Value Resistivity
has communication mode: S
datapoint type major number: 14
subject: 14.061
subject: 14.61
subject: Value Resistivity
type: DatapointType
type: NamedIndividual
comment: DPT 14.061: Value of resistivity
is assembled with: type.dpt.field.14.61.i0
label: Value Resistivity
dpt bit size max: 32
datapoint type minor number: 61

TimedStartStop
type: Class
subclass of: Class
  intersection of: Datapoint
subject: 65
subject: 420.65
subject: TimedStartStop
property identifier annotation: 65
interface object type annotation: 420

Weather Station
comment: Application funtion weather station aggregates outside measurement points.
subclass of: Monitoring
type: Class

Restriction
has value: CombinedStatus_HVA_HeatA
on property: pointName

type.dpt.field.19.1.i18.Reserved
type: NamedIndividual
type: Datapoint Type Field
includes reserved bit: type.bit.reserved
field type: r
field name: Reserved
field index: 18
field size: 3

LanguageCodeAlpha2 ASCII
has communication mode: S
subject: LanguageCodeAlpha2 ASCII
subject: 234.1
subject: 234.001
comment: a point representing DPT 234.001: LanguageCodeAlpha2 ASCII
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
dpt bit size max: 16
is assembled with: type.dpt.field.234.1.i0.Character2
is assembled with: type.dpt.field.234.1.i1.Character1
datapoint type major number: 234

Bathroom
comment: A bathroom or washroom is a room, typically in a home or other residential building, that contains either a bathtub or a shower (or both). Preferably used with an Room.
type: LocationUsage
type: NamedIndividual

type.dpt.field.21.1010.i3.ActivationStateOfChannel4
description: Activation state of channel 4
field name: ActivationStateOfChannel4
field type: B
field index: 3
field size: 1
includes KV pair: type.kvpair.21.1010.i3.0
includes KV pair: type.kvpair.21.1010.i3.1
type: Datapoint Type Field
type: NamedIndividual

Shutter Position Length
type: Class
subclass of: Function Point
subclass of: Restriction
  on property: adjustsEquipmentQualityKind
  has value: qk eq blindsactuator positionvector

Decreasing
type: NamedIndividual
type: State Type
description: This state type expresses that a value is changed relatively in a 'decreasing' manner, i.e. the value is lowered. This state type is the inverse of the 'Increasing' state type.

type.dpt.field.9.31.i0.fllr.VAL
description: value
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: F
includes digit: type.digit.f16
field name: VAL

type.dpt.field.7.2.i0
type: Datapoint Type Field
type: NamedIndividual
unit: MilliSEC
field index: 0
includes digit: type.digit.u16
field size: 16
field resolution: 1.0
field type: U

type.dpt.field.30.1010.i17.ActivationStateOfChannel18
comment: Activation state of channel 18
field type: B
type: Datapoint Type Field
type: NamedIndividual
field name: ActivationStateOfChannel18
includes KV pair: type.kvpair.30.1010.i17.0
includes KV pair: The visual effect of channel 18 is active = 1
field index: 17
field size: 1

Bank Holiday (No working day) = 0
value KNX: 0
value API: bankHoliday(NoWorkingDay)
type: NamedIndividual

Colour Set RGBW
type: Class
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  on property: has operation kind
  some values from: Class
property identifier annotation: 54
subject: CS_RGBW
subject: Colour Set RGBW
subject: 423.54
subject: 54
interface object type annotation: 423

Version
sub property of: applicationProgramData
range: positiveInteger
comment: An identifier to specify the (numerical) version of an application program.
type: DatatypeProperty
type: FunctionalProperty

Cool Stage A Actuator Calibration Mode
subclass of: Restriction
  has value: Bool
  on property: has datapoint type
subclass of: Function Point
type: Class

type.dpt.field.9.30.i0
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
field index: 0
includes digit: type.digit.f16 0 670433
field size: 16
field type: F
unit: MicroGM-PER-M3

type.dpt.field.249.x.i0
type: NamedIndividual
type: Datapoint Type Field
field type: A[n]
field index: 0
field size: 48
field string schema: raw
description: brightness colour temperature transition

Technical Room
type: LocationUsage
type: NamedIndividual
comment: A technical room is a space in a building that is used to host equipment. Preferably used with a Room.

Percent U8
has communication mode: S
type: NamedIndividual
type: DatapointType
datapoint type major number: 5
datapoint type minor number: 4
dpt bit size max: 8
label: Percent U8
is assembled with: Percent U8
subject: 5.4
subject: 5.004
subject: Percent U8
description: a point representing DPT 5.004: Percent U8

TempRoomSetpHeatEff
type: Class
subject: TempRoomSetpHeatEff
subject: 397.58
subject: 58
interface object type annotation: 397
subclass of: Restriction
  has value: Value Temp
  on property: has datapoint type
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
property identifier annotation: 58

has datapoint type
range: DatapointType
domain: Class
comment: To define the type (DPT) of a function point or datapoint. A function point represents runtime data, therefore the cardinality is of max 1 DPT. A datapoint represents config data, therefore the cardinality is of min 0 DPT (but it should be at least one).
type: ObjectProperty
inverse of: is datapoint type of

Succeeded
type: NamedIndividual
value KNX: 4
value API: Succeeded

type.dpt.field.205.17.i0.StatusCommand
field name: StatusCommand
field size: 8
field index: 0
field type: Z8
comment: standard Status/Command
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen

type.dpt.field.22.103.i1.ActiveMode
field index: 1
field name: ActiveMode
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: type.kvpair.22.103.i1.1
includes KV pair: type.kvpair.22.103.i1.0
comment: Active Mode
field type: B

Normal = 2
value KNX: 2
value API: normal
type: NamedIndividual

is product of
domain: Product
type: InverseFunctionalProperty
type: ObjectProperty
range: Equipment

Restriction
on property: pointName
has value: TempRoomSetpSetCoolShift

Installation
subclass of: Asset
subclass of: Restriction
  on property: comment
  all values from: string
subclass of: Class
comment: An installation consists of equipment that is assigned to a location. It is a deployed system (e.g. HVAC system or fire protection system) and consists of equipment (such as cabinets) and (application) functions that are used for a particular purpose. The (application) functions are hosted in this case at a location.
type: Class

type.dpt.field.21.2.i1.OwnIA
type: Datapoint Type Field
type: NamedIndividual
description: A datagram with the own Individual Address as Source Address has been received
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 1
field size: 1
field name: OwnIA

