Unsigned counter value
standard Status/Command
a point representing DPT 13.012: ReactiveEnergy
ReactiveEnergy
SCLOMode
Heat Stage A Actuator Fault
electric polarization
1 min = 10
Electricity meter = 2
cooling = 0
Detection error
Info On Off Output 7
general device fault (e.g. RAM, EEPROM, UI, watchdog, ...) = 1
DPT 14.016: Value of electrical conductivity
Value Electrical Conductivity
no fault = 0
Standby = 1
HTTP
a point representing DPT 13.1200: Delta Volume Liquid Litre
Delta Volume Liquid Litre
20 min = 18
DHWMode
Used for reading and setting tariff information from 1 to 254. However, the mapping between tariffs and the DPT values is not standardized. The value 0 equals 'no tariff available'. The value 255 is reserved.
Tariff
Reduced = 3
power, 10000 W = 47
validity of the fields CB and Step Code Brightness.
Slats are vertical or horizontal pieces of a window blind. Slats actuator is used to control an actuator equipment to regulate the light incidence (slats position/angle). Don't care if the slats position/angle is internally operated from the actuator by a motor or other means.
Slats Actuator
Mask Bit Info On Off Output 1
Water Change Over Status Sensor
TempRoomSetpUserOffset
a point representing DPT 9.007: Value Humidity
Value Humidity
Conditions a space using a heat exchanger integrated into the ceiling. A chilled beam is a type of radiation/convection HVAC system (as is an alternative design known as 'chilled ceiling') designed to heat and cool large buildings.
Chilled Beam
KNX IP
hurricane = 12
disabled (PSU/DPSU fixed off) = 0
Building protected = 2
chilled water flow te
watchdog reset detected = 10
A microwave oven (commonly referred to as a microwave) is an electric oven (EN 50523 home appliance device) that heats and cooks food by exposing it to electromagnetic radiation in the microwave frequency range.
Microwave Oven
This state type expresses that the comfort level, which is used for computations of HVAC systems, is chosen automatically.
HVAC Mode Auto
HumRelSetpHumEff
Cool Stage B Actuator Status
Application Area
is room segment of
MQTT
energy, 0,1 Wh = 2
a point representing DPT 20.011: ErrorClass System
ErrorClass System
Activation state of channel 17
DPT 14.009: Value of angular velocity
Value Angular Velocity
delay time (min)
Light Current Dimming Value
TempFlowWater
room temperature setpoint standby
Emergency Heat = 8
BurnerType
FuelType
Delay time until next change of tariff
Represents a ratio.
Decimal Factor
a point representing DPT 21.100: ForceSign
ForceSign
Room Temperature Sensor
DPT 14.070: Value of temperature difference
Value TemperatureDifference
disabled = 0
No Day of Week
locked = 1
The visual effect of channel 5 is active = 1
a point representing DPT 256.001: DateTime Period
DateTime Period
Cabling used to convey electricity (AC/DC) or data.
Wire
DPT 14.042: Value of luminous flux
Value Luminous Flux
Validity Slats Position
A hand dryer is an electrical appliance that has the primary function of drying hands.
Hand Dryer
The target value is directly overridden by the value of the source datapoint
ovrerides
None = 0
torque
Nak
Equipment to transfer waste heat into the atmosphere. A cooling tower is a device that rejects waste heat to the atmosphere through the cooling of a coolant stream, usually a water stream to a lower temperature.
Cooling Tower
Converter Mode according to the DALI converter state machine
Request Converter FT Info = 4
a point representing DPT 20.802: SABBehaviour Lock Unlock
SABBehaviour Lock Unlock
electric potential difference
Mask Bit Info On Off Output 7
boiler sequence is temporary not producing heat
Absolute actuator position demand (setpoint, valve linearized)
DPT 14.001: Value of angular acceleration
Value Acceleration Angular
Month and Day of Month field not valid = 1
is space of
updated value = 5
a point representing DPT 20.610: LoadTypeDetected
LoadTypeDetected
a point representing DPT 1.001: Switch
Switch
ComfortPushbutton
ModeSelect
fresh gale = 8
FanSpeedUser
The visual effect of channel 12 is active = 1
is point function type of
Substance with neither definite volume nor shape
Gas
actuator is currently in calibration mode
Sunshiny = 2
TempReturnAir
The upper boundary of the range with 95 % certainty the power value is in it
Info On Off Output 15
Info On Off Output 10
is application function of
second character of RegionCode, ASCII-coded
a point representing DPT 1.011: State
State
A ceiling is an overhead interior surface that covers the upper limits of a room.
Ceiling
corresponding Datapoint is in alarm
Historical three-phase = 2
Level 12 = 12
Minutes
ContrModeAct
Water in its gas form
Steam
This state type expresses that an equipment, such as a luminaire, is switched on. This state type is the inverse of the 'Off State' state type.
On State
electric displacement
a point representing DPT 20.804: BlindsControlMode
BlindsControlMode
This state type expresses that the movement of an equipment has stopped. Usually, this is associated with equipments that can be moved by a drive, such as valves, blinds, slats, windows, or doors.
Stopped Movement
The visual effect of channel 24 is active = 1
a point representing DPT 222.101: TempRoomSetpSetShiftF16[3]
TempRoomSetpSetShiftF16[3]
The visual effect of channel 16 is inactive = 0
Fault
The visual effect of channel 4 is active = 1
scene B = 1
Additional heating/cooling stage (2. Stage)
Video refers to the part of multimedia, which is dealing with visuals. The trade video contains applications for producing and capturing visual signals, such as images or movie clips.
Video
only move Up/Down mode (shutter) = 0
a point representing DPT 203.104: HVAC Air Flow Absolute Z
HVAC Air Flow Absolute Z
TempRoomSetpSetHeat
Info On Off Output 8
is point operation of
Mask Bit Info On Off Output 11
digit 5 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
Power profiles are configurations that set the energy consumption levels of equipment and systems to achieve a defined goal. Some examples of power profiles can be “Maximize output”, “Minimize energy consumption” or any custom level of performance.
Power Profile Based Control
Calculated = 1
leading edge (inductive load) = 1
a point representing DPT 1.1200: ConsumerProducer
ConsumerProducer
Mask Bit Info On Off Output 5
digit 3 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
Staircase Switch Request
is functional block of
EnOcean
Rain is water droplets that have condensed from atmospheric water vapor and then fall under gravity.
Rain
The visual effect of channel 15 is inactive = 0
scene A = 0
HeatCoolMode
Auto = 0
Normal = 2
instruction is related to abnormal condition
a point representing DPT 7.007: TimePeriodHrs
TimePeriodHrs
Lower end pos. reached
This field shall indicate whether the Brightness information in the field Brightness is valid or not.
Manual Control = 1
a point representing DPT 13.015: ReactiveEnergy kVARh
ReactiveEnergy kVARh
volume flow, 0,001 ml/s = 72
Relation to GMT
User Fan Speed Setting
Shutters and blinds = 50
a point representing DPT 1.1201: EnergyDirection
EnergyDirection
temperature absolute value °C
Activation state of channel 20
Application functions for 'operation mode based control'. A facility has various stages in its process cycle that include powering up, regular functioning, transitions, maintenance, and other similar stages. Operation Mode Based Control provides the monitoring actions related to each of these stages.
Operation Mode Based Control
ForcedPosition
An identifier to specify the (numerical) model version of an application program.
Model
2 stage = 2
a point representing DPT 7.003: TimePeriod10MSec
TimePeriod10MSec
a point representing DPT 234.001: LanguageCodeAlpha2 ASCII
LanguageCodeAlpha2 ASCII
SwitchOnOffForced
Test pending = 2
a point representing DPT 22.100: StatusDHWC
StatusDHWC
An intrusion system monitors a building or systems for malicious activity or policy violations.
Intrusion Detection
To define a quality kind that hosts a pedefined set of tags.
has quality kind
3-bit controlled
frequency
An atrium is a large open-air or skylight-covered space surrounded by a building.
Atrium
This state type expresses that mode 'Emergency Cooling' is chosen for the HVAC system. Usually, this mode indicates whether emergency cooling demand is requested for the HVAC system, e.g. for heat protection of a room. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Emergency Cool
Light Switch Request
To define the presence of a (tangible) equipment, such as a device as part of a cabinet (that is also an equipment).
has part
a point representing DPT 252.600: Relative Control RGBW
Relative Control RGBW
Supply air temperature heating setpoint
mass flow, 100 kg/h = 85
a point representing DPT 20.1200: MBus BreakerValve State
MBus BreakerValve State
Day of week field not valid = 1
Hardwired inhibit mode active = 3
Date and Time
By a MaC (ETS) allowed location usages for a building.
Mac building
Compressed Air = 9
Application Functions that controls the quantity 'water pressure'.
Water Difference Pressure Control
Mask Bit Info On Off Output 10
HVACModeUserEff
Heat Stage A Actuator Status
ControlModeEff
Building prot/Auto = 3
DHWLoadActive
character
a point representing DPT 1.019: Window Door
Window Door
inactive = 0
a point representing DPT 202.1: RelValue Z
RelValue Z
power, 0,01 kJ/h = 49
Version Number
The visual effect of channel 10 is inactive = 0
Blinds Status
The Domestic Hot Water Control Application Function represents a process of providing domestic hot water (DHW) for the kitchen and bathroom sinks, tubs and other appliances.
DHW Control
reactance
The visual effect of channel 3 is active = 1
some failure in boiler sequence: HPM itself or boiler(s) have a failure (mainly used for monitoring)
No ramp = 0
Unknown = 0
LDTR
A dressing room is a room to get dressed. Preferably used with a Room.
Dressing Room
Modbus
The visual effect of channel 6 is active = 1
2 min = 13
general protection fault = 12
no alarm is used = 0
alarm status of corresponding Datapoint is not acknowledged
composes input
a point representing DPT 5.005: DecimalFactor
DecimalFactor
Request Converter Test Result = 2
Automatic Control = 0
is phenomenon quality kind observed by
A channel is grouping datapoints together, which may linked to a related hardware (such as a terminal) and/or a related application program. It fulfils a certain functionality of the device, which is a collection of datapoints (when available with a standardized semantic meaning as functional block) and the related hardware connections (i.e. input or output terminals). A channel is derived from parent concepts that are specified as part of the EN 50090-6-2.
Channel
no control = 0
A relation from one floor to the next floor.
has upper floor
near gale / moderate gale = 7
one PB/binary input mode = 1
Application functions that controls the quantity 'air temperature'.
Air Temperature Control
Blinds Stop Trigger
'void' = 3
a point representing DPT 15.000: Access Data
Access Data
Light Dimming Sensor Basic
Group Address = 1
controls operation of stage 1 or base stage
Scattered clouds = 4
no action (dummy) = 0
a point representing DPT 21.001: StatusGen
StatusGen
no filtering, all supported received frames shall be passed to the cEMI client using L_Data.ind = 0
mass flow, 0,01 kg/h = 81
a point representing DPT 207.600: Status Lighting Actuator
Status Lighting Actuator
4-1-1 byte combined information
ok = 0
a point representing DPT 20.110: HeaterMode
HeaterMode
New / Lock (S-FSK) - Associated (G3-PLC) = 1
Application functions that controls the quantity 'air humidity'.
Air Humidity Control
a point representing DPT 9.026: Rain Amount
Rain Amount
IMAP
MBus
Brightness External
DPT 14.006: Value of an angle (in radiant)
Value AngleRad
volume, 0,01 l = 17
DPT 14.017: Value of density
Value Density
StatusStopOptim
This state type expresses that an equipment has a movement direction that can be interpreted as 'opening'. Usually, this is associated with equipments that can be moved by a drive in an horizontal axis or on a hinge, such as valves, windows, or doors.
Opening Movement
a point representing DPT 20.801: SABExceptBehaviour
SABExceptBehaviour
Asynchronous
Tuesday = 2
electrical energy
a point representing DPT 20.008: PSUMode
PSUMode
a point representing DPT 21.101: ForceSignCool
ForceSignCool
a point representing DPT 9.024: Power
Power
A garage is a walled, roofed structure for storing a vehicle or vehicles that may be part of or attached to a home ('attached garage'), or a separate outbuilding or shed ('detached garage'). Preferably used with an Room.
Garage
TempOutside
is point interface of
The visual effect of channel 17 is active = 1
Relates to the phenomenon of burning substances.
Fire
Heat and cool = 13
PE3 in progress = 3
The value of the point is a COMPLETE value and does not need any other point value to be usable (21 °C, fan speed 30 %).
Absolute Value
Failed, max delay exceeded = 4
a point representing DPT 1.018: Occupancy
Occupancy
Lighting = 20
Shall specify whether the colour component red shall be increased or decreased.
automatic once = 4
An identifier to specify the (numerical) version of an application program.
Version
is asset of
ChangeOverStatus
some failure in the water temperature controller
The visual effect of channel 16 is active = 1
a point representing DPT 13.001: Value 4 Count
Value 4 Count
Switch OnOff
a point representing DPT 2.006: Binary Value Control
Binary Value Control
a point representing DPT 20.001: SCLOMode
Backup Value = 0
Cool stage A for normal cooling = 3
the energy constraint allow the Resource Manager to describe what it considers as acceptable levels for avarate power for specific time periods
Free Cool = 10
Ack
A terrace is an external, raised, open, flat area in either a landscape (such as a park or garden) near a building, or as a roof terrace on a flat roof. Preferably used with an Space.
Terrace
The next active Tariff after expiration of the delay time
A Quality Kind with an observable quantity property that addresses a 'phenomenon', and the quantity property can only be indirectly determined.
observes phenomenon quality kind
A specific Application Function category for energy control that reflect an active process of planning, monitoring, and optimizing the energy production, consumption, distribution and storage. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Energy Control
2.x
master = 2
SynchronizationMode indicates that the actuator is currently executing a synchronization of the stroke model
HS - Hardwired inhibit
activated with security = 2
A utility room is generally the area where laundry is done, and is the descendant of the scullery. Preferably used with an Room. Preferably used with an Room.
Utility Room
Limits a numerical datapoint value in its applicative behavior to a maximum. Represents an external definition, hence it is also used from other concepts, therefore no domain is defined (merged ontologies -> intersection problems). The range xsd:decimal covers also numerical values with a fraction such as 12.34 or -13.56.
maximum
Ballast Failure
Protection of buildings, rooms, objects or persons against unwanted effects of solar radiation.
Shading
invalid = 255
TempRoom
power range for related to the given supply rate
A boiler is a closed vessel in which fluid (generally water) is heated. Equipment to generate hot water or steam for heating.
Boiler
9.x
Activation state of channel 5
Electrical circuit and its associated components such as breakers.
Circuit
Device Address = 0
The visual effect of channel 4 is inactive = 0
A specific Application Function category that controls the audio system. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Audio Control
The visual effect of channel 20 is inactive = 0
Mask Bit Info On Off Output 3
light air = 1
Fan Stage
This property allows to annotate a KNX-specific label.
Label (KNX-specific)
Certfication status of an application program.
certfication status
is datapoint type of
BackupMode
Activation state of channel 13
Up = 0
true = staircase lighting function is active, e.g. via input TimedStartStop.
The symbol is a glyph that is used to represent some concept, typically a unit or a quantity, in a compact form. For example, the symbol for an Ohm is a capital greek Omega. This contrasts with 'unit:abbreviation', which gives a short alphanumeric abbreviation for the unit, 'ohm' for Ohm.
symbol
auto (PSU/DPSU automatic on/off) = 2
Medium = 1
SwitchOnMode
off/on = 2
This state type relates to both primary and secondary stages of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages Both
corresponding Datapoint value is out of service
This state type expresses that a device is currently being calibrated. It cannot be expected to fulfill its usual functionality until it is fully operational once again.
Operational State Calibration
Activation state of channel 12
This state type expresses the state of no storm. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of no storm, storm protection is not required and this equipment might be used for shading purposes as intended. This state type is the inverse of the 'Storm State' state type.
No Storm
EquipmentType to remove heat from a liquid.
Chiller
Activation state of channel 11
validity of the Tariff data
A fan actuator.
Fan Actuator
electric current density
x-coordinate of the colour information
trigger (0) = 0
ContrMode
This state type expresses that an equipment is not in a forced state, i.e. no command with very high priority influenced the equipment's current value / position. The equipment's normal processing of input commands is executed. This state type is the inverse of the 'Forced State' state type.
Not Forced State
Fixed = 0
Positive = 0
EnableComfort
a point representing DPT 20.611: Converter Test Control
Converter Test Control
Rest mode active = 4
The visual effect of channel 1 is inactive = 0
magnetic field strength
normal setpoint = 0
'Delay' is the amount of time passing before a certain event is scheduled.
Delay
HourOfDay
Power Envelope is the aggregated measure of the extreme values of the power output over a period of time. Power Envelope Based Control allows you to set limits to these power envelopes for certain periods of time.
Power Envelope Based Control
TempRoomSetpUserAbs
magnetization
Indicator whether sequence is interruptible or not
The visual effect of channel 18 is active = 1
Heat Stage A On/Off = 1
MeteringDeviceType
The visual effect of channel 14 is inactive = 0
a point representing DPT 20.602: DALI Fade Time
DALI Fade Time
a point representing DPT 5.004: Percent U8
Percent U8
a point representing DPT 7.002: TimePeriodMsec
TimePeriodMsec
digit 1 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
CB and Step Code Brightness Validity
room temperature setpoint shift standby
Busmonitor Error Flags = 3
Used to refer to management client (MaC) specific data that are not present (with a unique resolvable identifier) within the KNX information model. With this 'link' reference shared data can be defined for the same entity, whereas the data are spread over different sources. Usually, the data are generated in different tools and finally used in a MaC, the latter can import the data chunks and compose them correctly to an full entity.
has component id
Close = 1
automatic (resistive, capacitive or inductive) = 0
Bank Holiday (No working day) = 0
a point representing DPT 207.105: StatusAct
StatusAct
emergency demand (heating or cooling) for room frost protection or de-icing
Warm Water meter (30 °C to 90 °C) = 6
a point representing DPT 205.017: Percent_V16_Z
Percent V16 Z
The visual effect of channel 14 is active = 1
Shutter Status
InAlarm
occupied = 0
SwitchOnOff
The visual effect of channel 9 is inactive = 0
StartSynchronization
DPT 14.066: Value of stress
Value Stress
power, 10000 kJ/h = 55
SABBehaviour_Lock_Unlock
Field string scheme, used to define a charset scheme of a KNX data field as part of an entire datapoint type (usually string/char DPTs). Same as for ETS XML data.
field string schema
a point representing DPT 1.012: Invert
Invert
value according additional parameter = 1
A quality kind (QK) describes a specific “type of interest” that is related to a value with a continuous, measurable physical quantity. The quantity can be figured out without any other context knowledge from any domain.
Quality Kind
a point representing DPT 20.1003: RF FilterSelect
RF FilterSelect
8-Bit Enum with Status/Command
digital input inverted = 2
DPT 14.045: Value of magnetic flux
Value Magnetic Flux
CloudCover
Ramp
Goto Rest Mode = 1
Rain Sensor
LoadTypeSet
a point representing DPT 1.008: Up Down
Up Down
A meeting room, conference room, or conference hall is a room provided for singular events such as business conferences and meetings. Preferably used with an Room.
