Cool Stage A Actuator Fault
Dim Send Style
target position is reached = 1
Substance with definite shape and volume
Solid
a point representing DPT 30.1010: Channel Activation 24
Channel Activation 24
DPT 14.071: Value of thermal capacity
Value Thermal Capacity
volume flow, 0,001 ml/s = 72
Speed is the magnitude of velocity, where velocity is seen as a vector (i.e., it includes a directional component). In contrast to velocity, speed is a scalar value.
Speed
instruction is related to abnormal condition
FanManual
LegioProtect = 1
A child OP relationship to a list that describes a quantity/countable characteristic “dimension” how an observation or actuation is made.
has quantity kind
The visual effect of channel 12 is active = 1
Application functions to monitor a 'fire alarm'.
Fire Alarming
BlindsControlMode
SwitchCool
invalid Group Object number (ASAP) = 17
Heat and cool = 13
A meeting room, conference room, or conference hall is a room provided for singular events such as business conferences and meetings. Preferably used with an Room.
Meeting Room
two PBs/binary inputs mode = 2
At least one of the inputs Wind-/Rain-/Frost-Alarm is ‘in alarm’
A leisure centre facility or building may include a swimming pool, large sports hall, squash courts, cafeteria, licensed bar, fitness suite, aerobics studios, outdoor grass and/or artificial pitches for football (soccer), hockey etc., a solarium, sauna and/or steam room. Preferably used with a Building.
Leisure
a point representing DPT 2.001: Switch Control
Switch Control
a point representing DPT 256.001: DateTime Period
DateTime Period
This state type expresses that an alternative room temperature setpoint (internal to the room setpoint manager) is used for temperature control in a room.
Type of Temperature Setpoint Alternative
TempRoomSetpHeatEffNext
FadeTime
A parent data property, used to express any kind of generic data that relates to a datapoint type.
datapoint type
a point representing DPT 7.012: UElCurrentmA
UElCurrentmA
A device used to operate functions and equipment in a room by pushing. Examples are push buttons used to switch light, indicate presence and similar use cases.
Button
a point representing DPT 21.105: StatusRCC
StatusRCC
standard Status/Command
Emergency Heat = 8
Current Colour RGB
A specific Application Function that controls energy production. The Application Function represents a process of generating energy to the consumer according to energy demand keeping losses in distribution and generation to an absolute minimum.
Generation Control
ok = 0
HVACModeNext
open on overvoltage = 2
Aquifer thermal energy storage (ATES) is the storage and recovery of thermal energy in the subsurface. ATES is applied to provide heating and cooling to buildings. Storage and recovery of thermal energy is achieved by extraction and injection of groundwater from aquifers using groundwater wells.
ATES
TempRoomSetpSetCoolEff
Application functions for "demand driven based control" is an approach to dynamically manage energy output based on the demand for energy that arises within the smart grid.
Demand Driven Based Control
Hardwired switch is on = 0
Dew Point Status
a point representing DPT 205.100: TempHVACAbs_Z
HVAC absolute Temperature
From MaC assigend installation hints as part of the project.
Installation Hints
LTRD
Shall specify whether the colour component red shall be increased or decreased.
The Domestic Hot Water Control Application Function represents a process of providing domestic hot water (DHW) for the kitchen and bathroom sinks, tubs and other appliances.
DHW Control
a point representing DPT 238.600: DALI Diagnostics
DALI Diagnostics
Return Air Temperature Sensor
An Air Handling Unit (AHU) is an Application Function that controls equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system. An AHU Application Function has usually subfunctions such as fanCtrl, pumpCtrl etc.
AHU Control
A refrigerator, colloquially fridge, is a commercial and home appliance (EN50523) consisting of a thermally insulated compartment and a heat pump (mechanical, electronic or chemical) that transfers heat from its inside to its external environment so that its inside is cooled to a temperature below the room temperature.
Refrigerator
Used to map a foreign protocol address to a KNX address identifier that is mapped to a specific datapoint. Due to the large number of protocols the data property is not explicitly modeled per (foreign) protocol; it is defined as a generic (bitwise unlimited) integer. Hence this the actual address identifier can be expressed as a large – but unstructured – bit field.
non KNX mapping address
luminous flux
Represents a percentage value between 0 and 100%.
Scaling
SceneNumber
Used to indicate that a KNX concept implements the KNX communication mode (S-Mode, LTE-Mode). Most likely, this can be assigned to KNX Datapoint Types and to KNX DPAs (i.e. those which are not present in S-Mode implementations of FBs)
has communication mode
This state type expresses that an equipment has a movement direction that can be interpreted as 'opening'. Usually, this is associated with equipments that can be moved by a drive in an horizontal axis or on a hinge, such as valves, windows, or doors.
Opening Movement
Field resolution, a factor for the value range of a KNX data field as part of an entire datapoint type.
field resolution
garbage = 41
off = 0
No failure detected = 1
Rest mode active = 4
Day of week field valid = 0
Manual Control = 1
charge density (surface)
This state type relates to both primary and secondary stages of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages Both
EmergPurge = 3
EquipmentType to meter a substance or phenomenon
Meter
TempRoomSetpUserAbs
HVAC VAC = 14
Activation state of channel 4
Version
no error = 0
No alarm = 0
resistivity
TempRoomSetpUserAbsEff
LED, trailing = 8
identifier of previous operation mode that was active before the state machine switched to the current one. CT=0 no previous operation mode declared
The user application is stopped
A car (or automobile) is a wheeled motor vehicle that is used for transportation.
Car
Protection of buildings, rooms, objects or persons against unwanted effects of solar radiation.
Shading
Light fixture using electricity to provide illumination.
Luminaire
Data Link Layer Raw Frames = 2
DPT 14.075: Value of torque
Value Torque
common flow temperature of ProdSegmH
Activation state of channel 14
2-byte unsigned value
Hosts 0...n vcard compatible addresses, usually fro a location. A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
has address
solid angle
cooling = 0
Heat cost allocator = 8
volume flow, 1000 l/h = 62
DPT 14.006: Value of an angle (in radiant)
Value AngleRad
Root node to host all core related concepts.
Core Thing
Represents values for counting from 0 to 255 counter pulses.
Value 1 U Count
a point representing DPT 225.001: ScalingSpeed
ScalingSpeed
The visual effect of channel 4 is active = 1
RF_FilterSelect
To define a general relation between different concepts. With the child properties a relation with a specific semantic meaning can be expressed (such as between locations, datapoints or function points). Due to the usage from several concepts the domain and range is not specified for this OP.
is referenced by
FanMode
leading edge (inductive load) = 1
master = 2
a point representing DPT 22.102: Combined Status HVA
Combined Status HVA
invalid connection number (TSAP) = 16
Level 3 = 3
room temperature setpoint shift standby
An engine or motor is a machine designed to convert one or more forms of energy into mechanical energy.
Engine
a point representing DPT 255.001: Geographical Location
Geographical Location
shift load priority
Switch On Off Red
DPT 14.030: Value of electromotive force
Value Electromotive Force
Preferably used with an Space.
Conduits
The visual effect of channel 15 is inactive = 0
BiBat Master
16-bit set
A container for objects in an installation which have a sort of economic value and is owned and managed by an entity, e.g. a service organization.
Asset
last actual value = 0
RainAlarm
Cyclically = 1
value before locking = 6
Used for reading and setting tariff information from 1 to 254. However, the mapping between tariffs and the DPT values is not standardized. The value 0 equals 'no tariff available'. The value 255 is reserved.
Tariff
Normal = 2
value according additional parameter = 3
Off/FrostProtection = 4
A software represents a collection of data or instructions that are installed (hosted) on a Device or Computer and tell it how to work. Software is a generic term used to refer to applications, scripts and programs that run on a Device.
Software
The visual effect of channel 5 is active = 1
The visual effect of channel 20 is inactive = 0
oil = 1
a point representing DPT 20.002: BuildingMode
BuildingMode
Standard single-phase = 3
HVAC User Mode active (means DP ‘HVACModeUser’ is different from ‘Auto’) = 1
character
identifier of the timer, has to start with 1
hardware fault = 4
ComfortProlongEff
energy, 100 kJ = 13
This state type expresses that the buildin protection room temperature setpoint is used for temperature control in a room.
Type of Temperature Setpoint Protection Mode
PE2 in progress = 2
a point representing DPT 24.001: VarString 8859-1
VarString 8859-1
Outside Temperature Sensor
a point representing DPT 20.1204: Euridis Communication Interface Status
Euridis Communication Interface Status
a point representing DPT 9.005: Value Wsp
Value Wsp
Room Setpoint Manager HVAC-Mode Driven
This state type expresses that an equipment is in an unlocked state. Typically, this means that the equipment reacts to new input commands as intended. This state type is the inverse of the 'locked' state type.
Unlocked State
SwitchPBModel
The visual effect of channel 3 is inactive = 0
Activation state of channel 9
Forced Position
The visual effect of channel 4 is inactive = 0
Shall specify whether the colour shall be increased or decreased.
Relative Set Value Control White
The value of the target point is sent as an update notification (triggered). The trigger is defined by the metadata source datapoint value.
is change of value of
volume flow, 1 ml/s = 75
a point representing DPT 1.008: Up Down
Up Down
A parent data property, used to express any kind of generic data that relates to an application program.
application program data
speed
SwitchOnOff
a point representing DPT 200.100: Heat/Cool Z
Heat/Cool Z
Actual Dimming Value Red
DPT 14.055: Value of phase angle (in degrees)
Value Phase AngleDeg
Cool
Conveyor to move people across a horizontal or inclined plane. A moving walkway, also known as an autowalk, moving pavement, moving sidewalk, people-mover, travolator, or travelator, is a slow-moving conveyor mechanism that transports people across a horizontal or inclined plane over a short to medium distance.
Moving Walkway
Backup Value = 0
electromotive force
a point representing DPT 20.102: HVACMode
HVACMode
Date that the resource became or will become available.
Date Available
ValveMode
LoadTypeDetected
An identifier to specify the (string based) order number of a vendor product. The order number scheme is vendor specific.
Order Number
An OP relationship to express the control/status relation, separated in KNX by using different function points (GAs) for each. A function point relates to another function point, with the specific meaning of FP x represents the status value of the (setpoint/comand value) of FP y.
is status of
FrostAlarm
Activation state of channel 12
SwitchOnOffControlCmd
EnOcean
The lower boundary of the range with 95 % certainty the power value is in it
DPT 14.012: Value of surface charge density
Value Charge DensitySurface
Heat Stage A Actuator Current Position
Height Position
list of fill level target profile element
To express a relation of a channel, implemented in a device.
has channel
The air supply control Application Function connects and coordinates air and energy flow between air treatment (e.g. air handling unit) and energy consumer (emission control).
Air Supply Control
error = 1
a point representing DPT 20.605: SwitchPBModel
Emergency mode active = 5
undefined load command received = 14
power, 1 kJ/h = 51
To define an asset included in other assets such as several equipment’s/ installations as part of an asset.
contains asset
2.x
Steam meter = 5
Specific Application Function for "Smart Grid control". A Smart grid is a network of transmission lines, substations, transformers that delivers electricity from points of generation to points of consumption with two-way communication to ensure efficient and reliable energy flow.
Smart Grid Control
a point representing DPT 1.003: Enable
Enable
a point representing DPT 205.102: HVACAirFlowRel_Z
HVAC Air Flow Relative Value
a point representing DPT 20.012: ErrorClass HVAC
ErrorClass HVAC
Date and Time
Field name, used to define a (user readable) name of a KNX data field as part of an entire datapoint type.
field name
A door lock is a way to secure a door. A lock is a mechanical or electronic fastening device that is released by a physical object such as a key, keycard, fingerprint, RFID card, security token or coin.
Door Lock
Preferably used with a Building.
Other Commercial
DPT 14.023: Value of electric field strength
Value Electric FieldStrength
Application Functions that controls the quantity 'water temperature'.
Water Temperature Control
automatic light control = 0
User Presence Switch
The visual effect of channel 7 is active = 1
Bank Holiday (No working day) = 0
energy
Re-Light / Reset Inhibit = 3
DPT 14.049: Value of magnetization
Value Magnetization
validity of PrelBurnerField
ControllerConnection = 2
Last modified time stamp, usually generated by Mac. May be used from other concepts, therefore no domain is defined.
last modified
power, 0,001 kJ/h = 48
Fault
output state is not valid = 0
Validity of field ActualValue
Delay time until next change of tariff
DPT 14.008: Value of angular momentum
Value Angular Momentum
The transfer of energy to a space or to the air by the existence of a temperature gradient between the source and the space or air. This process may take different forms, e.g. conduction, convection or radiation.
Heating
CombinedStatus_HVA_CoolB
HVACModeAct
TempRoomSetpUserOffsetEff
The atmosphere of Earth or air is the layer of gases retained by Earth's gravity that surrounds the planet and forms its planetary atmosphere.
Air
The visual effect of channel 20 is active = 1
The visual effect of channel 1 is active = 1
Building protection = 2
Switch On Off White
TempRoomSetpCoolEff
ApplicationArea
4-1-1 byte combined information
identifier of the resource manager. Must be unique within a single KNX system
a point representing DPT 7.007: TimePeriodHrs
TimePeriodHrs
Room Relative Humidity Sensor
Activation state of channel 18
a point representing DPT 17.001: SceneNumber
Wind is the natural movement of air or other gases relative to a planet's surface. Winds are commonly classified by their spatial scale, their speed and direction, the forces that cause them, the regions in which they occur, and their effect.
Wind
A roof is the top covering of a building, including all materials and constructions necessary to support it on the walls of the building or on uprights, providing protection against rain, snow, sunlight, extremes of temperature, and wind.
Roof
building protection setpoint = 2
Free Cool = 10
The visual effect of channel 21 is inactive = 0
This state type expresses that the highest level named 'Comfort' is chosen for the HVAC mode. Usually, the 'Comfort' level is associated with an occupied room. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Comfort
a point representing DPT 1.011: State
State
Video refers to the part of multimedia, which is dealing with visuals. The trade video contains applications for producing and capturing visual signals, such as images or movie clips.
Video
CFL, leading = 5
A hand dryer is an electrical appliance that has the primary function of drying hands.
Hand Dryer
power, 10000 W = 47
2-nibble set
Room or space used for electrical equipment such as switch cabinets, a fuese box etc. Preferably used with an Space.
Cabinet
The abstract notion of angle. Narrow concepts include plane angle and solid angle. While both plane angle and solid angle are dimensionless, they are actually length/length and area/area respectively.
Angle
Economy = 3
Defines the ability to read a datapoint. The r/w limits set with boolean values true (default) or false. It may be used to limit the access from a 3rd party interface or similar, set by a MaC.
readable
Info On Off Output 1
a point representing DPT 20.1206: Peak Event Notice
Peak Event Notice
IdentNumber
a point representing DPT 20.1203: Breaker Status
Breaker Status
A specific Application Function that controls, for example, the speed of a fan.
Fan Control
volume flow, 0,1 l/min = 67
TempReturnAir
the range of the fill level the leakage rate (LR) realtes to
Mask Bit Info On Off Output 15
Indicator whether sequence is interruptible or not
The tag represents information for a logical point, a diagnostic point that serves for monitoring.
Diagnostic Point
a point representing DPT 1.022: Scene AB
Scene AB
Substance with definite volume but takes the shape of its container
Liquid
Light Dimming Sensor Basic
Calibration Mode
SwitchOn message sent = 2
StatusStopOptim
percent
Off = 6
a point representing DPT 20.020: ActuatorConnectType
ActuatorConnectType
Light Current Status
8-bit set
A parent OP relationship to express a general relation to a tag. The relationship specifies the OWL range class :Tag, allowing to express any relation to one of the individuals as part of the sub classes of :Tag. As it is also just a generic top OP of specialized (sub) OP relationship predicates, only the latter SHOULD be used.
has tag
control = 1
Activation state of channel 10
false = 0
An office is a space where an organization's employees perform administrative work in order to support and realize objects and goals of the organization. Preferably used with a Building or Room.
Office
Valve (gas or water) = 33
datapoint type version
HeatCoolModeAct
TempRoom
TempReturnLimit
This state type expresses that an equipment, an alarm or a certain situation is active. An active equipment is fulfilling its intended functionality, whereas an active alarm means that the alarm state was triggered. An active situation means that a certain state has been reached. The tag 'Active State' is often used for situations that feature an enumeration of possible states (e.g. operational states, control modes, HVAC modes, ...) to make a boolean statement about one of these states. The state type 'Active State' is the inverse of the 'Inactive State' state type.
Active State
Refers to the third phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.
Phase L3
Absolute Set Value Control White
Tank used to store a substance for temporary holding. For example, a fuel tank (also called a petrol tank or gas tank) is a safe container for flammable fluids.
Storage Tank
HVACModeEffNext
'Duration' is the length of a time interval, i.e. the amount of time that passes between two distinct points in time.
Duration
Lighting = 20
Validity slats pos.
CalibrationMode
Cool = 3
Used with any location type.
Other
Info On Off Output 16
configuration fault = 3
A strong OP relationship to express a relation to a space contained in a location.
has space
A relation to a subclass of a location, e.g. a room as spatial sub-location of a floor.
has location
a point representing DPT 2.006: Binary Value Control
Binary Value Control
Current Time
This state type is a special type of a defect state. It expresses that the actual device hosting the datapoint is not working properly due to a short circuit. Thus, no valid value is available at the datapoint.
Operational State Defect Short Circuit
a point representing DPT 9.022: PowerDensity
PowerDensity
stop = 4
No Date
Application functions that controls the quantity 'air quality'.
Air Quality Control
Activation state of channel 7
Room Temperature Setpoint Manager
autonomous = 0
A Quality Kind with an actuatable quantity property that addresses a 'phenomenon', and the quantity property can only be indirectly influenced.
acts on phenomenon quality kind
HVACModeUserEff
Switch Current Status
a point representing DPT 21.103: StatusSDHWC
StatusSDHWC
a point representing DPT 1.009: Open Close
Open Close
A specific Application Function that represents a process to provide a supply media to the consumer according to energy demand keeping losses in distribution and generation to an absolute minimum. distrCtrl functions control usually energy flow via water or air in pipes or ducts from energy generation to energy consumer in rooms (emission control).
Distribution Control
Enable = 1
Auto = 0
TempRoomSetpSetCoolShift
BiBat information = 7
TempRoomSetpAct
Specifies for enumeration DPTs a numerical value, that is used from the KNX system at runtime.
value KNX
a point representing DPT 1.023: ShutterBlinds Mode
ShutterBlinds Mode
a point representing DPT 206.102: DHWModeNext
DHWModeNext
2-byte signed value
The visual effect of channel 6 is inactive = 0
notice PE3 in progress = 3
A quality kind (QK) describes a specific “type of interest” that is related to a value with a continuous, measurable physical quantity. The quantity can be figured out without any other context knowledge from any domain.
Quality Kind
A boiler is a closed vessel in which fluid (generally water) is heated. Equipment to generate hot water or steam for heating.
Boiler
Application functions that controls the quantity 'air temperature'.