Value Frequency
has communication mode: S
dpt bit size max: 32
is assembled with: type.dpt.field.14.33.i0
type: NamedIndividual
type: DatapointType
comment: DPT 14.033: Value of frequency
subject: 14.33
subject: Value Frequency
subject: 14.033
label: Value Frequency
datapoint type major number: 14
datapoint type minor number: 33

type.dpt.field.206.102.i0.DHWmode
includes KV pair: type.kvpair.206.102.i0.3
includes KV pair: LegioProtect = 1
includes KV pair: Normal = 2
includes KV pair: Undefined = 0
includes KV pair: Off/FrostProtection = 4
field type: N
field size: 8
comment: DHW mode
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: DHWmode

type.dpt.field.21.1010.i5.ActivationStateOfChannel6
comment: Activation state of channel 6
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: type.kvpair.21.1010.i5.1
includes KV pair: type.kvpair.21.1010.i5.0
field index: 5
field type: B
field name: ActivationStateOfChannel6

Restriction
on property: has operation kind
qualified cardinality: 1

LegioProtect = 1
value KNX: 1
value API: legioProtect
type: NamedIndividual

The visual effect of channel 2 is inactive = 0
value KNX: 0
type: NamedIndividual
value API: theVisualEffectOfChannel2IsInactive

mass flow, 0,1 kg/h = 82
value KNX: 82
value API: massFlow,0,1Kgh
type: NamedIndividual

insufficient non volatile memory = 6
type: NamedIndividual
value KNX: 6
value API: insufficientNonVolatileMemory

Revoked
value API: Revoked
value KNX: 2
type: NamedIndividual

type.dpt.field.td.i1.ID
field name: ID
includes digit: type.digit.u4 1 15
field index: 1
field type: U
type: Datapoint Type Field
type: NamedIndividual
field size: 4
description: identifier of the timer, has to start with 1

first: Restriction
  has value: 153
  on property: property identifier

EnableTempRoomSetpAlt
type: Class
subject: 396.51
subject: EnableTempRoomSetpAlt
subject: 51
interface object type annotation: 396
subclass of: Restriction
  on property: has datapoint type
  has value: enable
label: EnableTempRoomSetpAlt
property identifier annotation: 51

deactivation of priority = 1
type: NamedIndividual
value API: deactivationOfPriority
value KNX: 1

Restriction
on property: interface object type
has value: 103

Converter Status
has communication mode: S
is assembled with: type.dpt.field.244.600.i6.Reserved
is assembled with: type.dpt.field.244.600.i1.PP
is assembled with: type.dpt.field.244.600.i3.FP
is assembled with: type.dpt.field.244.600.i5.HSswitch
is assembled with: type.dpt.field.244.600.i2.DP
is assembled with: type.dpt.field.244.600.i7.CM
is assembled with: type.dpt.field.244.600.i0.CF
is assembled with: type.dpt.field.244.600.i4.HSinhibit
comment: a point representing DPT 244.600: Converter Status
subject: Converter Status
subject: 244.600
datapoint type major number: 244
type: NamedIndividual
type: DatapointType
dpt bit size max: 16
datapoint type minor number: 600

Historical three-phase = 2
value KNX: 2
type: NamedIndividual
value API: historicalThree-phase

Bool Control
has communication mode: S
is assembled with: c
is assembled with: Bool
subject: 2.2
subject: 2.002
subject: Bool Control
comment: a point representing DPT 2.002: Bool Control
type: DatapointType
type: NamedIndividual
datapoint type major number: 2
dpt bit size max: 2
label: Bool Control
datapoint type minor number: 2

no = 0
type: NamedIndividual
value KNX: 0
value API: no

22.x
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.22.x.i0
datapoint type major number: 22
subject: 22.major
subject: 22.x
dpt bit size max: 16

No ramp = 0
type: NamedIndividual
value KNX: 0
value API: noRamp

type.dpt.field.9.23.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 16
unit: http://qudt.org/vocab/unit/K
field type: F
includes digit: type.digit.f16
field resolution: 0.01

emFillingRate
is assembled with: type.dpt.field.9.33.i0.fr.VAL
type: DatapointType
type: NamedIndividual
datapoint type major number: 9
dpt bit size max: 16
description: filling rate
datapoint type minor number: 33

FanManualEff
type: Class
label: FanManualEff
property identifier annotation: 67
subclass of: Restriction
  on property: hasQualityKind
  has value: qk eq fanmotor angularvelocity room
interface object type annotation: 397
subject: 67
subject: 397.67
subject: FanManualEff

StatusGO
type: Class
subclass of: Restriction
  on property: has operation kind
subclass of: Restriction
  has value: StatusGen
  on property: has datapoint type
subclass of: Restriction
  on property: has operation kind
subject: 52
subject: StatusGO
subject: 321.52
interface object type annotation: 321
comment: This DPA represents a generic Status (Z8), as described in KNX Vol 3/7/2, section 4.1.2. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring to the device: Bit 0) OutOfService (modeled by the state type tag:operationalStateOutOfService); Bit 1) Fault (modeled by the state type tag:operationalStateFaulty); Bit 2) Overridden (device being in maintenance mode, modeled by the state type tag:operationalStateMaintenance); Bit 3) InAlarm (modeled by the state type tag:operationalStateInAlarm); Bit 4) AlarmUnAck (modeled by the state type tag:operationalStateAlarmPending)
property identifier annotation: 52

Switch On Off
type: Class
subclass of: Restriction
  on property: has operation kind
subject: OOA
subject: 61
subject: 421.61
subject: Switch On Off
interface object type annotation: 421
property identifier annotation: 61

Restriction
has value: 399
on property: interface object type

type.dpt.field.27.1.i9.IOO10
field type: B
field index: 9
field size: 1
comment: Info On Off Output 10
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: output state is On = 1
includes KV pair: output state is Off = 0
field name: IOO10

has floor
domain: Class
sub property of: has location
comment: A strong OP relationship to express a relation to a floor contained in a location.
type: ObjectProperty
inverse of: isFloorOf
range: Floor

OccMode
has communication mode: S
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
comment: a point representing DPT 20.003: OccMode
datapoint type minor number: 3
is assembled with: type.dpt.field.20.3.i0
dpt bit size max: 8
label: OccMode
subject: 20.003
subject: OccMode
subject: 20.3

type.dpt.field.15.0.i5.D1
includes digit: type.digit.u4 0 9
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
description: digit 1 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
field index: 5
field name: D1
field size: 4

type.dpt.field.512.510.i4.smddb.OM
includes counter: type.dpt.field.512.510.i1.smddbc.OM CNT
field index: 4
description: list of operation mode elements
includes DPT field: type.dpt.field.ddbc.om
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>