Meeting Room
HVAC Direct Electrical Heating = 12
estimated time that the timer needs once it has been started
Waste water meter = 40
digit 4 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
is equipment type of
Max time a device could be pause between the end of the previous running sequence and the start of this one
power, 0,001 kJ/h = 48
NoDem = 20
Audio refers to the part of multimedia, which is dealing with sounds. The trade audio contains applications for producing and capturing sound signals.
Audio
Heat Stage B Actuator Target Position
The visual effect of channel 2 is active = 1
conductivity, electrical
To define an operation kind that hosts a pedefined set of tags.
has operation kind
Heat meter = 4
power, 10 kJ/h = 52
Level 0 = 0
DPT 14.058: Value of pressure
Value Pressure
EnableCool
DPT 14.044: Value of magnetic field strength
Value Magnetic FieldStrength
capacitance
Increase or decrease the brightness.
Shall specify whether the colour component blue shall be increased or decreased.
In KNX used (numerical) identifier to address a specific interface object type reflecting a KNX functional block id. The range xsd:unsignedShort supports exactly the KNX value range from 0 to 65535.
interface object type
FTP
A floor is the bottom surface of a room or vehicle. Floors vary from simple dirt in a cave to many layered surfaces made with modern technology. Floors may be stone, wood, bamboo, metal or any other material that can support the expected load.
Floor
a point representing DPT 2.004: Ramp Control
Ramp Control
a point representing DPT 20.603: BlinkingMode
BlinkingMode
alarm info
stop = 4
DewPointStatus
An OP relationship to a list that describes the position of a point in a control loop.
has point function type
DPT 14.059: Value of reactance
Value Reactance
TimeDelay
A factory, manufacturing plant or a production plant is an industrial facility, often a complex consisting of several buildings filled with machinery, where workers manufacture items or operate machines which process each item into another. Preferably used with a Building.
Factory
CRC-error = 9
slave = 2
Activation state of channel 7
volume, 0,1 l = 18
TempRoomSetpSetHeatShift
indicates whether overload is critical (e.g. too low boiler temp.) or uncritical (e.g. requested boiler temperature can not be provided but boiler temperature is above critical lower limit)
Application function to provide a 'system clock' for the system.
System Clock
ErrorCode_Sup
Refers to the concentration of CO2 molecules in the air, measured in ppm. This is a specialization of quantitykind:Concentration.
Concentration, CO2
digit 2 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
RoomHMax
a point representing DPT 203.101: Wind Speed Z
Wind Speed Z
DPT 14.028: Value of electric potential difference
Value Electric PotentialDifference
a point representing DPT 218.001: Volume in Liter
VolumeLiter Z
Monday = 1
StatusGO
This DPA represents a generic Status (Z8), as described in KNX Vol 3/7/2, section 4.1.2. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring to the device: Bit 0) OutOfService (modeled by the state type tag:operationalStateOutOfService); Bit 1) Fault (modeled by the state type tag:operationalStateFaulty); Bit 2) Overridden (device being in maintenance mode, modeled by the state type tag:operationalStateMaintenance); Bit 3) InAlarm (modeled by the state type tag:operationalStateInAlarm); Bit 4) AlarmUnAck (modeled by the state type tag:operationalStateAlarmPending)
burner failure
Other = 0
ChangeOverStatusWater
a point representing DPT 231.001: Locale ASCII
Locale ASCII
auto = 0
luminous flux
DPT 14.063: Value of solid angle
Value SolidAngle
a point representing DPT 21.1010: Channel Activation 8
Channel Activation 8
30 min = 19
solid state fuel = 3
room temperature setpoint comfort
Overload
operation mode id the transition points to
Date Time
DPT 14.007: Value of an angle (in degrees)
Value AngleDeg
This state type expresses that the actual device hosting the datapoint is not working properly due to a failure. Thus, no valid value is available at the datapoint. The cause of the device failure cannot be specified any further.
Operational State Defect
energy, 0,1 MWh = 128
Heat Stage B Actuator Fault
Overcurrent
a point representing DPT 22.102: Combined Status HVA
Combined Status HVA
This means that the intended value is a (discrete) element from an enumeration (list), the numerical representation of the value does not express any semantical meaning or priority within the list.
Enumeration
Step
a point representing DPT 24.001: VarString 8859-1
VarString 8859-1
Water in its solid form
Ice
Heat and Cool = 13
output state is valid = 1
TempRoomSetpAct
basic alarm = 2
volume flow, 1000 l/h = 62
power, 0,1 GJ/h = 176
a point representing DPT 7.600: Absolute Color Temperature
Absolute Colour Temperature
has actionpoint
This state type expresses that the normal room temperature setpoint from the HMI or supervisor is used for temperature control in a room.
Type of Temperature Setpoint Normal
Direction 2
energy
LoadDetectionError
mass, 1000 kg = 30
TempDischargeAir
No failure detected = 1
ActCurrPosHeatStageB
Goto Inhibit Mode = 2
In KNX used (numerical) identifier to address a specific property as part of an interface object. The range xsd:unsignedByte supports exactly the KNX value range from 0 to 255. As a note, this is a mirror property to the data property "knx:propertyIdentifier" and must ONLY be used on annotated datapoint (dpa.x) classes, not on the actual individuals!
property identifier annotation
a point representing DPT 9.023: KelvinPerPercent
KelvinPerPercent
power, 1 GJ/h = 177
Light Switching Actuator Basic
Active = 1
fault = 1
Actual HVAC Emergency Mode
DownUp = 3
BlinkingDisabled = 0
Efficiency is the ratio of output power to input power.
Efficiency
ActCurrPosHeatStageA
Relates to the light colour value, measured in the xyY colour system. The coordinates x and y define the chromaticity of the colour, whereas the coordinate Y defines the luminance of the color.
Light colour xyY
The phenomenon of high temperatures. This can relate to high ambient temperatures (e.g. as a weather phenomenon or in buildings) or to high temperatures in devices (e.g. when in the danger of overheating).
Heat
to express a “metadata to runtime” relation between different datapoints. Datapoints may provide further information about other datapoints but not including to manipulate their actual value at runtime.
is meta data of
true = night mode is active e.g., via input NightMode; the actuator will autonomously switch off the light after a defined time period.
HS - Hardwired switch
includes datapoint type
Effective value of the comfort push button
Level 8 = 8
a point representing DPT 20.021: Cloud Cover
Cloud Cover
A dimmer is a device connected to a light fixture and used to lower the brightness of the light.
Dimmer
Frost Alarm
Heat cost allocator = 8
User Presence Switch
Unknown Device type = 15
General failure information
resistance
The visual effect of channel 9 is active = 1
Hardwired Inhibit is active = 1
list of fill level target profile element
A relation to a subclass of a location, e.g. a room as spatial sub-location of a floor.
has location
left to right = 0
Start of time period that will be covered by the power profile
TempRoomSetpSetCoolEff
Activation state of channel 19
a point representing DPT 1.024: DayNight
DayNight
Night Purge = 4
The volume of a solid object is the three-dimensional concept of how much space it occupies, often quantified numerically. One-dimensional figures (such as lines) and two-dimensional shapes (such as squares) are assigned zero volume in the three-dimensional space.
Volume
Validity slats pos.
Time delay
operation mode factor that defines the target power value within the given power range of the operation mode
Enable
Year field not valid = 1
error = 1
Sunny = 1
A technical room is a space in a building that is used to host equipment. Preferably used with a Room.
Technical Room
clear = 0
Hour
a point representing DPT 3.007: Control Dimming
Control Dimming
The upper boundary of the range with 68 % certainty the power value is in it
The lower boundary of the range with 100 % certainty the power value is in it
A specific Application Function category that controls application functions is a specific category that represents an expected behavior or functionality of an equipment such as a 2-step fan speed control or an aggregation of application functions such as Air Handler Unit etc. In addition, the behavior or rather the effect in the real world can be expressed with a QualityKind. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Equipment Control
reliable synchronisation source (radio, Internet) = 1
Used to control a (generic) actuator equipment. Don't care if the (generic functionality) is internally operated from the actuator by a motor or other means.
Actuator
Last download time stamp, usually generated by Mac. May be used from other concepts, therefore no domain is defined.
last downloaded
An item offered for sale; it can be assigned from any equipment. Manufacturers usually provide identifiers for each product they make. Identifier examples are type/model or version number or the order number.
Product
TempRoomSetpTariffShift
The visual effect of channel 1 is active = 1
ValInfField
Extended Relative Timestamp = 6
This state type expresses that an HVAC system has neither primary nor secondary stage (for its cooling or heating subsystem). In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages None
The visual effect of channel 19 is active = 1
a point representing DPT 20.803: SSSBMode
SSSBMode
Off = 6
A site segment subdivides a site, it is usually occupied by a building.
Site Segment
Liegenschaftsteil
DPT 14.036: Value of heat flow rate
Value Heat FlowRate
Dim Send Style
Load Management = 40
Thursday = 4
Electromagnetic radiation in the visible spectrum
Light
scene is active = 0
a point representing DPT 209.102: StatusCPM
StatusCPM
Activation state of channel 3
validity of the fields CC and Step Code Colour.
An air conditioning system is a system to satisfy requirements for temperature, humidity and air quality in rooms by adhering to these values within predefined limits.
Air Conditioning
operation mode id the transition starts from
Alarming is the automated alarm management in the event of alarms or faults in plants, subsystems or devices. The application function may contain a list of activ alarms, past alarms, alarm prioritization or sends a notification to recipients (e.g. email).
Alarming
energy, 0,01 kJ = 9
reading of access information code was not successful = 1
electric dipole moment
Relative Control RGB
alarm = 1
last received absolute setvalue = 2
A relation between two locations that share a common interface such as a wall or door, but do not intersect.
has adjacent location
a point representing DPT 238.600: DALI Diagnostics
DALI Diagnostics
a point representing DPT 20.605: SwitchPBModel
SwitchPBModel
Prioritised Mode Control
Absolute Set Value Control Green
Open / Close
A wellness room may contain facilities such as a sauna, pool, steam room, or whirlpool. A wellness room provides a variety of services for the purpose of improving health, beauty, and relaxation through personal care treatments such as massages and facials. Preferably used with an Room.
Wellness
a point representing DPT 20.116: Enable HC Stage
Enable HC Stage
luminous intensity
SMTP
Air Damper = 1
DayOfWeek
mass flow, 10000 kg/h = 87
is location of
Binary Information
Heat Stage A Actuator Calibration Mode
WindowStatusEff
This state type is a special type of a defect state. It expresses that the actual device hosting the datapoint is not working properly due to a short circuit. Thus, no valid value is available at the datapoint.
Operational State Defect Short Circuit
B1 with Date and Time
no failure = 0
A Quality Kind with an actuatable quantity property that addresses a 'phenomenon', and the quantity property can only be indirectly influenced.
acts on phenomenon quality kind
This state type expresses that mode 'Emergency Cooling' is chosen for the HVAC system. Usually, this mode indicates whether emergency heat demand is requested for the HVAC system, e.g. for frost protection of a room. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Emergency Heat
activity (radioactivity)
Water meter = 7
DamperMode
Overcast = 8
Start = 1
is room of
Working day = 1
Energy Direction
absolute load priority
Standard single-phase = 3
ChangeoverMode
Converter test result
The tag category contains individuals that describe for which purpose a location is used for.
Location Usages
a point representing DPT 20.113: StatusRoomSetp
StatusRoomSetp
TempFlowLimit
Unsigned relative value
To define the general presence of a functional block, implemented/realized in a device. The OP does not claim the operational (concurrent) presence of a certain FB at Runtime.
supports functional block
Passed max delay exceeded = 2
The visual effect of channel 15 is active = 1
An application function combines as set of individual functions to achieve its desired behavior, typically with a combination of devices exchanging information via their input and output datapoints. A number, state or comment may be edited in a MaC as a string (allows also non-number chars).
Application Functions
Metering and monitoring are used, for example, for efficient energy management.
Energy Management
The visual effect of channel 22 is inactive = 0
DPT 14.004: Value of the amount of substance (mol)
Value Mol
temperature difference
Equipment which adds moisture to air to increase humidity.
Humidifier
TempRoomSetpLoadShedShift
current factor that will be multiplied with given power range of the operation mode. will be set with a transition instruction
A section of piping that refers to those parts of distribution systems in buildings that are pipes, mostly for transporting water.
Pipe Section
a point representing DPT 12.001: Value 4 Ucount
Value 4 Ucount
TempRoomSetpHeatEff
Heats a space using pipes or cables embedded beneath floor. The most common kind of radiant heating is underfloor heating. There are three types of underfloor heating: hot air systems, hot water systems and electric systems.
Underfloor Heating
Used to control an actuator equipment to regulate the flow of air (damper). Don't care if the damper is internally operated from the actuator by a motor or other means.
Damper Actuator
16-bit set
This state type expresses that a device is currently in maintenance mode, i.e. it cannot be expected to fulfill its usual functionality until it is fully operational once again. Specific examples include ‘service mode’ or the ‘valve kick’ of valve actuators.
Operational State Maintenance
Stop Test = 4
sensor fault = 1
commodity quantity the power envelope refers to
This state type expresses that a room is occupied. The actual number of people is not of interest. This state type is the inverse of the 'Presence Unoccupied' state type.
Presence Occupied
WD field not valid = 1
Not occupied = 2
Preferably used with a Building.
Public Building
This state type expresses that a contact (e.g. a valve end position contact or a partition wall status, or window contact) is in an opened state. This state type is the inverse of the 'closed' state type.
Opened State
In KNX used (numerical) identifier to address a specific interface object. The range xsd:unsignedShort supports exactly the KNX value range from 0 to 65535. As a note, this is a mirror property to the data property "knx:objectType" and must ONLY be used on function block (fb.x) classes, not on the actual individuals!
interface object type annotation
A device for displaying visual information, such as text, images and shapes.
Screen
A washing machine (laundry machine, clothes washer, washer, or simply wash) is a home appliance (EN 50523) used to wash laundry.
Refrigerator
An OP relationship to express a relation from a functional block to datapoints as part of a FB. Such datapoints includes per definition additional semantic information, with this a FB can be composed with its mandatory/optional datapoints.
composes
is function point of
ActTargetPosHeatStageA
LTRP
is composed by
Activation state of channel 14
a point representing DPT 225.003: TariffNext
TariffNext
a point representing DPT 9.001: Value Temp
Value Temp
open = 1
validity of TempFlowProdSegmH field
Info On Off Output 13
supported commodities (b0 = electricity, b1 = gas, b2 = oil, b3 = 0/reserved)
HVACModeEff
Day / Night
is tag set of
a point representing DPT 232.600: Colour RGB
Colour RGB
Status E
To define a relation to a product from an equipment.
has product
HVACModeAct
digital input not inverted = 1
a point representing DPT 7.006: TimePeriodMin
TimePeriodMin
TempSetpShiftStdby
a point representing DPT 8.004: DeltaTime100MSec
DeltaTime100MSec
RelSetvalueControlCmd
a point representing DPT 20.020: ActuatorConnectType
ActuatorConnectType
The visual effect of channel 2 is inactive = 0
A functional subdivison of a location. Structurally, a room is defined by enclosing surfaces such as facades, walls or ceilings (e.g. a single-room office or hotel room) or, in the case of an open-plan office, it is created by organisational means (e.g. as a separate zone).
Room
energy, 100 kJ = 13
DPT 14.067: Value of surface tension
Value Surface Tension
Stop Date Time
No alarm = 0
Room Setpoint Manager Temperature Driven
The upper boundary of the range with 100 % certainty the power value is in it
ControlModeUser
Up/down position is forced by MoveUpDownForced input
send if value changed during powerdown = 2
Economic Heat/Cool Mode = 13
Hosts the unit of a datapoint (if applicable). A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
unit
some failure in the chiller
Indicator if sequences will run under abnormal conditions
The access trade is the selective access and control to resources (e.g. a place, information, etc.).
Access Control
acceleration
The visual effect of channel 11 is inactive = 0
On = 1
The trailing number of the minor datapoint type (DPT) in bits, specified in KNX with a numerical scheme. The minor type must be present for sub types but not for a major type. The range is used to include 0 (the KNX DPT numbering scheme starts at 0).
datapoint type minor number
mode 0 is active = 1
Shall specify whether the colour component green shall be increased or decreased.
An identifier to specify the (string based) order number of a vendor product. The order number scheme is vendor specific.
Order Number
timestamp when instruction shall be executed. In case the instruction type is SCHEDULE, ET will be the start time of the addressed sequence.
LoadFailedDetection
Direct current electricity
Electricity, DC
The visual effect of channel 12 is inactive = 0
Reset
Represents an ASCII character. The most significant bit shall always be 0. Encoding according to the ASCII table.
Character
Fresh air, e.g. for fancoils = 1
power, 1 kJ/h = 51
analog input -> 0% to 100% = 3
asynchronous = 0
system and functions of common interest = 1
Slats Position
current position=0 = 0
A room is a space in a building that is delimited by walls/windows, ceilings, floors and has a door or a passage to enter the room, it can be subdivided into locations of type room segment.
Raum
EnableH/CStage
magnetic flux
a point representing DPT 2.012: Invert Control
Invert Control
Uses for to define the current status of an entity, such as the building completion or installation status. May be used from other concepts, therefore no domain is defined.
state
LegioProtect = 1
The field Scent Activation shall indicate whether the scene with scene number SN is active or not.
Represents values for counting from 0 to 255 counter pulses.
Value 1 U Count
Radio converter (meter side) = 55
a point representing DPT 20.111: FanMode
FanMode
0 s (no fade) = 0
a point representing DPT 7.005: TimePeriodSec
TimePeriodSec
right to left = 1
A refrigerator, colloquially fridge, is a commercial and home appliance (EN50523) consisting of a thermally insulated compartment and a heat pump (mechanical, electronic or chemical) that transfers heat from its inside to its external environment so that its inside is cooled to a temperature below the room temperature.
Activation state of channel 24
A user operated light dimming request including an explicit dimming status. The light switch request inlcuding its status is inlcluded.
User Light Dimming
SensorSelect
An engine or motor is a machine designed to convert one or more forms of energy into mechanical energy.
Engine
StatusMorningBoost
Other Commercial
is point of
failure = 1
Cool Stage B Actuator Calibration Mode
Steam meter = 5
the range of the fill level that will be reached in the given time
no change = 2
value according additional parameter = 3
a point representing DPT 20.608: SwitchOnMode
a point representing DPT 205.102: HVACAirFlowRel_Z
HVAC Air Flow Relative Value
Application functions for "demand driven based control" is an approach to dynamically manage energy output based on the demand for energy that arises within the smart grid.