Air Temperature Control
actuator is currently in calibration mode
The visual effect of channel 9 is active = 1
A parent data property, used to express any kind of generic data that relates to an installation.
installation data
identifier of the timer, needs to be unique within the scope of the state machine
Undefined = 0
a point representing DPT 6.010: Value 1 Count
Value 1 Count
Working Day
notice PE2 in progress = 2
on = 1
a point representing DPT 20.803: SSSBMode
SSSBMode
Number of power sequences in a power sequence container
auto = 0
Inactive = 0
a point representing DPT 5.005: DecimalFactor
DecimalFactor
no fault = 0
Permission (informs about the access decision made by the controlling device)
Heating Mode Enabled
Units for HCA = 110
User interfaces are composed of one or more layers, including a human-machine interface (HMI) that interfaces machines with physical input hardware such as keyboards, mice, or game pads, and output hardware such as computer monitors, speakers, and printers.
HMI
Substance with neither definite volume nor shape
Gas
momentum
A bedroom or bedchamber is a room situated within a residential or accommodation unit characterised by its usage for sleeping. Preferably used with a Room.
Bedroom
void device type = 255
permanently running = 1
ActTargetPosHeatStageA
limit range defining upper and lower power values
An OP relationship to express a relation from a functional block to datapoints as part of a FB. Such datapoints includes per definition additional semantic information, with this a FB can be composed with its mandatory/optional datapoints.
composes
true = staircase lighting function is active, e.g. via input TimedStartStop.
Status D
power, 0,01 W = 41
the usage forecast allow the resource manager to communicate planned usage of a storage for a certain period of time in the future
Converter Mode according to the DALI converter state machine
RoomHConf
power, 100 W = 45
comfort prolongation User not active = 0
The visual effect of channel 14 is active = 1
mass flow, 100 kg/h = 85
ActualDimming-Value
a point representing DPT 201.100: HVAC Mode Z
HVAC Mode Z
last (value before bus power down) = 4
electric current
a point representing DPT 207.104: ActPosDemAbs
ActPosDemAbs
left to right = 0
Sky obstructed from view = 9
DPT 14.035: Value of heat capacity
Value Heat Capacity
Movement is locked, e.g. by DeviceLocked input
A strong OP relationship to express a relation to a site segment contained in a site.
has site segment
DPT 14.032: Value of force
Value Force
not forced = 0
TempFlowLimit
OverloadDetection
The tag category contains individuals that describe the location related oriented context for a measurement/adustment of an equipment or an observation/actuation of a phenomenon. It expresses a relation to a space (as a place of action or where an equipment is installed.
Locality
Activation state of channel 3
Passed max delay exceeded = 2
general device fault (e.g. RAM, EEPROM, UI, watchdog, ...) = 1
16-Bit Unsigned Value with Status/Command
FadeToControlCmd
Ventilation equipment to limit exposure to hazardous fumes. A fume hood (sometimes called a fume cupboard or fume closet) is a type of local ventilation device that is designed to limit exposure to hazardous or toxic fumes, vapors or dusts.
Fume Hood
The number of intervals into which the range of 0 % … 100 % is subdivided, or the break indication.
Step Code
TempSetpShiftStdby
DPT 14.011: Value of capacitance
Value Capacitance
a point representing DPT 13.1201: Delta Volume Cubic Metre
Delta Volume Cubic Metre
An equipment is often refered to as "Fixed Asset". Via an object property realationship an equipment has a relation to an element in the location, in most cases inside a building, for example, a whiteboard, a chair, a table, a fan or a motor, which one can assign a product category and/or product type.
Equipment
CombinedStatus_HVA_HeatB
DPT 14.050: Value of magneto motive force
Value MagnetomotiveForce
yes = 1
Building Protection = 4
is quality kind of
volume flow, 0,0001 l/min = 64
Cooling Load meter (inlet) = 10
a point representing DPT 20.111: FanMode
Video data and camera management function.
Normal (no fault) = 0
The tag category contains individuals that describe a specific application data source of a point, used in cases where the input of an point is affected from a superordinated application control (instead of the common control loop).
Origin
None = 0
Shift load priority = 1
all windows closed = 0
Relative Control RGB
Activation state of channel 5
power, 1000 kJ/h = 54
validity of the Time Period
Security = 30
Application functions that controls the quantity 'air volume'.
Air Volume Control
A ceiling is an overhead interior surface that covers the upper limits of a room.
Ceiling
An identifier to specify the (numerical) version of an application program.
a point representing DPT 21.104: FuelTypeSet
FuelTypeSet
a point representing DPT 20.1200: MBus BreakerValve State
MBus BreakerValve State
Variable air volume terminal unit. Variable air volume (VAV) is a type of heating, ventilating, and/or air-conditioning (HVAC) system. Unlike constant air volume (CAV) systems, which supply a constant airflow at a variable temperature, VAV systems vary the airflow at a constant temperature.
VAV
inactive = 0
output state is valid = 1
To define a representative entry point for datapoints with a gateway. With this datapoints in an installation can be exposed for different purposes, such as all datapoints on a 3rd Party API (gateway).
has proxy
FanStepUser
Slats are vertical or horizontal pieces of a window blind. Slats actuator is used to control an actuator equipment to regulate the light incidence (slats position/angle). Don't care if the slats position/angle is internally operated from the actuator by a motor or other means.
Slats Actuator
Warm water meter = 6
CoolingOnly = 1
DPT 14.059: Value of reactance
Value Reactance
The tag category contains individuals that describe the role of a Point in the control loop of an application function.
Point Function
Building in use = 0
CountVal
POP3
disabled (PSU/DPSU fixed off) = 0
A specific Application Function to optimize different energy storages.
Energy Storage Control
Room Temperature
a point representing DPT 207.105: StatusAct
StatusAct
Heats a space using pipes or cables embedded beneath floor. The most common kind of radiant heating is underfloor heating. There are three types of underfloor heating: hot air systems, hot water systems and electric systems.
Underfloor Heating
timestamp when last transition was executed
A building represents a whole building that hosts several other elements such as stacked floors or spaces or rooms. The concept can be mapped to a IfcBuilding.
Gebäude
Building
The visual effect of channel 2 is active = 1
DPT 14.037: Value of heat quantity
Value Heat Quantity
drive is moving = 0
a point representing DPT 7.013: Brightness
Brightness
disabled = 0
In geometric measurements, length most commonly refers to the estimated dimension of an object. In some contexts, the term "length" is reserved for a certain dimension of an object along which the length is measured.
Length
This state type expresses that a scene is activated in scene-controlled instrumentations by restoring a previously learnt value. This covers both activating a scene based on a scene number (e.g. 0-63) or by choosing between two scenes (e.g. Scene A or Scene B).
Scene Recall
Actual HVAC Emergency Mode
LegioProtActive
Building not used = 1
asynchronous = 0
Historical single-phase = 1
HVACEmergMode
In KNX used (numerical) identifier to address a specific property as part of an interface object. The range xsd:unsignedByte supports exactly the KNX value range from 0 to 255. As a note, this is a mirror property to the data property "knx:propertyIdentifier" and must ONLY be used on annotated datapoint (dpa.x) classes, not on the actual individuals!
property identifier annotation
NumberedSceneControl
Relates to the light colour value, measured in the xyY colour system. The coordinates x and y define the chromaticity of the colour, whereas the coordinate Y defines the luminance of the color.
Light colour xyY
Time synchronization coordinates independent clocks on different devices.
Time Synchronization
Current Date
Relative Set Value Control Blue
inactive (no message sent) = 0
energy, 0,1 Wh = 2
Cool Stage A Actuator Valve Kick
4-byte signed value
is equipment type of
KNX
Cloudless = 0
Colour Level White
Occupied = 0
RF Control Octet and Serial Number or DoA = 2
positions
Fire safety deals with preventive actions against fire events (incidents, accidents, and other unwanted conditions) caused by unintentional, human error and/or technical deficiencies, and with the limitation or control of such incidents.
Fire Safety
ChangeOverStatus
mass flow, 10000 kg/h = 87
DPT 14.079: Value of work
Value Work
Magic Number
SW fault = 5
DPT 14.045: Value of magnetic flux
Value Magnetic Flux
power, 10 W = 44
simple alarm = 1
Year field not valid = 1
a point representing DPT 205.101: TempHVACRel_Z
HVAC relative Temperature
power return mode
a point representing DPT 8.011: Rotation Angle
Rotation Angle
DayOfMonth
The visual effect of channel 17 is inactive = 0
Hour of day, Minutes and Seconds field valid = 0
HVAC User Mode not active = 0
Last download time stamp, usually generated by Mac. May be used from other concepts, therefore no domain is defined.
last downloaded
F32F32
9.x
alarm info
move Up/Down + StepStop mode (blind) = 1
scene B = 1
a point representing DPT 250.600: Converter Info Fix
Converter Info Fix
This state type expresses that the white part of RGBW light color is referred to. It is mostly used in lighting applications that use the RGBW color model.
Chromaticity White
Alarming is the automated alarm management in the event of alarms or faults in plants, subsystems or devices. The application function may contain a list of activ alarms, past alarms, alarm prioritization or sends a notification to recipients (e.g. email).
Alarming
frequency, angular (pulsatance)
Fresh air, e.g. for fancoils = 1
The visual effect of channel 16 is inactive = 0
Used to represents an URN.
identifier
is room segment of
Language as in DPT_Language-CodeAlpha2_ASCII (234.001) this is ISO 639-1 alpha-2
A classroom or schoolroom is a learning space in which both children and adults learn. Preferably used with a Room.
Classroom
WindowStatusEff
The visual effect of channel 1 is inactive = 0
Cool Stage B Actuator Current Position
Underload
some failure in the chiller
Power Envelope is the aggregated measure of the extreme values of the power output over a period of time. Power Envelope Based Control allows you to set limits to these power envelopes for certain periods of time.
Power Envelope Based Control
a point representing DPT 2.007: Step Control
Step Control
a point representing DPT 232.600: Colour RGB
Colour RGB
LockDevice
Wind Sensor
DownUp = 3
one push button/binary input, MoveUp / StepUp message sent = 2
Activation state of channel 8
Info On Off Output 6
energy, 10000 kJ = 15
a point representing DPT 254.600: Relative Control RGB
A command is classified as a direct adjustment, such as a Point used from manage functionalities to send imperative commands to control actuators.
Command
a point representing DPT 20.1209: Type TIC Channel
Type TIC Channel
Breaker/Valve is closed = 0
a point representing DPT 21.107: Combined Status RTSM
Combined Status RTSM
is floor of
scene is inactive = 1
DPT 14.073: Value of thermoelectric power
Value ThermoelectricPower
validity of the Tariff data
a point representing DPT 20.005: LightApplicationMode
LightApplicationMode
Relation to GMT
A wall is a building element that physically separates two or more neighbouring locations (typically rooms).
Wall
Up/down position is forced by MoveUpDownForced input
has application function
energy, 1000 kJ = 14
a point representing DPT 20.004: Priority
Priority
This field shall indicate whether the Brightness information in the field Brightness is valid or not.
Index of access identification code
occupied = 0
DPT 14.063: Value of solid angle
Value SolidAngle
Lamp Failure
running in intervals = 2
HVAC Terminal Units = 13
Binary Information
DPT 14.018: Value of electric charge
Value Electric Charge
a point representing DPT 20.109: DamperMode
DamperMode
This state type expresses that an equipment is controlled manually, rather than being controlled automatically. The equipment's value / position is the result of an input command with high priority, such as a manual control command. Other input commands of normal priority (e.g. automatic commands from a controller) are ignored, i.e. they were overridden by the high-priority command. This state type is the inverse of the 'Override Mode Automatic' state type.
Override Mode Manual
A dimmer is a device connected to a light fixture and used to lower the brightness of the light.
Dimmer
This state type expresses that some alarm condition for a datapoint occurred. No assumption about the validity of the datapoint’s value can be made.
Operational State In Alarm
Setpoint Manager Relative Humidity
Generic concentration without a specific type. In chemistry, concentration is defined as the abundance of a constituent divided by the total volume of a mixture. The term concentration can be applied to any kind of chemical mixture, but most frequently it refers to solutes in solutions.
Concentration
clear = 0
HVACModeUser
No Layer = 255
wind speed absolute value m/s
operation mode id the transition points to
Info On Off Output 11
An OP relationship to a list that describes the primary protocol that a datapoint uses to send its data.
operates on protocol
Constant air volume terminal unit. Constant air volume (CAV) is a type of heating, ventilating, and air-conditioning (HVAC) system. In a simple CAV system, the supply air flow rate is constant, but the supply air temperature is varied to meet the thermal loads of a space.
CAV
enable = 0
x-coordinate of the colour information
Down = 1
amount of substance
ActCurrPos
A specific Application Function that controls the electical power network (e.g. fuses, circuit breakers etc.) from distribution transformer to consumers. The voltage level of a low-voltage distribution system is typically equal to the mains voltage of electrical appliances.
Low-voltage Power Distribution
FanManualEff
Level 15 = 15
a point representing DPT 20.612: Converter Control
Converter Control
supported commodities (b0 = electricity, b1 = gas, b2 = oil, b3 = 0/reserved)
Request Converter PDT Info = 6
two PBs/binary inputs mode = 4
mass, 1 kg = 27
a point representing DPT 20.006: ApplicationArea
y-coordinate of the colour information
The visual effect of channel 11 is active = 1
a point representing DPT 20.611: Converter Test Control
Converter Test Control
a point representing DPT 20.120: ADAType
ADAType
is point function type of
LDSBMode
An OP relationship to a list that describes the runtime interworking interface type of a datapoint. A datapoint usually reflects a logical or physical (input/output) point, combinations with other (parameter/diagnostic) tags are possible.
has point interface
This state type expresses that the ventilation system is inactive, i.e. performing neither humidification nor dehumidification tasks.
Humidification Mode Inactive
TempRoomSetpAbs
Activation state of channel 15
gentle brezze = 3
ActiveElectricalEnergy
Fan Speed Current
Stations or other buildings used for public transport such as train stations, bus stations or metro stations. Preferably used with a Building.
Transportation
The visual effect of channel 13 is inactive = 0
DPT 14.054: Value of phase angle (in radiant)
Value Phase AngleRad
Converter Status
ForceRequest
DPT 14.017: Value of density
Value Density
HVACModeEff
not locked = 0
A relation from one floor to the next floor.
has lower floor
activate the scene corresponding to the field Scene Number = 0
Absolute Set Value Control Red
volume, 0,001 l = 16
Blinds Stop Step
a point representing DPT 23.001: OnOff Action
OnOff Action
room temperature setpoint economy
Refers to a trade that is concerned with windows and doors and their positions / openings.
Window/ Door Opening
Activation state of channel 24
Switch On Off Blue
Night Purge = 4
Up = 0
A human friendly title (short text), used to define user specific data for an individual. Edited in a MaC or from predefined product data or dictionary content. No limitation of the actual amaount, external entites may add additional language depended text. The 'Range' is not limited to a string, allowing to express also text in several languages (note W3C does not define a range).
title (name)
Level 2 = 2
Laundry refers to the washing of clothing and other textiles, and, more broadly, their drying and ironing as well. Preferably used with an Room.
Laundry Room
a point representing DPT 236.001: Prioritised Mode Control
Prioritised Mode Control
is point priority of
The tag category contains individuals allowing to express how a point value has to be interpreted (mathematically or logically) in order to affect the behavior of the system.
Point Operation
a point representing DPT 20.106: HVACEmergMode
a point representing DPT 7.002: TimePeriodMsec
TimePeriodMsec
The visual effect of channel 22 is active = 1
A specific Application Function category that controls the audio system. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Audio Control
WindowSwitch
Current Date and Time
DPT 14.058: Value of pressure
Value Pressure
Mask Bit Info On Off Output 8
a point representing DPT 212.100: TempRoomSetpSetShift[3]
TempRoomSetpSetShift[3]
Mask Bit Info On Off Output 1
Associated with electricity or with electrical force, power, or energy.
Electricity
DPT 14.039: Value of length
Value Length
is composed by
Other device type = 0
A child OP relationship to a list that describes the interest characteristic “type of interest” on what an observation or actuation is made.
has phenomenon type
a point representing DPT 235.001: Tariff ActiveEnergy
Tariff ActiveEnergy
Hour
A function point groups typically more than one point needed to express the communication link between all the points. The points provide the input/output data interfaces of the devices in an installation. A function point is derived from parent concepts that are specified as part of the EN 50090-6-2.
Function Point
Status E
ModeSelect
electric flux
Cooling load meter (outlet) = 10
The value of the target datapoint is sent at the latest after a certain duration. The duration is defined by the metadata datapoint's value.
is heartbeat of
standby = 1
insufficient non volatile memory = 6
Invert
3 min = 15
The visual effect of channel 8 is inactive = 0
is trade operated by
Validity Height Position
no alarm is used = 0
validity of TempFlowProdSegmH field
work
The visual effect of channel 8 is active = 1
This state type expresses that the second-highest level named 'Standby' (or 'Pre-Comfort') is chosen for the HVAC mode. Usually, the 'Standby' level is associated with an unoccupied room that needs to be able to reach the 'Comfort' level in a short period of time. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Standby
To define the existence of KNX standardized functionality block, implemented in a channel. Since a FB is specified with a certain set of mandatory and optional datapoints a channel needs to define at least the mandatory datapoints.
comprises
The term reception or front desk is used in many hotels for an administrative department where a receptionist's duties also may include room reservations and assignment, guest registration, cashier work, credit checks, key control, and mail and message service.
Reception
volume flow, 0,1 ml/s = 74
TempSetpEco
The tag represents information for a logical point, a communication interworking (logical) output Point, it sends data.
Logical Output Point
Activation state of channel 11
"Displacement" is the shortest distance from the initial to the final position of a point P.
Displacement
Emergency Steam Mode = 17
Mask Bit Info On Off Output 11
Used to control an actuator equipment to regulate the light incidence (blinds or shutter position). Don't care if the blinds position is internally operated from the actuator by a motor or other means.
Blinds Actuator
Building protected = 2
Day = 0
Battery Charge Level
A heat pump is a device that can heat a building (or part of a building) by transferring thermal energy from the outside using the refrigeration cycle. Many heat pumps can also operate in the opposite direction, cooling the building by removing heat from the enclosed space and ejecting it outside. Units that only provide cooling are called air conditioners.
Heat Pump
SwitchOnMode
validity of the absolute brightness
HVAC Hot Water Heating = 11
Heat = 1
A kitchen is a room or part of a room used for cooking and food preparation in a dwelling or in a commercial establishment. Preferably used with an Room.
Kitchen
timestamp when this constraint will be valid
includes datapoint field
mass, 0,1 kg = 26
A machine that has the primary function of printing a stream of characters onto paper or other media.
Printer
a point representing DPT 20.613: Converter Data Request
Converter Data Request
A power supply is an electrical device that supplies electric power to an electrical load. The main purpose of a power supply is to convert electric current from a source to the correct voltage, current, and frequency to power the load.