Scheduler
comment: Scheduling in a building automation system is the process of systematically matching the use of heating, ventilation and air conditioning equipment with tenant occupancy schedules which is typically calendar-based.
subclass of: plantMngmtCtrl
type: Class

type.dpt.field.253.600.i5.cB
description: Shall specify whether the brightness shall be increased or decreased.
includes KV pair: Decrease = 0
includes KV pair: type.kvpair.increase
field name: cB
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 5
field type: B

Restriction
on class: Class
on property: has operation kind
qualified cardinality: 1

void device type = 255
value API: voidDeviceType
value KNX: 255
type: NamedIndividual

type.dpt.field.225.1.i0.Percent
type: Datapoint Type Field
type: NamedIndividual
description: percent
field index: 0
includes DPT: scaling
field size: 8
field name: Percent

detection not possible or error = 3
type: NamedIndividual
value KNX: 3
value API: detectionNotPossibleOrError

type.dpt.field.psc.i2.SQ SEL
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual
field index: 2
description: Selected power sequence container
field size: 4
field name: SQ_SEL
field type: U

Restriction
on property: property identifier
has value: 70

DALI Fade Time
has communication mode: S
datapoint type major number: 20
subject: 20.602
subject: DALI Fade Time
datapoint type minor number: 602
comment: a point representing DPT 20.602: DALI Fade Time
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.20.602.i0
dpt bit size max: 8
label: DALI Fade Time

Inactive = 0
type: NamedIndividual
value KNX: 0
value API: inactive

Restriction
on property: pointName
has value: HumRelSetpUserEff

type.dpt.field.246.600.i3.BatteryFullyCharged
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
field index: 3
field size: 1
description: Battery Fully Charged
field name: BatteryFullyCharged

The visual effect of channel 9 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel9IsInactive

DT in progress = 8
value KNX: 8
value API: dTInProgress
type: NamedIndividual

type.dpt.field.219.1.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 3
includes reserved bit: type.bit.reserved
field size: 5
field type: r
field name: Reserved

type.dpt.field.22.102.i3.ValveKick
includes KV pair: Not active = 0
includes KV pair: type.kvpair.active
type: Datapoint Type Field
type: NamedIndividual
field type: B
field index: 3
comment: Valve kick
field size: 1
field name: ValveKick

type.dpt.field.21.103.i1.SDHWLoadActive
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
comment: SDHWLoadActive
field type: B
field index: 1
field name: SDHWLoadActive
type: Datapoint Type Field
type: NamedIndividual
field size: 1

type.dpt.field.30.1010.i3.ActivationStateOfChannel4
includes KV pair: The visual effect of channel 4 is active = 1
includes KV pair: The visual effect of channel 4 is inactive = 0
type: Datapoint Type Field
type: NamedIndividual
comment: Activation state of channel 4
field type: B
field index: 3
field name: ActivationStateOfChannel4
field size: 1

Off/FrostProtect = 4
value API: offFrostProtect
value KNX: 4
type: NamedIndividual

Restriction
on property: has cardinality
has value: one

type.digit.u8 0 10
range max: 10
range min: 0
type: NamedIndividual

type.dpt.field.14.78.i0
includes digit: type.digit.f32
field resolution: 1.0
unit: http://qudt.org/vocab/unit/N
field size: 32
type: Datapoint Type Field
type: NamedIndividual
comment: weight
field index: 0
field type: F

FlowRate m3/h
has communication mode: S
type: NamedIndividual
type: DatapointType
comment: a point representing DPT 13.002: FlowRate m3/h
subject: FlowRate m3/h
subject: 13.2
subject: 13.002
datapoint type minor number: 2
is assembled with: type.dpt.field.13.2.i0
datapoint type major number: 13
dpt bit size max: 32

Value MagnetomotiveForce
has communication mode: S
datapoint type major number: 14
dpt bit size max: 32
label: Value MagnetomotiveForce
type: NamedIndividual
type: DatapointType
subject: 14.050
subject: Value MagnetomotiveForce
subject: 14.50
is assembled with: type.dpt.field.14.50.i0
datapoint type minor number: 50
description: DPT 14.050: Value of magneto motive force

type.dpt.field.244.600.i1.PP
includes KV pair: Unknown = 0
includes KV pair: Test pending = 2
includes KV pair: type.kvpair.testNotPending
description: Partial Duration Test Pending
field index: 1
field type: N
field name: PP
type: Datapoint Type Field
type: NamedIndividual
field size: 2

is implemented by
range: Application Program
domain: Functionality
type: FunctionalProperty
type: ObjectProperty

Standby = 2
value API: standby
type: NamedIndividual
value KNX: 2
is applicable datapoint enum of: hvacModeStandby

Restriction
has value: many
on property: has cardinality

has adjacent location
comment: A relation between two locations that share a common interface such as a wall or door, but do not intersect.
domain: Location
type: IrreflexiveProperty
type: ObjectProperty
type: SymmetricProperty
sub property of: refers to
range: Location

rest: nil
first: Restriction
  has value: 417
  on property: interface object type

first: Restriction
  on property: interface object type
  has value: 160
rest: nil

type.dpt.field.11.1.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 4
field name: Reserved
field index: 3
field type: r

type.dpt.field.513.500.i1.rol.C1
type: Datapoint Type Field
type: NamedIndividual
includes KV pair: Consumer
includes KV pair: type.kvpair.rolNone
includes KV pair: type.kvpair.rolProducer
includes KV pair: type.kvpair.rolConsumerAndProducer
description: roles for commodity GAS
field name: C1
field size: 2
field index: 1
field type: U

Restriction
has value: many
on property: has cardinality

The visual effect of channel 8 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel8IsActive
value KNX: 1

type.dpt.field.219.1.i1.AlarmUnAck
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
comment: AlarmUnAck
field type: B
field index: 1
field size: 1
field name: AlarmUnAck
type: Datapoint Type Field
type: NamedIndividual

output state is Off = 0
type: NamedIndividual
value KNX: 0
value API: outputStateIsOff

type.dpt.field.250.600.i0.BrightnessStepValidity
includes KV pair: valid = 1
includes KV pair: type.kvpair.invalid
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field type: B
field name: BrightnessStepValidity
field size: 1
comment: CB and Step Code Brightness Validity

Restriction
has value: many
on property: has cardinality

type.dpt.field.14.73.i0
unit: V-PER-K
field size: 32
field type: F
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
comment: thermoelectric power
field index: 0

type.dpt.field.14.44.i0
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field size: 32
comment: magnetic field strength
field index: 0
field type: F
unit: A-PER-M
includes digit: type.digit.f32