Demand Driven Based Control
BiBat Slave
DPT 14.030: Value of electromotive force
Value Electromotive Force
Request Converter DT Info = 5
temperature relative value offset K
a point representing DPT 225.002: Scaling Step Time
Scaling Step Time
moderate breeze = 4
a point representing DPT 20.013: Time Delay
Time Delay
Colour Actuator RGB(W)
This state type expresses that the second-highest level named 'Standby' (or 'Pre-Comfort') is chosen for the HVAC mode. Usually, the 'Standby' level is associated with an unoccupied room that needs to be able to reach the 'Comfort' level in a short period of time. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Standby
Heat Mode = 1
Switch Current Status
Shall specify the fading step size or to the code to stop the fading of the colour red
The tag category contains individuals that describe a specific application data source of a point, used in cases where the input of an point is affected from a superordinated application control (instead of the common control loop).
Origin
Start Date Time
Activation state of channel 6
Level 6 = 6
a point representing DPT 1.005: Alarm
Alarm
LED, leading = 7
mode 1 is active = 2
enabled (PSU/DPSU fixed on) = 1
power
a point representing DPT 20.100: FuelType
electromotive force
DPT 14.054: Value of phase angle (in radiant)
Value Phase AngleRad
An application program represents a piece of software that implements a functionality. Moreover, specific confifuration parameters may be used to control how the functionality is operating at Runtime.
Application Program
volume flow, 1 ml/s = 75
StatusMorningBoostH
Heat stage B for heating with two stages (A + B) = 2
A numerical address identifier, used in KNX to address a set of (registered) receivers, similar to an IP multicast address.
group address
A Datapoint exposes an internal state of a device that can be directly accessed (read) and optionally manipulated (write).
Datapoint
A specific Application Function category that controls a quantity (e.g. temperature, pressure) of the phenomenon water. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Water Control
Wind Sensor
FrostAlarm
An identifier to specify the (string based) erial number of a device.
serial number
No Date
WindAlarm
stage 2 / modulation active
insufficient non volatile memory = 6
Window Switch
Represents a ISO 8859-1 character. Encoding according to the character set ISO-8859-1 (Western Europe)
a point representing DPT 265.009: DateTime OpenClose
DateTime OpenClose
a point representing DPT 241.800: StatusSAB
StatusSAB
Consumer / Producer
datapoint type version
ActTargetFanSpeed
StatusEcoC
Current Date and Time
The tag category contains individuals that describe the runtime interworking interface type of a point.
Point Interface
No Layer = 255
DPT 14.1200: Value of volume flux (in cubic meters per hour)
Volume Flux for Meters
Address Indicator
permanently running = 1
filtering by Domain Address and by Serial number table = 3
Day
A parent OP relationship to express a general relation to a tag. The relationship specifies the OWL range class :Tag, allowing to express any relation to one of the individuals as part of the sub classes of :Tag. As it is also just a generic top OP of specialized (sub) OP relationship predicates, only the latter SHOULD be used.
has tag
shift load priority
a point representing DPT 209.100: StatusHPM
StatusHPM
a point representing DPT 23.102: HVAC PB Action
HVAC PB Action
Start
Cool = 3
SDHWLoadActive
Nearly overcast = 7
is equipment quality kind adjusted by
TempRoomSetpAbs
a point representing DPT 29.010: ActiveEnergy V64
ActiveEnergy V64
a point representing DPT 201.108: Occ Mode Z
Occ Mode Z
a point representing DPT 205.100: TempHVACAbs_Z
HVAC absolute Temperature
The value of the target point is sent at the earliest after a certain duration. The duration is defined by the metadata datapoint's value.
is minimal repetition of
This state type expresses the state of frost. Usually, this state is related to the protection of shading equipment such as blinds and slats, as their drive might be damaged when trying to move frozen blinds or slats. In case of frost, the equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Frost' state type.
Frost State
Enable = 1
The visual effect of channel 20 is active = 1
a point representing DPT 1.017: Trigger
Trigger
Room Temperature
Room AQ Sensor
Heat (inlet) = 12
An educational institution is a place where people of different ages gain an education, including preschools, childcare, primary-elementary schools, secondary-high schools, and universities. They provide a large variety of learning environments and learning spaces. Preferably used with a Building.
Educational
Started by Gateway = 2
Activation state of channel 8
The leading number of the major datapoint type (DPT) in bits, specified in KNX with a numerical scheme. The major type must be present for sub types and for a major type. The range is used to include 0 (the KNX DPT numbering scheme starts at 0).
datapoint type major number
a point representing DPT 30.1010: Channel Activation 24
Channel Activation 24
volume flow, 0,1 l/h = 58
power, 10 W = 44
DoA
control = 1
An imaginary horizontal plane situated at the nominal working height in an interior space. Most illuminance and daylight factor measurements and calculations are made for points on this plane.
Work Plane
Arbeitsbereich
The tag represents information for a logical point, a diagnostic point that serves for monitoring.
Diagnostic Point
a point representing DPT 21.107: Combined Status RTSM
Combined Status RTSM
Generic concentration without a specific type. In chemistry, concentration is defined as the abundance of a constituent divided by the total volume of a mixture. The term concentration can be applied to any kind of chemical mixture, but most frequently it refers to solutes in solutions.
Concentration
FanSpeed
RF_FilterSelect
a point representing DPT 21.103: StatusSDHWC
StatusSDHWC
2-byte signed value
volume flow, 10000 ml/s = 79
Precool = 5
Undefined = 0
manual light control = 1
This state type expresses that an equipment has a movement direction that can be interpreted as 'closing'. Usually, this is associated with equipments that can be moved by a drive in an horizontal axis or on a hinge, such as valves, windows, or doors.
Closing Movement
Timed StartStop
Latitude information
This state type expresses the 'humidification' mode of the ventilation system. Usually, this is related to raising the relative air humidity by adding moist air to a room.
Humidification Mode
a point representing DPT 20.103: DHWMode
not active = 0
HVAC VAC = 14
HeatCoolModeAct
DPT 14.011: Value of capacitance
Value Capacitance
volume flow, 0,01 ml/s = 73
The user application is stopped
Cooling load meter (inlet) = 11
Cool Stage A Actuator Calibration Mode
The field Storage function shall indicate whether the set value(s) for the scene number SN can be modified at runtime through DPT_SceneControl or not.
Overheat-Alarm
a point representing DPT 22.1010: Channel Activation 16
Channel Activation 16
a point representing DPT 20.600: Behaviour Lock Unlock
Behaviour Lock Unlock
Heat Stage B Actuator Current Position
Sky obstructed from view = 9
MBus address
This state type expresses that a room is unoccupied, i.e. no people are in the room. This state type is the inverse of the 'Presence Occupied' state type.
Presence Unoccupied
Shall specify the fading step size or to the code to stop the fading of the colour blue
Oil
ComfortProlongEff
Ventilation equipment to limit exposure to hazardous fumes. A fume hood (sometimes called a fume cupboard or fume closet) is a type of local ventilation device that is designed to limit exposure to hazardous or toxic fumes, vapors or dusts.
Fume Hood
Level 11 = 11
Refers to the concentration of particles in the air, measured in ppm. This is a specialization of quantitykind:Concentration.
Concentration, Smoke
Activation state of channel 2
number of fill level target profile elements
Forced Position
Scheduling in a building automation system is the process of systematically matching the use of heating, ventilation and air conditioning equipment with tenant occupancy schedules which is typically calendar-based.
Scheduler
a point representing DPT 22.101: StatusRHCC
StatusRHCC
is equipment quality kind measured by
High = 1
a point representing DPT 201.100: HVAC Mode Z
HVAC Mode Z
A command is classified as a direct adjustment, such as a Point used from manage functionalities to send imperative commands to control actuators.
Command
a point representing DPT 7.001: Value 2 Ucount
Value 2 Ucount
memory allocation command with size 0 received = 8
The value does not carry data to calculate with, only the access to it can already be interpreted.
a point representing DPT 2.003: Enable Control
Enable Control
a point representing DPT 7.010: PropDataType
PropDataType
Inhibit mode active = 2
A generic concept to represents an interface to data. A point can carry additional meta data, provided by tags and/or feature of interests. To describe a point more precise the class has several subclasses.
Point
power, 100 kJ/h = 53
A roof is the top covering of a building, including all materials and constructions necessary to support it on the walls of the building or on uprights, providing protection against rain, snow, sunlight, extremes of temperature, and wind.
Roof
BinarySceneRecall
a point representing DPT 20.609: LoadTypeSet
HVAC User Mode active (means DP ‘HVACModeUser’ is different from ‘Auto’) = 1
Actuator setvalue is locally overridden, e.g. via a local user interface
Defines the ability to read a datapoint. The r/w limits set with boolean values true (default) or false. It may be used to limit the access from a 3rd party interface or similar, set by a MaC.
readable
mass, 0,001 kg = 24
power, 1 W = 43
a point representing DPT 5.010: Value 1 Ucount
Value 1 Ucount
a point representing DPT 275.101: TempRoomSetpSetShiftF16[4]
Room Temperature Setpoint Shift
magnetic moment
a point representing DPT 1.013: Dim Send Style
Light Absolute Setvalue Request
volume flow, 0,001 l/min = 65
Light Relative Dimming Request
Shall specify the fading step size or to the code to stop the fading of the colour green
This state type expresses that the blue part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.
Chromaticity Blue
a point representing DPT 213.100: TempRoomSetpSet[4]
TempRoomSetpSet[4]
RelDimmingSpeed
Used to indicate the cardinality of a point. This is part of a point's access type in the specification Vol 7 and can be 'one' (1 -> this for inputs or this -> 1 for outputs) or 'many' (N -> this for inputs or this -> N for outputs).
has cardinality
Cooling Load meter (outlet) = 11
a point representing DPT 12.1200: VolumeLiquid Litre
VolumeLiquid Litre
duration the timer is active when started
TempRoomSetpUserOffsetEff
Data Link Layer = 0
DALI Device Address or DALI Group Address
a point representing DPT 9.008: Value AirQuality
Value AirQuality
A multimedia room is a space in a building that is used to contain multimedia gadgets such like consoles and entertainment. Preferably used with a Room.
Multimedia Room
An OP relationship to express a relation to an equipment from a location. This allows to define the presence of a (tangible) equipment, such as a device as part of a location. Mainly it expresses the “assembly place” of an equipment. The here meant location (domain) is the "installation location" of the equipment, also a device. To retrieve the "place of action" of a device it is needed to traverse from a device/datapoint -> functionPoint/application function/../location.
contains equipment
A garden is a planned space, usually outdoors, set aside for the cultivation, display, and enjoyment of plants and other forms of nature. Preferably used with an outside Location or Space.
Garden
Hosts the HTTP scheme with an URI part for the gateway as a resolvable name or as an IPv4 or IPv6 address. A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
authority sort of request URI
Wednesday = 3
In physics, a fluid is a liquid, gas, or other material that continuously deforms (flows) under an applied shear stress, or external force.
Fluid
Longitude information
8-bit set
light breeze = 2
Fault = 1
False = 0
deactivation of priority
Light fixture using electricity to provide illumination.
Luminaire
Passed in time = 1
Project installation number, usually generated by a Mac (edited by an installer).
Project Installation Number
Used to map a foreign protocol address to a KNX address identifier that is mapped to a specific datapoint. Due to the large number of protocols the data property is not explicitly modeled per (foreign) protocol; it is defined as a generic (bitwise unlimited) integer. Hence this the actual address identifier can be expressed as a large – but unstructured – bit field.
non KNX mapping address
scene control
Heat Stage B Actuator Valve Kick
The visual effect of channel 13 is inactive = 0
invalid opcode detected = 11
Rain Alarm
LightControlMode
Shall specify the fading step size or to the code to stop the fading of the colour
A health facility is, in general, any location where healthcare is provided. Health facilities are clinics and doctor's offices or urgent care centers with elaborate emergency rooms. Preferably used with a Building or a Site/Space.
Health Care
Specifies the maximum bit size of a datapoint type (DPT) in bits (variable datapoint types may define less as max, therefore 'max').
datapoint type bit size max
a point representing DPT 202.2: UCount Value 8 Z
UCount Value 8 Z
a point representing DPT 201.102: DHW Mode Z
DHW Mode Z
A location is a physical named geographical place that is used to identify a point, an area or room, inside or outside of a building. This generic location root node simplifies the replacement of the entire location model.
Location
A villa is a upper class country house. Preferably used with a Building.
Villa
has lower floor
Normal = 0
a point representing DPT 6.001: Percent V8
Percent V8
Status C
DayOfMonth
a point representing DPT 20.101: BurnerType
Morning Warmup = 2
TempRoomSetpUserAbsEff
The tag represents information for a logical point, a communication interworking (logical) input Point, it receives data.
Logical Input Point
actual actuator position
Day = 0
A hotel is an establishment that provides paid lodging on a short-term basis. Preferably used with a Building.
Hotel
A strong OP relationship to express a relation to a room segment contained in a room or room segment.
has room segment
PresenceStatus
SensorConnection = 1
The tag represents information for a logical point, a communication interworking (logical) output Point, it sends data.
Logical Output Point
DPT 14.012: Value of surface charge density
Value Charge DensitySurface
Lamp Failure
mode 2 is active = 4
room temperature setpoint shift standby (delta value)
To define a generic set of tags with no limitation on the amount. The tag set may represent a quality kind or process kind.
has tag set
identifier of the timer, needs to be unique within the scope of the state machine
The value is a continuous stream of totalization, the tag does not define any relation to a value dimension (metering data in unit kWh, amount of person as unitless number).
Totalized Value
a point representing DPT 20.1208: TIC Type
TIC Type
Specific Application Function for "Smart Grid control". A Smart grid is a network of transmission lines, substations, transformers that delivers electricity from points of generation to points of consumption with two-way communication to ensure efficient and reliable energy flow.
Smart Grid Control
EmergDepressure = 2
amount of substance
'Duration' is the length of a time interval, i.e. the amount of time that passes between two distinct points in time.
Duration
room temperature setpoint shift economy
"Distance" is a numerical description of how far apart objects are.
Distance
SwitchOnOffControlCmd
DPT 14.035: Value of heat capacity
Value Heat Capacity
volume in liter
TempRoomSetpAbsNext
Number of power sequences in a power sequence container
Bool
User HVAC Display
frequency, angular (pulsatance)
Info On Off Output 14
Status of HVAC Mode User
In geometric measurements, length most commonly refers to the estimated dimension of an object. In some contexts, the term "length" is reserved for a certain dimension of an object along which the length is measured.
Length
night round = 2
ZWave
DPT 14.055: Value of phase angle (in degrees)
Value Phase AngleDeg
Economy = 3
volume flow, 100 ml/s = 77
Field size, used to define the actual size in bits of a KNX data field as part of an entire datapoint type. The size may be not present, in case of an inluded datapoint type (DPT).
field size
A car (or automobile) is a wheeled motor vehicle that is used for transportation.
Car
Breaker/Valve is released = 2
Breaker (electricity) = 32
5.x
a point representing DPT 1.015: Reset
Low = 0
a point representing DPT 7.011: Length mm
Length mm
Saturday = 6
DHWLegio
deactivation of priority = 1
Steam oven (also called combi-steamers, hot-air steamers, combination steam-convection ovens, or simply combi ovens) are cooking appliances (EN 50523) typically used in professional catering or food service operations.
Steam Oven
The number of intervals into which the range of 0 % … 100 % is subdivided, or the break indication.
Step Code
a point representing DPT 9.006: Pressure
Pressure
Battery used to store electric energy.
Battery
electric field strength
boiler sequence is permanently off (manual switch or failure)
The visual effect of channel 7 is active = 1
comfort prolongation User not active = 0
NightMode
ForceRequest
heat, quantity of
a point representing DPT 21.102: StatusRHC
StatusRHC
is implemented by
Enclosure for electrical and control equipment.
Panel
has application function
is locality of
This state type expresses that a datapoint’s main value is corrupted due to failure. The device itself is operational. Typical usages are a sensor value is corrupted due to a hardware problem (data is invalid) or a database value is corrupted (due to loss off backup power, erased EEPROM etc).
Operational State Faulty
Conveyor to move people across a horizontal or inclined plane. A moving walkway, also known as an autowalk, moving pavement, moving sidewalk, people-mover, travolator, or travelator, is a slow-moving conveyor mechanism that transports people across a horizontal or inclined plane over a short to medium distance.
Moving Walkway
weight
garbage = 41
TempRoomSetpSetCoolShift
power, 1 MW = 169
Mask Bit Info On Off Output 6
is actionpoint of
Heat Stage B Proportional = 3
DPT 14.040: Value of light quantity
Value Light Quantity
A strong OP relationship to express a relation to a room in a location.
has room
DPT 14.072: Value of thermal conductivity
Value Thermal Conductivity
a point representing DPT 21.002: Device Control
Device Control
Refers to information that originates from algorithms, i.e. usually computed by a controller device.
Automatic
defines wich timers are blocking for this transition. each of the 16 timers could be referenced by setting the bits 0-15 to 0 (not blocking) or 1 (blocking)
Substance with definite shape and volume
Solid
a point representing DPT 213.102: TempRoomSetpSetShift[4]
TempRoomSetpSetShift[4]
inverse value of InfoOnOff is sent = 3
Lower predef. pos. reached, typ. height 100 %, slats-angle < 100 %
AbsSetvalueControlCmd
Scene AB
The term reception or front desk is used in many hotels for an administrative department where a receptionist's duties also may include room reservations and assignment, guest registration, cashier work, credit checks, key control, and mail and message service.
Reception
extended alarm = 3
A swimming pool, swimming bath, wading pool, paddling pool, or simply pool, is a structure designed to hold water to enable swimming or other leisure activities. Preferably used with an Space.
Pool
The visual effect of channel 24 is inactive = 0
Outside Temperature
CombinedStatus_HVA_HeatB
is applicable datapoint enum of
area
true = 1
True = 1
TempSetpStdby
The visual effect of channel 10 is active = 1
6.x
DHW operating mode
Stop = 0
Activation state of channel 4
TimedStartStop
DHW mode
down = 1
DPT 14.078: Value of weight
Value Weight
a point representing DPT 2.010: Start Control
Start Control
a point representing DPT 1.003: Enable
FanStepUser
Actual controller Mode
not occupied = 2
WD field valid = 0
User interfaces are composed of one or more layers, including a human-machine interface (HMI) that interfaces machines with physical input hardware such as keyboards, mice, or game pads, and output hardware such as computer monitors, speakers, and printers.
HMI
identifier of the current operation mode
4.x
Frost Sensor
Voltage, also referred to as Electric Tension, is the difference between electrical potentials of two points. For an irrotational electric field, the voltage is independent of the path between the two points a and b.
Electrical Voltage
DPT 14.074: Value of time
Value Time
permanently off (manual switch or failure)
Encryption of access information
A kitchen is a room or part of a room used for cooking and food preparation in a dwelling or in a commercial establishment. Preferably used with an Room.
Kitchen
a point representing DPT 21.105: StatusRCC
StatusRCC
Colour Level White
solid angle
EquipmentType to meter a substance or phenomenon
Meter
DPT 14.077: Value of volume flux
Value Volume Flux
not accepted = 0
ActuatorErrorInfo
Specifies for enumeration DPTs a numerical value, that is used from the KNX system at runtime.
value KNX
set = 1
The visual effect of channel 8 is inactive = 0
Building Protection = 4
Magic Number
Short Circuit
Energy is the quantity characterizing the ability of a system to do work.