Power Supply
detection not possible or error = 3
ActualDimmingValue
Activation state of channel 16
No ramp = 0
a point representing DPT 20.801: SABExceptBehaviour
SABExceptBehaviour
a point representing DPT 9.028: Value Wsp kmh
Value Wsp kmh
manual light control = 1
A generic concept of a KNX datapoint type (DPT). Each present individual represents a corresponding DPT of KNX. The chosen individual name follows a defined structure. A datapoint type is derived from parent concepts that are specified as part of the EN 50090-6-2.
Datapoint Type
Info On Off Output 2
length
StartSynchronization
A dishwasher is a home appliance machine (EN 50523) that is used to clean dishware, cookware, and cutlery automatically.
Dishwasher
power, 0,1 W = 42
Revision Number
This shall be the number of the scene for which the DPT-value contains the configuration information.
Absolute actuator position demand (setpoint, valve linearized)
volume flow, 10 ml/s = 76
configuration/ diagnostics
This state type expresses that the actual device hosting the datapoint is not working properly due to a failure. Thus, no valid value is available at the datapoint. The cause of the device failure cannot be specified any further.
Operational State Defect
A general OP relationship to express a relation of location individuals to individuals which are outside of a particular building. The location to be outside (as the domain) MUST fulfil the boundary conditions to be allowed outside. Example is a relation to an outdoor location which does not directly belong to a building (e.g. garden).
has outside
Bus/System = 14
room temperature setpoint shift comfort
magnetic moment
VAV = 2
WD field valid = 0
1,25 min = 11
MasterSlaveMode
The lower boundary of the range with 100 % certainty the power value is in it
a point representing DPT 203.101: Wind Speed Z
Wind Speed Z
a point representing DPT 20.116: Enable HC Stage
Enable HC Stage
A location is a physical named geographical place that is used to identify a point, an area or room, inside or outside of a building. This generic location root node simplifies the replacement of the entire location model.
Location
This state type expresses that a device is currently in maintenance mode, i.e. it cannot be expected to fulfill its usual functionality until it is fully operational once again. Specific examples include ‘service mode’ or the ‘valve kick’ of valve actuators.
Operational State Maintenance
Ack
A hallway or corridor is an interior space in a building that is used to connect other rooms. Preferably used with an Room.
Hallway
a point representing DPT 209.101: TempRoomDemAbs
TempRoomDemAbs
Undervoltage
a point representing DPT 9.001: Value Temp
Value Temp
Represents a ratio.
Decimal Factor
no change = 2
Frost Alarm
A specific Application Function category that controls a customized setting of different trades for an activity or situation. Scene controllers are intelligent pre-configured settings that orchestrate multiple devices and settings with a single touch of a button or a simple voice command. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Scene Control
actual actuator position
Increase or decrease the brightness.
Cool stage B for cooling with two stages (A + B) = 4
Log Number
EnableHeat
filtering by Domain Address and by Serial number table = 3
This state type expresses that the movement of an equipment has stopped. Usually, this is associated with equipments that can be moved by a drive, such as valves, blinds, slats, windows, or doors.
Stopped Movement
HourOfDay
3.x
a point representing DPT 9.021: Value Curr
Value Curr
HVAC general FBs = 10
Fault = 1
An address is represented by an external ontology object, which has data properties such as country-name, locality (city), street-address.
External Address
DPT 14.078: Value of weight
Value Weight
Registered (S-FSK) - reserved (G3-PLC) = 2
Point name, used to indicate the name of a point. This is used in assigning names to the (input/output) points of functional blocks
point name
Colour_Relative Control_RGB
first character of RegionCode, ASCII-coded
a point representing DPT 10.001: TimeOfDay
TimeOfDay
HVAC operating mode
Precool = 5
Longitude information
HeatCoolMode
DHWPushActive
a point representing DPT 20.802: SABBehaviour Lock Unlock
SABBehaviour Lock Unlock
Restriction of target height pos., pos. can not be reached
a point representing DPT 9.023: KelvinPerPercent
KelvinPerPercent
This OP defines what predefined application function can be preferably used with a collection of datapoints. The collection may be expressed with a common functionality or more detailed with a functional block or channel (subclasses of functionality).
is applicable functionality of
Activation state of channel 2
A façade is generally the front part or exterior of a building. Mainly used as a building facade.
Facade
A user operated light switch request including an explicit switch status.
User Light Switching
Unsigned relative value
CombinedStatus_RTC
DPT 14.042: Value of luminous flux
Value Luminous Flux
communication fault = 2
A gym (also known as a fitness club, fitness center, health spa, and health club) is a place that houses exercise equipment for the purpose of physical exercise.
Gym
deactivated = 0
DHWLoadActive
Level 11 = 11
This state type relates to the secondary stage of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages Secondary
DPT 14.033: Value of frequency
Value Frequency
PresenceStatus
Colour Level Green
burner failure
a point representing DPT 20.115: HumDehumMode
HumDehumMode
Busmonitor Error Flags = 3
Standby = 2
Discharge air, e.g. for VAV = 3
status
Converter Failure
humidification = 1
timestamp when the instruction has to be executed
The value does not carry data to calculate with, only the access to it can already be interpreted.
Trigger
Colour Level Red
This field shall indicate whether the colour infor-mation in the fields x-axis and y-axis is valid or not.
TempRoomSetpSetHeatEff
Used to define the current number of an entity, such as the building number. May be used from other concepets, therefore no domain is defined.
number
The visual effect of channel 6 is active = 1
a point representing DPT 1.013: Dim Send Style
Water in its solid form
Ice
Medium
volume flow, 0,01 l/min = 66
Blinds Status
a point representing DPT 13.012: ReactiveEnergy
ReactiveEnergy
The visual effect of channel 10 is inactive = 0
Level 12 = 12
at base condition = 2
DPT 14.040: Value of light quantity
Value Light Quantity
a point representing DPT 8.004: DeltaTime100MSec
DeltaTime100MSec
a point representing DPT 7.011: Length mm
Length mm
Hardwired inhibit mode active = 3
Group Object Type exceeds (PID_MAX_APDU_LENGTH - 2) = 18
DPT 14.072: Value of thermal conductivity
Value Thermal Conductivity
is room of
FanStep
1-bit
limit range is related to abnormal condition
A Point representing history/ trend data with a log of timestamp/value pairs. Only this tag value is allowed to be used together with other tags from this category, such as to define a Datapoint expressing a history log of process values.
Heat Stage B Actuator Calibration Mode
Haystack
ActTargetPosCoolStageB
Unknown = 0
Flow Rate in m³/h with high resolution
Relative air quality value
HVACContrMode
DPT 14.031: Value of energy
Value Energy
TempRoomSetpHeatEff
indicates if power reduction is necessary (validity of PwrReduction)
auto (PSU/DPSU automatic on/off) = 2
Water in its gas form
Steam
electric potential
reliable synchronisation source (radio, Internet) = 1
SummerMode
Window Door
a point representing DPT 244.600: Converter Status
room temperature setpoint shift building protection
The visual effect of channel 24 is active = 1
Refers to the concentration of volatile organic compounds (TVOC) in the air, measured in ppm. This is a specialization of quantitykind:Concentration.
This state type relates to the primary stage of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages Primary
Extended Relative Timestamp = 6
alarm position is DOWN = 2
Stop Date Time
DetectedLoadType
failure = 1
Illuminance is the total luminous flux incident on a surface, per unit area. It is a measure of the intensity of the incident light, wavelength-weighted by the luminosity function to correlate with human brightness perception. As a note, focus is the light source, which is mostly NOT the interest in the building control domain.
Luminance
ControlModeUser
priority level
validity of the fields CB and Step Code Colour Blue.
a point representing DPT 205.017: Percent_V16_Z
Percent V16 Z
The manufacturer of an application program or product (as a note, a device is part of a product).
manufacturer
CombinedStatus_RTSM
Reduced = 3
timestamp when instruction shall be executed. In case the instruction type is SCHEDULE, ET will be the start time of the addressed sequence.
Relating to energy from the sun.
Sun
Direction 1
weight
uncritical = 0
Public Building
ActCurrPosCoolStageB
The trailing number of the minor datapoint type (DPT) in bits, specified in KNX with a numerical scheme. The minor type must be present for sub types but not for a major type. The range is used to include 0 (the KNX DPT numbering scheme starts at 0).
datapoint type minor number
date
is equipment of
luminance
is equipment quality kind adjusted by
4-byte unsigned value
By a MaC (ETS) allowed location usages for a floor.
MaC floor
a point representing DPT 2.002: Bool Control
Bool Control
reset command (trigger) = 1
a point representing DPT 21.001: StatusGen
StatusGen
TempRoomSetpCoolEffNext
Ice = 11
Single close = 1
Month and Day of Month fields valid = 0
This state type expresses that an equipment or a functionality is enabled. An enabled equipment may become active and fulfill its intended functionality. Being in 'Enabled State' makes no assumption on whether the equipment is currently active or inactive, but it merely expresses the state that the equipment is allowed to be active. Similarly, an enabled functionality is available to the system, i.e. it may contribute to the system's overall functionality. Usually, the equipment or functionality is enabled by management functionality, such as a building management system. This state type is the inverse of the 'Disabled State' state type.
Enabled State
Normal = 0
A point contains a warning that draws attention to something that usually does not need immediate attention.
Alert
Maximum Heating Mode = 12
The next active Tariff after expiration of the delay time
16-Bit Signed Value & 8-Bit Set
An identifier to specify the (string based) erial number of a device.
serial number
Shutter and Blinds Mode
a point representing DPT 205.103: HVACAirQualRel_Z
HVAC Air Quality Relative Value
a point representing DPT 245.600: Converter Test Result
Converter Test Result
A store room is a room within a house where equipment not used in day-to-day activities is kept.
Store Room
dehumidification = 2
SCLOMode
a point representing DPT 201.105: EnableHCStage Z
EnableHCStage Z
An electrical installation is a group of items of electrical equipment that are permanently electrically connected together and can be supplied with electricity from the works of an electricity entity or from a generating source. An electrical installation contains the electrical wiring of buildings, transmission lines, stationary machines, fuses, and related equipment.
Electrical
A programmable logic controller (PLC) or programmable controller is an industrial computer that has been ruggedized and adapted for the control of manufacturing processes, such as assembly lines, machines, robotic devices, or any activity that requires high reliability, ease of programming, and process fault diagnosis.
Programmable Controller
The tag category contains individuals that describe the numerical quantity of the measurement/adjustment (equipment) or observation/actuation (phenomenon).
Quantity Kind
at least one comfort push button is pressed = 1
no filtering, all supported received frames shall be passed to the cEMI client using L_Data.ind = 0
DPT 14.022: Value of electric displacement
Value Electric Displacement
mass flow, 0,1 kg/h = 82
Refers to distribution systems used to transport substances (and phenomena) such as water, air, or heat back to the specific centralized plants in a building. The distribution systems interface with the individual rooms at the start of the return part of the distribution system.
Return Section
room temperature setpoint shift comfort (delta value)
Application functions to monitor an 'intrusion alarm'.
Intrusion Alarming
An identifier to specify the (string based) media where this product can be used. Usually, IP, RF, TP.
Media Type
ActTargetFanSpeedEff
SolarLoadSufficient
Reset Lamp Time = 4
Breaker (electricity) = 32
The visual effect of channel 18 is inactive = 0
Application function for 'shutter control'.
User Shutter Control
heat, quantity of
unknown = 0
Ack_Sup
a point representing DPT 13.015: ReactiveEnergy kVARh
ReactiveEnergy kVARh
Time = UT+X+1 = 1
TempOutside
A generic concept to describe the individual parts of a KNX datapoint type. A datapoint type field is derived from parent concepts that are specified as part of the EN 50090-6-2.
Datapoint Type Field
2,5 min = 14
The visual effect of channel 15 is active = 1
LightControlMode
one PB/binary input; SwitchOnOff inverts on each transmission = 1
DPT 14.047: Value of magnetic moment
Value Magnetic Moment
activity (radioactivity)
validity of the fields CC and Step Code Colour.
entrance access
a point representing DPT 265.011: DateTime State
DateTime State
Refers to distribution systems used to supply a room with e.g. heat, water, or air. Usually, those substances (and the energy they carry) originate in specific plants, which are mostly centralized for each building. From there, the distribution systems transport substances to the individual rooms.
Supply Section
This state type expresses that an equipment, such as a luminaire, is switched off. This state type is the inverse of the 'On State' state type.
Off State
fresh breeze = 5
A trend application function monitors live and historical, time-indexed, quantitative etc. data, for example, for visuaization.
Trend
Convertor error
acceleration
power, 1000 W = 46
"Distance" is a numerical description of how far apart objects are.
Distance
A strong OP relationship to express a relation to building contained in a site.
has building
has actionpoint
a point representing DPT 203.100: HVAC Air Qual Z
HVAC Air Qual Z
a point representing DPT 26.001: SceneInfo
SceneInfo
Entertainment buildings or places host a form of activity that holds the attention and interest of an audience or gives pleasure and delight. Examples are cinemas, operas, theatres, museum etc. Preferably used with a Building.
Entertainment
A dressing room is a room to get dressed. Preferably used with a Room.
Dressing Room
a point representing DPT 201.104: HVAC Contr Mode Z
HVAC Contr Mode Z
Extended emergency mode active = 6
a point representing DPT 20.101: BurnerType
BurnerType
DT in progress = 8
mode 0 is active = 1
Start
The field Storage function shall indicate whether the set value(s) for the scene number SN can be modified at runtime through DPT_SceneControl or not.
volume flow, 10000 ml/s = 79
energy, 0,001 kJ = 8
a point representing DPT 9.007: Value Humidity
Value Humidity
Instruction to force the state machine switching from one operation mode to another or just set a new new value of the operation mode factor
Asynchronous
has location usage
BlinkingDisabled = 0
a point representing DPT 1.021: Logical Function
Logical Function
Cool Stage B Actuator Fault
Metering and monitoring are used, for example, for efficient energy management.
Energy Management
DPT 14.065: Value of speed
Value Speed
valve (gas or water) = 33
Level 8 = 8
Heat (inlet) = 12
SwitchOnOffForced
SDHWLoadActive
room temperature setpoint shift economy (delta value)
Water (chemical formula H2O) is an inorganic, transparent, tasteless, odorless, and nearly colorless chemical substance, which is the main constituent of Earth's hydrosphere and the fluids of all known living organisms.
Water
LoadPriority
A dining room is a room for consuming food. Preferably used with an Room.
Dining Room
Historical = 0
mass flux
corresponding Datapoint value is out of service
A garden is a planned space, usually outdoors, set aside for the cultivation, display, and enjoyment of plants and other forms of nature. Preferably used with an outside Location or Space.
Garden
6.x
HumRelSetpHumEff
TempSetpShiftComf
"Width" is the middle of three dimensions: length, width, thickness.
Width
A washing machine (laundry machine, clothes washer, washer, or simply wash) is a home appliance (EN 50523) used to wash laundry.
last received absolute setvalue = 2
volume flux
RoomHMax
CB and Step Code Brightness Validity
a point representing DPT 209.103: StatusWTC
StatusWTC
filtering by KNX Serial Number table = 2
includes reserved bit(s)
A technical room is a space in a building that is used to host equipment. Preferably used with a Room.
Technical Room
violent storm = 11
validity of the fields CG and Step Code Colour Green.
Time is a basic component of the measuring system used to sequence events, to compare the durations of events and the intervals between them, and to quantify the motions of objects.
Time
identifier of this instruction. value shall be unique. Old IDs will be reused.
This state type expresses that an equipment is in a locked state, which usually indicates that the equipment will not react on new input commands until the locked state is lifted. This state type is the inverse of the 'unlocked' state type.
Locked State
defines wich timers will start when executing this transition . each of the 16 timers could be referenced by setting the bits 0-15 to 0 (not starting) or 1 (starting)
DPT 14.067: Value of surface tension
Value Surface Tension
A swimming pool, swimming bath, wading pool, paddling pool, or simply pool, is a structure designed to hold water to enable swimming or other leisure activities. Preferably used with an Space.
Pool
Date Time
Frost Sensor
a point representing DPT 9.024: Power
Power
DPT 14.009: Value of angular velocity
Value Angular Velocity
A balcony (from Italian: balcone, 'scaffold') is a platform projecting from the wall of a building, supported by columns or console brackets, and enclosed with a balustrade, usually above the ground floor. Preferably used with an Space.
Balcony
a point representing DPT 12.001: Value 4 Ucount
Value 4 Ucount
Economy/Nothing = 2
System & functions of common interest = 1
Step
calibration pending, waiting on trigger = 4
DewPointStatus
DPT 14.052: Value of mass flux
Value MassFlux
HeatingDisabled
solid state fuel = 3
trailing edge (resistive - or capacitive load) = 2
Break = 0
Room AQ Sensor
4-byte float value
This state type expresses that an equipment or a functionality is disabled. A disabled equipment is inactive, cannot be activated and thus is not able to fulfill its intended functionality. Similarly, a disabled functionality is not available in the system. Usually, the equipment or functionality is disabled by management functionality, such as a building management system. This state type is the inverse of the 'Enabled State' state type.
Disabled State
whole gale / storm = 10
permanently off (manual switch or failure)
Short Circuit
The visual effect of channel 12 is inactive = 0
Converter test result
volume flow, 100 l/min = 70
PDT in progress = 9
Off/FrostProtect = 4
CoolingDisabled
power, 0,1 kJ/h = 50
Refers to the concentration of CO2 molecules in the air, measured in ppm. This is a specialization of quantitykind:Concentration.
Concentration, CO2
HumRelSetpUserEff
The visual effect of channel 13 is active = 1
Level 7 = 7
a point representing DPT 7.005: TimePeriodSec
TimePeriodSec
slave = 1
activated without security = 1
a point representing DPT 1.006: Binary Value
Binary Value
The upper boundary of the range with 68 % certainty the power value is in it
learn the scene corresponding to the field Scene Number = 1
stage 1 or base stage active
Inverted = 1
Discharge Temperature Sensor
Blinds Position Percentage
Info On Off Output 15
Bluetooth
The visual effect of channel 16 is active = 1
Colour Actuator RGB(W)
inactive = 1
In KNX used (numerical) identifier to address a specific interface object type reflecting a KNX functional block id. The range xsd:unsignedShort supports exactly the KNX value range from 0 to 65535.
interface object type
Absolute Set Value Control Green
NightMode
Actuator setvalue is locally overridden, e.g. via a local user interface
a point representing DPT 20.1001: AddInfoTypes
AddInfoTypes
AlarmText_Sup
a point representing DPT 20.003: OccMode
OccMode
SSSB
Application function for 'blinds control'.
User Blinds Control
Heat Stage B Actuator Valve Kick
enable stage A = 1
includes counter
The visual effect of channel 22 is inactive = 0
WindowStatus
Service mode
Waste water meter = 40
Mask Bit Info On Off Output 16
Reset
a point representing DPT 23.002: Alarm Reaction
Alarm Reaction
Timed StartStop
a point representing DPT 253.600: Relative Control xyY
Relative Control xyY
consequence type of the power constraint
A bathroom or washroom is a room, typically in a home or other residential building, that contains either a bathtub or a shower (or both). Preferably used with an Room.