2 stage = 2
value API: 2Stage
value KNX: 2
type: NamedIndividual

volume flow, 100 l/min = 70
value KNX: 70
type: NamedIndividual
value API: volumeFlow,100Lmin

volume flow, 100 ml/s = 77
value API: volumeFlow,100Mls
type: NamedIndividual
value KNX: 77

is location usage of
type: ObjectProperty
range: Location
domain: LocationUsage
sub property of: isTagOf

type.dpt.field.525.500.i4.fv.Lower 68PPR
description: The lower boundary of the range with 68 % certainty the power value is in it
field index: 4
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field name: Lower_68PPR
includes DPT: Power

type.dpt.field.200.101.i0.StatusCommand
field size: 8
type: Datapoint Type Field
type: NamedIndividual
includes DPT: StatusGen
field index: 0
field type: Z8
comment: standard Status/Command
field name: StatusCommand

type.dpt.field.22.1000.i4.RF
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
comment: RF
field index: 4
field name: RF

Restriction
on property: interface object type
has value: 423

The visual effect of channel 11 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel11IsInactiv

Air Damper = 1
value API: airDamper
value KNX: 1
type: NamedIndividual

Restriction
has value: 57
on property: property identifier

The visual effect of channel 15 is inactive = 0
type: NamedIndividual
value KNX: 0
value API: theVisualEffectOfChannel15IsInactiv

Cloudy = 5
value API: cloudy
value KNX: 5
type: NamedIndividual

StatusCPM
has communication mode: LTE
label: StatusCPM
datapoint type minor number: 102
comment: a point representing DPT 209.102: StatusCPM
dpt bit size max: 24
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.209.102.i2.Reserved
is assembled with: type.dpt.field.209.102.i1.NoCoolAvailable
is assembled with: type.dpt.field.209.102.i0.TempFlowValid
is assembled with: type.dpt.field.209.102.i1.Fault
is assembled with: type.dpt.field.209.102.i0.OffPerm
is assembled with: type.dpt.field.209.102.i3.TempFlowProdSegmC
subject: 209.102
subject: StatusCPM
datapoint type major number: 209

has outside
sub property of: has location
comment: A general OP relationship to express a relation of location individuals to individuals which are outside of a particular building. The location to be outside (as the domain) MUST fulfil the boundary conditions to be allowed outside. Example is a relation to an outdoor location which does not directly belong to a building (e.g. garden).
range: Outside
inverse of: isOutsideOf
type: ObjectProperty

value before locking = 6
type: NamedIndividual
value KNX: 6
value API: valueBeforeLocking

HeatCoolMode
type: Class
subject: 151
subject: HeatCoolMode
subject: 261.151
interface object type annotation: 261
label: HeatCoolMode
subclass of: Restriction
  on property: has datapoint type
  has value: Heat/Cool
property identifier annotation: 151

HVACModeUserEff
type: Class
label: HVACModeUserEff
subject: HVACModeUserEff
subject: 52
subject: 397.52
subclass of: Restriction
  on property: has datapoint type
  has value: HVACMode
interface object type annotation: 397
property identifier annotation: 52

valid = 0
value API: valid
value KNX: 0
type: NamedIndividual

Unit
comment: (SI) unit class for function points (FP) and datapoints.
type: Class

Restriction
on property: interface object type
has value: 101

Restriction
on property: pointName
has value: ActTargetFanSpeedEff

type.dpt.field.240.800.i4.HeightPosition
comment: Height Position
field type: U
type: Datapoint Type Field
type: NamedIndividual
field name: HeightPosition
field resolution: 0.3921566
unit: PERCENT
field size: 8
includes digit: type.digit.u8
field index: 4

Restriction
has value: one
on property: has cardinality

Restriction
on property: pointName
has value: AbsSetvalueControl

Unlocked State
description: This state type expresses that an equipment is in an unlocked state. Typically, this means that the equipment reacts to new input commands as intended. This state type is the inverse of the 'locked' state type.
type: State Type
type: NamedIndividual

type.dpt.field.21.105.i0.Fault
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: Fault
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field type: B
description: Fault
field size: 1

Fan only = 9
value API: fanOnly
type: NamedIndividual
value KNX: 9

type.dpt.field.14.64.i0
field size: 32
field type: F
unit: W-PER-M2
includes digit: type.digit.f32
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
description: sound intensity
field index: 0

Restriction
has value: 121
on property: interface object type

type.dpt.field.275.100.i3.TempSetpComf
field index: 3
field type: F
field name: TempSetpComf
unit: DEG C
field size: 16
field resolution: 0.01
includes digit: type.digit.f16 neg27300 65534
type: Datapoint Type Field
type: NamedIndividual
comment: room temperature setpoint comfort

type.dpt.field.22.101.i3.TempReturnLimit
field name: TempReturnLimit
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
field index: 3
comment: TempReturnLimit
field size: 1
type: Datapoint Type Field
type: NamedIndividual

Restriction
has value: 72
on property: property identifier

type.digit.u5 0 24
range min: 0
type: NamedIndividual
range max: 24

logical function AND = 1
type: NamedIndividual
value API: logicalFunctionAND
value KNX: 1

rest: nil
first: Restriction
  has value: one
  on property: has cardinality

type.dpt.field.20.113.i0
includes KV pair: type.kvpair.20.113.i0.0
includes KV pair: alternative setpoint = 1
includes KV pair: building protection setpoint = 2
field size: 8
comment: StatusRoomSetup
field type: N
type: Datapoint Type Field
type: NamedIndividual
field index: 0

Emergency Heat = 8
value KNX: 8
value API: emergencyHeat
type: NamedIndividual

type.dpt.field.8.4.i0
field size: 16
type: Datapoint Type Field
type: NamedIndividual
field type: V
unit: MilliSEC
field index: 0
includes digit: type.digit.s16
field resolution: 100.0

CombinedStatus_RTSM
type: Class
subclass of: Restriction
  has value: Combined Status RTSM
  on property: has datapoint type
property identifier annotation: 92
interface object type annotation: 398
subject: 398.92
subject: 92
subject: CombinedStatus_RTSM

Absolute Set Value Control Blue
type: Class
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
subject: 423.64
subject: Absolute Set Value Control Blue
subject: 64
subject: ASV_B
label: Absolute Set Value Control Blue
interface object type annotation: 423
property identifier annotation: 64

Switching
type: Class
subject: GPDO
comment: Application function for generic 'switch control'.
subclass of: Restriction
  on property: has function point
  on class: Switch Current Status
  qualified cardinality: 1
subclass of: switchCtrl

Restriction
qualified cardinality: 1
on property: certfication status
on data range: string

Restriction
has value: many
on property: has cardinality

Restriction
on property: interface object type
has value: 423

scene B = 1
value API: sceneB
value KNX: 1
type: NamedIndividual

ActTargetFanSpeed
type: Class
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  on property: has operation kind
  some values from: Class
interface object type annotation: 399
subject: ActTargetFanSpeed
subject: 399.112
subject: 112
property identifier annotation: 112

mass flow, 10 kg/h = 84
type: NamedIndividual
value API: massFlow,10Kgh
value KNX: 84