Energy
Info On Off Output 1
Volumetric Flow Rate, (also known as volume flow rate, rate of fluid flow or volume velocity) is the volume of fluid which passes through a given surface per unit time.
Volume Flow Rate
Used to indicate that an entity is not yet completely defined and should be excluded from use in MaCs. Note 1: if this property has the value false, it must be treated exactly as if ths property would not be present at all. Note 2: If an entity has been completed for MaC use, this property must be removed from the entity.
is incomplete
configuration/ diagnostics
DPT 14.051: Value of mass
Value Mass
not occupied = 0
identifier of the resource manager. Must be unique within a single KNX system
electric charge
two PBs/binary inputs mode = 4
a point representing DPT 201.109: HVAC Emerg Mode Z
HVAC Emerg Mode Z
Cool Stage A Actuator Current Position
DPT 14.047: Value of magnetic moment
Value Magnetic Moment
is phenomenon quality kind actet on by
Relative timestamp = 4
Current Time
Heat Stage A Proportional = 2
fresh breeze = 5
DPT 14.052: Value of mass flux
Value MassFlux
insufficient volatile memory = 7
Used to represent the current version of the content for the MaC.
mac version
presence simulation = 1
a point representing DPT 242.600: Colour xyY
Colour xyY
Emergency Cool Mode = 16
Reset Duration Test Done = 6
HVACModeEffNext
Start Function Test (FT) = 1
Request Battery Info = 3
volume flow, 100 l/min = 70
Activation state of channel 16
TempRoomSetpSetCool
Working Day
a point representing DPT 26.001: SceneInfo
SceneInfo
Cool Stage A Actuator Target Position
Height Position
Heat Stage A Actuator Valve Kick
Heat Stage B Actuator Status
actuator position is manually overridden
Level 5 = 5
a point representing DPT 201.105: EnableHCStage Z
EnableHCStage Z
no error = 0
ManufactID
Effective value of the presence status
boiler sequence switched off due to local summer/winter mode (mainly used for monitoring)
TP1
The Application Function controls the 'air temperature' of a room or zone (group of rooms or space) individually, thereby maximizing comfort and minimizing energy costs. The control loop often uses the outside temperature or a reference room temperature as a process variable.
Zone Heating Control
Shall specify the fading step size or to the code to stop the fading of the brightness
(SI) unit class for function points (FP) and datapoints.
Unit
At least one of the inputs Wind-/Rain-/Frost-Alarm is ‘in alarm’
unknown = 0
Room Relative Humidity Sensor
DPT 14.057: Value of power factor
Value Power Factor
Contract number of an installation, usually generated by Mac (edited by an installer).
contract number
off = 0
uncritical = 0
a point representing DPT 23.003: UpDown Action
UpDown Action
mode level
The value of the target point is sent as an update notification (triggered). The trigger is defined by the metadata source datapoint value.
is change of value of
Application functions that controls the quantity 'air pressure.'
Air Pressure Control
time period
is channel of
memory function value = 4
Behaviour_Bus_Power_Up_Down
a point representing DPT 254.600: Relative Control RGB
A unitary, factory-made enclosure with a fan and coil that recirculates air in a space and performs one or more of the functions of cleaning, heating, cooling, humidifying, dehumidifying, or ventilating the air. Unit heaters are examples of FCUs.
Fan Coil Unit
DetectedLoadType
one push button/binary input, MoveUp / StepUp message sent = 2
a point representing DPT 2.008: Direction 1 Control
Direction 1 Control
3.x
a point representing DPT 200.101: Binary Value Z
Binary Value Z
Cool stage B for cooling with two stages (A + B) = 4
is grouped by
electric potential
To define the existence of several function points as part of an application function. Application functions without any function points are possible but useless (a MaC may not prevent to remove them all).
has function point
not forced = 0
2,5 min = 14
Zigbee
autonomous = 0
Level 15 = 15
CountVal
An OP relationship to express the control/status relation, separated in KNX by using different function points (GAs) for each. A function point relates to another function point, with the specific meaning of FP x represents the status value of the (setpoint/comand value) of FP y.
is status of
Enclosure or chassis used to mount computer and networking gear. For example, a 19-inch rack is a standardized frame or enclosure for mounting multiple electronic equipment modules.
Rack
DPT 14.025: Value of electric flux density
Value Electric FluxDensity
The tag represents information for a logical point, a parameter point that changes an application behavior, mainly used at configuration. It SHALL not be used together with a setpoint value point (:sp) from point function class.
Parameter Point
a point representing DPT 9.004: Value Lux
Value Lux
New / Unlock (S-SFK) - Not Associated (G3-PLC) = 0
Keep Last State = 1
a point representing DPT 9.022: PowerDensity
PowerDensity
room temperature setpoint building protection
The visual effect of channel 5 is inactive = 0
DPT 14.020: Value of electric current density
Value Electric CurrentDensity
No WD
Represents an angle from 0 to 360 degrees.
Angle
no day = 0
This OP relationship allows to refine the applicative semantics of a datapoint, classified with a state type.
relates to state type
Application functions that controls the quantity 'air quality'.
Air Quality Control
Manua operation (overridden)
a point representing DPT 20.612: Converter Control
Converter Control
Current Colour RGBW
a point representing DPT 225.001: ScalingSpeed
ScalingSpeed
a point representing DPT 206.104: OccModeNext
OccModeNext
a point representing DPT 9.030: Concentration µg/m3
Concentration µg/m3
BuildingMode
DHWPushActive
A Cabinet is a physical enclosure for electrical or electronic equipment such as automatic switches, fuses, circuit breakers, control devices, timers and similar.
Disable = 0
Inverted = 1
Signaling for evacuation of occupants of a building in case of a danger.
Safety Lighting
colour transition xyY
a point representing DPT 20.102: HVACMode
HVACMode
ErrorClass_HVAC
AlarmClassType
Light Current Status
enable stage A = 1
Physical housing for electrical circuits, fuses, and breakers. A electric panel (also known as distribution board, panelboard, breaker panel, DB board or DB box) is a component of an electricity supply system that divides an electrical power feed into subsidiary circuits while providing a protective fuse or circuit breaker for each circuit in a common enclosure.
Electrical Panel
a point representing DPT 20.1002: RF ModeSelect
RF ModeSelect
is proxy for
a point representing DPT 20.112: MasterSlaveMode
MasterSlaveMode
Indicator for time related type of interests, more granular defined with a quantity kind
Temporal
Cool Stage A Actuator Overridden
A child OP relationship to a list that describes the generic locality characteristic where an observation or actuation is made. It is a generic “place of action”, when e.g., assigned to a room this means “the action happens in a place that is a room” but not in which room exactly, this is a room instance of an installation.
has locality
a point representing DPT 207.100: StatusBUC
StatusBUC
This OP defines what predefined application function can be preferably used with a collection of datapoints. The collection may be expressed with a common functionality or more detailed with a functional block or channel (subclasses of functionality).
is applicable functionality of
Colour Set RGBW
HumRelSetpDehumEff
Associated with electricity or with electrical force, power, or energy.
Electricity
Service mode
Info On Off Output 5
energy, 0,001 Wh = 0
at least one comfort push button is pressed = 1
Language as in DPT_Language-CodeAlpha2_ASCII (234.001) this is ISO 639-1 alpha-2
Producer = 1
An office is a space where an organization's employees perform administrative work in order to support and realize objects and goals of the organization. Preferably used with a Building or Room.
Office
Movement is locked, e.g. by DeviceLocked input
ActTargetPos
HeatingOnly = 2
VAV = 2
A window is an opening in a wall, door, roof, or vehicle that allows the exchange of light and may also allow the passage of sound and sometimes air.
Window
Application funtion weather station aggregates outside measurement points.
Weather Station
A door lock is a way to secure a door. A lock is a mechanical or electronic fastening device that is released by a physical object such as a key, keycard, fingerprint, RFID card, security token or coin.
Door Lock
Oil meter = 1
volume flow, 1000 ml/s = 78
limit range is related to abnormal condition
"Dew Point Temperature" is the temperature at which vapour in air reaches saturation.
Dew Point Temperature
Motor used with a pump to move fluid.
Pump
PL110
Info On Off Output 4
A network bridge is a computer networking device that creates a single, aggregate network from multiple communication networks or network segments (typically on OSI Layer 2). Bridging is distinct from routing. Routing allows multiple networks to communicate independently and yet remain separate, whereas bridging connects two separate networks as if they were a single network.
Network Bridge
Time delay = 5
Wind is the natural movement of air or other gases relative to a planet's surface. Winds are commonly classified by their spatial scale, their speed and direction, the forces that cause them, the regions in which they occur, and their effect.
Wind
This state type expresses that a value is changed relatively in a 'decreasing' manner, i.e. the value is lowered. This state type is the inverse of the 'Increasing' state type.
Decreasing
a point representing DPT 8.002: DeltaTimeMsec
DeltaTimeMsec
Actual Dimming Value Blue
Used to represents keywords, key phrases, or classification codes.
subject
DPT 14.060: Value of resistance
Value Resistance
OccMode
includes reserved bit(s)
The manufacturer of an application program or product (as a note, a device is part of a product).
manufacturer
priority level
NumberedSceneControl
a point representing DPT 21.106: StatusAHU
StatusAHU
mass flow, 1000 kg/h = 86
"Frequency" is the number of occurrences of a repeating event per unit time. The repetition of the events may be periodic (that is. the length of time between event repetitions is fixed) or aperiodic (i.e. the length of time between event repetitions varies). Therefore, we distinguish between periodic and aperiodic frequencies. In the SI system, periodic frequency is measured in hertz (Hz) or multiples of hertz, while aperiodic frequency is measured in becquerel (Bq). In spectroscopy, v is mostly used. Light passing through different media keeps its frequency, but not its wavelength or wavenumber.
Frequency
Colour Level Red
HVAC General FB's = 10
a point representing DPT 20.1001: AddInfoTypes
AddInfoTypes
Relative Set Value Control White
Movement Detector for Lighting
comfort prolongation User active = 1
PE2 in progress = 2
room temperature setpoint economy
electric flux density
This state type expresses that an alternative room temperature setpoint (internal to the room setpoint manager) is used for temperature control in a room.
Type of Temperature Setpoint Alternative
phase angle, degrees
Entertainment buildings or places host a form of activity that holds the attention and interest of an audience or gives pleasure and delight. Examples are cinemas, operas, theatres, museum etc. Preferably used with a Building.
Entertainment
HW fault = 4
Step Code Brightness
output state is not valid = 0
16-Bit Signed Value & 8-Bit Set
first character of RegionCode, ASCII-coded
asynchronous + BiBat Slave = 2
This state type expresses that mode 'Cooling' is chosen for the HVAC system. Usually, this mode is associated with default cooling functionality of the HVAC system. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Cooling
Started automatically = 1
invalid connection number (TSAP) = 16
Switch Request
a point representing DPT 206.100: HVACModeNext
HVACModeNext
Failure detected = 2
SSSB
Application function for 'blinds control'.
User Blinds Control
The visual effect of channel 23 is active = 1
Device Address
the usage forecast allow the resource manager to communicate planned usage of a storage for a certain period of time in the future
TempSetpShiftComf
Standby = 2
a point representing DPT 20.121: BackupMode
DPT 14.024: Value of electric flux
Value Electric Flux
a point representing DPT 20.003: OccMode
Colour Relative Control RGBW
includes digit
Shutter Stop Step
This state type expresses the state of no heavy rainfall. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of no heavy rainfall, no protection is required and this equipment might be used for shading purposes as intended. This state type is the inverse of the 'Rainfall State' state type.
No Rainfall
A specific Application Function that controls, for example, the speed of a pump.
Pump Control
CombinedStatus_RTC
This state type expresses the 'dehumidification' mode of the ventilation system. Usually, this is related to lowering the relative air humidity by removing moist air and replacing it with dry air.
Dehumidification Mode
a point representing DPT 203.102: Sun Intensity Z
Sun Intensity Z
mass, 1 kg = 27
a point representing DPT 13.013: ActiveEnergy kWh
Active Energy kWh
A Quality Kind with at least one measurable quantity property that addresses equipment, and the quantity property can be directly determined.
measures equipment quality kind
occupancy mode
a point representing DPT 207.102: ValueDemBoc
ValueDemBoc
An OP relationship to a list that describes the application areas in which a aspect (incl. subclasses) or a datapoint is used. An (parent) entity may inherit all trades from its underlying childs, this is domain/application specific.
operates for trade
a point representing DPT 13.014: ApparantEnergy kVAh
ApparantEnergy kVAh
A vane is a flat blade which pushes or is pushed by air (wind) or water, and forms part of a machine such as a fan, a windmill, or a ship's propeller. A vane position indicates or controls air flow direction
Vane
Liquid phase produced by the condensation of steam or other gas
Condensate
Cool Stage B Actuator Current Position
A programmable logic controller (PLC) or programmable controller is an industrial computer that has been ruggedized and adapted for the control of manufacturing processes, such as assembly lines, machines, robotic devices, or any activity that requires high reliability, ease of programming, and process fault diagnosis.
Programmable Controller
Start Partial Duration Test (PDT) = 3
Return Air Temperature Sensor
A Domestic Hot Water (DHW) system delivers hot water to fixtures used by people at the sink, shower, tub and any other appliance where water may contact humans. They typically work by delivering hot water through a centralized storage tank separate from water that may be used for steam or hydronic heating.
Domestic Hot Water
From MaC assigend individual address (IA).
Individual Address
This state type expresses that mode 'Off' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system being idle, i.e. neither heating nor cooling functionality being required. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Off
Smoke is a suspension of airborne particulates and gases emitted when a material undergoes combustion, together with the quantity of air that is entrained or otherwise mixed into the mass. It is commonly an unwanted by-product of fires.
Smoke
Status of comfort prolongation User
Level 9 = 9
FanStep
is equipment of
a point representing DPT 253.600: Relative Control xyY
Relative Control xyY
amplitude
clock with ext. sync signal = 1
Application Functions that controls the quantity 'water temperature'.
Water Temperature Control
Friday = 5
This state type expresses that a contact (e.g. a valve end position contact or a partition wall status, or window contact) is in closed state. This state type is the inverse of the 'opened' state type.
Closed State
HVAC Terminal Units = 13
UpDown = 2
DT in progress = 8
cEMI Transport Layer = 6
Requested power reduction
EnableTempRoomSetpAlt
a point representing DPT 20.1207: Peak Event
Peak Event
Cool Stage A Actuator Status
learn the scene corresponding to the field Scene Number = 1
Level 2 = 2
This state type expresses that an equipment, an alarm or a certain situation is inactive. An inactive equipment is not working, which means it cannot fulfill its intended functionality. An inactive alarm means that the alarm state was not triggered. Finally, an inactive situation means that a certain state has not been reached. The tag 'Inactive State' is often used for situations that feature an enumeration of possible states (e.g. operational states, control modes, HVAC modes, ...) to make a boolean statement about one of these states. The state type 'Inactive State' is the inverse of the 'Active State' state type.
Inactive State
a point representing DPT 12.101: LongTimePeriod Min
LongTimePeriod Min
Validity height pos.
energy, 100 Wh = 5
a point representing DPT 200.100: Heat/Cool Z
Heat/Cool Z
A specific Application Function category that controls a customized setting of different trades for an activity or situation. Scene controllers are intelligent pre-configured settings that orchestrate multiple devices and settings with a single touch of a button or a simple voice command. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Scene Control
Function Test Pending
at base condition = 2
Partial Duration Test Pending
ComfortProlongUser
EmergShutdown = 4
A Gateway is a network node (Device) that connects two networks with different transmission protocols and data formats typically between OSI Layers 4-5 (e.g. KNX and BACnet).
Network Gateway
y-coordinate of the colour information
To define the existence of KNX standardized functionality block, implemented in a channel. Since a FB is specified with a certain set of mandatory and optional datapoints a channel needs to define at least the mandatory datapoints.
comprises
CombinedStatus_RTSM
a point representing DPT 20.109: DamperMode
Time = UT+X = 0
A home cinema is a space in a building that is used to enjoy movies. Preferably used with an Room.
Home Cinema
time
flat that is set to true when the timer is currently running
A specific Application Function that represents a process to provide a supply media to the consumer according to energy demand keeping losses in distribution and generation to an absolute minimum. distrCtrl functions control usually energy flow via water or air in pipes or ducts from energy generation to energy consumer in rooms (emission control).
Distribution Control
2-byte float value
ActTargetPosCoolStageB
Time is a basic component of the measuring system used to sequence events, to compare the durations of events and the intervals between them, and to quantify the motions of objects.
Time
notice PE2 in progress = 2
1-byte
System & functions of common interest = 1
A leisure centre facility or building may include a swimming pool, large sports hall, squash courts, cafeteria, licensed bar, fitness suite, aerobics studios, outdoor grass and/or artificial pitches for football (soccer), hockey etc., a solarium, sauna and/or steam room. Preferably used with a Building.
Leisure
closed = 0
a point representing DPT 209.101: TempRoomDemAbs
TempRoomDemAbs
enable both stages = 3
DPT 14.032: Value of force
Value Force
A child OP relationship to a list allowing to describe a non-quantifiable/non-countable characteristic where an observation or actuation is made.
has state kind
Angular Velocity refers to how fast an object rotates or revolves relative to another point. It is defined as the change of angle per unit time and usually measured in Hertz (1/s).
Angular Velocity
a point representing DPT 218.002: Flow Rate in m3/h Z
FlowRate m3/h Z
Info On Off Output 2
Application Mode
a point representing DPT 7.013: Brightness
Brightness
A wall is a building element that physically separates two or more neighbouring locations (typically rooms).
Wall
process fault / controller fault = 2
a point representing DPT 250.600: Converter Info Fix
Converter Info Fix
is floor of
angle, degree
not valid = 1
Year
output state is On = 1
This state type expresses that the lowest level named 'Protection' is chosen for the HVAC mode. Usually, the 'Protection' level is associated with a focus on building and equipment protection (e.g. against frost damage). This level is used for rooms or buildings, which will not be used for a longer time, such as holidays. Additionally, the 'Protection' level is chosen for a room if windows in this room are opened. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Protection
Stairs are a structure designed to bridge a large vertical distance between lower and higher levels by dividing it into smaller vertical distances.
Staircase
KNX SN
Hour of day, Minutes and Seconds field not valid = 1
SceneNumber
power range the device will operate for the given time period
ActTargetPosHeatStageB
a point representing DPT 20.106: HVACEmergMode
HVACEmergMode
This state type expresses that an equipment, such as a luminaire, is switched off. This state type is the inverse of the 'On State' state type.
Off State
a point representing DPT 13.1201: Delta Volume Cubic Metre
Delta Volume Cubic Metre
AlarmText_Sup
Video data and camera management function.
a point representing DPT 2.007: Step Control
Step Control
The value of the point is NOT A COMPLETE value but needs to be added to another value to be usable, such as the current comfort temperature setpoint + 2 degree celsius. As the examples explain, there is no distingtion if it needs to be added to itself or another value.