Bathroom
A specific Application Function category that provides illumination and controls luminaries. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Lighting Control
electric potential difference
Request Converter Status = 1
no action (dummy) = 0
a point representing DPT 2.010: Start Control
Start Control
A datagram with the own Individual Address as Source Address has been received
deactivation of priority
a point representing DPT 9.030: Concentration µg/m3
Concentration µg/m3
Request Converter FT Info = 4
A health facility is, in general, any location where healthcare is provided. Health facilities are clinics and doctor's offices or urgent care centers with elaborate emergency rooms. Preferably used with a Building or a Site/Space.
Health Care
The tag category contains individuals that describe for which purpose a location is used for.
Location Usages
Copyright 2023, KNX Association, Brussels-Diegem, Belgium. Permission is hereby granted, free of charge, to any person obtaining a copy of this software and associated documentation files (the “Software”), to deal in the Software without restriction, including without limitation the rights to use, copy, modify, merge, publish, distribute, sublicense, and/or sell copies of the Software, and to permit persons to whom the Software is furnished to do so, subject to the following conditions: The above copyright notice and this permission notice shall be included in all copies or substantial portions of the Software. THE SOFTWARE IS PROVIDED “AS IS”, WITHOUT WARRANTY OF ANY KIND, EXPRESS OR IMPLIED, INCLUDING BUT NOT LIMITED TO THE WARRANTIES OF MERCHANTABILITY, FITNESS FOR A PARTICULAR PURPOSE AND NONINFRINGEMENT. IN NO EVENT SHALL THE AUTHORS OR COPYRIGHT HOLDERS BE LIABLE FOR ANY CLAIM, DAMAGES OR OTHER LIABILITY, WHETHER IN AN ACTION OF CONTRACT, TORT OR OTHERWISE, ARISING FROM, OUT OF OR IN CONNECTION WITH THE SOFTWARE OR THE USE OR OTHER DEALINGS IN THE SOFTWARE.
Represents the combined KNX Information Model with its individual (core/knx/location/tag) models. The Core model represents the commonly known IoT and building control domain concepts of an installation. The KNX model represents the KNX System part of an installation. The Location model represents the spatial location structure of an installation. The Tag model represents a set of entities, each with a standardized semantical meaning that is independent from any actual installation. The date of the last update of the model - usually regarding the dictionary content - is shown in the DCTERMS property dcterms:available. See also the corresponding version identifier at class core:Thing.
The terms of service can be found under https://www.knx.org/knx-en/privacy. The applied license agreement is a MIT License from https://opensource.org/licenses/MIT.
KNX Information Ontology
a point representing DPT 20.1003: RF FilterSelect
RF FilterSelect
Represents a (numerical, countable) position, such as %.
Position Vector
electric polarization
magnetic field strength
The visual effect of channel 23 is inactive = 0
power, 1 MW = 169
a point representing DPT 19.001: DateTime
DateTime
Normal mode active, all OK = 1
a point representing DPT 225.003: TariffNext
TariffNext
a point representing DPT 20.022: PowerReturnMode
PowerReturnMode
This state type expresses that an equipment is not in a forced state, i.e. no command with very high priority influenced the equipment's current value / position. The equipment's normal processing of input commands is executed. This state type is the inverse of the 'Forced State' state type.
Not Forced State
a point representing DPT 1.001: Switch
Switch
Lower predef. pos. reached, typ. height 100 %, slats-angle < 100 %
Request Converter Info Fix = 8
Mask Bit Info On Off Output 14
TimeStamp_Sup
Validity of TempRoomDem. ‘false’ means also ‘no demand’
Cool Stage B Actuator Valve Kick
room temperature setpoint comfort
Shall specify the fading step size or to the code to stop the fading of the colour red
a point representing DPT 20.007: AlarmClassType
AlarmClassType
Shutter Stop Step
normal = 0
no = 0
A loudspeaker (commonly referred to as a speaker or speaker driver) is one type of electroacoustic transducer, that is, a device that converts an electrical audio signal into a corresponding sound.
Speaker
energy, 1 GJ = 137
Light Relative Dimming Request
The visual effect of channel 2 is inactive = 0
Heat stage B for heating with two stages (A + B) = 2
modulating = 3
The phenomenon of high temperatures. This can relate to high ambient temperatures (e.g. as a weather phenomenon or in buildings) or to high temperatures in devices (e.g. when in the danger of overheating).
Heat
fresh gale = 8
Wednesday = 3
Used to control a (generic) actuator equipment. Don't care if the (generic functionality) is internally operated from the actuator by a motor or other means.
Actuator
a point representing DPT 20.1002: RF ModeSelect
RF ModeSelect
To define a relation to a product from an equipment.
has product
automatic (resistive, capacitive or inductive) = 0
is application program of
Shall specify whether the colour component blue shall be increased or decreased.
Garbage = 41
Activation state of channel 6
This state type expresses the state of no frost. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case no frost has been detected, no frost protection is required and this equipment might be used as intended. This state type is the inverse of the 'Frost State' state type.
No Frost
CFL, trailing = 6
energy, 0,1 GJ = 136
acceleration, angular
This state type expresses the state of storm. Usually, this state is related to the protection of shading equipment such as blinds and slats, which can be damaged due to high wind speeds. In case of storm, this equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Storm' state type.
Storm State
Up / Down
true = 1
Info On Off Output 8
Mask Bit Info On Off Output 6
ControlModeEff
ManufactID
CombinedStatus_HVA_HeatA
Dehumidification = 14
Colour Set RGBW
clock without ext. sync signal = 0
DHW temperature setpoint for Off/FrostProtect operating mode
a point representing DPT 2.008: Direction 1 Control
Direction 1 Control
ChangeoverMode
Info On Off Output 3
energy, 1 kJ = 11
TempSetpComf
Not active = 0
Sensor is a Peripheral that measures physical input from its environment and converts it into data that can be interpreted by either a human or a machine.
Sensor
EmergDepressure = 2
BlinkingWithAcknowledge = 2
AQRoom
forced = 1
30 min = 19
a point representing DPT 207.100: StatusBUC
StatusBUC
scene is active = 0
Alarm
a point representing DPT 28.001: UTF-8
UTF-8
A fan actuator.
Fan Actuator
Electricity meter = 2
Comfort = 1
TempRoomSetpUserOffset
Ballast Failure
Volumetric Flow Rate, (also known as volume flow rate, rate of fluid flow or volume velocity) is the volume of fluid which passes through a given surface per unit time.
Volume Flow Rate
mass, 0,001 kg = 24
Current Valve position
mass flow, 0,01 kg/h = 81
Oil
TimedStartStop
volume, 10 l = 20
surface tension
absolute load priority
The visual effect of channel 24 is inactive = 0
Relative Control RGBW
Shall specify the fading step size or to the code to stop the fading of the colour white
Cool Stage B Actuator Target Position
LTRF
Data Link Layer Busmonitor = 1
a point representing DPT 6.001: Percent V8
Percent V8
power, 0,1 GJ/h = 176
Effective value of the comfort push button
alarm = 1
a point representing DPT 20.1208: TIC Type
TIC Type
a point representing DPT 201.109: HVAC Emerg Mode Z
HVAC Emerg Mode Z
conductivity, electrical
a point representing DPT 22.103: Combined Status RTC
Combined Status RTC
Heat Stage A Actuator Fault
This state type expresses that the red part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.
Chromaticity Red
is composed by input
energy, 1 Wh = 3
The tag category contains individuals allowing to express that a point value originates from another system with a specific/underlying communication protocol.
Protocol
a point representing DPT 201.108: Occ Mode Z
Occ Mode Z
DPT 14.024: Value of electric flux
Value Electric Flux
A multimedia room is a space in a building that is used to contain multimedia gadgets such like consoles and entertainment. Preferably used with a Room.
Multimedia Room
Battery Failure
a point representing DPT 21.1010: Channel Activation 8
Channel Activation 8
Consumer = 0
a point representing DPT 20.1207: Peak Event
Peak Event
(SI) unit class for function points (FP) and datapoints.
Unit
A functional block represents a software element that has internal storage and produces a computable result with output values when executed with a particular set of input values.
Functional Block
no occupancy from presence detectors = 0
volume flow, 1 l/h = 59
Effective value of the presence status
Standard three-phase = 4
two push buttons/binary inputs mode = 4
a point representing DPT 2.012: Invert Control
Invert Control
Power is the rate at which work is performed or energy is transmitted, or the amount of energy required or expended for a given unit of time. As a rate of change of work done or the energy of a subsystem, power is work divided by time.
Mask Bit Info On Off Output 2
5.x
1 min = 10
Physical housing for electrical circuits, fuses, and breakers. A electric panel (also known as distribution board, panelboard, breaker panel, DB board or DB box) is a component of an electricity supply system that divides an electrical power feed into subsidiary circuits while providing a protective fuse or circuit breaker for each circuit in a common enclosure.
Electrical Panel
2 stage = 2
Active Mode
HS - Hardwired inhibit
a point representing DPT 209.100: StatusHPM
StatusHPM
Limits a numerical datapoint value in its applicative behavior to a maximum. Represents an external definition, hence it is also used from other concepts, therefore no domain is defined (merged ontologies -> intersection problems). The range xsd:decimal covers also numerical values with a fraction such as 12.34 or -13.56.
maximum
Phenomenon Quality Kind
EnableComfort
Level 14 = 14
To a device assigned trade, whereas the trade definitions (names/structures) can be freely defined by the MaC user. The trade definitions MAY have a logical relation to the KIM trade tags. A device is assigned to one trade only.
assigend trades
digit 3 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
To define a generic set of tags with no limitation on the amount. The tag set may represent a quality kind or process kind.
has tag set
The tag represents information for a logical point, a communication interworking (logical) input Point, it receives data.
Logical Input Point
An OP relationship to a list that describes the position of a point in a control loop.
has point function type
Compressed Air = 9
Day
system and functions of common interest = 1
process fault / controller fault = 2
power, 0,01 kJ/h = 49
a point representing DPT 12.102: LongTimePeriod Hrs
LongTimePeriod Hrs
Entrance generally refers to the place of entering like a lobby, foyer, gate, door, or road or the permission to do so. Preferably used with an Room.
Entrance
actuator has a failure
To represent a location, used to express a spatial location structure. The defined location model class/subclass structure does not reflect the hierarchy of a real world spatial building, such as a site/building with floors, rooms and/or spaces.
Ort
a point representing DPT 20.001: SCLOMode
A stand-alone house (also called a single-detached dwelling, detached residence or detached house) is a free-standing residential building. Preferably used with a Building or Site/Space.
Familiy House
LoadFailedDetection
KNX SN
waste water meter = 40
Shutter Position Percentage
a point representing DPT 20.013: Time Delay
Time Delay
area
Fan Stage
FanSpeed
Protection
includes key value pair
HVAC Valve Actuator
Activation state of channel 19
RelDimmingSpeed
Smoke is a suspension of airborne particulates and gases emitted when a material undergoes combustion, together with the quantity of air that is entrained or otherwise mixed into the mass. It is commonly an unwanted by-product of fires.
Smoke
a point representing DPT 7.006: TimePeriodMin
TimePeriodMin
extended alarm = 3
logical function OR = 0
This state type expresses that a room is unoccupied, i.e. no people are in the room. This state type is the inverse of the 'Presence Occupied' state type.
Presence Unoccupied
Signed value with classification and validity
no alarm = 0
A child OP relationship to a list that describes the generic locality characteristic where an observation or actuation is made. It is a generic “place of action”, when e.g., assigned to a room this means “the action happens in a place that is a room” but not in which room exactly, this is a room instance of an installation.
has locality
DPT 14.064: Value of sound intensity
Value Sound Intensity
language code ISO 639-1
A strong OP relationship to express a relation to a room segment contained in a room or room segment.
has room segment
Current lighting level in %. In case of a switching actuator LSAB the range is limited to the discrete values 0 % and 100 %.
a point representing DPT 242.600: Colour xyY
Colour xyY
The symbol is a glyph that is used to represent some concept, typically a unit or a quantity, in a compact form. For example, the symbol for an Ohm is a capital greek Omega. This contrasts with 'unit:abbreviation', which gives a short alphanumeric abbreviation for the unit, 'ohm' for Ohm.
symbol
ErrorClass_System
composes input
delay time (min)
room temperature setpoint shift standby (delta value)
volume flow, 1000 ml/s = 78
a point representing DPT 1.1201: EnergyDirection
EnergyDirection
Heat Stage A Actuator Valve Kick
A human friendly description (longer text), used to define user specific data for an individual. Edited in a MaC or from predefined product data or dictionary content. No limitation of the actual amaount, external entites may add additional language depended text. The 'Range' is not limited to a string, allowing to express also text in several languages (note W3C does not define a range).
description
a point representing DPT 20.609: LoadTypeSet
LoadTypeSet
AbsSetvalueControl
This state type expresses that an HVAC system has neither primary nor secondary stage (for its cooling or heating subsystem). In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages None
a point representing DPT 207.600: Status Lighting Actuator
Status Lighting Actuator
resistance
CloudCover
DHWMode
a point representing DPT 5.001: Scaling
second character of RegionCode, ASCII-coded
a point representing DPT 1.002: Bool
Bool
OverheatAlarm
is location of
at least one window opened = 1
The visual effect of channel 7 is inactive = 0
The target value represents a status of a corresponding source datapoint.
has status
A specific Application Function that controls, for example, the speed of a pump.
Pump Control
room temperature setpoint standby
A villa is a upper class country house. Preferably used with a Building.
Villa
temperature difference
This state type expresses that the green part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.
Chromaticity Green
current position=0 = 0
a point representing DPT 12.1200: VolumeLiquid Litre
VolumeLiquid Litre
Building not in use = 1
Other = 0
Cool Stage A Actuator Current Position
A Device can be any electronic equipment with some computing ability that has a firmware, optionally with input and output terminals (I/O), an Application Program that provides as set of Points as the interface for the I/O operations, and parameter values controlling the behavior of the I/O operations at Runtime.
Duration Test Pending
Calculated = 1
An item offered for sale; it can be assigned from any equipment. Manufacturers usually provide identifiers for each product they make. Identifier examples are type/model or version number or the order number.
Product
Group Address = 1
power range the device will operate for the given time period
Oversupply
Actual relative power %
Monday = 1
Indicator whether sequence is selected to be executed within the power sequence container
absolute temperature value
DPT 14.069: Value of absolute temperature
Value Absolute Temperature
temperature, common
critical = 1
DPT 14.057: Value of power factor
Value Power Factor
A functionality represents a concrete piece of software and a set of any type of interfaces (mainly Points) that is needed to accomplish a task for which a Device is designed for.
Functionality
Cooling Mode Enabled
Movement Trigger
volume flow, 0,001 l/h = 56
Position unchanged = 0
5 min = 16
Thread
is point interface of
"Frequency" is the number of occurrences of a repeating event per unit time. The repetition of the events may be periodic (that is. the length of time between event repetitions is fixed) or aperiodic (i.e. the length of time between event repetitions varies). Therefore, we distinguish between periodic and aperiodic frequencies. In the SI system, periodic frequency is measured in hertz (Hz) or multiples of hertz, while aperiodic frequency is measured in becquerel (Bq). In spectroscopy, v is mostly used. Light passing through different media keeps its frequency, but not its wavelength or wavenumber.
Frequency
a point representing DPT 225.002: Scaling Step Time
Scaling Step Time
Expresses if an location is outside in perspective of a Building. A Space, Site or SiteSegment can be outside of a Building.
Outside
Außenbereich
On = 1
Switch OnOff
StatusStartOptim
This state type expresses that an equipment, such as a luminaire, is switched on. This state type is the inverse of the 'Off State' state type.
On State
A generic referencing mechanism between one or more points that reflects a specific view of the installation.
Aspect
a point representing DPT 1.015: Reset
Heat Stage A Actuator Calibration Mode
3-bit controlled
validity of the Absolute Colour Temperature
At least one DPT field must be present for a datapoint type (DPT).
is assembled with
mass, 10 kg = 28
ZWave
DPT 14.041: Value of luminance
Value Luminance
A specific Application Function category for overall management functions of a plant or a part of a plant. For example, a Scheduler automatically schedules the systems, such as heating, ventilation, and lighting, to coordinate with facility usage. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Plant Management Control
temperature (absolute)
An Air Handling Unit (AHU) is an equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system.
Air Handling Unit
Breaker/Valve is released = 2
no comfort push button is pressed = 0
no failure = 0
7.x
CombinedStatus_FA
24 times channel activation
TempRoomSetpSetHeatShift
a point representing DPT 13.100: LongDeltaTimeSec
LongDeltaTimeSec
2 min = 13
To define the existence of an application program as part of a device, except it is a pure HW, such as a power supply or similar. Devices may support more than one application program, at runtime in an installation usually one.
hosts
power, 0,1 MW = 168
Heat Stage B Actuator Fault
is building of
a point representing DPT 20.008: PSUMode
PSUMode
Level 0 = 0
Activation state of channel 17
is location usage of
Sunshiny = 2
No Day of Week
Mask Bit Info On Off Output 5
a point representing DPT 213.102: TempRoomSetpSetShift[4]
TempRoomSetpSetShift[4]
a point representing DPT 20.603: BlinkingMode
BlinkingMode
Illuminance is the total luminous flux incident on a surface, per unit area. It is a measure of the intensity of the incident light. As a note, focus is the light source, which is mostly the interest in the building control domain.
Illuminance
Failure detected = 2
validity of TempWater field
The visual effect of channel 10 is active = 1
Shall specify whether the colour component green shall be increased or decreased.
a point representing DPT 22.1010: Channel Activation 16
Channel Activation 16
time
status of all timers wether they are running or not. each bit declares the status of the timer with the id of the bit position. bn = 0 means timer n is not running, bn = 1 means timer n is running
StatusGO
This DPA represents a generic Status (Z8), as described in KNX Vol 3/7/2, section 4.1.2. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring to the device: Bit 0) OutOfService (modeled by the state type tag:operationalStateOutOfService); Bit 1) Fault (modeled by the state type tag:operationalStateFaulty); Bit 2) Overridden (device being in maintenance mode, modeled by the state type tag:operationalStateMaintenance); Bit 3) InAlarm (modeled by the state type tag:operationalStateInAlarm); Bit 4) AlarmUnAck (modeled by the state type tag:operationalStateAlarmPending)
Time = UT+X = 0
Refers to the first phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.
Phase L1
UserChangeOverMode
other fault = 4
8-bit signed value
A strong OP relationship to express a relation to a floor contained in a location.
has floor
a point representing DPT 20.104: LoadPriority
The access trade is the selective access and control to resources (e.g. a place, information, etc.).
Access Control
A Cabinet is a physical enclosure for electrical or electronic equipment such as automatic switches, fuses, circuit breakers, control devices, timers and similar.
Effective value of the window status
A Quality Kind with at least one adjustable quantity property that addresses an 'equipment', and the quantity property can be directly changed.
adjusts equipment quality kind
energy, 10000 Wh = 7
Modbus
volume, 100 l = 21
Failed, max delay exceeded = 4
An OP relationship to a list that describes the application areas in which a aspect (incl. subclasses) or a datapoint is used. An (parent) entity may inherit all trades from its underlying childs, this is domain/application specific.
operates for trade
Shutter Position Length
a point representing DPT 22.101: StatusRHCC
StatusRHCC
8-Bit Enum with Status/Command
A terrace is an external, raised, open, flat area in either a landscape (such as a park or garden) near a building, or as a roof terrace on a flat roof. Preferably used with an Space.