Tariff ActiveEnergy
has communication mode: S
datapoint type major number: 235
is assembled with: type.dpt.field.235.1.i3.Tariff
is assembled with: type.dpt.field.235.1.i4.ActiveElectricalEnergy
is assembled with: type.dpt.field.235.1.i2.Reserved
is assembled with: type.dpt.field.235.1.i1.E
is assembled with: type.dpt.field.235.1.i0.T
label: Tariff ActiveEnergy
type: NamedIndividual
type: DatapointType
datapoint type minor number: 1
subject: 235.1
subject: 235.001
subject: Tariff ActiveEnergy
dpt bit size max: 48
description: a point representing DPT 235.001: Tariff ActiveEnergy

Restriction
on property: pointName
has value: SwitchOnOffForced

type.dpt.field.21.103.i3.Reserved
includes reserved bit: type.bit.reserved
field size: 5
field index: 3
field type: r
field name: Reserved
type: Datapoint Type Field
type: NamedIndividual

no error = 0
type: NamedIndividual
value API: noError
value KNX: 0

type.dpt.field.244.600.i7.CM
includes KV pair: PDT in progress = 9
includes KV pair: FT in progress = 7
includes KV pair: type.kvpair.244.600.i7.2
includes KV pair: type.kvpair.244.600.i7.3
includes KV pair: type.kvpair.244.600.i7.4
includes KV pair: DT in progress = 8
includes KV pair: Unknown = 0
includes KV pair: Extended emergency mode active = 6
includes KV pair: Emergency mode active = 5
includes KV pair: type.kvpair.244.600.i7.1
field name: CM
field type: N
comment: Converter Mode according to the DALI converter state machine
type: Datapoint Type Field
type: NamedIndividual
field size: 4
field index: 7

Restriction
on property: interface object type
has value: 804

Direction 1
type: Datapoint Type Field
type: NamedIndividual
field name: direction1
field index: 0
field size: 1
includes DPT: Up Down

volume flow, 0,1 l/min = 67
type: NamedIndividual
value KNX: 67
value API: volumeFlow,0,1Lmin

Undefined = 0
type: NamedIndividual
value KNX: 0
value API: undefined

type.dpt.field.14.36.i0
field type: F
field index: 0
field resolution: 1.0
comment: heat flow rate
field size: 32
unit: http://qudt.org/vocab/unit/W
type: Datapoint Type Field
type: NamedIndividual
includes digit: type.digit.f32

Microwave Oven
comment: A microwave oven (commonly referred to as a microwave) is an electric oven (EN 50523 home appliance device) that heats and cooks food by exposing it to electromagnetic radiation in the microwave frequency range.
type: NamedIndividual
type: EquipmentType

Ramp
has communication mode: S
subject: 1.004
subject: Ramp
subject: 1.4
description: a point representing DPT 1.004: Ramp
type: NamedIndividual
type: DatapointType
datapoint type minor number: 4
is assembled with: Ramp
datapoint type major number: 1
dpt bit size max: 1

Peak Event
has communication mode: S
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
comment: a point representing DPT 20.1207: Peak Event
subject: Peak Event
subject: 20.1207
datapoint type major number: 20
datapoint type minor number: 1207
is assembled with: type.dpt.field.20.1207.i0

process fault / controller fault = 2
value KNX: 2
type: NamedIndividual
value API: processFaultControllerFault

PDT in progress = 9
type: NamedIndividual
value KNX: 9
value API: pDTInProgress

Restriction
has value: Info On Off
on property: pointName

New / Lock (S-FSK) - Associated (G3-PLC) = 1
value API: newLock(S-FSK)-Associated(G3-PLC)
value KNX: 1
type: NamedIndividual

type.dpt.field.209.100.i3.OffPerm
comment: boiler sequence is permanently off (manual switch or failure)
includes DPT: Bool
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field name: OffPerm
field index: 3

type.dpt.field.14.24.i0
type: NamedIndividual
type: Datapoint Type Field
unit: http://qudt.org/vocab/unit/C
field index: 0
field type: F
includes digit: type.digit.f32
description: electric flux
field resolution: 1.0
field size: 32

Calculated = 1
type: NamedIndividual
value KNX: 1
value API: calculated

Consumer = 0
type: NamedIndividual
value API: consumer
value KNX: 0

type.dpt.field.21.106.i0.Fault
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: Fault
field type: B
includes KV pair: type.kvpair.false
includes KV pair: type.kvpair.true
comment: Fault
field size: 1

Input Source
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 1.14
subject: 1.014
subject: Input Source
datapoint type major number: 1
dpt bit size max: 1
is assembled with: Input Source
comment: a point representing DPT 1.014: Input Source
label: Input Source
datapoint type minor number: 14

WindowStatusEff
type: Class
interface object type annotation: 398
subject: 91
subject: WindowStatusEff
subject: 398.91
property identifier annotation: 91

Air Handling Unit
description: An Air Handling Unit (AHU) is an equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system.
type: NamedIndividual
type: EquipmentType

Restriction
on property: interface object type
has value: 100

Restriction
has value: 398
on property: interface object type

first: Restriction
  on property: interface object type
  has value: 397
rest: nil

type.dpt.field.15.0.i9.D5
field index: 9
field type: U
field resolution: 1.0
includes digit: type.digit.u4 0 9
type: Datapoint Type Field
type: NamedIndividual
comment: digit 5 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
field size: 4
field name: D5

type.dpt.field.512.506.i4.smombc.OM
includes counter: type.dpt.field.512.506.i1.smombc.OM CNT
field index: 4
field name: OM
description: list of operation modes
type: Datapoint Type Field
type: NamedIndividual
includes DPT field: type.dpt.field.ombc.om
field type: D<n>

no action (dummy) = 0
type: NamedIndividual
value KNX: 0
value API: noAction(dummy)

type.dpt.pe.i0
type: Datapoint Type Field
type: NamedIndividual
field type: D<n>
field index: 0
includes DPT field: type.dpt.pe.i1.DUR
includes DPT field: type.dpt.pe.i0.LR
description: power envelop element

Direction 1 Control
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: Direction 1
is assembled with: c
subject: 2.8
subject: 2.008
subject: Direction 1 Control
datapoint type minor number: 8
datapoint type major number: 2
dpt bit size max: 2
label: Direction 1 Control
comment: a point representing DPT 2.008: Direction 1 Control

notice PE1 in progress = 1
value KNX: 1
value API: noticePE1InProgress
type: NamedIndividual

Load Management = 40
value API: loadManagement
type: NamedIndividual
value KNX: 40