Relative Value
This state type expresses that an equipment has a movement direction that can be interpreted as 'downwards'. Usually, this is associated with equipments that can be moved by a drive along a vertical axis, such as blinds or slats.
Downwards Movement
4-byte unsigned value
positions
surface tension
An identifier to specify the (numerical) hardware version of a device.
hardware
Consumer = 0
a point representing DPT 8.006: DeltaTimeMin
DeltaTimeMin
gas = 2
Input Source
An apartment (American English), or flat (British English, Indian English, South African English), is a self-contained housing unit (a type of residential real estate) that occupies part of a building, generally on a single story. Preferably used with a Building.
Apartment
DPT 14.076: Value of volume
Value Volume
Comfort = 1
a point representing DPT 2.005: Alarm Control
Alarm Control
a point representing DPT 20.002: BuildingMode
A tumble dryer, also known as clothes dryer or simply dryer, is a powered household appliance (EN50523) that is used to remove moisture from a load of clothing, bedding and other textiles, usually shortly after they are washed in a washing machine.
Tumble Dryer
building protection setpoint = 2
DPT 14.064: Value of sound intensity
Value Sound Intensity
3-byte colour RGB
Normal (no fault) = 0
Laundry refers to the washing of clothing and other textiles, and, more broadly, their drying and ironing as well. Preferably used with an Room.
Laundry Room
ErrorClass_System
The tag category contains individuals that describe the location related oriented context for a measurement/adustment of an equipment or an observation/actuation of a phenomenon. It expresses a relation to a space (as a place of action or where an equipment is installed.
Locality
Date that the resource became or will become available.
Date Available
Mask Bit Info On Off Output 9
no alarm = 0
The visual effect of channel 13 is active = 1
The visual effect of channel 3 is inactive = 0
density
Ice = 11
Switch On Off White
A specific Application Function category for overall management functions of a plant or a part of a plant. For example, a Scheduler automatically schedules the systems, such as heating, ventilation, and lighting, to coordinate with facility usage. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Plant Management Control
duration that gives the seconds that this limit range stays valid
An OP relationship to a list that describes the runtime interworking operation type of the value of a point. Examples are absolute values, values representing an offset or realtive values.
has point operation
Bluetooth
volume flow, 1000 l/min = 71
a point representing DPT 9.020: Value Volt
Value Volt
Battery Fully Charged
The transfer of energy to a space or to the air by the existence of a temperature gradient between the source and the space or air. This process may take different forms, e.g. conduction, convection or radiation.
Heating
a point representing DPT 20.1206: Peak Event Notice
Peak Event Notice
timestamp when last transition was executed
DPT 14.034: Value of angular frequency (pulsatance)
Value Angular Frequency
Level 7 = 7
A stand-alone house (also called a single-detached dwelling, detached residence or detached house) is a free-standing residential building. Preferably used with a Building or Site/Space.
Familiy House
last actual value = 0
Test = 7
unreliable synchronisation source (mains, local quartz) = 0
a point representing DPT 2.009: Direction 2 Control
Direction 2 Control
a point representing DPT 27.001: CombinedInfoOnOff
CombinedInfoOnOff
A generic referencing mechanism between one or more points that reflects a specific view of the installation.
Aspect
DPT 14.039: Value of length
Value Length
Instruction to force the state machine switching from one operation mode to another or just set a new new value of the operation mode factor
This field shall indicate whether the colour infor-mation in the fields x-axis and y-axis is valid or not.
Shift load priority = 1
ActTargetPosCoolStageA
Relative air quality value
Very cloudy = 6
Cool Stage B Actuator Target Position
true = actuator setvalue is locally overridden, e.g. via a local user interface
Convertor error
Units for HCA = 110
a point representing DPT 2.011: State Control
State Control
Cool Stage B Actuator Fault
UserChangeOverMode
activated without security = 1
This state type expresses that the green part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.
Chromaticity Green
This state type expresses that the alarm status of a datapoint is not yet acknowledged by an operator. No assumption about the validity of the datapoint’s value can be made.
Operational State Alarm Pending
Activation state of channel 15
Actual Dimming Value White
Cool
valid = 0
A setpoint is classified as an indirect adjustment, such as Point representing the desired or target value for a process value of a system.
Setpoint value
TempRoomSetpCoolEff
temperature sensor input = 4
volume, 0,001 l = 16
stress
Enclosure used to move people between floors. An elevator or lift is a cable-assisted, hydraulic cylinder-assisted, or roller-track assisted machine that vertically transports people or freight between floors, levels, or decks of a building, vessel, or other structure.
Elevator
The tag category contains individuals that describe the role of a Point in the control loop of an application function.
Point Function
No Year
a point representing DPT 20.014: Beaufort Wind Force Scale
Beaufort Wind Force Scale
gentle brezze = 3
Cool Stage B Actuator Overridden
compressibility
corresponding Datapoint Main value is corrupted due to failure
A device used to operate functions and equipment in a room by pushing. Examples are push buttons used to switch light, indicate presence and similar use cases.
Button
Group Address Table is not sorted = 15
DPT 14.005: Value of an amplitude
Value Amplitude
energy, 0,1 GJ = 136
A building is a structure with a roof and walls standing more or less permanently in one place, such as a house or factory.
Building
volume flow, 10 l/min = 69
DPT 14.037: Value of heat quantity
Value Heat Quantity
A specific Application Function that controls energy production. The Application Function represents a process of generating energy to the consumer according to energy demand keeping losses in distribution and generation to an absolute minimum.
Generation Control
Decrease = 0
trailing edge (resistive - or capacitive load) = 2
WithoutAcknowledge = 1
energy, 10000 kJ = 15
Converter Status
The visual effect of channel 6 is inactive = 0
open on PLC or Euridis command = 4
ApplicationArea
two push buttons/binary inputs mode = 4
true = actuator is locked, e.g., via input LockDevice.
This state type expresses that mode 'Free Cool' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system performing a cooling task by using cold ambient air instead of an energy-intensive chiller unit. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Free Cool
a point representing DPT 9.021: Value Curr
Value Curr
ligth, quantity of
a point representing DPT 1.009: Open Close
Open Close
A strong OP relationship to express a relation to building contained in a site.
has building
This state type relates to the secondary stage of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages Secondary
EmergFire = 5
The lower boundary of the range with 68 % certainty the power value is in it
7.x
DPT 14.065: Value of speed
Value Speed
Heats a space using exposed pipes or coils. Radiators are heat exchangers used to transfer thermal energy from one medium to another for the purpose of cooling and heating. The majority of radiators are constructed to function in cars, buildings, and electronics.
Radiator
ActuatorStatus
timer declarations defining ID and duration
status
identifier of the timer, has to start with 1
Security = 30
A room segment is an indoor space that represents a subdivision of a room, it can be further subdivided into locations of type room segment.
Room Segment
Raumteil
room temperature setpoint shift comfort (delta value)
Points with other operation types rather than a datapoint. It asynchronously pushes event data to consumers (see thing description).
Eventpoint
a point representing DPT 201.107: Building Mode Z
Building Mode Z
a point representing DPT 8.012: Length m
Length m
Level 1 = 1
Signed value with classification and validity
Absolute Set Value Control White
DPT 14.079: Value of work
Value Work
Underload
TempRoomSetpCoolEffNext
a point representing DPT 20.1202: Gas Measurement Condition
Gas Measurement Condition
at measurement condition = 3
a point representing DPT 16.001: String 8859 1
String 8859 1
Night = 1
A Point representing history/ trend data with a log of timestamp/value pairs. Only this tag value is allowed to be used together with other tags from this category, such as to define a Datapoint expressing a history log of process values.
mass, 10000 kg = 31
A hospital is a health care institution providing patient treatment with specialized health science and auxiliary healthcare staff and medical equipment. Preferably used with a Building.
Hospital
calibration pending, waiting on trigger = 4
Cool Stage A Actuator Fault
controls stage 2 for two stage burner
A specific Application Function that controls, for example, the speed of a fan.
Fan Control
a point representing DPT 20.1203: Breaker Status
Breaker Status
entrance access
A section of ductwork that refers to those parts of distribution systems in buildings that are ducts, mostly for transporting air.
Duct Section
Copyright 2023, KNX Association, Brussels-Diegem, Belgium. Permission is hereby granted, free of charge, to any person obtaining a copy of this software and associated documentation files (the “Software”), to deal in the Software without restriction, including without limitation the rights to use, copy, modify, merge, publish, distribute, sublicense, and/or sell copies of the Software, and to permit persons to whom the Software is furnished to do so, subject to the following conditions: The above copyright notice and this permission notice shall be included in all copies or substantial portions of the Software. THE SOFTWARE IS PROVIDED “AS IS”, WITHOUT WARRANTY OF ANY KIND, EXPRESS OR IMPLIED, INCLUDING BUT NOT LIMITED TO THE WARRANTIES OF MERCHANTABILITY, FITNESS FOR A PARTICULAR PURPOSE AND NONINFRINGEMENT. IN NO EVENT SHALL THE AUTHORS OR COPYRIGHT HOLDERS BE LIABLE FOR ANY CLAIM, DAMAGES OR OTHER LIABILITY, WHETHER IN AN ACTION OF CONTRACT, TORT OR OTHERWISE, ARISING FROM, OUT OF OR IN CONNECTION WITH THE SOFTWARE OR THE USE OR OTHER DEALINGS IN THE SOFTWARE.
Represents the combined KNX Information Model with its individual (core/knx/location/tag) models. The Core model represents the commonly known IoT and building control domain concepts of an installation. The KNX model represents the KNX System part of an installation. The Location model represents the spatial location structure of an installation. The Tag model represents a set of entities, each with a standardized semantical meaning that is independent from any actual installation. The date of the last update of the model - usually regarding the dictionary content - is shown in the DCTERMS property dcterms:available. See also the corresponding version identifier at class core:Thing.
The terms of service can be found under https://www.knx.org/knx-en/privacy. The applied license agreement is a MIT License from https://opensource.org/licenses/MIT.
KNX Information Ontology
a point representing DPT 2.001: Switch Control
Switch Control
a point representing DPT 29.011: ApparantEnergy V64
ApparantEnergy V64
magnetic flux density
a point representing DPT 207.104: ActPosDemAbs
ActPosDemAbs
To define a relation to a point from an aspect. Aspects without any points is possible.
groups
alarm position is DOWN = 2
Activation state of channel 10
Request Converter PDT Info = 6
Request Converter Info = 7
To define a general relation between different concepts. With the child properties a relation with a specific semantic meaning can be expressed (such as between locations, datapoints or function points). Due to the usage from several concepts the domain and range is not specified for this OP.
is referenced by
Locked Position
FanActive
a point representing DPT 235.001: Tariff ActiveEnergy
Tariff ActiveEnergy
AQRoom
DHW temperature setpoint for LegioProtect operating mode
temperature, common
Undervoltage
energy, 10000 Wh = 7
LTRD
An Application Function for a generic switching of an equipment, such as an actuator terminal or similar.
Status A
Alternating current electricity
Electricity, AC
Relative Set Value Control Red
LED, trailing = 8
Level 4 = 4
Application function for generic 'switch control'.
Switching
Version identifier that has generated an installation, usually generated by a Mac.
DPT 14.041: Value of luminance
Value Luminance
a point representing DPT 20.607: DimmPBModel
DimmPBModel
Aquifer thermal energy storage (ATES) is the storage and recovery of thermal energy in the subsurface. ATES is applied to provide heating and cooling to buildings. Storage and recovery of thermal energy is achieved by extraction and injection of groundwater from aquifers using groundwater wells.
ATES
TimeStamp_Sup
Data Link Layer Raw Frames = 2
StatusStartOptim
actuator fault = 3
Info On Off Output 3
Duration Test Pending
Colour Set RGB
energy, 1 MWh = 129
power, 100 W = 45
Gateway
ActTargetFanSpeedEff
A point representing an enabling/disabeling of a (sub) functionality.
Activation
TempReturnLimit
The power forecast of a power sequence slot
Activation state of channel 9
1,25 min = 11
Light Dimming Actuator Basic
Current lighting level in %. In case of a switching actuator LSAB the range is limited to the discrete values 0 % and 100 %.
A parent data property, used to express any kind of generic data that relates to a product.
product data
TempRoomSetpSetHeatEff
Info On Off
DPT 14.031: Value of energy
Value Energy
no comfort push button is pressed = 0
humidification = 1
a point representing DPT 16.000: String ASCII
String ASCII
A bathroom or washroom is a room, typically in a home or other residential building, that contains either a bathtub or a shower (or both). Preferably used with an Room.
Bathroom
15 min = 17
normal = 0
heating = 1
a point representing DPT 2.002: Bool Control
Bool Control
This DPA changes the activation state of the comfort prolongation. Thus, it defines the two states tag:active and tag:inactive, which relate to the comfort level (represented as the state type tag:hvacModeComfort).
Level 14 = 14
a point representing DPT 1.007: Step
The hot water distribution Application Function connects and coordinates water and energy flow between energy generation/production (heating) and energy consumer (emission control).
Hot Water Distribution
a point representing DPT 1.022: Scene AB
has datapoint
Break = 0
The Application Function controls the air temperature of an single room, thereby maximizing comfort and minimizing energy costs.
Individual Room Control
is location usage of
Breaker/Valve is closed = 0
CFL, leading = 5
software fault = 5
Brightness of the colour
a point representing DPT 9.002: Value Temp D
Value Temp D
resistivity
simple alarm = 1
Restriction of slats height pos., pos. can not be reached
A balcony (from Italian: balcone, 'scaffold') is a platform projecting from the wall of a building, supported by columns or console brackets, and enclosed with a balustrade, usually above the ground floor. Preferably used with an Space.
Balcony
An electrical installation is a group of items of electrical equipment that are permanently electrically connected together and can be supplied with electricity from the works of an electricity entity or from a generating source. An electrical installation contains the electrical wiring of buildings, transmission lines, stationary machines, fuses, and related equipment.
Electrical
A strong OP relationship to express a relation to a floor contained in a location.
has floor
Comfort/Economy = 0
Default values, used to fill KNX data fields with proper content in case no related data are provided from an external entity such as an API. The type of “fieldDefault” depends on the type of the field it is associated to. It is ... for (field type): 0 or 1 (B), xsd:positiveInteger (U), xsd:integer (V), xsd:float (F), xsd:integer (N, as it contains the KIM-value part of a key-value-pair), xsd:string (A and A[n]). Field types D<n> and Z8 will not contain a fieldDefault value.
field default
conductance
a point representing DPT 8.003: DeltaTime10MSec
DeltaTime10MSec
DefectiveLoad
a point representing DPT 9.010: Value Time 1
Value Time 1
A human friendly title (short text), used to define user specific data for an individual. Edited in a MaC or from predefined product data or dictionary content. No limitation of the actual amaount, external entites may add additional language depended text. The 'Range' is not limited to a string, allowing to express also text in several languages (note W3C does not define a range).
title (name)
In thermodynamics, enthalpy is the sum of the internal energy and the product of pressure and volume of a system.
Enthalpy
Other device type = 0
Building in use = 0
HumRelSetpUserEff
ActiveElectricalEnergy
Error Class
no occupancy from presence detectors = 0
a point representing DPT 20.604: LightControlMode
Used with any location type.
Other
a point representing DPT 1.016: Ack
open on overvoltage = 2
Represents a person in the contect of the building domain. Hence this there is no need to distinguish on the level of living entities.
Person
Read = 1
The tag represents information for a physical point, a hardwired (physical) analogue or digital input point, from the perspective of the application program.
Physical Sensor Point
A specific Application Function that controls the electical power network (e.g. fuses, circuit breakers etc.) from distribution transformer to consumers. The voltage level of a low-voltage distribution system is typically equal to the mains voltage of electrical appliances.
Low-voltage Power Distribution
Room or space used for electrical equipment such as switch cabinets, a fuese box etc. Preferably used with an Space.
Cabinet
value before locking = 6
Validity of field ActualValue
Time synchronization coordinates independent clocks on different devices.
Time Synchronization
DPT 14.014: Value of compressibility
Value Compressibility
a point representing DPT 20.004: Priority
Priority
validity of the absolute brightness
To define the existence of an application program as part of a device, except it is a pure HW, such as a power supply or similar. Devices may support more than one application program, at runtime in an installation usually one.
hosts
Registered (S-FSK) - reserved (G3-PLC) = 2
modulating = 3
Shall specify whether the colour shall be increased or decreased.
a point representing DPT 20.108: ValveMode
ValveMode
occupied = 1
is composed by input
A generic comment, used from several concepts to express the content edited by a MaC (such as an installation comment).
comment
ActualDimmingValue
A heat pump is a device that can heat a building (or part of a building) by transferring thermal energy from the outside using the refrigeration cycle. Many heat pumps can also operate in the opposite direction, cooling the building by removing heat from the enclosed space and ejecting it outside. Units that only provide cooling are called air conditioners.
Heat Pump
To define the type (DPT) of a function point or datapoint. A function point represents runtime data, therefore the cardinality is of max 1 DPT. A datapoint represents config data, therefore the cardinality is of min 0 DPT (but it should be at least one).
has datapoint type
Thread
running in intervals = 2
volume flow, 0,1 l/min = 67
OtherEnergySourceActive
PE1 in progress = 1
Cloudless = 0
Economy/Nothing = 2
Temperature is a physical property of matter that quantitatively expresses the common notions of hot and cold.
Temperature
Effective value of the window status
volume flow, 0,01 l/h = 57
DPT 14.029: Value of electromagnetic moment
Value ElectromagneticMoment
OverloadDetection
POP3
HVACModeUser
3x 2-byte float value
disable = 1
BacNet
Unsigned time-value for calculating fading time.
Light Switching Sensor Basic
Points with other operation types rather than a datapoint. It allows to invoke a function to manipulate states (see thing description).
Actionpoint
Cool Stage A Actuator Valve Kick
An identifier to specify the (string based) media where this product can be used. Usually, IP, RF, TP.
Media Type
duration in which fill level will reach a value in FLR
DPT 14.021: Value of electric dipole moment
Value Electric DipoleMoment
SatusECO
angular momentum
a point representing DPT 13.010: ActiveEnergy
Active Energy
defines wich timers will start when executing this transition . each of the 16 timers could be referenced by setting the bits 0-15 to 0 (not starting) or 1 (starting)
includes key value pair
Heat stage A for normal heating = 1
Sensor is a Peripheral that measures physical input from its environment and converts it into data that can be interpreted by either a human or a machine.
Sensor
a point representing DPT 21.1000: RF ModeInfo
RF ModeInfo
a point representing DPT 13.011: ApparantEnergy
ApparantEnergy
is phenomenon type of
Locked
Last modified time stamp, usually generated by Mac. May be used from other concepts, therefore no domain is defined.
last modified
The tag category contains individuals allowing to describe the specific application area/ operational domain in which a Point, Application Function or Function point is used. Trade is a subdivision of knowledge by technical field or electrical and mechanical installations.