Terrace
valid = 0
validity of the fields CS and Step Code Saturation.
ActTargetPos
Inhibit mode active = 2
A point representing an enabling/disabeling of a (sub) functionality.
Activation
self inductance
disable = 1
volume flow, 100 l/h = 61
A floor is the bottom surface of a room or vehicle. Floors vary from simple dirt in a cave to many layered surfaces made with modern technology. Floors may be stone, wood, bamboo, metal or any other material that can support the expected load.
Floor
Start = 1
This state type expresses that an equipment is controlled by an automatic algorithm, rather than being controlled manually. The equipment's input commands are computed by e.g. a controller and interpreted with a normal priority. This state type is the inverse of the 'Override Mode Manual' state type.
Override Mode Automatic
Day / Night
mode 2 is active = 4
active = 0
DPT 14.043: Value of luminous intensity
Value Luminous Intensity
oBIX
The tag represents information for a physical point, a hardwired (physical) analogue or digital output point, from the perspective of the application program
Physical Actuator Point
Room Temperature Controller
true = actuator setvalue is locally overridden, e.g. via a local user interface
a point representing DPT 222.101: TempRoomSetpSetShiftF16[3]
TempRoomSetpSetShiftF16[3]
power factor
By a MaC (ETS) allowed location usages for a building.
Mac building
Cooling Load meter (outlet) = 11
DPT 14.074: Value of time
Value Time
Contract number of an installation, usually generated by Mac (edited by an installer).
contract number
Cabling used to convey electricity (AC/DC) or data.
Wire
is channel of
trigger (0) = 0
Overheat-Alarm
To define the type (DPT) of a function point or datapoint. A function point represents runtime data, therefore the cardinality is of max 1 DPT. A datapoint represents config data, therefore the cardinality is of min 0 DPT (but it should be at least one).
has datapoint type
Economic Heat/Cool Mode = 13
Off = 0
Points with other operation types rather than a datapoint. It asynchronously pushes event data to consumers (see thing description).
Eventpoint
Open = 0
A room is a space in a building that is delimited by walls/windows, ceilings, floors and has a door or a passage to enter the room, it can be subdivided into locations of type room segment.
Raum
Room
StatusRoomSetup
Light Absolute Setvalue Request
Certfication status of an application program.
certfication status
analog input -> 0% to 100% = 3
SatusECO
a point representing DPT 9.008: Value AirQuality
Value AirQuality
Device for toggling a state.
Other Residential
is actionpoint of
Heat Stage B Proportional = 3
Heat Stage A Actuator Overridden
A hospital is a health care institution providing patient treatment with specialized health science and auxiliary healthcare staff and medical equipment. Preferably used with a Building.
Hospital
BinarySceneTeachIn
1.x
A relation between two locations that share a common interface such as a wall or door, but do not intersect.
has adjacent location
mass, 1000 kg = 30
light breeze = 2
some failure in boiler sequence: HPM itself or boiler(s) have a failure (mainly used for monitoring)
The tag category contains individuals that describe a phenomonom (including substances) that can only be indirectly observed or actuated upon as part of the building control system. The tag category does not describe concrete existing things, for example the person John Smith.
Phenomenon
A channel is grouping datapoints together, which may linked to a related hardware (such as a terminal) and/or a related application program. It fulfils a certain functionality of the device, which is a collection of datapoints (when available with a standardized semantic meaning as functional block) and the related hardware connections (i.e. input or output terminals). A channel is derived from parent concepts that are specified as part of the EN 50090-6-2.
Channel
a point representing DPT 8.002: DeltaTimeMsec
DeltaTimeMsec
A user operated staircase light switch/trigger request including an explicit status.
Staircase Lighting
Energy Direction
stage 2 / modulation active
An intrusion system monitors a building or systems for malicious activity or policy violations.
Intrusion Detection
DPT 14.066: Value of stress
Value Stress
a point representing DPT 202.2: UCount Value 8 Z
UCount Value 8 Z
Keep Last State = 1
Low = 0
3x 2-byte float value
near gale / moderate gale = 7
Electromagnetic radiation in the visible spectrum
Light
a point representing DPT 5.010: Value 1 Ucount
Value 1 Ucount
End of time period that will be covered by the power profile
The Application Function controls the 'air temperature' of a room or zone (group of rooms or space) individually, thereby maximizing comfort and minimizing energy costs. The control loop often uses the outside temperature or a reference room temperature as a process variable.
Zone Heating Control
time period
Started automatically = 1
unreliable synchronisation source (mains, local quartz) = 0
Cool stage A for normal cooling = 3
value according additional parameter = 1
a point representing DPT 23.003: UpDown Action
UpDown Action
V32Z8
HeatingOnly = 2
This state type expresses that mode 'Emergency Cooling' is chosen for the HVAC system. Usually, this mode indicates whether emergency cooling demand is requested for the HVAC system, e.g. for heat protection of a room. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Emergency Cool
Activation state of channel 23
sound intensity
up = 0
a point representing DPT 246.600: Battery Info
Battery Info
A cooktop (American English), hob (British English), or stovetop (American English), is a home appliance device (EN 50523: gas cooktop, hob or induction hob) commonly used for cooking that is commonly found in kitchens and used to apply heat to the base of pans or pots.
Cooktop
cEMI Transport Layer = 6
a point representing DPT 7.001: Value 2 Ucount
Value 2 Ucount
Time delay = 5
power, 10 kJ/h = 52
a point representing DPT 234.001: LanguageCodeAlpha2 ASCII
LanguageCodeAlpha2 ASCII
accepted = 1
This state type expresses that the alarm status of a datapoint is not yet acknowledged by an operator. No assumption about the validity of the datapoint’s value can be made.
Operational State Alarm Pending
Used to indicate that an entity is not yet completely defined and should be excluded from use in MaCs. Note 1: if this property has the value false, it must be treated exactly as if ths property would not be present at all. Note 2: If an entity has been completed for MaC use, this property must be removed from the entity.
is incomplete
By a MaC (ETS) allowed location usages for a site.
MaC site
building mode
Lightly cloudy = 3
To define a relation to a point from an aspect. Aspects without any points is possible.
groups
ActCurrPosHeatStageB
Blinds Slat Position Degrees
The value of the point is NOT A COMPLETE value but needs to be added to another value to be usable, such as the current comfort temperature setpoint + 2 degree celsius. As the examples explain, there is no distingtion if it needs to be added to itself or another value.
Relative Value
inverse value of InfoOnOff is sent = 3
StatusEcoC
electric dipole moment
Info On Off
a point representing DPT 20.121: BackupMode
BackupMode
not occupied = 0
the range of the fill level that will be reached in the given time
Scattered clouds = 4
Version identifier that has generated an installation, usually generated by a Mac.
mac version
a point representing DPT 249.600: Converter Test Info
Converter Test Info
open = 1
DPT 14.027: Value of electric potential
Value Electric Potential
volume, 1000 l = 22
A user operated room temperature control including actual room/outside temperature inputs and valve control outputs.
Room Temperature Control
Used to control an actuator equipment to regulate regulate the flow of fluid (valve position). Don't care if the valve position is internally operated from the actuator by a motor or other means.
Valve Actuator
timestamp when the constraints becomes valid
scene number
Manua operation (overridden)
master = 1
a point representing DPT 20.608: SwitchOnMode
flat that is set to true when the timer is currently running
current factor that will be multiplied with given power range of the operation mode. will be set with a transition instruction
From MaC assigend individual address (IA).
Individual Address
FanSpeedUser
SwitchHeat
ComfortProlongUser
Shall specify the fading step size or to the code to stop the fading of the colour green
Unsigned time-value for calculating fading time.
No WD
The visual effect of channel 3 is active = 1
ActTargetPosCoolStageA
open on overheat with a current value under the maximum switching current value = 6
a point representing DPT 7.010: PropDataType
PropDataType
Supply air temperature cooling setpoint
Equipment to transfer waste heat into the atmosphere. A cooling tower is a device that rejects waste heat to the atmosphere through the cooling of a coolant stream, usually a water stream to a lower temperature.
Cooling Tower
Info On Off Output 13
The volume of a solid object is the three-dimensional concept of how much space it occupies, often quantified numerically. One-dimensional figures (such as lines) and two-dimensional shapes (such as squares) are assigned zero volume in the three-dimensional space.
Volume
a point representing DPT 20.014: Beaufort Wind Force Scale
Beaufort Wind Force Scale
Application functions that controls the quantity 'air humidity'.
Air Humidity Control
Activation state of channel 1
DPT 14.036: Value of heat flow rate
Value Heat FlowRate
a point representing DPT 13.011: ApparantEnergy
ApparantEnergy
magnetization
ChangeOverStatusWater
indicates whether overload is critical (e.g. too low boiler temp.) or uncritical (e.g. requested boiler temperature can not be provided but boiler temperature is above critical lower limit)
DPT 14.007: Value of an angle (in degrees)
Value AngleDeg
To define a functionality (=collection of datapoints) as part of an application program.
implements
volume
Scene number
An operation kind describes by what means the quantity kind value of a specific 'type of interest' from a QK or the state type value is used. The same OK individual MAY refer to arbitrary QK individuals.
Operation Kind
A generic concept to represents an interface to data. A point can carry additional meta data, provided by tags and/or feature of interests. To describe a point more precise the class has several subclasses.
Point
a point representing DPT 1.004: Ramp
Ramp
Morning Warmup = 2
Heat meter = 4
Defines the ability to write a datapoint. The r/w limits set with boolean values true (default) or false. It may be used to limit the access from a 3rd party interface or similar, set by a MaC.
writable
A generic comment, used from several concepts to express the content edited by a MaC (such as an installation comment).
comment
DHW operating mode
Cool Stage B Actuator Status
a point representing DPT 1.017: Trigger
a point representing DPT 2.004: Ramp Control
Ramp Control
DPT 14.025: Value of electric flux density
Value Electric FluxDensity
An atrium is a large open-air or skylight-covered space surrounded by a building.
Atrium
This state type expresses that the blue part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.
Chromaticity Blue
Battery used to store electric energy.
Battery
Application Area
validity of the fields CW and Step Code Colour White.
This state type expresses that a contact (e.g. a valve end position contact or a partition wall status, or window contact) is in closed state. This state type is the inverse of the 'opened' state type.
Closed State
a point representing DPT 220.100: Next Temperature and Time Delay
TempHVACAbsNext
a point representing DPT 20.011: ErrorClass System
ErrorClass System
occupancy at least from one presence detector = 1
Level 4 = 4
light air = 1
a point representing DPT 9.003: Value Temp A
Value Temp A
is state kind of
Light Switching Actuator Basic
corresponding Datapoint is in alarm
Water meter = 7
electric displacement
Combined Switch On Off
a point representing DPT 217.001: Version
Zigbee
ActuatorErrorInfo
3-byte colour RGB
Heat Stage B Actuator Current Position
a point representing DPT 1.005: Alarm
do not send = 0
to express a “metadata to runtime” relation between different datapoints. Datapoints may provide further information about other datapoints but not including to manipulate their actual value at runtime.
is meta data of
DHW temperature setpoint for Reduced operating mode
is proxy for
Fixed = 0
OtherEnergySourceActive
Relative Set Value Control Red
A parent data property, used to express any kind of generic data that relates to a function point.
function point data
timestamp when this constraint will be invalid
InfoOnOff
electric current density
Decrease = 0
DPT 14.029: Value of electromagnetic moment
Value ElectromagneticMoment
HVAC mode
A Device can be any electronic equipment with some computing ability that has a firmware or supports the installation of software. Examples are pumps, dampers, valves, sensors, detectors, limit switches, remote/local switches or automation devices.
Device
basic alarm = 2
Reset Duration Test Done = 6
true = actuator is locked, e.g., via input LockDevice.
A Point provides the current (measured) value of a quantity kind or the current (status) value of a state kind.
Process Variable
Shall specify whether the colour component white shall be increased or decreased.
The value of the point is a COMPLETE value and does not need any other point value to be usable (21 °C, fan speed 30 %).
Absolute Value
DayOfWeek
Heat/Cool for changeover applications = 5
energy, 0,01 Wh = 1
room temperature setpoint shift building protection (delta value)
timer declarations defining ID and duration
a point representing DPT 16.001: String 8859 1
String 8859 1
not active = 0
Quality of clock
SolarEnergySupport
TempRoomSetpLoadShedShift
SNMP
The visual effect of channel 14 is inactive = 0
A child OP relationship allowing to define the equipment where an observation or actuation is made upon.
has equipment type
The value is a continuous stream of totalization, the tag does not define any relation to a value dimension (metering data in unit kWh, amount of person as unitless number).
Totalized Value
LampFailure
amplitude
Read = 1
Represents a ISO 8859-1 character. Encoding according to the character set ISO-8859-1 (Western Europe)
Character
An airport is an aerodrome with extended facilities, mostly for commercial air transport. Preferably used with a Site or Location.
Airport
To express an “impact to cause” relation between different datapoints. Datapoints may affect other datapoint values, including manipulating their actual value at runtime.
influences
NoDem = 20
occupancy mode
a point representing DPT 20.100: FuelType
FuelType
a point representing DPT 203.102: Sun Intensity Z
Sun Intensity Z
FanActive
Brightness External
This state type expresses that mode 'Free Cool' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system performing a cooling task by using cold ambient air instead of an energy-intensive chiller unit. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Free Cool
a point representing DPT 21.601: LightActuatorErrorInfo
LightActuatorErrorInfo
LED, leading = 7
some failure in the water temperature controller
has datapoint
mode level
Sunny = 1
ActTargetPosHeatStageB
reactance
a point representing DPT 1.1200: ConsumerProducer
ConsumerProducer
This state type expresses that a value is changed relatively in a 'decreasing' manner, i.e. the value is lowered. This state type is the inverse of the 'Increasing' state type.
Decreasing
a point representing DPT 240.800: CombinedPosition
CombinedPosition
closed = 0
a point representing DPT 20.804: BlindsControlMode
The visual effect of channel 5 is inactive = 0
EnableCool
controls operation of stage 1 or base stage
volume flow, 100 ml/s = 77
a point representing DPT 20.600: Behaviour Lock Unlock
Behaviour Lock Unlock
DHW temperature setpoint for Normal operating mode
Level 6 = 6
Thursday = 4
a point representing DPT 7.003: TimePeriod10MSec
TimePeriod10MSec
ValveKick
An Application Function for a generic switching of an equipment, such as an actuator terminal or similar.
Used to refer to management client (MaC) specific data that are not present (with a unique resolvable identifier) within the KNX information model. With this 'link' reference shared data can be defined for the same entity, whereas the data are spread over different sources. Usually, the data are generated in different tools and finally used in a MaC, the latter can import the data chunks and compose them correctly to an full entity.
has component id
InfoOnOffFromDimmingActuator
a point representing DPT 265.009: DateTime OpenClose
DateTime OpenClose
Supply air, e.g. for VAV = 2
Overrun
Outside Temperature
not running = 0
enabled (PSU/DPSU fixed on) = 1
a point representing DPT 265.005: DateTime Alarm
DateTime Alarm
volume, 1 l = 19
Electrical circuits for direct currents. This is a specialization of the tag "Circuit".
Circuit, DC
trigger (1) = 1
Audio refers to the part of multimedia, which is dealing with sounds. The trade audio contains applications for producing and capturing sound signals.
Audio
2-byte float value
DPT 14.038: Value of impedance
Value Impedance
Refers to information that originates from algorithms, i.e. usually computed by a controller device.
Automatic
Efficiency is the ratio of output power to input power.
Efficiency
current position>0 = 1
Day of week field not valid = 1
corresponding Datapoint Main value is corrupted due to failure
RelSetvalueControlCmd
Actual Dimming Value Green
Cool Stage A Actuator Overridden
only move Up/Down mode (shutter) = 0
activated with security = 2
Staircase Switch Request
Weather is the state of the atmosphere, describing for example the degree to which it is hot or cold, wet or dry, calm or stormy, clear or cloudy.
Weather
validity of the ActiveElectricalEnergy data
1-bit controlled
Unknown Device type = 15
updated value = 5
Slats Position
Goto Rest Mode = 1
Minutes
SolarEnergyOnly
temperature sensor input = 4
The visual effect of channel 17 is active = 1
Info On Off Output 5
A point represents an alarm status of a functionality that typically needs immediate attention.
a point representing DPT 21.1000: RF ModeInfo
RF ModeInfo
a point representing DPT 234.002: RegionCodeAlpha2 ASCII
RegionCodeAlpha2 ASCII
Enclosure for electrical and control equipment.
Panel
Info On Off Output 9
a point representing DPT 213.101: TempDHWSetpSet[4]
TempDHWSetpSet[4]
A section of piping that refers to those parts of distribution systems in buildings that are pipes, mostly for transporting water.
Pipe Section
Absolut load priority = 2
a point representing DPT 1.012: Invert
Error Class
32-bit set
presence simulation = 1
emergency demand (heating or cooling) for room frost protection or de-icing
DPT 14.1201: Value of volume flux (in litres per second)
Volume Flux ls
HVAC Direct Electrical Heating = 12
A parent data property, used to express any kind of generic data that relates to a product.
product data
mass, 0,01 kg = 25
Motor used with a pump to move fluid.
Pump
StatusPreCool
has upper floor
A specific Application Function category for 'monitoring' a zone, equipment or energy consumption (metering). The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Monitoring
16-bit unsigned value & 8-bit enum
impedance
a point representing DPT 21.106: StatusAHU
StatusAHU
a point representing DPT 238.001: SceneConfig
SceneConfig
Overridden
This DPA refers to the actuator being manually overridden. In contrast to the Z8 general status fields, in this case the Overridden status information refers to the actual manual operation (and not to an overridden state due to maintenance as does the Z8 field). The overridden state refers to the actual position of the valve (and thus to the specific property Position Vector), which is why the QualityKind is used at this point.
heat capacity
A parent data property, used to express any kind of generic data that relates to a device.
device data
power, 1 W = 43
DHW mode
a point representing DPT 4.002: Char 8859-1
Char 8859-1
corresponding Datapoint Main value is overridden
volume flow, 1000 l/min = 71
CombinedStatus_HVA_CoolA
Switch On Off Green
This state type expresses that a room is occupied. The actual number of people is not of interest. This state type is the inverse of the 'Presence Unoccupied' state type.
Presence Occupied
Activation state of channel 20
defines wich timers are blocking for this transition. each of the 16 timers could be referenced by setting the bits 0-15 to 0 (not blocking) or 1 (blocking)
a point representing DPT 206.100: HVACModeNext
Hardwired Inhibit is inactive = 0
a point representing DPT 20.110: HeaterMode
HeaterMode
a point representing DPT 265.001: DateTime Switch
DateTime Switch
scene A = 0
volume flow, 0,001 l/min = 65
a point representing DPT 203.104: HVAC Air Flow Absolute Z
HVAC Air Flow Absolute Z
Level 1 = 1
number of fill level target profile elements
Ventilation is the intentional introduction of outdoor air into a space. Ventilation is a mechanical system in a building that brings in fresh outdoor air and removes the contaminated indoor air.