Restriction
has value: 63
on property: property identifier

type.dpt.field.250.600.i6.StepCodeColourTemperature
includes digit: type.digit.u3
comment: Step Code Colour Temperature
field type: U
field resolution: 1.0
field size: 3
field name: StepCodeColourTemperature
type: Datapoint Type Field
type: NamedIndividual
field index: 6

type.dpt.field.229.x.i0
type: Datapoint Type Field
type: NamedIndividual
field type: A[n]
field index: 0
comment: 4-1-1 byte combined information
field size: 48
field string schema: raw

Restriction
on property: has operation kind
qualified cardinality: 1

Building Protection = 4
value API: buildingProtection
is applicable datapoint enum of: HVAC Mode Protection
value KNX: 4
type: NamedIndividual

type.dpt.field.512.512.i2.uf.FE
includes counter: type.dpt.field.512.512.i1.uf.FE CNT
field name: FE
includes DPT field: type.dpt.field.uf.i0
description: list of usage forecast elements
type: Datapoint Type Field
type: NamedIndividual
field index: 2
field type: D<n>

type.dpt.field.14.13.i0
includes digit: type.digit.f32
unit: C-PER-M3
comment: charge density (volume)
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 32
field type: F

type.dpt.field.218.1.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: StatusCommand
field type: Z8
field size: 8
comment: standard Status/Command
includes DPT: StatusGen

type.dpt.field.20.100.i0
type: NamedIndividual
type: Datapoint Type Field
includes KV pair: type.kvpair.20.100.i0.0
includes KV pair: type.kvpair.20.100.i0.2
includes KV pair: oil = 1
includes KV pair: type.kvpair.20.100.i0.3
field index: 0
field size: 8
comment: FuelType
field type: N

all windows closed = 0
value API: allWindowsClosed
type: NamedIndividual
value KNX: 0

Standard three-phase = 4
type: NamedIndividual
value API: standardThree-phase
value KNX: 4

type.dpt.field.14.50.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
unit: http://qudt.org/vocab/unit/A
field type: F
description: magneto motive force
includes digit: type.digit.f32

Water Temperature Control
type: Class
subclass of: Water Control
comment: Application Functions that controls the quantity 'water temperature'.

Fluid
comment: In physics, a fluid is a liquid, gas, or other material that continuously deforms (flows) under an applied shear stress, or external force.
type: NamedIndividual
type: Phenomenon

mass, 10000 kg = 31
type: NamedIndividual
value KNX: 31
value API: mass,10000Kg

Outside Temperature
subclass of: Function Point
type: Class

cooling = 0
type: NamedIndividual
value KNX: 0
value API: cooling

Volume Flow Rate
type: NamedIndividual
type: Quantity Kind
description: Volumetric Flow Rate, (also known as volume flow rate, rate of fluid flow or volume velocity) is the volume of fluid which passes through a given surface per unit time.

emStateMachineOMBC
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.512.506.i3.smombc.Reserved
is assembled with: type.dpt.field.512.506.i2.smombc.TRAN CNT
is assembled with: type.dpt.field.512.506.i0.smombc.COM
is assembled with: type.dpt.field.512.506.i1.smombc.OM CNT
is assembled with: type.dpt.field.512.506.i4.smombc.OM
is assembled with: type.dpt.field.512.506.i5.smombc.TRAN
datapoint type minor number: 506
dpt bit size max: 1792
datapoint type major number: 512

type.dpt.field.7.7.i0
unit: HR
includes digit: type.digit.u16
field size: 16
field type: U
field resolution: 1.0
type: Datapoint Type Field
type: NamedIndividual
field index: 0

Ramp
label: Ramp
includes KV pair: No ramp = 0
includes KV pair: type.kvpair.1.4.i0.1
type: Datapoint Type Field
type: NamedIndividual
field size: 1
field index: 0
field type: B

Value Activity
has communication mode: S
type: DatapointType
type: NamedIndividual
subject: 14.003
subject: Value Activity
subject: 14.3
datapoint type major number: 14
dpt bit size max: 32
label: Value Activity
description: DPT 14.003: Value of activity (radioactivity)
datapoint type minor number: 3
is assembled with: type.dpt.field.14.3.i0

Binary Value
type: Datapoint Type Field
type: NamedIndividual
field name: binaryValue
includes DPT: Binary Value
field index: 0
field size: 1

Restriction
min qualified cardinality: 1
on property: is assembled with
on class: Datapoint Type Field

Restriction
has value: 414
on property: interface object type

The visual effect of channel 3 is active = 1
value API: theVisualEffectOfChannel3IsActive
value KNX: 1
type: NamedIndividual

Emergency Cool Mode = 16
value API: emergencyCoolMode
value KNX: 16
type: NamedIndividual

rest:
  first: Restriction
    has value: 418
    on property: interface object type
  rest: nil

volume flow, 10 ml/s = 76
type: NamedIndividual
value KNX: 76
value API: volumeFlow,10Mls

Relative timestamp = 4
value KNX: 4
value API: relativeTimestamp
type: NamedIndividual

Restriction
on property: interface object type
has value: 399

occupied = 0
type: NamedIndividual
value KNX: 0
value API: occupied

C-PER-M3
symbol: C/m³
type: NamedIndividual
type: Unit

type.dpt.field.513.500.i0.rol.C0
includes KV pair: type.kvpair.rolNone
includes KV pair: type.kvpair.rolConsumerAndProducer
includes KV pair: Consumer
includes KV pair: type.kvpair.rolProducer
description: roles for commodity ELECTRICITY
field size: 2
field type: U
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: C0

rest: nil
first: Restriction
  on property: interface object type
  has value: 399

Restriction
on property: interface object type
has value: 398

DateTime State
has communication mode: S
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.265.11.i1.Reserved
is assembled with: type.dpt.field.265.11.i0.BinaryInformation
is assembled with: type.dpt.field.265.11.i2.DateAndTime
subject: 265.11
subject: 265.011
subject: DateTime State
comment: a point representing DPT 265.011: DateTime State
label: DateTime State
datapoint type minor number: 11
dpt bit size max: 72
datapoint type major number: 265

security mode
comment: The current state of a function point according to its security, used from installations that specifies an explicit and (by an installer) intended security behavior for the communication.
type: DatatypeProperty
type: FunctionalProperty
sub property of: function point data

Restriction
has value: 802
on property: interface object type

The visual effect of channel 9 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel9IsInactive
value KNX: 0