Trade
breaker (electricity) = 32
length
Cooling Mode Enabled
SwitchOff message sent = 1
a point representing DPT 12.102: LongTimePeriod Hrs
LongTimePeriod Hrs
This DPA switches the comfort level to Comfort. Thus it is represented as a trigger point, that relates to the Comfort level (represented by the state type tag:hvacModeComfort)
brightness colour temperature transition
no notice in progress = 0
power factor
A functionality represents a concrete piece of software and a set of any type of interfaces (mainly Points) that is needed to accomplish a task for which a Device is designed for.
Functionality
trailing edge (capacitive load) = 2
A nursery is usually, in American connotations, a bedroom within a house or other dwelling set aside for an infant or toddler. Preferably used with an Room.
Nursery
This state type expresses that an equipment or a functionality is disabled. A disabled equipment is inactive, cannot be activated and thus is not able to fulfill its intended functionality. Similarly, a disabled functionality is not available in the system. Usually, the equipment or functionality is disabled by management functionality, such as a building management system. This state type is the inverse of the 'Enabled State' state type.
Disabled State
Relating to energy from the sun.
Sun
mass, 100 kg = 29
ValveKick
Scene number
Info On Off Output 12
Absolute Set Value Control Blue
RF Control Octet and Serial Number or DoA = 2
Verify Mode is on
DPT 14.010: Value of an area
Value Area
A basement or cellar is one or more floors of a building that are completely or partly below the ground floor.
Basement
This state type expresses that mode 'Night Purge' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system exchanging the used air in the building during the night. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Night Purge
DPT 14.049: Value of magnetization
Value Magnetization
Field index, used to identify the correct position of a KNX data field as part of an entire datapoint type.
field index
At least one DPT field must be present for a datapoint type (DPT).
is assembled with
room temperature setpoint shift building protection (delta value)
work
Illuminance is the total luminous flux incident on a surface, per unit area. It is a measure of the intensity of the incident light. As a note, focus is the light source, which is mostly the interest in the building control domain.
Illuminance
validity of PrelBurnerField
a point representing DPT 201.104: HVAC Contr Mode Z
HVAC Contr Mode Z
A software represents a collection of data or instructions that are installed (hosted) on a Device or Computer and tell it how to work. Software is a generic term used to refer to applications, scripts and programs that run on a Device.
Software
logical function OR = 0
An installation consists of equipment that is assigned to a location. It is a deployed system (e.g. HVAC system or fire protection system) and consists of equipment (such as cabinets) and (application) functions that are used for a particular purpose. The (application) functions are hosted in this case at a location.
Installation
Represents a (numerical, countable) position, such as %.
Position Vector
This state type expresses that the white part of RGBW light color is referred to. It is mostly used in lighting applications that use the RGBW color model.
Chromaticity White
Blinds Slat Position Degrees
limit range defining upper and lower power values
The abstract notion of angle. Narrow concepts include plane angle and solid angle. While both plane angle and solid angle are dimensionless, they are actually length/length and area/area respectively.
validity of the fields CW and Step Code Colour White.
dehumidification = 2
Mask Bit Info On Off Output 4
actuator has a failure
DPT 14.000: Value of acceleration
Value Acceleration
mass flow, 0,001 kg/h = 80
This state type expresses that mode 'Auto' is chosen for the HVAC system. Usually, this mode is associated with a local controller selecting the appropriate mode for the HVAC system (e.g. based on sensor data). In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Auto
Info OnOff
A desktop, laptop, PDA or other type of computer that can be moved from one place to another and connected to an electrical supply via a plugged outlet.
Computer
a point representing DPT 1.006: Binary Value
Binary Value
a point representing DPT 4.002: Char 8859-1
Char 8859-1
An OP relationship to a list that describes the runtime interworking source of a point or function point. Examples are default, user or managment.
has origin
HVAC Hot Water Heating = 11
Discharge air, e.g. for VAV = 3
A specific Application Function category that controls the solar irradiance by means of motorized sun protection. Very often there are protection functions that interfere with the sun protection. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Shading Control
power return mode
DPT 14.013: Value of volume charge density
Value Charge DensityVolume
power, 0,1 kJ/h = 50
a point representing DPT 4.001: Char ASCII
Char ASCII
a point representing DPT 20.601: Behaviour Bus Power Up Down
Behaviour Bus Power Up Down
Read or Response
CommMode
Luminous Flux or Luminous Power is the measure of the perceived power of light. It differs from radiant flux, the measure of the total power of light emitted, in that luminous flux is adjusted to reflect the varying sensitivity of the human eye to different wavelengths of light.
Luminous Flux
A store room is a room within a house where equipment not used in day-to-day activities is kept.
Store Room
V32Z8
DPT 14.003: Value of activity (radioactivity)
Value Activity
is site segment of
a point representing DPT 18.001: SceneControl
SceneControl
is eventpoint of
Used to represents an URN.
identifier
forced = 1
By a MaC (ETS) allowed location usages for a floor.
MaC floor
energy, 1000 Wh = 6
Overheat
HVAC operating mode
DHW temperature setpoint for Reduced operating mode
SW fault = 5
Time = UT+X+1 = 1
ActCurrFanSpeed
a point representing DPT 234.002: RegionCodeAlpha2 ASCII
RegionCodeAlpha2 ASCII
validity of the fields CR and Step Code Colour Red.
From MaC assigend installation hints as part of the project.
Installation Hints
on/off = 3
5 min = 16
Response or spontaneous sending = 0
Off = 0
volume, 10 l = 20
TempRoomSetpHeatEffNext
To express an “impact to cause” relation between different datapoints. Datapoints may affect other datapoint values, including manipulating their actual value at runtime.
influences
Refers to a trade that is concerned with windows and doors and their positions / openings.
Window/ Door Opening
a point representing DPT 21.1001: RF FilterInfo
RF FilterInfo
volume, 10000 l = 23
Shutters & Blinds = 50
yes = 1
validity of the ActiveElectricalEnergy data
InfoOnOff
SwitchCool
DPT 14.018: Value of electric charge
Value Electric Charge
StatusRoomSetup
a point representing DPT 20.105: HVACContrMode
HVACContrMode
Shall specify the fading step size or to the code to stop the fading of the saturation
LTRF
is building of
1 stage = 1
at least one window opened = 1
A dishwasher is a home appliance machine (EN 50523) that is used to clean dishware, cookware, and cutlery automatically.
Dishwasher
power, 0,001 W = 40
a point representing DPT 249.600: Converter Test Info
Converter Test Info
not valid = 0
Used to indicate that a KNX concept implements the KNX communication mode (S-Mode, LTE-Mode). Most likely, this can be assigned to KNX Datapoint Types and to KNX DPAs (i.e. those which are not present in S-Mode implementations of FBs)
has communication mode
a point representing DPT 20.006: ApplicationArea
The air supply control Application Function connects and coordinates air and energy flow between air treatment (e.g. air handling unit) and energy consumer (emission control).
Air Supply Control
This state type expresses that a value is changed relatively in an 'increasing' manner, i.e. the value is raised. This state type is the inverse of the 'Decreasing' state type.
Increasing
Relative Set Value Control Blue
one PB/binary input, On / DimUp message sent = 2
thermal capacity
Cool Mode = 0
16-Bit Unsigned Value with Status/Command
LPDTR
2-byte unsigned value
volume flow, 100 l/h = 61
Activation state of channel 22
Restore Factory Default Settings = 0
SwitchOn message sent = 2
Shall specify the fading step size or to the code to stop the fading of the colour white
This state type relates to the primary stage of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.
Heating-Cooling Stages Primary
Down = 1
self inductance
a point representing DPT 9.009: Value AirFlow
Value AirFlow
By a MaC (ETS) allowed location usages for a room.
MaC room
Electrical circuits for alternative currents. This is a specialization of the tag "Circuit".
Circuit, AC
The coold water distribution Application Function connects and coordinates water and energy flow between production of chilled water (cooling) and consumer (emission control).
Cold Water Distribution
A container for objects in an installation which have a sort of economic value and is owned and managed by an entity, e.g. a service organization.
Asset
A specific Application Function category that controls a quantity (e.g., temperature, pressure) of the phenomenon air. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Air Control
room temperature setpoint shift economy (delta value)
Group Object Type exceeds (PID_MAX_APDU_LENGTH - 2) = 18
no = 0
is application program of
DHWNorm
a point representing DPT 20.017: SensorSelect
acceleration, angular
SwitchHeat
volume flow, 0,0001 l/min = 64
defines whether this is an abnormal condition or not
DPT 14.002: Value of activation energy
Value Activation Energy
The visual effect of channel 7 is inactive = 0
Parking is the act of stopping and disengaging a vehicle and leaving it unoccupied. Preferably used with an Space.
Parking
DPT 14.073: Value of thermoelectric power
Value ThermoelectricPower
a point representing DPT 13.002: FlowRate m3/h
FlowRate m3/h
Heating / Cooling
Busy
The tag category contains individuals allowing to express that a point value originates from another system with a specific/underlying communication protocol.
Protocol
An identifier to specify the (numerical) firmware version of a device.
firmware
filtering by KNX Serial Number table = 2
'Electric Current' is the flow (movement) of electric charge. This QUDT-based tag is equal to the Haystack tag https://project-haystack.org/doc/lib-phScience/elec-current
Electric Current
on = 1
has location usage
HVAC general FBs = 10
no peak event = 0
a point representing DPT 6.010: Value 1 Count
Value 1 Count
Tank used to store a substance for temporary holding. For example, a fuel tank (also called a petrol tank or gas tank) is a safe container for flammable fluids.
Storage Tank
Ventilation is the intentional introduction of outdoor air into a space. Ventilation is a mechanical system in a building that brings in fresh outdoor air and removes the contaminated indoor air.
Ventilation
Mask Bit Info On Off Output 15
1,5 min = 12
a point representing DPT 6.020: Status Mode 3
Status Mode 3
StatusTempRoomSetpEff
Colour RGBW
thermoelectric power
Emergency mode active = 5
BiBat information = 7
a point representing DPT 21.104: FuelTypeSet
FuelTypeSet
HVAC User Mode not active = 0
notice PE1 in progress = 1
An oven is a tool which is used to expose materials to a hot environment. Ovens contain a hollow chamber and provide a means of heating the chamber in a controlled way. Ovens are often used for cooking (home appliances EN 50523: gas oven or electical oven), where they can be used to heat food to a desired temperature.
Oven
second character of LanguageCode, ASCII-coded
OverheatAlarm
Level 3 = 3
Year field valid = 0
a point representing DPT 8.001: Value 2 Count
Value 2 Count
Seconds
Locale information
volume flow, 1 l/min = 68
a point representing DPT 236.001: Prioritised Mode Control
Switch On Off
room temperature setpoint shift comfort
output state is Off = 0
DPT 14.038: Value of impedance
Value Impedance
is operation kind of
Electrical circuits for direct currents. This is a specialization of the tag "Circuit".
Circuit, DC
open on overload = 1
The visual effect of channel 18 is inactive = 0
Emergency Steam Mode = 17
Validity Height Position
a point representing DPT 246.600: Battery Info
Battery Info
Alarm Priority
other fault = 4
SolarEnergySupport
SolarLoadSufficient
Extended emergency mode active = 6
A Point provides the current (measured) value of a quantity kind or the current (status) value of a state kind.
Process Variable
1-bit
energy, 1 GJ = 137
Shutter Position Percentage
DoA and KNX SN
a point representing DPT 7.012: UElCurrentmA
UElCurrentmA
The visual effect of channel 23 is inactive = 0
Actual Dimming Value Green
Gas device = 3
Fan only = 9
Inactive = 0
This state type expresses that a datapoint is accessible but out of service, i.e., the main value is void and may contain any value. The device itself is operational. Typical usages are an optional sensor is not connected (out of service, sensor data is invalid) or a configuration parameter is void (function disabled).
Operational State Out Of Service
angular velocity
Extract air, e.g. for VAV = 4
Represents a percentage value between 0 and 100%.
Scaling
2-nibble set
This state type expresses the state of heavy rainfall. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case of heavy rainfall, this equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Rainfall' state type.
Rainfall State
Absolute Set Value Control Red
This shall be the number of the scene for which the DPT-value contains the configuration information.
acknowledge command (trigger), e.g. for alarming = 1
Refers to information that originates in a management system, e.g. a central building management system.
Management
a point representing DPT 20.022: PowerReturnMode
PowerReturnMode
a point representing DPT 12.100: LongTimePeriod Sec
LongTimePeriod Sec
Preferably used with an Space.
Conduits
Indicated whether the target position is reached of the drive is moving
is protocol operated by
digit 6 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
power, 0,01 W = 41
active = 0
TempSetpShiftEco
a point representing DPT 212.101: TempRoomSetpSet[3]
TempRoomSetpSet[3]
a point representing DPT 20.107: ChangeoverMode
a point representing DPT 20.1205: PLC Status
PLC Status
angle, radiant
a point representing DPT 13.100: LongDeltaTimeSec
LongDeltaTimeSec
Refers to the concentration of volatile organic compounds (TVOC) in the air, measured in ppm. This is a specialization of quantitykind:Concentration.
Numbered Scene Control
Off/FrostProtect = 4
a point representing DPT 28.001: UTF-8
UTF-8
magnetic polarization
This state type expresses that an equipment is controlled manually, rather than being controlled automatically. The equipment's value / position is the result of an input command with high priority, such as a manual control command. Other input commands of normal priority (e.g. automatic commands from a controller) are ignored, i.e. they were overridden by the high-priority command. This state type is the inverse of the 'Override Mode Automatic' state type.
Override Mode Manual
The tag represents information for a physical point, a hardwired (physical) analogue or digital output point, from the perspective of the application program
Physical Actuator Point
3 min = 15
Blinds Slat Position Percentage
open on overheat with a current value over the maximum switching current value = 5
Hardwired switch is off = 1
The target value represents a status of a corresponding source datapoint.
has status
Logical Function
a point representing DPT 8.007: DeltaTimeHrs
DeltaTimeHrs
deactivated = 0
a point representing DPT 245.600: Converter Test Result
Converter Test Result
CombinedStatus_HVA_CoolB
In KNX used (numerical) identifier to address a specific property as part of an interface object. The range xsd:unsignedByte supports exactly the KNX value range from 0 to 255.
property identifier
Cool Stage B Actuator Valve Kick
Reset Function Test Done Flag = 5
execution time when the sequence will start or was started
a point representing DPT 9.005: Value Wsp
Value Wsp
This state type expresses that an equipment, an alarm or a certain situation is active. An active equipment is fulfilling its intended functionality, whereas an active alarm means that the alarm state was triggered. An active situation means that a certain state has been reached. The tag 'Active State' is often used for situations that feature an enumeration of possible states (e.g. operational states, control modes, HVAC modes, ...) to make a boolean statement about one of these states. The state type 'Active State' is the inverse of the 'Inactive State' state type.
Active State
4-byte float value
Fan Speed Current
DPT 14.048: Value of magnetic polarization
Value Magnetic Polarization
A point representing a current state.
Situation
a point representing DPT 22.103: Combined Status RTC
Combined Status RTC
KNX
A strong OP relationship to express a relation to a space contained in a location.
has space
Single open = 2
FT in progress = 7
a point representing DPT 5.003: Angle
Equipment that converts electrical energy into mechanical energy.
Motor
DPT 14.019: Value of electric current
Value Electric Current
Increase = 1
mass, 0,01 kg = 25
Activation state of channel 1
EnableHeatEff
Restriction of target height pos., pos. can not be reached
Heat = 1
A door is a hinged or otherwise movable barrier that allows ingress (entry) into and egress (exit) from an enclosure.
Door
LDSBMode
Valve kick
A specific Application Function category that provides illumination and controls luminaries. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Lighting Control
Step Code Colour Temperature
An Air Handling Unit (AHU) is an Application Function that controls equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system. An AHU Application Function has usually subfunctions such as fanCtrl, pumpCtrl etc.
AHU Control
Dehumidification = 14
oBIX
A bedroom or bedchamber is a room situated within a residential or accommodation unit characterised by its usage for sleeping. Preferably used with a Room.
Bedroom
Protection
WindowSwitch
percent
void device type = 255
scene number
identification if the power envolope refers to an abnormal condition
is quality kind of
This state type expresses the state of storm. Usually, this state is related to the protection of shading equipment such as blinds and slats, which can be damaged due to high wind speeds. In case of storm, this equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Storm' state type.
Storm State
To define a functionality (=collection of datapoints) as part of an application program.
implements
The tag category contains individuals allowing to express how a point value has to be interpreted (mathematically or logically) in order to affect the behavior of the system.
Point Operation
one PB/binary input; SwitchOnOff inverts on each transmission = 1
volume flow, 0,1 ml/s = 74
language code ISO 639-1
Behaviour_Lock_Unlock
To express a relation of a channel, implemented in a device.
has channel
8-bit signed value
a point representing DPT 3.008: Control Blinds
Control Blinds
last (value before bus power down) = 4
a point representing DPT 25.1000: DoubleNibble
DoubleNibble
A specific Application Function to optimize different energy storages.
Energy Storage Control
includes datapoint field
Historical = 0
a point representing DPT 251.600: Converter Info
Converter Info
energy, 0,01 Wh = 1
undefined load command received = 14
Staircase Trigger Request
1-bit controlled
Entrance generally refers to the place of entering like a lobby, foyer, gate, door, or road or the permission to do so. Preferably used with an Room.
Entrance
Hardwired switch is on = 0
a point representing DPT 9.027: Value Temp F
Value Temp F
EmergPressure = 1
Weather is the state of the atmosphere, describing for example the degree to which it is hot or cold, wet or dry, calm or stormy, clear or cloudy.
Weather
communication fault = 2
Limits a numerical datapoint type value to a minimum (range min) as a literal, to express float and integer values. May be used from several concepts, such as a DPT. The range is used to limit it for signed/unsigned integers and float values.
range min
hardware fault = 4
a point representing DPT 237.600: DALI Control Gear Diagnostic
DALI Control Gear Diagnostic
enable = 0
true = forced on/off control is active, e.g., via input SwitchedOnOffForced
Request Converter Status = 1
a point representing DPT 20.1000: CommMode
timestamp when this constraint will be valid
a point representing DPT 220.100: Next Temperature and Time Delay
TempHVACAbsNext
Info On Off Output 6
temperature converted = 1
The value of the target datapoint is sent at the latest after a certain duration. The duration is defined by the metadata datapoint's value.
is heartbeat of
Switch On Off Red
activation of priority = 0
This state type expresses that an equipment has a movement direction that can be interpreted as 'upwards'. Usually, this is associated with equipments that can be moved by a drive along a vertical axis, such as blinds or slats.
Upwards Movement
The visual effect of channel 19 is inactive = 0
a point representing DPT 20.012: ErrorClass HVAC
ErrorClass HVAC
Info On Off Output 16
Not active = 0
is composed by output
Data Link Layer Busmonitor = 1
a point representing DPT 20.007: AlarmClassType
electromagnetic moment
is outside of
a point representing DPT 9.011: Value Time 2
Value Time 2
General failure of the actuator or the drive
Activation state of channel 21
reset command (trigger) = 1
Application functions that controls the quantity 'air volume'.