Ventilation
A site segment subdivides a site, it is usually occupied by a building.
Liegenschaftsteil
Site Segment
is point operation of
To define the presence of a (tangible) equipment, such as a device as part of a cabinet (that is also an equipment).
has part
A tumble dryer, also known as clothes dryer or simply dryer, is a powered household appliance (EN50523) that is used to remove moisture from a load of clothing, bedding and other textiles, usually shortly after they are washed in a washing machine.
Tumble Dryer
HS - Hardwired switch
gas = 2
a point representing DPT 20.607: DimmPBModel
DimmPBModel
Refers to the concentration of particles in the air, measured in ppm. This is a specialization of quantitykind:Concentration.
Concentration, Smoke
a point representing DPT 1.014: Input Source
Input Source
a point representing DPT 3.007: Control Dimming
Control Dimming
Unsigned counter value
In physics, a fluid is a liquid, gas, or other material that continuously deforms (flows) under an applied shear stress, or external force.
Fluid
A garage is a walled, roofed structure for storing a vehicle or vehicles that may be part of or attached to a home ('attached garage'), or a separate outbuilding or shed ('detached garage'). Preferably used with an Room.
Garage
TempRoomSetpSetHeat
digit 1 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
The value of the target point is sent at the earliest after a certain duration. The duration is defined by the metadata datapoint's value.
is minimal repetition of
A home cinema is a space in a building that is used to enjoy movies. Preferably used with an Room.
Home Cinema
energy, 10 Wh = 4
is function point of
SwitchOff message sent = 1
a point representing DPT 7.004: TimePeriod100MSec
TimePeriod100MSec
a point representing DPT 25.1000: DoubleNibble
DoubleNibble
CRC-error = 9
A point representing a validity assessment of a datapoint value.
Validity
Panel housing controllers and networking gear. A control panel is a flat, often vertical, area where control or monitoring instruments are displayed or it is an enclosed unit that is the part of a system that users can access, such as the control panel of a security system (also called control unit).
Controls panel
A specific Application Function category that controls a quantity (e.g. temperature, pressure) of the phenomenon water. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Water Control
Alternating current electricity
Electricity, AC
electric charge
This state type expresses the state of no storm. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of no storm, storm protection is not required and this equipment might be used for shading purposes as intended. This state type is the inverse of the 'Storm State' state type.
No Storm
DPT 14.019: Value of electric current
Value Electric Current
is protocol operated by
filtering by Domain Address = 1
a point representing DPT 20.112: MasterSlaveMode
Data Link Layer = 0
volume flow, 1 l/min = 68
An OP relationship to a list that describes the runtime interworking operation type of the value of a point. Examples are absolute values, values representing an offset or realtive values.
has point operation
An application function combines as set of individual functions to achieve its desired behavior, typically with a combination of devices exchanging information via their input and output datapoints. A number, state or comment may be edited in a MaC as a string (allows also non-number chars).
Application Functions
HW fault = 4
Specifies for enumeration DPTs a string value, that can be used from an (external) API at runtime.
value API
deactivation of priority = 1
DPT 14.051: Value of mass
Value Mass
a point representing DPT 13.1200: Delta Volume Liquid Litre
Delta Volume Liquid Litre
Standard = 1
A factory, manufacturing plant or a production plant is an industrial facility, often a complex consisting of several buildings filled with machinery, where workers manufacture items or operate machines which process each item into another. Preferably used with a Building.
Factory
is composed by output
DPT 14.016: Value of electrical conductivity
Value Electrical Conductivity
Warm Water meter (30 °C to 90 °C) = 6
Water Change Over Status Sensor
open on PLC or Euridis command = 4
A vertical shaft in a building which allows the passage of an elevator from floor to floor. Preferably used with a Space.
Elevator Shaft
A network bridge is a computer networking device that creates a single, aggregate network from multiple communication networks or network segments (typically on OSI Layer 2). Bridging is distinct from routing. Routing allows multiple networks to communicate independently and yet remain separate, whereas bridging connects two separate networks as if they were a single network.
Network Bridge
DPT 14.028: Value of electric potential difference
Value Electric PotentialDifference
Angular Velocity refers to how fast an object rotates or revolves relative to another point. It is defined as the change of angle per unit time and usually measured in Hertz (1/s).
Angular Velocity
digital input inverted = 2
TimeDelay
The leading number of the major datapoint type (DPT) in bits, specified in KNX with a numerical scheme. The major type must be present for sub types and for a major type. The range is used to include 0 (the KNX DPT numbering scheme starts at 0).
datapoint type major number
Friday = 5
a point representing DPT 2.005: Alarm Control
Alarm Control
Fan only = 9
A Domestic Hot Water (DHW) system delivers hot water to fixtures used by people at the sink, shower, tub and any other appliance where water may contact humans. They typically work by delivering hot water through a centralized storage tank separate from water that may be used for steam or hydronic heating.
Domestic Hot Water
Busy
EnableTempRoomSetpAlt
a point representing DPT 13.010: ActiveEnergy
Active Energy
An OP relationship to express a relation to an equipment from a location. This allows to define the presence of a (tangible) equipment, such as a device as part of a location. Mainly it expresses the “assembly place” of an equipment. The here meant location (domain) is the "installation location" of the equipment, also a device. To retrieve the "place of action" of a device it is needed to traverse from a device/datapoint -> functionPoint/application function/../location.
contains equipment
Default values, used to fill KNX data fields with proper content in case no related data are provided from an external entity such as an API. The type of “fieldDefault” depends on the type of the field it is associated to. It is ... for (field type): 0 or 1 (B), xsd:positiveInteger (U), xsd:integer (V), xsd:float (F), xsd:integer (N, as it contains the KIM-value part of a key-value-pair), xsd:string (A and A[n]). Field types D<n> and Z8 will not contain a fieldDefault value.
field default
StatusMorningBoostH
Load Management = 40
set = 1
a point representing DPT 243.600: Colour Transition
Colour Transition
Color temperature is the color of light emitted by an idealized opaque, non-reflective body at a particular temperature measured in kelvins. The color temperature scale is used to categorize the color of light emitted by other light sources regardless of their temperature. Color temperatures over 5000 K are called "cool colors" (bluish), while lower color temperatures (2700–3000 K) are called "warm colors" (yellowish).
Light Colour Temperature
Numbered Scene Control
Time delay
a point representing DPT 9.004: Value Lux
Value Lux
A specific Application Function category for energy control that reflect an active process of planning, monitoring, and optimizing the energy production, consumption, distribution and storage. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Energy Control
DHWNorm
The visual effect of channel 21 is active = 1
Goto Inhibit Mode = 2
conductance
strong breeze = 6
digit 6 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
a point representing DPT 231.001: Locale ASCII
Locale ASCII
a point representing DPT 18.001: SceneControl
SceneControl
Application Functions that controls the quantity 'water pressure'.
Water Difference Pressure Control
Current Colour RGBW
Mask Bit Info On Off Output 10
a point representing DPT 13.014: ApparantEnergy kVAh
ApparantEnergy kVAh
The visual effect of channel 11 is inactive = 0
Colour Set RGB
An apartment (American English), or flat (British English, Indian English, South African English), is a self-contained housing unit (a type of residential real estate) that occupies part of a building, generally on a single story. Preferably used with a Building.
Apartment
Start Date Time
Device Address
boiler sequence switched off due to local summer/winter mode (mainly used for monitoring)
This state type expresses that a contact (e.g. a valve end position contact or a partition wall status, or window contact) is in an opened state. This state type is the inverse of the 'closed' state type.
Opened State
temporarily no cooling in the production segment available
a point representing DPT 5.006: Tariff
Battery Information
Application functions that controls the quantity 'air pressure.'
Air Pressure Control
sensor fault = 1
reading of access information code was not successful = 1
DPT 14.077: Value of volume flux
Value Volume Flux
Latitude information
is part of
digit 5 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
a point representing DPT 20.1202: Gas Measurement Condition
Gas Measurement Condition
This state type expresses that mode 'Auto' is chosen for the HVAC system. Usually, this mode is associated with a local controller selecting the appropriate mode for the HVAC system (e.g. based on sensor data). In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Auto
a point representing DPT 13.001: Value 4 Count
Value 4 Count
This state type expresses that an equipment, an alarm or a certain situation is inactive. An inactive equipment is not working, which means it cannot fulfill its intended functionality. An inactive alarm means that the alarm state was not triggered. Finally, an inactive situation means that a certain state has not been reached. The tag 'Inactive State' is often used for situations that feature an enumeration of possible states (e.g. operational states, control modes, HVAC modes, ...) to make a boolean statement about one of these states. The state type 'Inactive State' is the inverse of the 'Active State' state type.
Inactive State
A Quality Kind with an observable quantity property that addresses a 'phenomenon', and the quantity property can only be indirectly determined.
observes phenomenon quality kind
Locale information
Open / Close
send if value changed during powerdown = 2
automatic once = 4
The visual effect of channel 18 is active = 1
activation energy
The value of the target point is explained with further details by the metadata datapoint's value.
is description of
alternative setpoint = 1
a point representing DPT 275.101: TempRoomSetpSetShiftF16[4]
Room Temperature Setpoint Shift
a point representing DPT 5.100: Fan Stage
Cloudy = 5
Activation state of channel 13
Physical unit used for driving mechanically actuated final controlling elements. Examples of actuating drives are electric, hydraulic or pneumatic actuating drives, diaphragm systems or piston actuators (see IEC 60050-351).
Drive
undefined = 0
AlarmUnAck
"Dew Point Temperature" is the temperature at which vapour in air reaches saturation.
Dew Point Temperature
a point representing DPT 9.006: Pressure
Pressure
a point representing DPT 21.002: Device Control
Device Control
force
8.x
Steam oven (also called combi-steamers, hot-air steamers, combination steam-convection ovens, or simply combi ovens) are cooking appliances (EN 50523) typically used in professional catering or food service operations.
Steam Oven
volume flow, 10 l/h = 60
actuator position is manually overridden
a point representing DPT 21.101: ForceSignCool
ForceSignCool
Light Current Dimming Value
'Delay' is the amount of time passing before a certain event is scheduled.
Delay
'void' = 3
angular velocity
Movement Detector for Lighting
is site segment of
This state type expresses that the normal room temperature setpoint from the HMI or supervisor is used for temperature control in a room.
Type of Temperature Setpoint Normal
Behaviour_Lock_Unlock
This state type expresses that mode 'Emergency Cooling' is chosen for the HVAC system. Usually, this mode indicates whether emergency heat demand is requested for the HVAC system, e.g. for frost protection of a room. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Emergency Heat
a point representing DPT 2.003: Enable Control
Enable Control
RelSetvalueControl
To define an operation kind that hosts a pedefined set of tags.
has operation kind
Function Test Pending
duration the timer is active when started
1 stage = 1
Additional heating/cooling stage (2. Stage)
This state type expresses that an equipment is in a forced state, i.e. its current value / position is a result of a command with very high priority. The equipment's normal processing of input commands is bypassed and the high priority input command is executed as-is. This state type is the inverse of the 'Not Forced State' state type.
Forced State
A basement or cellar is one or more floors of a building that are completely or partly below the ground floor.
Basement
Represents an ASCII character. The most significant bit shall always be 0. Encoding according to the ASCII table.
Dew Point Status Sensor
Lighting or illumination is the deliberate application of light to achieve some aesthetic or practical effect. Lighting includes use of both artificial light sources such as lamps and natural illumination of interiors from daylight.
Lighting
Refers to the second phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.
Phase L2
Cooling load meter (inlet) = 11
Brightness of the colour
invalid opcode detected = 11
Heat Stage B Actuator Overridden
An oven is a tool which is used to expose materials to a hot environment. Ovens contain a hollow chamber and provide a means of heating the chamber in a controlled way. Ovens are often used for cooking (home appliances EN 50523: gas oven or electical oven), where they can be used to heat food to a desired temperature.
Oven
Occupancy
Extract air, e.g. for VAV = 4
mass, 10000 kg = 31
Heat Stage B Actuator Status
A specific Application Function category that controls application functions is a specific category that represents an expected behavior or functionality of an equipment such as a 2-step fan speed control or an aggregation of application functions such as Air Handler Unit etc. In addition, the behavior or rather the effect in the real world can be expressed with a QualityKind. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Equipment Control
This state type expresses that a value is changed relatively in an 'increasing' manner, i.e. the value is raised. This state type is the inverse of the 'Decreasing' state type.
Increasing
duration that gives the seconds that this limit range stays valid
alarm status of corresponding Datapoint is not acknowledged
No test pending = 1
SolidState
This state type expresses the 'dehumidification' mode of the ventilation system. Usually, this is related to lowering the relative air humidity by removing moist air and replacing it with dry air.
Dehumidification Mode
HumRelSetpDehumEff
LoadDetectionError
a point representing DPT 20.604: LightControlMode
Room Setpoint Manager Temperature Driven
volume, 10000 l = 23
a point representing DPT 2.009: Direction 2 Control
Direction 2 Control
energy, 0,1 MWh = 128
a point representing DPT 213.100: TempRoomSetpSet[4]
TempRoomSetpSet[4]
angle, radiant
energy, 0,001 Wh = 0
a point representing DPT 12.101: LongTimePeriod Min
LongTimePeriod Min
a point representing DPT 12.100: LongTimePeriod Sec
LongTimePeriod Sec
DPT 14.021: Value of electric dipole moment
Value Electric DipoleMoment
hurricane = 12
A space is an area or volume providing certain functions of a building, it represents any kind of physical space that belongs to a building. A Space can also be outside of a building. The concept can be mapped to a IfcSpace.
Bereich
Space
LTRP
Relative timestamp = 4
Actual Dimming Value White
Scheduling in a building automation system is the process of systematically matching the use of heating, ventilation and air conditioning equipment with tenant occupancy schedules which is typically calendar-based.
Scheduler
ActuatorStatus
TempSetpShiftEco
TP1
EmergShutdown = 4
operation mode factor that defines the target power value within the given power range of the operation mode
true = forced on/off control is active, e.g., via input SwitchedOnOffForced
thermoelectric power
a point representing DPT 237.600: DALI Control Gear Diagnostic
DALI Control Gear Diagnostic
Info On Off Output 7
open on load shedding = 3
Status C
a point representing DPT 9.010: Value Time 1
Value Time 1
An air conditioning system is a system to satisfy requirements for temperature, humidity and air quality in rooms by adhering to these values within predefined limits.
Air Conditioning
room temperature setpoint building protection
open on overheat with a current value over the maximum switching current value = 5
a point representing DPT 275.100: TempRoomSetpSetF16[4]
Room Temperature Setpoint
Year
a point representing DPT 20.103: DHWMode
Direct current electricity
Electricity, DC
is asset of
Light Dimming Actuator Basic
is implemented by
A functional subdivison of a location. Structurally, a room is defined by enclosing surfaces such as facades, walls or ceilings (e.g. a single-room office or hotel room) or, in the case of an open-plan office, it is created by organisational means (e.g. as a separate zone).
Alarming is the automated alarm management in the event of alarms or faults in plants, subsystems or devices.
EnableH/CStage
on/off = 3
True = 1
Shutters and blinds = 50
Field type, used to define a (coding) type of a KNX data field as part of an entire datapoint type, specified in KNX (not all types are used in the KIM). A Character A[n] String of n characters B Boolean / Bit set C Control E Exponent F Floating point value M Mantissa N eNumeration r Reserved bit or field S Sign U Unsigned value V 2's Complement signed value Z8 Standardised Status/Command (8 bit)
field type
boiler sequence is permanently off (manual switch or failure)
FT in progress = 7
EnableCoolEff
StatusTempRoomSetpEff
A Datapoint exposes an internal state of a device that can be directly accessed (read) and optionally manipulated (write).
Datapoint
To define a generic relation from a functionality to several points. A functionality without any points is possible.
has point
Shall specify the fading step size or to the code to stop the fading of the colour blue
a point representing DPT 22.1000: Media
Media
Region as in DPT_RegionCode-Alpha2_ASCII (234.002) this is ISO 3166-1 alpha-2
Request Battery Info = 3
Hosts the HTTP scheme with an URI part for the gateway as a resolvable name or as an IPv4 or IPv6 address. A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
authority sort of request URI
The power forecast of a power sequence slot
a point representing DPT 20.113: StatusRoomSetp
StatusRoomSetp
heating = 1
DPT 14.005: Value of an amplitude
Value Amplitude
validity of the fields CR and Step Code Colour Red.
Shall specify whether the saturation of the colour shall be increased or decreased.
MBus address
Status of HVAC Mode User
temperature relative value offset K
Shall specify whether the brightness shall be increased or decreased.
Project installation number, usually generated by a Mac (edited by an installer).
Project Installation Number
CoAP
actuator fault = 3
Stop Test = 4
Electrical circuit and its associated components such as breakers.
Circuit
energy, 1 MWh = 129
'Electric Current' is the flow (movement) of electric charge. This QUDT-based tag is equal to the Haystack tag https://project-haystack.org/doc/lib-phScience/elec-current
Electric Current
memory allocation command with size 0 received = 8
Locked
Device Address = 0
Application functions for "fill rate based control". Fill rate is the percentage of demand that can be met without lagging in supply. By using fill-rate as the basis for determining the energy production, conservation and optimization of energy can be done without failing to satisfy demands.
Fill Rate Based Control
a point representing DPT 29.010: ActiveEnergy V64
ActiveEnergy V64
Sun intensity W/m2
is eventpoint of
The current state of a function point according to its security, used from installations that specifies an explicit and (by an installer) intended security behavior for the communication.
security mode
DPT 14.015: Value of conductance
Value Conductance
electric field strength
a point representing DPT 1.018: Occupancy
This state type expresses the state of heavy rainfall. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of heavy rainfall, this equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Rainfall' state type.
Rainfall State
WD field not valid = 1
Ramp = 1
a point representing DPT 7.600: Absolute Color Temperature
Absolute Colour Temperature
a point representing DPT 3.008: Control Blinds
Control Blinds
DPT 14.004: Value of the amount of substance (mol)
Value Mol
A microwave oven (commonly referred to as a microwave) is an electric oven (EN 50523 home appliance device) that heats and cooks food by exposing it to electromagnetic radiation in the microwave frequency range.
Microwave Oven
magnetic flux
energy, 0,01 kJ = 9
comfort prolongation User active = 1
duration in which fill level will reach a value in FLR
is operation kind of
TempRoomSetpTariffShift
a point representing DPT 229.001: MeteringValue
MeteringValue
This OP relationship allows to refine the applicative semantics of a datapoint, classified with a state type.
relates to state type
This state type expresses that a datapoint’s main value is corrupted due to failure. The device itself is operational. Typical usages are a sensor value is corrupted due to a hardware problem (data is invalid) or a database value is corrupted (due to loss off backup power, erased EEPROM etc).