ForceSignCool
has communication mode: LTE
datapoint type major number: 21
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.21.101.i1.Reserved
is assembled with: type.dpt.field.21.101.i0.ForceRequest
datapoint type minor number: 101
dpt bit size max: 8
subject: ForceSignCool
subject: 21.101
comment: a point representing DPT 21.101: ForceSignCool

type.dpt.pe.i0.LR
description: limit range defining upper and lower power values
field name: LR
type: Datapoint Type Field
type: NamedIndividual
field size: 32
includes DPT: emPowerRange
field index: 0

Restriction
on property: has operation kind
qualified cardinality: 1

field type
type: DatatypeProperty
type: FunctionalProperty
sub property of: datapointTypeDataField
comment: Field type, used to define a (coding) type of a KNX data field as part of an entire datapoint type, specified in KNX (not all types are used in the KIM). A Character A[n] String of n characters B Boolean / Bit set C Control E Exponent F Floating point value M Mantissa N eNumeration r Reserved bit or field S Sign U Unsigned value V 2's Complement signed value Z8 Standardised Status/Command (8 bit)

Staircase Status
subclass of: Function Point
subclass of: Restriction
  on property: observesPhenomenonQualityKind
  has value: qk ph light illuminance
type: Class

Haystack
type: NamedIndividual
type: Protocol

property identifier
range: unsignedByte
comment: In KNX used (numerical) identifier to address a specific property as part of an interface object. The range xsd:unsignedByte supports exactly the KNX value range from 0 to 255.
type: FunctionalProperty
type: DatatypeProperty
domain: Datapoint

datapoint type minor number
comment: The trailing number of the minor datapoint type (DPT) in bits, specified in KNX with a numerical scheme. The minor type must be present for sub types but not for a major type. The range is used to include 0 (the KNX DPT numbering scheme starts at 0).
type: FunctionalProperty
type: DatatypeProperty
sub property of: datapoint type
range: nonNegativeInteger

15 s = 6
value API: 15S
type: NamedIndividual
value KNX: 6

type.dpt.field.21.1001.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
includes reserved bit: type.bit.reserved
field size: 5
field name: Reserved
field index: 3
field type: r

is point priority of
domain: Origin
type: ObjectProperty
type: InverseFunctionalProperty
sub property of: isTagOf
range: Operation Kind

type.dpt.field.246.x.i0
type: Datapoint Type Field
type: NamedIndividual
comment: Battery Information
field type: A[n]
field index: 0
field size: 16
field string schema: raw

Value 1 Ucount
has communication mode: S
subject: Value 1 Ucount
subject: 5.10
subject: 5.010
type: NamedIndividual
type: DatapointType
datapoint type major number: 5
comment: a point representing DPT 5.010: Value 1 Ucount
is assembled with: Value 1 U Count
dpt bit size max: 8
label: Value 1 Ucount
datapoint type minor number: 10

Delta Volume Cubic Metre
has communication mode: S
label: Delta Volume Cubic Metre
datapoint type major number: 13
type: DatapointType
type: NamedIndividual
subject: 13.1201
subject: Delta Volume Cubic Metre
dpt bit size max: 32
is assembled with: type.dpt.field.13.1201.i0
datapoint type minor number: 1201
comment: a point representing DPT 13.1201: Delta Volume Cubic Metre

emPowerEnvelopeInstruction
is assembled with: type.dpt.field.512.503.i2.pei.IT
is assembled with: type.dpt.field.512.503.i5.pei.PC ID
is assembled with: type.dpt.field.512.503.i4.pei.ET
is assembled with: type.dpt.field.512.503.i3.pei.Reserved
is assembled with: type.dpt.field.512.503.i7.pei.PE CNT
is assembled with: type.dpt.field.512.503.i0.pei.ID
is assembled with: type.dpt.field.512.503.i1.pei.AC
is assembled with: type.dpt.field.512.503.i8.pei.PWR ENV
is assembled with: type.dpt.field.512.503.pei.Reserved
type: NamedIndividual
type: DatapointType
datapoint type minor number: 503
dpt bit size max: 1792
datapoint type major number: 512

Setpoint value
type: Point Function
type: NamedIndividual
description: A setpoint is classified as an indirect adjustment, such as Point representing the desired or target value for a process value of a system.

Wind Speed Z
has communication mode: LTE
datapoint type major number: 203
datapoint type minor number: 101
dpt bit size max: 24
comment: a point representing DPT 203.101: Wind Speed Z
subject: 203.101
subject: Wind Speed Z
label: Wind Speed Z
type: DatapointType
type: NamedIndividual
is assembled with: type.dpt.field.203.101.i0.StatusCommand
is assembled with: type.dpt.field.203.101.i1.WindSpeed

Restriction
on property: pointName
has value: Relative Set Value Control Green

Restriction
has value: many
on property: has cardinality

TimePeriodMsec
has communication mode: S
type: NamedIndividual
type: DatapointType
subject: 7.2
subject: TimePeriodMsec
subject: 7.002
datapoint type minor number: 2
dpt bit size max: 16
is assembled with: type.dpt.field.7.2.i0
description: a point representing DPT 7.002: TimePeriodMsec
label: TimePeriodMsec
datapoint type major number: 7

Restriction
on property: pointName
has value: TimedStartStop

The visual effect of channel 10 is active = 1
value KNX: 1
value API: theVisualEffectOfChannel10IsActive
type: NamedIndividual

Absolute Set Value Control White
type: Class
label: Absolute Set Value Control White
subject: ASV_W
subject: Absolute Set Value Control White
subject: 423.67
subject: 67
interface object type annotation: 423
property identifier annotation: 67

Light Switching Sensor Basic
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: ControlModeUser
subclass of: Restriction
  on property: isComposedByOutput
  max qualified cardinality: 1
  on class: TimedStartStop
type: Class
label: Light Switching Sensor Basic
interface object type annotation: 421
subject: LSSB
subject: Light Switching Sensor Basic
subject: 421

OverloadDetection
type: Class
label: OverloadDetection
subject: 418.57
subject: OverloadDetection
subject: 57
interface object type annotation: 418
property identifier annotation: 57

type.dpt.field.522.500.i4.si.CID
includes digit: type.digit.u4 1 15
description: sequence container ID
field index: 4
field name: CID
field type: U
type: Datapoint Type Field
type: NamedIndividual
field size: 4

Restriction
on property: property identifier
has value: 74

12.x
has communication mode: S
subject: 12.x
subject: 12.major
label: 12.x
dpt bit size max: 32
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.12.x.i0
datapoint type major number: 12

comfort prolongation User active = 1
value KNX: 1
type: NamedIndividual
value API: comfortProlongationUserActive

Restriction
on property: pointName
has value: ComfortPushbutton

type.dpt.field.27.1.i15.IOO16
field name: IOO16
comment: Info On Off Output 16
field index: 15
type: Datapoint Type Field
type: NamedIndividual
field size: 1
includes KV pair: output state is On = 1
includes KV pair: output state is Off = 0
field type: B