Air Volume Control
volume, 1000 l = 22
a point representing DPT 238.001: SceneConfig
SceneConfig
A trend application function monitors live and historical, time-indexed, quantitative etc. data, for example, for visuaization.
Trend
TempSetpEco
a point representing DPT 20.005: LightApplicationMode
LightApplicationMode
critical = 1
is point priority of
Room Temperature Setpoint Manager
charge density (volume)
is tag of
a point representing DPT 1.004: Ramp
Field name, used to define a (user readable) name of a KNX data field as part of an entire datapoint type.
field name
Used to control a motor equipment to create air flow with a fan. The interest is the motor and not the actuator equipment, containing the motor.
Fan Motor
a point representing DPT 1.100: Heat/Cool
Heat/Cool
General actuator failure
Panel housing controllers and networking gear. A control panel is a flat, often vertical, area where control or monitoring instruments are displayed or it is an enclosed unit that is the part of a system that users can access, such as the control panel of a security system (also called control unit).
Controls panel
a point representing DPT 21.601: LightActuatorErrorInfo
LightActuatorErrorInfo
A parent data property, used to express any kind of generic data that relates to an installation.
installation data
a point representing DPT 20.122: StartSynchronization
A machine that has the primary function of printing a stream of characters onto paper or other media.
Printer
is product of
CombinedStatus_HVA_CoolA
calm (no wind) = 0
a point representing DPT 20.606: PBAction
PBAction
a point representing DPT 265.012: DateTime Invert
DateTime Invert
a point representing DPT 265.001: DateTime Switch
DateTime Switch
Mask Bit Info On Off Output 12
DPT 14.027: Value of electric potential
Value Electric Potential
IdentNumber
energy, 1000 kJ = 14
Upper end pos. reached
validity of TempWater field
A Quality Kind with at least one adjustable quantity property that addresses an 'equipment', and the quantity property can be directly changed.
adjusts equipment quality kind
Refers to distribution systems used to supply a room with e.g. heat, water, or air. Usually, those substances (and the energy they carry) originate in specific plants, which are mostly centralized for each building. From there, the distribution systems transport substances to the individual rooms.
Supply Section
StatusEcoH
RainAlarm
open on overheat with a current value under the maximum switching current value = 6
temperature (absolute)
Test manually stopped = 5
one push button/binary input, MoveDown / StepDown message sent = 3
notice PE3 in progress = 3
automatic light control = 0
Cooling load meter (outlet) = 10
waste water meter = 40
Combined Switch On Off
a point representing DPT 23.002: Alarm Reaction
Alarm Reaction
is comprised by
LegioProtActive
false = 0
Refers to the second phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.
Phase L2
LockDevice
The visual effect of channel 8 is active = 1
Calibration Mode
A general OP relationship to express a relation of location individuals to individuals which are outside of a particular building. The location to be outside (as the domain) MUST fulfil the boundary conditions to be allowed outside. Example is a relation to an outdoor location which does not directly belong to a building (e.g. garden).
has outside
Re-Light / Reset Inhibit = 3
is datapoint of
This state type expresses that a device is able to operate as intended. Thus, it can fulfill its designated functionality and its datapoints offer valid and correct values.
Operational State Operational
validity of the fields CB and Step Code Colour Blue.
Cyclically = 1
a point representing DPT 23.001: OnOff Action
OnOff Action
Hardwired Inhibit is inactive = 0
A Router is a network node (Device) that that forwards data packets between computer networks typically between OSI Layers 3. A router does not change application layer content.
Network Router
corresponding Datapoint Main value is overridden
8.x
The unacknowledged IPv6 (multicast) group notification address, corresponding to a KNX group address. It is used for KNX IoT installations using IPv6, set by the MaC for an individual Installation.
IPv6 multcast address
Heat Stage A Actuator Overridden
Root node to host all core related concepts.
Core Thing
volume flow, 10000 l/h = 63
Equipment to transfer heat between two working fluids. For example, a coil is a heat exchanger used to heat or cool air.
Heat Exchanger
Oversupply
Start Duration Test (DT) = 2
scene is inactive = 1
SwitchPBAction
CombinedStatus_HVA_HeatA
volume flow, 0,01 l/min = 66
An OP relationship to a list that describes the primary protocol that a datapoint uses to send its data.
operates on protocol
DPT 14.026: Value of electric polarization
Value Electric Polarization
detection not possible or error = 3
Sun intensity W/m2
Info On Off Output 9
power, 0,1 W = 42
A parent data property, used to express any kind of generic data that relates to an application program.
application program data
FadeToControlCmd
DPT 14.008: Value of angular momentum
Value Angular Momentum
Shutter and Blinds Mode
An address is represented by an external ontology object, which has data properties such as country-name, locality (city), street-address.
External Address
temporarily no cooling in the production segment available
electric current
Revision Number
This state type expresses that the ventilation system is inactive, i.e. performing neither humidification nor dehumidification tasks.
Humidification Mode Inactive
This state type expresses that some alarm condition for a datapoint occurred. No assumption about the validity of the datapoint’s value can be made.
Operational State In Alarm
16-bit unsigned value & 8-bit enum
A parent data property, used to express any kind of generic data that relates to a datapoint type.
datapoint type
a point representing DPT 275.100: TempRoomSetpSetF16[4]
Room Temperature Setpoint
Start/stop = 0
Standard Summer Time
Fan Speed Target
a point representing DPT 244.600: Converter Status
A toilet is a small room used for privately accessing the sanitation fixture (toilet) for urination and defecation. Toilet rooms often include a sink (basin) with soap/handwash for handwashing, as this is important for personal hygiene.
Restroom
Hour of day, Minutes and Seconds field valid = 0
This state type expresses that an equipment is controlled by an automatic algorithm, rather than being controlled manually. The equipment's input commands are computed by e.g. a controller and interpreted with a normal priority. This state type is the inverse of the 'Override Mode Manual' state type.
Override Mode Automatic
switch mode only (non-dimmable load) = 3
all windows closed = 0
SummerMode
A child OP relationship to a list that describes a quantity/countable characteristic “dimension” how an observation or actuation is made.
has quantity kind
Info On Off Output 11
Application function for 'shutter control'.
User Shutter Control
a point representing DPT 20.1209: Type TIC Channel
Type TIC Channel
Outside Temperature Sensor
WindowStatus
identifier of this instruction. value shall be unique. Old IDs will be reused.
a point representing DPT 206.105: BuildingModeNext
BuildingModeNext
DPT 14.022: Value of electric displacement
Value Electric Displacement
Building not used = 1
Actual Dimming Value Red
Represents a percentage value with 1% resolution for 0 to 255%.
Medium
power, 1000 W = 46
invalid = 0
RoomHConf
DPT 14.062: Value of self inductance
Value SelfInductance
A cooling system keeps air cool and dry within a home, office, or other buildings. Refrigration is the cooling of a space or substance below the environmental temperature.
Cooling
Lighting or illumination is the deliberate application of light to achieve some aesthetic or practical effect. Lighting includes use of both artificial light sources such as lamps and natural illumination of interiors from daylight.
Lighting
valve is currently executing a valve kick
open on load shedding = 3
standby = 1
A parent data property, used to express any kind of generic data that relates to an datapoint type field.
datapoint type field
a point representing DPT 224.100: TempSupplyAirSetpSet
TempSupplyAirSetpSet
A functional subdivison of a location, consisting of one or several usually adjoining buildings.
Site
a point representing DPT 240.800: CombinedPosition
CombinedPosition
Dew Point Status Sensor
DPT 14.023: Value of electric field strength
Value Electric FieldStrength
Movement Trigger
A parent data property, used to express any kind of generic data that relates to a function point.
function point data
Hosts specific information that depends on the field type.
includes
Relative Humidity is the ratio of the partial pressure of water vapor in an air-water mixture to the saturated vapor pressure of water at a prescribed temperature. The relative humidity of air depends not only on temperature but also on the pressure of the system of interest.
Relative Humidity
"Displacement" is the shortest distance from the initial to the final position of a point P.
Displacement
Failed, test executed in time = 3
a point representing DPT 20.104: LoadPriority
LoadPriority
a point representing DPT 230.1000: MBus Address
MBus Address
Building not in use = 1
Shall specify whether the saturation of the colour shall be increased or decreased.
Speed is the magnitude of velocity, where velocity is seen as a vector (i.e., it includes a directional component). In contrast to velocity, speed is a scalar value.
Speed
A façade is generally the front part or exterior of a building. Mainly used as a building facade.
Facade
8-bit unsigned value
The visual effect of channel 21 is active = 1
asynchronous + BiBat Master = 1
a point representing DPT 12.1201: Volume M3
Volume m3
This state type expresses that the highest level named 'Comfort' is chosen for the HVAC mode. Usually, the 'Comfort' level is associated with an occupied room. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Comfort
Mask Bit Info On Off Output 8
Water (chemical formula H2O) is an inorganic, transparent, tasteless, odorless, and nearly colorless chemical substance, which is the main constituent of Earth's hydrosphere and the fluids of all known living organisms.
Water
End of time period that will be covered by the power profile
Heat Stage B Actuator Overridden
The visual effect of channel 17 is inactive = 0
Lightly cloudy = 3
absolute temperature value
mass flow, 10 kg/h = 84
Variable air volume terminal unit. Variable air volume (VAV) is a type of heating, ventilating, and/or air-conditioning (HVAC) system. Unlike constant air volume (CAV) systems, which supply a constant airflow at a variable temperature, VAV systems vary the airflow at a constant temperature.
VAV
The value of the target point is explained with further details by the metadata datapoint's value.
is description of
Mask Bit Info On Off Output 13
CFL, trailing = 6
strong gale = 9
By a MaC (ETS) allowed location usages for a site.
MaC site
The tag category contains individuals that describe a phenomonom (including substances) that can only be indirectly observed or actuated upon as part of the building control system. The tag category does not describe concrete existing things, for example the person John Smith.
Phenomenon
Application functions to monitor an 'intrusion alarm'.
Intrusion Alarming
An Air Handling Unit (AHU) is an equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system.
Air Handling Unit
strong breeze = 6
Controller status. on: controller is working (default if not supported). off: controller is stopped; no control of water temperature
DPT 14.061: Value of resistivity
Value Resistivity
character string
send always = 1
a point representing DPT 265.005: DateTime Alarm
DateTime Alarm
Mask Bit Info On Off Output 16
The visual effect of channel 21 is inactive = 0
stage 1 or base stage active
Validity of TempRoomDem. ‘false’ means also ‘no demand’
This state type expresses that a scene is activated in scene-controlled instrumentations by restoring a previously learnt value. This covers both activating a scene based on a scene number (e.g. 0-63) or by choosing between two scenes (e.g. Scene A or Scene B).
Scene Recall
The tag category contains individuals that describe the numerical quantity of the measurement/adjustment (equipment) or observation/actuation (phenomenon).
Quantity Kind
CCT and Step Code Colour Validity
This state type expresses that an equipment is in a forced state, i.e. its current value / position is a result of a command with very high priority. The equipment's normal processing of input commands is bypassed and the high priority input command is executed as-is. This state type is the inverse of the 'Not Forced State' state type.
Forced State
Blinds Position Length
Hosts 0...n vcard compatible addresses, usually fro a location. A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
has address
a point representing DPT 8.010: Percent V16
Percent V16
alternative setpoint = 1
ForcedPositionEnable
This state type expresses that a scene is taught in scene-controlled instrumentations by storing a value for later recall. This covers both teaching a scene based on a scene number (e.g. 0-63) or for one of two scenes (e.g. Scene A or Scene B).
Scene Save
Absolut load priority = 2
To represent a location, used to express a spatial location structure. The defined location model class/subclass structure does not reflect the hierarchy of a real world spatial building, such as a site/building with floors, rooms and/or spaces.
Ort
Position unchanged = 0
Ack_Sup
Day of week field valid = 0
Refers to information that originates from user action, e.g. issueing light switching commands or selecting setpoints.
User
Discharge Temperature Sensor
inactive = 1
Substance with definite volume but takes the shape of its container
Liquid
identifier of previous operation mode that was active before the state machine switched to the current one. CT=0 no previous operation mode declared
A human friendly description (longer text), used to define user specific data for an individual. Edited in a MaC or from predefined product data or dictionary content. No limitation of the actual amaount, external entites may add additional language depended text. The 'Range' is not limited to a string, allowing to express also text in several languages (note W3C does not define a range).
description
a point representing DPT 20.1204: Euridis Communication Interface Status
Euridis Communication Interface Status
Other Residential
Validity of ActPosDem. ‘false’ means also ‘no demand’
8-Bit Unsigned Value & 8-Bit Set
heat capacity
HumRelSetpUser
inactive (no message sent) = 0
Pressure is an effect which occurs when a force is applied on a surface. Pressure is the amount of force acting on a unit area. Pressure is distinct from stress, as the former is the ratio of the component of force normal to a surface to the surface area. Stress is a tensor that relates the vector force to the vector area.
is state kind of
The relation is meant to be outside a building (outdoor is the same).
Outside
Setpoint Manager Relative Humidity
Colour Level Green
Standard = 1
ActualDimming-Value
occupancy at least from one presence detector = 1
RelSetvalueControl
A specific Application Function category for 'monitoring' a zone, equipment or energy consumption (metering). The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
Monitoring
EnableHeat
Index of access identification code
Wind Force Scale
TempSetpComf
mass flow, 0,1 kg/h = 82
"Height" is the measurement of vertical distance, but has two meanings in common use. It can either indicate how "tall" something is, or how "high up" it is.
Height
speed
Direction 1
Battery Duration Failure
Flow Rate in m³/h with high resolution
a point representing DPT 1.021: Logical Function
up = 0
activate the scene corresponding to the field Scene Number = 0
volume
A loudspeaker (commonly referred to as a speaker or speaker driver) is one type of electroacoustic transducer, that is, a device that converts an electrical audio signal into a corresponding sound.
Speaker
A gym (also known as a fitness club, fitness center, health spa, and health club) is a place that houses exercise equipment for the purpose of physical exercise.
Gym
a point representing DPT 9.028: Value Wsp kmh
Value Wsp kmh
a point representing DPT 10.001: TimeOfDay
TimeOfDay
a point representing DPT 13.016: ActiveEnergy MWh
ActiveEnergy MWh
Equipment Quality Kind
energy, 1 kJ = 11
charge density (surface)
master = 1
A user operated staircase light switch/trigger request including an explicit status.
Staircase Lighting
common flow temperature of ProdSegmH
violent storm = 11
composes ouput
configuration fault = 3
a point representing DPT 206.102: DHWModeNext
DHWModeNext
energy, 10 Wh = 4
a point representing DPT 219.001: AlarmInfo
AlarmInfo
requested room temperature setpoint
Increase or decrease the colour temperature.
DPT 14.053: Value of momentum
Value Momentum
CombinedStatus_FA
Colour_Relative Control_RGB
mass flux
Low = 2
volume flux
supported control types, set bitwise b0 = PEBC b1 = PPBC b2 = OMBC b3 = FRBC b4 = DDBC b5-b7 = reserved
Mask Bit Info On Off Output 2
Supply air, e.g. for VAV = 2
Application functions for "fill rate based control". Fill rate is the percentage of demand that can be met without lagging in supply. By using fill-rate as the basis for determining the energy production, conservation and optimization of energy can be done without failing to satisfy demands.
Fill Rate Based Control
mass, 10 kg = 28
wind speed absolute value m/s
Converter Failure
ActCurrPosCoolStageA
Specifies for enumeration DPTs a string value, that can be used from an (external) API at runtime.
value API
pressure
two PBs/binary inputs mode = 2
DPT 14.043: Value of luminous intensity
Value Luminous Intensity
Scene Sensor
a point representing DPT 217.001: Version
Constant air volume terminal unit. Constant air volume (CAV) is a type of heating, ventilating, and air-conditioning (HVAC) system. In a simple CAV system, the supply air flow rate is constant, but the supply air temperature is varied to meet the thermal loads of a space.
CAV
DPT 14.056: Value of power
Value Power
Field type, used to define a (coding) type of a KNX data field as part of an entire datapoint type, specified in KNX (not all types are used in the KIM). A Character A[n] String of n characters B Boolean / Bit set C Control E Exponent F Floating point value M Mantissa N eNumeration r Reserved bit or field S Sign U Unsigned value V 2's Complement signed value Z8 Standardised Status/Command (8 bit)
field type
Cloudy = 5
accepted = 1
F32F32
timestamp when the instruction has to be executed
Move up or down.
a point representing DPT 222.100: TempRoomSetpSetF16[3]
TempRoomSetpSetF16[3]
Used to control an actuator equipment to regulate the light incidence (blinds or shutter position). Don't care if the blinds position is internally operated from the actuator by a motor or other means.
Blinds Actuator
A generic concept of a KNX datapoint type (DPT). Each present individual represents a corresponding DPT of KNX. The chosen individual name follows a defined structure. A datapoint type is derived from parent concepts that are specified as part of the EN 50090-6-2.
Datapoint Type
A hallway or corridor is an interior space in a building that is used to connect other rooms. Preferably used with an Room.
Hallway
DPT 14.071: Value of thermal capacity
Value Thermal Capacity
A power supply is an electrical device that supplies electric power to an electrical load. The main purpose of a power supply is to convert electric current from a source to the correct voltage, current, and frequency to power the load.
Power Supply
target position is reached = 1
A dining room is a room for consuming food. Preferably used with an Room.
Dining Room
a point representing DPT 1.014: Input Source
a point representing DPT 229.001: MeteringValue
MeteringValue
roles of this RM according to commodities
sound intensity
A point representing a dynamic limitation for an essential variable or a process value.
Limit
mass, 0,1 kg = 26
Physical unit used for driving mechanically actuated final controlling elements. Examples of actuating drives are electric, hydraulic or pneumatic actuating drives, diaphragm systems or piston actuators (see IEC 60050-351).
Drive
The visual effect of channel 11 is active = 1
thermal conductivity
This state type is a special type of a defect state. It expresses that the actual device hosting the datapoint is not working properly due to an overload. Thus, no valid value is available at the datapoint.
Operational State Defect Overload
An airport is an aerodrome with extended facilities, mostly for commercial air transport. Preferably used with a Site or Location.
Airport
trigger (1) = 1
Overrun
User HVAC Room Settings
not running = 0
DPT 14.069: Value of absolute temperature
Value Absolute Temperature
A point contains a warning that draws attention to something that usually does not need immediate attention.
Alert
Status D
A point represents an alarm status of a functionality that typically needs immediate attention.
A site represents a collection of buildings and grounds that belong to a given institution. A site is usually at the top of a location or rather building hierarchy. The concept can be mapped to a IfcSite.
Liegenschaft
power, 0,1 MW = 168
current position>0 = 1
energy, 1 Wh = 3
scaling speed
alarm (RTC locked) = 1
Garbage = 41
Status B
Combined Info On Off
validity of the fields CG and Step Code Colour Green.
ActCurrPosCoolStageB
Shutter Move Up Down
Negative = 1
HeatingDisabled
A parent data property, used to express any kind of generic data that relates to a device.
device data
An escalator is a moving staircase which carries people between floors of a building or structure. It consists of a motor-driven chain of individually linked steps on a track which cycle on a pair of tracks which keep them horizontal.