Operational State Faulty
strong gale = 9
A nursery is usually, in American connotations, a bedroom within a house or other dwelling set aside for an infant or toddler. Preferably used with an Room.
Nursery
volume flow, 10 l/min = 69
Start Function Test (FT) = 1
Shutter Stop Trigger
General actuator failure
Controller inactive
invalid = 255
identifier of the current operation mode
requested room temperature setpoint
a point representing DPT 8.003: DeltaTime10MSec
DeltaTime10MSec
energy, 10 kJ = 12
colour transition xyY
Oil meter = 1
Hosts the unit of a datapoint (if applicable). A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
unit
The tag represents information for a physical point, a hardwired (physical) analogue or digital input point, from the perspective of the application program.
Physical Sensor Point
a point representing DPT 21.102: StatusRHC
StatusRHC
DPT 14.061: Value of resistivity
Value Resistivity
Level 13 = 13
Validity Slats Position
is locality of
A tag set combines different tags in a set, to express a joint concept with a specific semantical meaning.
Tag Set
power
supported control types, set bitwise b0 = PEBC b1 = PPBC b2 = OMBC b3 = FRBC b4 = DDBC b5-b7 = reserved
thermal conductivity
Encryption of access information
enable stage B = 2
Field string scheme, used to define a charset scheme of a KNX data field as part of an entire datapoint type (usually string/char DPTs). Same as for ETS XML data.
field string schema
Used to represent the current version of the content for the MaC.
a point representing DPT 241.800: StatusSAB
StatusSAB
MQTT
is applicable datapoint enum of
The hot water distribution Application Function connects and coordinates water and energy flow between energy generation/production (heating) and energy consumer (emission control).
Hot Water Distribution
An escalator is a moving staircase which carries people between floors of a building or structure. It consists of a motor-driven chain of individually linked steps on a track which cycle on a pair of tracks which keep them horizontal.
Escalator
This state type expresses that a device is currently being calibrated. It cannot be expected to fulfill its usual functionality until it is fully operational once again.
Operational State Calibration
volume, 0,01 l = 17
a point representing DPT 12.1201: Volume M3
Volume m3
a point representing DPT 251.600: Converter Info
Converter Info
A section of ductwork that refers to those parts of distribution systems in buildings that are ducts, mostly for transporting air.
Duct Section
The target value is directly overridden by the value of the source datapoint
ovrerides
Cool Stage A Actuator Target Position
A utility room is generally the area where laundry is done, and is the descendant of the scullery. Preferably used with an Room. Preferably used with an Room.
Utility Room
A Gateway is a network node (Device) that connects two networks with different transmission protocols and data formats typically between OSI Layers 4-5 (e.g. KNX and BACnet).
Gateway
not occupied = 2
General failure of the actuator or the drive
Fan Speed Target
Request Converter Test Result = 2
a point representing DPT 200.101: Binary Value Z
Binary Value Z
DPT 14.1200: Value of volume flux (in cubic meters per hour)
Volume Flux for Meters
Direction 2
In Western architecture, a living room, also called a lounge room (Australian English), lounge (British English), sitting room (British English), or drawing room, is a room for relaxing and socializing in a residential house or apartment. Preferably used with an Room.
Living Room
Restriction of slats height pos., pos. can not be reached
calm (no wind) = 0
Increase = 1
a point representing DPT 1.010: Start
Step Code Brightness
is outside of
This property allows to annotate a KNX-specific label.
Label (KNX-specific)
Detection error
a point representing DPT 209.102: StatusCPM
StatusCPM
Conditions a space using a heat exchanger integrated into the ceiling. A chilled beam is a type of radiation/convection HVAC system (as is an alternative design known as 'chilled ceiling') designed to heat and cool large buildings.
Chilled Beam
a point representing DPT 9.020: Value Volt
Value Volt
a point representing DPT 23.102: HVAC PB Action
HVAC PB Action
DPT 14.056: Value of power
Value Power
output state is On = 1
Mask Bit Info On Off Output 12
Test = 7
a point representing DPT 218.002: Flow Rate in m3/h Z
FlowRate m3/h Z
TempRoomSetpSetCool
night round = 2
WithoutAcknowledge = 1
Used to represent the current version of the content for the semantic dictionary.
dictionary version
ContrModeAct
power, 100 kJ/h = 53
1,5 min = 12
Comfort/Economy = 0
Cool Stage A Actuator Status
This state type expresses that an equipment has a movement direction that can be interpreted as 'closing'. Usually, this is associated with equipments that can be moved by a drive in an horizontal axis or on a hinge, such as valves, windows, or doors.
Closing Movement
estimated time that the timer needs once it has been started
Application function for generic 'switch control'.
Switching
Parking is the act of stopping and disengaging a vehicle and leaving it unoccupied. Preferably used with an Space.
Parking
This state type expresses that the second-lowest level named 'Economy' is chosen for the HVAC mode. Usually, the 'Economy' level is associated with a room that is unoccupied for longer periods in time (e.g. during the night). In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Economy
switch mode only (non-dimmable load) = 3
"Height" is the measurement of vertical distance, but has two meanings in common use. It can either indicate how "tall" something is, or how "high up" it is.
Height
A parent data property, used to express any kind of generic data that relates to an datapoint type field.
datapoint type field
Heating / Cooling
Info On Off Output 14
ForcedPosition
Overload
Sunday = 7
a point representing DPT 206.105: BuildingModeNext
BuildingModeNext
The visual effect of channel 9 is inactive = 0
Breaker/Valve is open = 1
Equipment which adds moisture to air to increase humidity.
Humidifier
Colour Relative Control RGBW
a point representing DPT 8.007: DeltaTimeHrs
DeltaTimeHrs
MBus
Low = 2
volume flow, 0,01 ml/s = 73
A Router is a network node (Device) that that forwards data packets between computer networks typically between OSI Layers 3. A router does not change application layer content.
Network Router
Electrical circuits for alternative currents. This is a specialization of the tag "Circuit".
Circuit, AC
Seconds
This state type expresses that mode 'Heating' is chosen for the HVAC system. Usually, this mode is associated with default heating functionality of the HVAC system. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Heating
This means that the intended value is a (discrete) element from an enumeration (list), the numerical representation of the value does not express any semantical meaning or priority within the list.
Enumeration
Automatic Control = 0
ActCurrentFanSpeed
send always = 1
Window Switch
a point representing DPT 8.005: DeltaTimeSec
DeltaTimeSec
DPT 14.068: Value of common temperature
Value Common Temperature
The field Scent Activation shall indicate whether the scene with scene number SN is active or not.
volume flow, 0,01 l/h = 57
Failed, test executed in time = 3
4.x
electrical energy
SynchronizationMode indicates that the actuator is currently executing a synchronization of the stroke model
ComfortPushbutton
digit 2 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
A window is an opening in a wall, door, roof, or vehicle that allows the exchange of light and may also allow the passage of sound and sometimes air.
Window
A child OP relationship to a list allowing to describe a non-quantifiable/non-countable characteristic where an observation or actuation is made.
has state kind
a point representing DPT 20.108: ValveMode
MeteringDeviceType
Application Mode
Blinds Stop Trigger
a point representing DPT 4.001: Char ASCII
Char ASCII
User HVAC Room Settings
is phenomenon quality kind observed by
no control = 0
a point representing DPT 207.101: LockSign
LockSign
Heat Stage A Proportional = 2
volume flow, 0,1 l/h = 58
This state type expresses that the comfort level, which is used for computations of HVAC systems, is chosen automatically.
HVAC Mode Auto
a point representing DPT 15.000: Access Data
Access Data
BacNet
EquipmentType to remove heat from a liquid.
Chiller
EmergPressure = 1
Verify Mode is on
PL medium Domain Address = 1
This state type expresses that a device is able to operate as intended. Thus, it can fulfill its designated functionality and its datapoints offer valid and correct values.
Operational State Operational
Locked Position
An educational institution is a place where people of different ages gain an education, including preschools, childcare, primary-elementary schools, secondary-high schools, and universities. They provide a large variety of learning environments and learning spaces. Preferably used with a Building.
Educational
phase angle, degrees
scene control
a point representing DPT 1.007: Step
off/on = 2
execution time when the sequence will start or was started
occupied = 1
a point representing DPT 29.011: ApparantEnergy V64
ApparantEnergy V64
Limits a numerical datapoint value in its applicative behavior to a minimum. Represents an external definition, hence it is also used from other concepts, therefore no domain is defined (merged ontologies -> intersection problems). The range xsd:decimal covers also numerical values with a fraction such as 12.34 or -13.56.
minimum
HumRelRoom
StatusEcoH
A toilet is a small room used for privately accessing the sanitation fixture (toilet) for urination and defecation. Toilet rooms often include a sink (basin) with soap/handwash for handwashing, as this is important for personal hygiene.
Restroom
Passed in time = 1
A building is a structure with a roof and walls standing more or less permanently in one place, such as a house or factory.
general protection fault = 12
Status of comfort prolongation User
StatusMorningBoost
BinarySceneRecall
DHWLegio
In classical geometry, the "Diameter" of a circle is any straight line segment that passes through the center of the circle and whose endpoints lie on the circle.
Diameter
Enclosure or chassis used to mount computer and networking gear. For example, a 19-inch rack is a standardized frame or enclosure for mounting multiple electronic equipment modules.
Rack
The tag category contains individuals that describe the runtime interworking interface type of a point.
Point Interface
Relative demand %: for modulating burner
one PB/binary input, On / DimUp message sent = 2
An imaginary horizontal plane situated at the nominal working height in an interior space. Most illuminance and daylight factor measurements and calculations are made for points on this plane.
Work Plane
Arbeitsbereich
ActCurrFanSpeed
composes ouput
one PB/binary input, Off / DimDown message sent = 3
Cool Mode = 0
locked = 1
Gas meter = 3
Response or spontaneous sending = 0
UpDown = 2
controls stage 2 for two stage burner
Very cloudy = 6
character string
magnetic polarization
electromagnetic moment
Test pending = 2
AbsSetvalueControlCmd
torque
ActCurrPosCoolStageA
slave = 2
Level 5 = 5
ErrorCode_Sup
a point representing DPT 11.001: Date
Date
The tag category contains individuals allowing to describe the specific application area/ operational domain in which a Point, Application Function or Function point is used. Trade is a subdivision of knowledge by technical field or electrical and mechanical installations.
Trade
Read direction (e.g. of badge). If not used (e.g. electronic key) set to zero.
Night = 1
Uses for to define the current status of an entity, such as the building completion or installation status. May be used from other concepts, therefore no domain is defined.
state
Hosts specific information that depends on the field type.
includes
DPT 14.026: Value of electric polarization
Value Electric Polarization
Field index, used to identify the correct position of a KNX data field as part of an entire datapoint type.
field index
a point representing DPT 20.122: StartSynchronization
The coold water distribution Application Function connects and coordinates water and energy flow between production of chilled water (cooling) and consumer (emission control).
Cold Water Distribution
The tag category contains individuals that describe specific state types in the control loop of an Application Function. An individual state type is the result of an interpretation of process variables or other states in the control loop. Each state type has a semantically predefined, discrete meaning that can only be figured out together with other context knowledge from the domain of building control. A state type is not assigned with a specific Runtime value, moreover, at least two state types are required to form the set of applicable options, used in the control loop.
State Type
Active = 1
InAlarm
Radio converter (meter side) = 55
a point representing DPT 13.016: ActiveEnergy MWh
ActiveEnergy MWh
a point representing DPT 252.600: Relative Control RGBW
includes datapoint type
Hardwired switch is off = 1
Historical three-phase = 2
alarm position is UP = 1
a point representing DPT 20.021: Cloud Cover
Cloud Cover
a point representing DPT 206.104: OccModeNext
OccModeNext
Light Switching Sensor Basic
User Fan Speed Setting
mass flow, 1000 kg/h = 86
A Quality Kind with at least one measurable quantity property that addresses equipment, and the quantity property can be directly determined.
measures equipment quality kind
Valve kick
angular momentum
Hardwired Inhibit is active = 1
Overcurrent
software fault = 5
Month
Max time a device could be pause between the end of the previous running sequence and the start of this one
Refers to information that originates in a management system, e.g. a central building management system.
Management
An identifier to specify the (numerical) hardware version of a device.
hardware
logical function AND = 1
Stairs are a structure designed to bridge a large vertical distance between lower and higher levels by dividing it into smaller vertical distances.
Staircase
The visual effect of channel 19 is active = 1
0 s (no fade) = 0
DPT 14.002: Value of activation energy
Value Activation Energy
a point representing DPT 222.100: TempRoomSetpSetF16[3]
TempRoomSetpSetF16[3]
stress
Group Address Table is not sorted = 15
DPT 14.062: Value of self inductance
Value SelfInductance
a point representing DPT 8.001: Value 2 Count
Value 2 Count
commodity quantity the power envelope refers to
An identifier to specify the (numerical) model version of an application program.
Model
Start Partial Duration Test (PDT) = 3
Equipment that converts electrical energy into mechanical energy.
Motor
a point representing DPT 9.025: Value Volume Flow
Value Volume Flow
Close = 1
volume in liter
capacitance
Read or Response
a point representing DPT 20.610: LoadTypeDetected
Cool Stage B Actuator Overridden
one push button/binary input = 1
Building prot/Auto = 3
B1 with Date and Time
a point representing DPT 20.601: Behaviour Bus Power Up Down
Behaviour Bus Power Up Down
Info On Off Output 10
Power profiles are configurations that set the energy consumption levels of equipment and systems to achieve a defined goal. Some examples of power profiles can be “Maximize output”, “Minimize energy consumption” or any custom level of performance.
Power Profile Based Control
a point representing DPT 8.006: DeltaTimeMin
DeltaTimeMin
Staircase Trigger Request
Represents the fact that the quantity is a date (any format statement is out of scope in this tag category), without any part relating to the time of day.
DPT 14.013: Value of volume charge density
Value Charge DensityVolume
magnetic flux density
DPT 14.046: Value of magnetic flux density
Value Magnetic FluxDensity
a point representing DPT 224.100: TempSupplyAirSetpSet
TempSupplyAirSetpSet
This state type expresses the state of no heavy rainfall. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of no heavy rainfall, no protection is required and this equipment might be used for shading purposes as intended. This state type is the inverse of the 'Rainfall State' state type.
No Rainfall
a point representing DPT 1.019: Window Door
Producer = 1
This state type expresses the state of frost. Usually, this state is related to the protection of shading equipment such as blinds and slats, as their drive might be damaged when trying to move frozen blinds or slats. In case of frost, the equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Frost' state type.
Frost State
ForcedPositionEnable
TempRoomSetpAbsNext
EnableHeatEff
Room Temperature Sensor
Nearly overcast = 7
A desktop, laptop, PDA or other type of computer that can be moved from one place to another and connected to an electrical supply via a plugged outlet.
Computer
Not inverted = 0
insufficient volatile memory = 7
LDTR
Alarm Priority
energy, 1000 Wh = 6
volume flow, 10000 l/h = 63
2-bit set
Info On Off Output 4
To define a quality kind that hosts a pedefined set of tags.
has quality kind
SwitchPBAction
Year field valid = 0
CCT and Step Code Colour Validity
true = actuator is in state DIMMING. false = actuator is not in state DIMMING. Not applicable for switching actuator LSAB.
alarm (RTC locked) = 1
a point representing DPT 230.1000: MBus Address
MBus Address
power range for related to the given supply rate
An identifier to specify the (numerical) firmware version of a device.
firmware
Supply air temperature heating setpoint
Heat Stage A Actuator Status
Relative Humidity is the ratio of the partial pressure of water vapor in an air-water mixture to the saturated vapor pressure of water at a prescribed temperature. The relative humidity of air depends not only on temperature but also on the pressure of the system of interest.
Relative Humidity
heat flow rate
ActCurrPosHeatStageA
true = night mode is active e.g., via input NightMode; the actuator will autonomously switch off the light after a defined time period.
The upper boundary of the range with 100 % certainty the power value is in it
A room segment is an indoor space that represents a subdivision of a room, it can be further subdivided into locations of type room segment.
Room Segment
Raumteil
User HVAC Display
Comfort/Nothing = 1
Wind Force Scale
Positive = 0
Controller status. on: controller is working (default if not supported). off: controller is stopped; no control of water temperature
A specific Application Function category that controls the solar irradiance by means of motorized sun protection. Very often there are protection functions that interfere with the sun protection. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Shading Control
moderate breeze = 4
time when this instruction will be executed
This state type expresses the 'humidification' mode of the ventilation system. Usually, this is related to raising the relative air humidity by adding moist air to a room.
Humidification Mode
Represents an angle from 0 to 360 degrees.
Pressure is an effect which occurs when a force is applied on a surface. Pressure is the amount of force acting on a unit area. Pressure is distinct from stress, as the former is the ratio of the component of force normal to a surface to the surface area. Stress is a tensor that relates the vector force to the vector area.
Level 10 = 10
Nak
down = 1
Equipment Quality Kind
In KNX used (numerical) identifier to address a specific property as part of an interface object. The range xsd:unsignedByte supports exactly the KNX value range from 0 to 255.
property identifier
at measurement condition = 3
Single open = 2
valve is currently executing a valve kick
includes digit
Limits a numerical datapoint type value to a maximum (range max) as a literal, to express float and integer values. May be used from several concepts, such as a DPT. The range is used to limit it for signed/unsigned integers and float values.
range max
Used to control an actuator equipment to regulate the flow of air (damper). Don't care if the damper is internally operated from the actuator by a motor or other means.
Damper Actuator
Switch Request
a point representing DPT 13.013: ActiveEnergy kWh
Active Energy kWh
The upper boundary of the range with 95 % certainty the power value is in it
temperature converted = 1
angle, degree
Colour RGBW
The tag represents information for a logical point, a parameter point that changes an application behavior, mainly used at configuration. It SHALL not be used together with a setpoint value point (:sp) from point function class.
Parameter Point
Equipment to transfer heat between two working fluids. For example, a coil is a heat exchanger used to heat or cool air.
Heat Exchanger
DPT 14.060: Value of resistance
Value Resistance
Used to indicate the cardinality of a point. This is part of a point's access type in the specification Vol 7 and can be 'one' (1 -> this for inputs or this -> 1 for outputs) or 'many' (N -> this for inputs or this -> N for outputs).
has cardinality
AddInfoType
Activation state of channel 22
Standard Summer Time
SMTP
Hour of day, Minutes and Seconds field not valid = 1
This state type is a special type of a defect state. It expresses that the actual device hosting the datapoint is not working properly due to an overload. Thus, no valid value is available at the datapoint.
Operational State Defect Overload
mass
is tag set of
Move up or down.
High = 0
Shall specify the fading step size or to the code to stop the fading of the colour
Represents a person in the contect of the building domain. Hence this there is no need to distinguish on the level of living entities.
Person
Application functions for 'operation mode based control'. A facility has various stages in its process cycle that include powering up, regular functioning, transitions, maintenance, and other similar stages. Operation Mode Based Control provides the monitoring actions related to each of these stages.