Restriction
has value: 399
on property: interface object type

rest: nil
first: Restriction
  has value: many
  on property: has cardinality

Restriction
has value: one
on property: has cardinality

type.dpt.field.512.507.i2.smfrbc.TRAN CNT
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual
field index: 2
field name: TRAN_CNT
field size: 4
field type: U
description: number of transtions

The visual effect of channel 1 is active = 1
value KNX: 1
type: NamedIndividual
value API: theVisualEffectOfChannel1IsActive

type.dpt.field.30.1010.i16.ActivationStateOfChannel17
field index: 16
field type: B
field size: 1
field name: ActivationStateOfChannel17
includes KV pair: type.kvpair.30.1010.i16.0
includes KV pair: The visual effect of channel 17 is active = 1
type: Datapoint Type Field
type: NamedIndividual
comment: Activation state of channel 17

type.digit.u8 0 44
range min: 0
range max: 44
type: NamedIndividual

type.dpt.field.222.101.i2.TempSetpShiftComf
includes digit: type.digit.f16
field resolution: 0.01
type: Datapoint Type Field
type: NamedIndividual
field name: TempSetpShiftComf
field size: 16
unit: http://qudt.org/vocab/unit/K
field type: F
comment: TempSetpShiftComf
field index: 2

Value Compressibility
has communication mode: S
subject: 14.14
subject: 14.014
subject: Value Compressibility
comment: DPT 14.014: Value of compressibility
type: DatapointType
type: NamedIndividual
label: Value Compressibility
is assembled with: type.dpt.field.14.14.i0
datapoint type major number: 14
dpt bit size max: 32
datapoint type minor number: 14

CFL, leading = 5
value API: cFL,Leading
type: NamedIndividual
value KNX: 5

type.dpt.field.265.12.i0.BinaryInformation
field name: BinaryInformation
type: Datapoint Type Field
type: NamedIndividual
comment: Binary Information
includes DPT: Invert
field index: 0
field size: 1

TempDischargeAir
type: Class
subject: 51
subject: TempDischargeAir
subject: 328.51
subclass of: Restriction
  has value: qk ph air temperature supplysection
  on property: hasQualityKind
property identifier annotation: 51
label: TempDischargeAir
interface object type annotation: 328

oBIX
type: Protocol
type: NamedIndividual

237.x
has communication mode: S
datapoint type major number: 237
type: NamedIndividual
type: DatapointType
is assembled with: type.dpt.field.237.x.i0
subject: 237.x
subject: 237.major
dpt bit size max: 16

Tag
comment: A tag is an information that describes the data or content that it is assigned to. Tags are typically nonhierarchical keywords (individuals) used, for example, for datapoints, application functions but also for internet bookmarks, digital images, videos, files and so on.
type: Class
subclass of: Thing

Temperature
type: Quantity Kind
type: NamedIndividual
description: Temperature is a physical property of matter that quantitatively expresses the common notions of hot and cold.

type.dpt.field.30.1010.i8.ActivationStateOfChannel9
comment: Activation state of channel 9
field type: B
includes KV pair: The visual effect of channel 9 is inactive = 0
includes KV pair: type.kvpair.30.1010.i8.1
field index: 8
field name: ActivationStateOfChannel9
type: Datapoint Type Field
type: NamedIndividual
field size: 1

UElCurrentmA
has communication mode: S
subject: 7.012
subject: UElCurrentmA
subject: 7.12
description: a point representing DPT 7.012: UElCurrentmA
dpt bit size max: 16
is assembled with: type.dpt.field.7.12.i0
datapoint type major number: 7
type: NamedIndividual
type: DatapointType
datapoint type minor number: 12

The visual effect of channel 21 is active = 1
value KNX: 1
type: NamedIndividual
value API: theVisualEffectOfChannel21IsActive

type.dpt.field.265.1.i2.DateAndTime
description: Date and Time
field name: DateAndTime
type: Datapoint Type Field
type: NamedIndividual
includes DPT: DateTime
field size: 64
field index: 2

occupancy at least from one presence detector = 1
value KNX: 1
value API: occupancyAtLeastFromOnePresenceDete
type: NamedIndividual

RF ModeSelect
has communication mode: S
datapoint type minor number: 1002
dpt bit size max: 8
type: DatapointType
type: NamedIndividual
datapoint type major number: 20
comment: a point representing DPT 20.1002: RF ModeSelect
subject: 20.1002
subject: RF ModeSelect
label: RF ModeSelect
is assembled with: type.dpt.field.20.1002.i0

type.dpt.field.frbc.om.i0.ID
field type: U
includes digit: type.digit.u4
type: Datapoint Type Field
type: NamedIndividual
field size: 4
description: identifier of operation mode element
field index: 0
field name: ID

Inactive State
type: State Type
type: NamedIndividual
description: This state type expresses that an equipment, an alarm or a certain situation is inactive. An inactive equipment is not working, which means it cannot fulfill its intended functionality. An inactive alarm means that the alarm state was not triggered. Finally, an inactive situation means that a certain state has not been reached. The tag 'Inactive State' is often used for situations that feature an enumeration of possible states (e.g. operational states, control modes, HVAC modes, ...) to make a boolean statement about one of these states. The state type 'Inactive State' is the inverse of the 'Active State' state type.

type.dpt.field.27.1.i26.MaskBitIOO11
description: Mask Bit Info On Off Output 11
type: Datapoint Type Field
type: NamedIndividual
field name: MaskBitIOO11
field size: 1
includes KV pair: type.kvpair.outputStateValid
includes KV pair: type.kvpair.outputStateNotValid
field type: B
field index: 26

Binary Value
has communication mode: S
comment: a point representing DPT 1.006: Binary Value
type: DatapointType
type: NamedIndividual
subject: 1.6
subject: 1.006
subject: Binary Value
dpt bit size max: 1
label: Binary Value
datapoint type major number: 1
datapoint type minor number: 6
is assembled with: Binary Value

Cloudless = 0
value API: cloudless
type: NamedIndividual
value KNX: 0

send if value changed during powerdown = 2
type: NamedIndividual
value API: sendIfValueChangedDuringPowerdown
value KNX: 2

Restriction
on property: property identifier
has value: 64

Room Segment
subclass of: Space
label: Raumteil @de
comment: A room segment is an indoor space that represents a subdivision of a room, it can be further subdivided into locations of type room segment.
type: Class

Building
comment: A building is a structure with a roof and walls standing more or less permanently in one place, such as a house or factory.
type: Locality
type: NamedIndividual

rest:
  first: Restriction
    on property: interface object type
    has value: 397
  rest: nil
first: Restriction
  on property: property identifier
  has value: 53