Operation Mode Based Control
mass flow, 0,001 kg/h = 80
activation of priority = 0
DPT 14.000: Value of acceleration
Value Acceleration
has eventpoint
is grouped by
Level 9 = 9
Specifies the maximum bit size of a datapoint type (DPT) in bits (variable datapoint types may define less as max, therefore 'max').
datapoint type bit size max
Disable = 0
Requested power reduction
The visual effect of channel 19 is inactive = 0
asynchronous + BiBat Master = 1
a point representing DPT 20.017: SensorSelect
SensorSelect
invalid = 0
Switch On Off
The tag category contains individuals that describe a tangible and/or movable equipment that can be actively observed or actuated upon as part of the building control system (in contrast to passive equipment's of the building, for example a pipe or a duct).
Used to represents keywords, key phrases, or classification codes.
subject
frequency
a point representing DPT 20.602: DALI Fade Time
DALI Fade Time
A hotel is an establishment that provides paid lodging on a short-term basis. Preferably used with a Building.
Hotel
Shutter Move Up Down
output state is Off = 0
FTP
Activation state of channel 21
DPT 14.020: Value of electric current density
Value Electric CurrentDensity
a point representing DPT 21.1001: RF FilterInfo
RF FilterInfo
The Application Function controls the air temperature of an single room, thereby maximizing comfort and minimizing energy costs.
Individual Room Control
Validity of ActPosDem. ‘false’ means also ‘no demand’
Heat Stage B Actuator Target Position
Relative Set Value Control Green
Combined Info On Off
This state type expresses that an equipment has a movement direction that can be interpreted as 'upwards'. Usually, this is associated with equipments that can be moved by a drive along a vertical axis, such as blinds or slats.
Upwards Movement
Application Funtion 'meter' aggregates consumption measurement points of one or many metering devices.
Temperature is a physical property of matter that quantitatively expresses the common notions of hot and cold.
Temperature
a point representing DPT 207.102: ValueDemBoc
ValueDemBoc
is application function of
Calibration Mode = 15
1-byte
a point representing DPT 9.029: Humidity
Humidity
Heats a space using exposed pipes or coils. Radiators are heat exchangers used to transfer thermal energy from one medium to another for the purpose of cooling and heating. The majority of radiators are constructed to function in cars, buildings, and electronics.
Radiator
Start/stop = 0
This property models the dimming level of a luminaire. This also is used for the individual colour parts, in which case it shall be used in combination with the corresponding chromaticity tags of category StateType (R/G/B/W).
Dimming Level
PL110
notice PE1 in progress = 1
is tag of
a point representing DPT 9.026: Rain Amount
Rain Amount
TempDischargeAir
Shutter Status
Increase or decrease the colour temperature.
a point representing DPT 6.020: Status Mode 3
Status Mode 3
Air Damper = 1
fault = 1
mass flow, 10 kg/h = 84
TempFlowWater
PE1 in progress = 1
no notice in progress = 0
Light Switch Request
A site represents a collection of buildings and grounds that belong to a given institution. A site is usually at the top of a location or rather building hierarchy. The concept can be mapped to a IfcSite.
Liegenschaft
Site
Test manually stopped = 5
Dali
a point representing DPT 20.1205: PLC Status
PLC Status
Reset Function Test Done Flag = 5
acknowledge command (trigger), e.g. for alarming = 1
power, 10000 kJ/h = 55
breaker (electricity) = 32
a point representing DPT 2.011: State Control
State Control
compressibility
This state type expresses that mode 'Night Purge' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system exchanging the used air in the building during the night. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Night Purge
first character of LanguageCode, ASCII-coded
Application function to provide a 'system clock' for the system.
System Clock
Request Converter Info = 7
No Year
This state type expresses that an equipment has a movement direction that can be interpreted as 'downwards'. Usually, this is associated with equipments that can be moved by a drive along a vertical axis, such as blinds or slats.
Downwards Movement
Standby = 1
a point representing DPT 20.1000: CommMode
CommMode
a point representing DPT 1.100: Heat/Cool
Heat/Cool
DPT 14.044: Value of magnetic field strength
Value Magnetic FieldStrength
Used to control a motor equipment to create air flow with a fan. The interest is the motor and not the actuator equipment, containing the motor.
Fan Motor
Start of time period that will be covered by the power profile
Battery Duration Failure
KNX IP
Month and Day of Month field not valid = 1
To define a general relation between different concepts. With the child properties a relation with a specific semantic meaning can be expressed (such as between locations). Due to the usage from several concepts the domain and range is not specified for this OP.
refers to
not valid = 1
Colour Level Blue
chilled water flow te
Address Indicator
Negative = 1
Signaling for evacuation of occupants of a building in case of a danger.
Safety Lighting
Cool Stage A Actuator Calibration Mode
A generic functional subdivison of a location, which represents any physical space that belongs to a building.
digit 4 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
is product of
DefectiveLoad
room temperature setpoint shift economy
a point representing DPT 20.107: ChangeoverMode
Actual Dimming Value Blue
is phenomenon quality kind actet on by
ValInfField
HTTP
Not occupied = 2
is space of
one PB/binary input mode = 1
A bar, also known as a saloon, a tavern or tippling house, or sometimes as a pub or club, is a retail business establishment that serves alcoholic beverages, such as beer, wine, liquor, cocktails, and other beverages such as mineral water and soft drinks.
Bar
A specific Application Function category that controls a quantity (e.g., temperature, pressure) of the phenomenon air. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Air Control
DPT 14.048: Value of magnetic polarization
Value Magnetic Polarization
Mask Bit Info On Off Output 4
ActTargetFanSpeed
EmergFire = 5
Lower end pos. reached
is functional block of
boiler sequence is temporary not producing heat
Refers to information that originates from user action, e.g. issueing light switching commands or selecting setpoints.
User
Heat Stage A Actuator Target Position
is phenomenon type of
DPT 14.014: Value of compressibility
Value Compressibility
pressure
a point representing DPT 219.001: AlarmInfo
AlarmInfo
Alarm = 1
Mask Bit Info On Off Output 9
maximal table length exceeded = 13
A door is a hinged or otherwise movable barrier that allows ingress (entry) into and egress (exit) from an enclosure.
Door
Status B
is point of
DPT 14.010: Value of an area
Value Area
TempOptimShiftActive
Validity height pos.
a point representing DPT 1.016: Ack
Overheat
a point representing DPT 20.114: Metering DeviceType
Metering DeviceType
a point representing DPT 21.100: ForceSign
ForceSign
DPT 14.034: Value of angular frequency (pulsatance)
Value Angular Frequency
Battery Fully Charged
Status A
a point representing DPT 265.012: DateTime Invert
DateTime Invert
Field size, used to define the actual size in bits of a KNX data field as part of an entire datapoint type. The size may be not present, in case of an inluded datapoint type (DPT).
field size
phase angle, radiant
a point representing DPT 201.107: Building Mode Z
Building Mode Z
Blinds Move Up Down
is datapoint type of
volume, 0,1 l = 18
Absolute Set Value Control Blue
A specific Application Function to optimize different energy consumers. An emissionCtrl is an energy saving Application Functions and routines based on the actual use of a building (space), depending on real user needs, to avoid unnecessary energy use and CO2 emissions.
Emission Control
DPT 14.003: Value of activity (radioactivity)
Value Activity
DPT 14.070: Value of temperature difference
Value TemperatureDifference
a point representing DPT 5.004: Percent U8
Percent U8
right to left = 1
Shutters & Blinds = 50
No Time
15 min = 17
Step Code Colour Temperature
8-bit unsigned value
a point representing DPT 9.002: Value Temp D
Value Temp D
IMAP
Start Duration Test (DT) = 2
8-Bit Unsigned Value & 8-Bit Set
charge density (volume)
An application program represents a piece of software that implements a functionality. Moreover, specific confifuration parameters may be used to control how the functionality is operating at Runtime.
Application Program
TempSetpStdby
Started by Gateway = 2
no day = 0
This DPA switches the comfort level to Comfort. Thus it is represented as a trigger point, that relates to the Comfort level (represented by the state type tag:hvacModeComfort)
Upper end pos. reached
Blinds Slat Position Percentage
luminous intensity
A setpoint is classified as an indirect adjustment, such as Point representing the desired or target value for a process value of a system.
Setpoint value
Enclosure used to move people between floors. An elevator or lift is a cable-assisted, hydraulic cylinder-assisted, or roller-track assisted machine that vertically transports people or freight between floors, levels, or decks of a building, vessel, or other structure.
Elevator
Working day = 1
open on overload = 1
A point representing a dynamic limitation for an essential variable or a process value.
Limit
This state type expresses that mode 'Off' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system being idle, i.e. neither heating nor cooling functionality being required. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Off
BiBat Slave
To define the general presence of a functional block, implemented/realized in a device. The OP does not claim the operational (concurrent) presence of a certain FB at Runtime.
supports functional block
A numerical address identifier, used in KNX to address a set of (registered) receivers, similar to an IP multicast address.
group address
By a MaC (ETS) allowed location usages for a room.
MaC room
Mask Bit Info On Off Output 3
This state type expresses that mode 'Pre-Cool' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system cooling an unoccupied room in a predictive manner in order for the room to be at the desired temperature once the room is scheduled to be used. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Pre-Cool
A cooling system keeps air cool and dry within a home, office, or other buildings. Refrigration is the cooling of a space or substance below the environmental temperature.
Cooling
A unitary, factory-made enclosure with a fan and coil that recirculates air in a space and performs one or more of the functions of cleaning, heating, cooling, humidifying, dehumidifying, or ventilating the air. Unit heaters are examples of FCUs.
Fan Coil Unit
Rain is water droplets that have condensed from atmospheric water vapor and then fall under gravity.
Rain
a point representing DPT 9.011: Value Time 2
Value Time 2
defines whether this is an abnormal condition or not
density
energy, 0,1 kJ = 10
ligth, quantity of
a point representing DPT 9.027: Value Temp F
Value Temp F
Relates to the phenomenon of burning substances.
Fire
An OP relationship to a list that describes the runtime interworking source of a point or function point. Examples are default, user or managment.
has origin
normal setpoint = 0
Luminous Flux or Luminous Power is the measure of the perceived power of light. It differs from radiant flux, the measure of the total power of light emitted, in that luminous flux is adjusted to reflect the varying sensitivity of the human eye to different wavelengths of light.
Luminous Flux
Points with other operation types rather than a datapoint. It allows to invoke a function to manipulate states (see thing description).
Actionpoint
a point representing DPT 20.606: PBAction
PBAction
temperature absolute value °C
Actual controller Mode
WindAlarm
a point representing DPT 5.003: Angle
A vane is a flat blade which pushes or is pushed by air (wind) or water, and forms part of a machine such as a fan, a windmill, or a ship's propeller. A vane position indicates or controls air flow direction
Vane
Indicator if sequences will run under abnormal conditions
Saturday = 6
clock with ext. sync signal = 1
identification if the power envolope refers to an abnormal condition
In KNX used (numerical) identifier to address a specific interface object. The range xsd:unsignedShort supports exactly the KNX value range from 0 to 65535. As a note, this is a mirror property to the data property "knx:objectType" and must ONLY be used on function block (fb.x) classes, not on the actual individuals!
interface object type annotation
asynchronous + BiBat Slave = 2
A functional subdivison of a location, consisting of one or several usually adjoining buildings.
TempFloor
Version Number
Medium = 1
Overcast = 8
roles of this RM according to commodities
Gas device = 3
is comprised by
not accepted = 0
a point representing DPT 1.024: DayNight
DayNight
HVAC General FB's = 10
SABBehaviour_Lock_Unlock
thermal capacity
Limits a numerical datapoint type value to a minimum (range min) as a literal, to express float and integer values. May be used from several concepts, such as a DPT. The range is used to limit it for signed/unsigned integers and float values.
range min
Energy is the quantity characterizing the ability of a system to do work.
Energy
electric flux density
enable both stages = 3
memory function value = 4
watchdog reset detected = 10
DoA
a point representing DPT 212.101: TempRoomSetpSet[3]
TempRoomSetpSet[3]
DALI Device Address or DALI Group Address
Synchronisation source reliability
SensorConnection = 1
The lower boundary of the range with 68 % certainty the power value is in it
Network Gateway
This state type expresses that the lowest level named 'Protection' is chosen for the HVAC mode. Usually, the 'Protection' level is associated with a focus on building and equipment protection (e.g. against frost damage). This level is used for rooms or buildings, which will not be used for a longer time, such as holidays. Additionally, the 'Protection' level is chosen for a room if windows in this room are opened. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Protection
Heat Stage A On/Off = 1
A device for displaying visual information, such as text, images and shapes.
Screen
ContrModeSecondary
Stop = 0
Info OnOff
Indicator for time related type of interests, more granular defined with a quantity kind
Temporal
a point representing DPT 8.012: Length m
Length m
DPT 14.001: Value of angular acceleration
Value Acceleration Angular
This state type expresses that a datapoint is accessible but out of service, i.e., the main value is void and may contain any value. The device itself is operational. Typical usages are an optional sensor is not connected (out of service, sensor data is invalid) or a configuration parameter is void (function disabled).
Operational State Out Of Service
Voltage, also referred to as Electric Tension, is the difference between electrical potentials of two points. For an irrotational electric field, the voltage is independent of the path between the two points a and b.
Electrical Voltage
power, 0,001 W = 40
Indicated whether the target position is reached of the drive is moving
CombinedStatus_HVA
This DPA represents a combined status of a Heating Valve Actuator. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring (mostly) to the device, which are modeled by the respective tag:operationalStateXYZ tags, if not otherwise stated: Bit 0) Current Valve Position (referring to the property PositionVector, modeled by the state types tag:opened and tag:closed); Bit 1) Short Circuit; Bit 2) Overload; Bit 3) Valve kick (very specific for valves, abstractly modeled by the state type tag:operationalStateMaintenance); Bit 4) Service Mode (modeled by the state type tag:operationalStateMaintenance as well); Bit 5) Manual operation (overridden) - in this case the Overridden status information refers to the actual manual operation (similar to DPA 400.71 the overridden state refers to the actual position of the valve (and thus to the specific property Position Vector), which is why the QualityKind is used at this point; Bit 6) Forced Position (modeled by tag:forced); Bit 7) Locked Position (modeled by tag:locked); and Bit 8) Calibration Mode.
Shall specify the fading step size or to the code to stop the fading of the saturation
Heat stage A for normal heating = 1
scaling speed
A wellness room may contain facilities such as a sauna, pool, steam room, or whirlpool. A wellness room provides a variety of services for the purpose of improving health, beauty, and relaxation through personal care treatments such as massages and facials. Preferably used with an Room.
Wellness
Mask Bit Info On Off Output 7
Consumer / Producer
power, 1 GJ/h = 177
New / Lock (S-FSK) - Associated (G3-PLC) = 1
brightness colour temperature transition
Rain Sensor
trailing edge (capacitive load) = 2
a point representing DPT 29.012: ReactiveEnergy V64
ReactiveEnergy V64
20 min = 18
is datapoint of
a point representing DPT 20.105: HVACContrMode
Rain Alarm
New / Unlock (S-SFK) - Not Associated (G3-PLC) = 0
Represents a percentage value with 1% resolution for 0 to 255%.
The unacknowledged IPv6 (multicast) group notification address, corresponding to a KNX group address. It is used for KNX IoT installations using IPv6, set by the MaC for an individual Installation.
IPv6 multcast address
An installation consists of equipment that is assigned to a location. It is a deployed system (e.g. HVAC system or fire protection system) and consists of equipment (such as cabinets) and (application) functions that are used for a particular purpose. The (application) functions are hosted in this case at a location.
Installation
DPT 14.076: Value of volume
Value Volume
A floor is a level or plane concept in a building, it is separating a building into horizontal spaces. A floor can have spaces assigned, in particular a room. The concept can be mapped to a IfcBuildingStorey.
Etage
operation mode id the transition starts from
a point representing DPT 22.100: StatusDHWC
StatusDHWC
a point representing DPT 9.009: Value AirFlow
Value AirFlow
Heat Mode = 1
To define the existence of several function points as part of an application function. Application functions without any function points are possible but useless (a MaC may not prevent to remove them all).
has function point
a point representing DPT 201.102: DHW Mode Z
DHW Mode Z
Blinds Position Length
one push button/binary input, MoveDown / StepDown message sent = 3
Liquid phase produced by the condensation of steam or other gas
Condensate
Partial Duration Test Pending
This DPA changes the activation state of the comfort prolongation. Thus, it defines the two states tag:active and tag:inactive, which relate to the comfort level (represented as the state type tag:hvacModeComfort).
Emergency Cool Mode = 16
a point representing DPT 202.1: RelValue Z
RelValue Z
A tag is an information that describes the data or content that it is assigned to. Tags are typically nonhierarchical keywords (individuals) used, for example, for datapoints, application functions but also for internet bookmarks, digital images, videos, files and so on.
Tag
Info On Off Output 12
DHW temperature setpoint for LegioProtect operating mode
The relation is meant to be outside a building (outdoor is the same).
LPDTR
a point representing DPT 218.001: Volume in Liter
VolumeLiter Z
High = 1
magneto motive force
no peak event = 0
DPT 14.053: Value of momentum
Value Momentum
A point representing a current state.
Situation
The visual effect of channel 23 is active = 1
DoA and KNX SN
Behaviour_Bus_Power_Up_Down
validity of the fields CB and Step Code Brightness.
HumRelSetpUser
PE3 in progress = 3
Scene Sensor
This state type expresses that mode 'Cooling' is chosen for the HVAC system. Usually, this mode is associated with default cooling functionality of the HVAC system. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Cooling
a point representing DPT 27.001: CombinedInfoOnOff
CombinedInfoOnOff
the energy constraint allow the Resource Manager to describe what it considers as acceptable levels for avarate power for specific time periods
False = 0
not valid = 0
Restore Factory Default Settings = 0
Wind Alarm
Cool Stage B Actuator Calibration Mode
a point representing DPT 13.002: FlowRate m3/h
FlowRate m3/h
a point representing DPT 16.000: String ASCII
String ASCII
a point representing DPT 8.010: Percent V16
Percent V16
A strong OP relationship to express a relation to a room in a location.
has room
Mask Bit Info On Off Output 13
Heat and Cool = 13
mode 1 is active = 2
In thermodynamics, enthalpy is the sum of the internal energy and the product of pressure and volume of a system.
Enthalpy
valid = 1
is equipment quality kind measured by
Staircase Status
This state type expresses that a scene is taught in scene-controlled instrumentations by storing a value for later recall. This covers both teaching a scene based on a scene number (e.g. 0-63) or for one of two scenes (e.g. Scene A or Scene B).
Scene Save
digital input not inverted = 1
ContrMode
second character of LanguageCode, ASCII-coded
Application funtion weather station aggregates outside measurement points.
Weather Station
Tuesday = 2
ErrorClass_HVAC
energy, 100 Wh = 5
mass flow, 1 kg/h = 83
Request Converter DT Info = 5
A user operated light dimming request including an explicit dimming status. The light switch request inlcuding its status is inlcluded.
User Light Dimming
General failure information
Shall specify the fading step size or to the code to stop the fading of the brightness
mass, 100 kg = 29