Escalator
A generic functional subdivison of a location, which represents any physical space that belongs to a building.
Space
invalid Group Object number (ASAP) = 17
The visual effect of channel 22 is active = 1
a point representing DPT 9.025: Value Volume Flow
Value Volume Flow
EnableCoolEff
Color temperature is the color of light emitted by an idealized opaque, non-reflective body at a particular temperature measured in kelvins. The color temperature scale is used to categorize the color of light emitted by other light sources regardless of their temperature. Color temperatures over 5000 K are called "cool colors" (bluish), while lower color temperatures (2700–3000 K) are called "warm colors" (yellowish).
Light Colour Temperature
CoolingOnly = 1
heat flow rate
ControllerConnection = 2
Historical single-phase = 1
DPT 14.015: Value of conductance
Value Conductance
logical function AND = 1
move Up/Down + StepStop mode (blind) = 1
do not send = 0
DPT 14.046: Value of magnetic flux density
Value Magnetic FluxDensity
Heat/Cool for changeover applications = 5
BiBat Master
the range of the fill level the leakage rate (LR) realtes to
Cooling Load meter (inlet) = 10
A Device can be any electronic equipment with some computing ability that has a firmware, optionally with input and output terminals (I/O), an Application Program that provides as set of Points as the interface for the I/O operations, and parameter values controlling the behavior of the I/O operations at Runtime.
A functional block represents a software element that has internal storage and produces a computable result with output values when executed with a particular set of input values.
Functional Block
momentum
AbsSetvalueControl
energy, 0,001 kJ = 8
Breaker/Valve is open = 1
FanManual
Quality of clock
A child OP relationship allowing to define the equipment where an observation or actuation is made upon.
has equipment type
HumDehumMode
A vertical shaft in a building which allows the passage of an elevator from floor to floor. Preferably used with a Space.
Elevator Shaft
To define an asset included in other assets such as several equipment’s/ installations as part of an asset.
contains asset
DPT 14.068: Value of common temperature
Value Common Temperature
a point representing DPT 7.004: TimePeriod100MSec
TimePeriod100MSec
To a device assigned trade, whereas the trade definitions (names/structures) can be freely defined by the MaC user. The trade definitions MAY have a logical relation to the KIM trade tags. A device is assigned to one trade only.
assigend trades
clock without ext. sync signal = 0
Reset Lamp Time = 4
a point representing DPT 243.600: Colour Transition
Colour Transition
CoolingDisabled
Heat Stage A Actuator Target Position
status of all timers wether they are running or not. each bit declares the status of the timer with the id of the bit position. bn = 0 means timer n is not running, bn = 1 means timer n is running
whole gale / storm = 10
Active Mode
To define a representative entry point for datapoints with a gateway. With this datapoints in an installation can be exposed for different purposes, such as all datapoints on a 3rd Party API (gateway).
has proxy
a point representing DPT 205.103: HVACAirQualRel_Z
HVAC Air Quality Relative Value
A child OP relationship to a list that describes the interest characteristic “type of interest” on what an observation or actuation is made.
has phenomenon type
Off/FrostProtection = 4
Illuminance is the total luminous flux incident on a surface, per unit area. It is a measure of the intensity of the incident light, wavelength-weighted by the luminosity function to correlate with human brightness perception. As a note, focus is the light source, which is mostly NOT the interest in the building control domain.
Luminance
ActCurrentFanSpeed
A tag set combines different tags in a set, to express a joint concept with a specific semantical meaning.
Tag Set
Blinds Position Percentage
electric flux
This state type expresses that an equipment is in a locked state, which usually indicates that the equipment will not react on new input commands until the locked state is lifted. This state type is the inverse of the 'unlocked' state type.
Locked State
A tag is an information that describes the data or content that it is assigned to. Tags are typically nonhierarchical keywords (individuals) used, for example, for datapoints, application functions but also for internet bookmarks, digital images, videos, files and so on.
Tag
Maximum Heating Mode = 12
undefined = 0
Switch On Off Blue
FadeTime
1.x
ADAType
Application Funtion 'meter' aggregates consumption measurement points of one or many metering devices.
4-byte signed value
Fire safety deals with preventive actions against fire events (incidents, accidents, and other unwanted conditions) caused by unintentional, human error and/or technical deficiencies, and with the limitation or control of such incidents.
Fire Safety
No Time
HVAC mode
validity of the fields CS and Step Code Saturation.
Comfort/Nothing = 1
This property models the dimming level of a luminaire. This also is used for the individual colour parts, in which case it shall be used in combination with the corresponding chromaticity tags of category StateType (R/G/B/W).
Dimming Level
A building represents a whole building that hosts several other elements such as stacked floors or spaces or rooms. The concept can be mapped to a IfcBuilding.
Gebäude
CombinedStatus_HVA
This DPA represents a combined status of a Heating Valve Actuator. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring (mostly) to the device, which are modeled by the respective tag:operationalStateXYZ tags, if not otherwise stated: Bit 0) Current Valve Position (referring to the property PositionVector, modeled by the state types tag:opened and tag:closed); Bit 1) Short Circuit; Bit 2) Overload; Bit 3) Valve kick (very specific for valves, abstractly modeled by the state type tag:operationalStateMaintenance); Bit 4) Service Mode (modeled by the state type tag:operationalStateMaintenance as well); Bit 5) Manual operation (overridden) - in this case the Overridden status information refers to the actual manual operation (similar to DPA 400.71 the overridden state refers to the actual position of the valve (and thus to the specific property Position Vector), which is why the QualityKind is used at this point; Bit 6) Forced Position (modeled by tag:forced); Bit 7) Locked Position (modeled by tag:locked); and Bit 8) Calibration Mode.
validity of the Time Period
DPT 14.050: Value of magneto motive force
Value MagnetomotiveForce
volume flow, 10 l/h = 60
timestamp when this constraint will be invalid
includes counter
Defines the ability to write a datapoint. The r/w limits set with boolean values true (default) or false. It may be used to limit the access from a 3rd party interface or similar, set by a MaC.
writable
volume flow, 1 l/h = 59
FanManualEff
a point representing DPT 9.029: Humidity
Humidity
a point representing DPT 8.005: DeltaTimeSec
DeltaTimeSec
A generic concept to describe the individual parts of a KNX datapoint type. A datapoint type field is derived from parent concepts that are specified as part of the EN 50090-6-2.
Datapoint Type Field
A datagram with the own Individual Address as Source Address has been received
The tag category contains individuals that describe specific state types in the control loop of an Application Function. An individual state type is the result of an interpretation of process variables or other states in the control loop. Each state type has a semantically predefined, discrete meaning that can only be figured out together with other context knowledge from the domain of building control. A state type is not assigned with a specific Runtime value, moreover, at least two state types are required to form the set of applicable options, used in the control loop.
State Type
Open = 0
An operation kind describes by what means the quantity kind value of a specific 'type of interest' from a QK or the state type value is used. The same OK individual MAY refer to arbitrary QK individuals.
Operation Kind
volume flow, 10 ml/s = 76
The tag category contains individuals that describe a tangible and/or movable equipment that can be actively observed or actuated upon as part of the building control system (in contrast to passive equipment's of the building, for example a pipe or a duct).
Equipment
A user operated room temperature control including actual room/outside temperature inputs and valve control outputs.
Room Temperature Control
volume, 1 l = 19
Battery Failure
EmergPurge = 3
drive is moving = 0
volume flow, 0,001 l/h = 56
This state type expresses that the buildin protection room temperature setpoint is used for temperature control in a room.
Type of Temperature Setpoint Protection Mode
Wind Alarm
CoAP
Heat Stage A Actuator Current Position
a point representing DPT 203.100: HVAC Air Qual Z
HVAC Air Qual Z
To define a general relation between different concepts. With the child properties a relation with a specific semantic meaning can be expressed (such as between locations). Due to the usage from several concepts the domain and range is not specified for this OP.
refers to
Month
Represents the fact that the quantity is a date (any format statement is out of scope in this tag category), without any part relating to the time of day.
Date
Not inverted = 0
This state type expresses that mode 'Heating' is chosen for the HVAC system. Usually, this mode is associated with default heating functionality of the HVAC system. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Heating
StatusPreCool
valid = 1
Alarming is the automated alarm management in the event of alarms or faults in plants, subsystems or devices.
volume, 100 l = 21
A point representing a validity assessment of a datapoint value.
Validity
Month and Day of Month fields valid = 0
Level 13 = 13
alarm position is UP = 1
Level 10 = 10
32-bit set
a point representing DPT 20.115: HumDehumMode
SolidState
An OP relationship to a list that describes the runtime interworking interface type of a datapoint. A datapoint usually reflects a logical or physical (input/output) point, combinations with other (parameter/diagnostic) tags are possible.
has point interface
energy, 0,1 kJ = 10
A bar, also known as a saloon, a tavern or tippling house, or sometimes as a pub or club, is a retail business establishment that serves alcoholic beverages, such as beer, wine, liquor, cocktails, and other beverages such as mineral water and soft drinks.
Bar
Overridden
This DPA refers to the actuator being manually overridden. In contrast to the Z8 general status fields, in this case the Overridden status information refers to the actual manual operation (and not to an overridden state due to maintenance as does the Z8 field). The overridden state refers to the actual position of the valve (and thus to the specific property Position Vector), which is why the QualityKind is used at this point.
Used to represent the current version of the content for the semantic dictionary.
dictionary version
Synchronisation source reliability
A space is an area or volume providing certain functions of a building, it represents any kind of physical space that belongs to a building. A Space can also be outside of a building. The concept can be mapped to a IfcSpace.
Bereich
Shutter Stop Trigger
first character of LanguageCode, ASCII-coded
Indicator whether sequence is selected to be executed within the power sequence container
mass flow, 1 kg/h = 83
Gas meter = 3
A classroom or schoolroom is a learning space in which both children and adults learn. Preferably used with a Room.
Classroom
Request Converter Info Fix = 8
Used to control an actuator equipment to regulate regulate the flow of fluid (valve position). Don't care if the valve position is internally operated from the actuator by a motor or other means.
Valve Actuator
Building protection = 2
High = 0
power, 1000 kJ/h = 54
luminance
Current Date
Alarm = 1
a point representing DPT 5.001: Scaling
Heating Mode Enabled
Current Colour RGB
Standard three-phase = 4
2-bit set
Refers to the third phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.
Phase L3
This state type expresses that an equipment is in an unlocked state. Typically, this means that the equipment reacts to new input commands as intended. This state type is the inverse of the 'locked' state type.
Unlocked State
Valve (gas or water) = 33
ContrModeSecondary
mass
Room Setpoint Manager HVAC-Mode Driven
A function point groups typically more than one point needed to express the communication link between all the points. The points provide the input/output data interfaces of the devices in an installation. A function point is derived from parent concepts that are specified as part of the EN 50090-6-2.
Function Point
TempOptimShiftActive
CalibrationMode
DHW temperature setpoint for Off/FrostProtect operating mode
a point representing DPT 5.100: Fan Stage
room temperature setpoint shift building protection
Limits a numerical datapoint type value to a maximum (range max) as a literal, to express float and integer values. May be used from several concepts, such as a DPT. The range is used to limit it for signed/unsigned integers and float values.
range max
enable stage B = 2
PDT in progress = 9
A Device can be any electronic equipment with some computing ability that has a firmware or supports the installation of software. Examples are pumps, dampers, valves, sensors, detectors, limit switches, remote/local switches or automation devices.
Device
a point representing DPT 255.001: Geographical Location
Geographical Location
one push button/binary input = 1
This state type expresses the state of no frost. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case no frost has been detected, no frost protection is required and this equipment might be used as intended. This state type is the inverse of the 'Frost State' state type.
No Frost
a point representing DPT 19.001: DateTime
DateTime
Refers to distribution systems used to transport substances (and phenomena) such as water, air, or heat back to the specific centralized plants in a building. The distribution systems interface with the individual rooms at the start of the return part of the distribution system.
Return Section
activation energy
Battery Charge Level
valve (gas or water) = 33
a point representing DPT 212.100: TempRoomSetpSetShift[3]
TempRoomSetpSetShift[3]
Actual relative power %
Used to define the current number of an entity, such as the building number. May be used from other concepets, therefore no domain is defined.
number
Activation state of channel 23
one PB/binary input, Off / DimDown message sent = 3
Battery Information
A cooktop (American English), hob (British English), or stovetop (American English), is a home appliance device (EN 50523: gas cooktop, hob or induction hob) commonly used for cooking that is commonly found in kitchens and used to apply heat to the base of pans or pots.
Cooktop
a point representing DPT 20.114: Metering DeviceType
Metering DeviceType
LampFailure
DHW temperature setpoint for Normal operating mode
Blinds Move Up Down
Log Number
Refers to the first phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.
Phase L1
Haystack
a point representing DPT 207.101: LockSign
LockSign
Mask Bit Info On Off Output 14
The lower boundary of the range with 95 % certainty the power value is in it
Bus/System = 14
building mode
DPT 14.033: Value of frequency
Value Frequency
Application functions to monitor a 'fire alarm'.
Fire Alarming
a point representing DPT 213.101: TempDHWSetpSet[4]
TempDHWSetpSet[4]
Shutter Position Length
AddInfoType
Shall specify whether the brightness shall be increased or decreased.
Dew Point Status
A user operated light switch request including an explicit switch status.
User Light Switching
Ramp = 1
indicates if power reduction is necessary (validity of PwrReduction)
Calibration Mode = 15
Relative Set Value Control Green
In Western architecture, a living room, also called a lounge room (Australian English), lounge (British English), sitting room (British English), or drawing room, is a room for relaxing and socializing in a residential house or apartment. Preferably used with an Room.
Living Room
Heat Stage B Actuator Calibration Mode
Controller inactive
Normal mode active, all OK = 1
Permission (informs about the access decision made by the controlling device)
Limits a numerical datapoint value in its applicative behavior to a minimum. Represents an external definition, hence it is also used from other concepts, therefore no domain is defined (merged ontologies -> intersection problems). The range xsd:decimal covers also numerical values with a fraction such as 12.34 or -13.56.
minimum
Up / Down
slave = 1
HumRelRoom
a point representing DPT 9.003: Value Temp A
Value Temp A
a point representing DPT 17.001: SceneNumber
a point representing DPT 5.006: Tariff
timestamp when the constraints becomes valid
Warm water meter = 6
PL medium Domain Address = 1
a point representing DPT 1.010: Start
a point representing DPT 1.023: ShutterBlinds Mode
ShutterBlinds Mode
Blinds Stop Step
a point representing DPT 20.613: Converter Data Request
Converter Data Request
Read direction (e.g. of badge). If not used (e.g. electronic key) set to zero.
ActCurrPos
This state type expresses that the second-lowest level named 'Economy' is chosen for the HVAC mode. Usually, the 'Economy' level is associated with a room that is unoccupied for longer periods in time (e.g. during the night). In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.
HVAC Mode Economy
A specific Application Function to optimize different energy consumers. An emissionCtrl is an energy saving Application Functions and routines based on the actual use of a building (space), depending on real user needs, to avoid unnecessary energy use and CO2 emissions.
Emission Control
date
Dali
maximal table length exceeded = 13
BinarySceneTeachIn
In classical geometry, the "Diameter" of a circle is any straight line segment that passes through the center of the circle and whose endpoints lie on the circle.
Diameter
DPT 14.1201: Value of volume flux (in litres per second)
Volume Flux ls
AlarmUnAck
is part of
This state type expresses that an equipment or a functionality is enabled. An enabled equipment may become active and fulfill its intended functionality. Being in 'Enabled State' makes no assumption on whether the equipment is currently active or inactive, but it merely expresses the state that the equipment is allowed to be active. Similarly, an enabled functionality is available to the system, i.e. it may contribute to the system's overall functionality. Usually, the equipment or functionality is enabled by management functionality, such as a building management system. This state type is the inverse of the 'Disabled State' state type.
Enabled State
To define a generic relation from a functionality to several points. A functionality without any points is possible.
has point
Field resolution, a factor for the value range of a KNX data field as part of an entire datapoint type.
field resolution
InfoOnOffFromDimmingActuator
Room Temperature Controller
not locked = 0
SolarEnergyOnly
The atmosphere of Earth or air is the layer of gases retained by Earth's gravity that surrounds the planet and forms its planetary atmosphere.
Air
BlinkingWithAcknowledge = 2
24 times channel activation
Device for toggling a state.
force
Region as in DPT_RegionCode-Alpha2_ASCII (234.002) this is ISO 3166-1 alpha-2
phase angle, radiant
Single close = 1
filtering by Domain Address = 1
a point representing DPT 265.011: DateTime State
DateTime State
Power is the rate at which work is performed or energy is transmitted, or the amount of energy required or expended for a given unit of time. As a rate of change of work done or the energy of a subsystem, power is work divided by time.
Point name, used to indicate the name of a point. This is used in assigning names to the (input/output) points of functional blocks
point name
a point representing DPT 205.101: TempHVACRel_Z
HVAC relative Temperature
validity of the Absolute Colour Temperature
a point representing DPT 29.012: ReactiveEnergy V64
ReactiveEnergy V64
time when this instruction will be executed
a point representing DPT 11.001: Date
oil = 1
Activation state of channel 18
consequence type of the power constraint
A strong OP relationship to express a relation to a site segment contained in a site.
has site segment
Staircase Status
DPT 14.075: Value of torque
Value Torque
Shall specify whether the colour component white shall be increased or decreased.
An equipment is often refered to as "Fixed Asset". Via an object property realationship an equipment has a relation to an element in the location, in most cases inside a building, for example, a whiteboard, a chair, a table, a fan or a motor, which one can assign a product category and/or product type.
has eventpoint
Phenomenon Quality Kind
Occupied = 0
a point representing DPT 209.103: StatusWTC
StatusWTC
TempFloor
Expresses if an location is outside in perspective of a Building. A Space, Site or SiteSegment can be outside of a Building.
Außenbereich
magneto motive force
A floor is a level or plane concept in a building, it is separating a building into horizontal spaces. A floor can have spaces assigned, in particular a room. The concept can be mapped to a IfcBuildingStorey.
Etage
Relative demand %: for modulating burner
The current state of a function point according to its security, used from installations that specifies an explicit and (by an installer) intended security behavior for the communication.
security mode
Supply air temperature cooling setpoint
Current Valve position
SNMP
Colour Level Blue
a point representing DPT 22.1000: Media
Media
impedance
HVAC Valve Actuator
No test pending = 1
energy, 10 kJ = 12
is trade operated by
a point representing DPT 1.002: Bool
Sunday = 7
This state type expresses that the red part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.
Chromaticity Red
This state type expresses that mode 'Pre-Cool' is chosen for the HVAC system. Usually, this mode is associated with the HVAC system cooling an unoccupied room in a predictive manner in order for the room to be at the desired temperature once the room is scheduled to be used. In general, the control mode is also known as 'HVAC Control Mode' and is used for expressing functionalities in HVAC systems, such as "Heating", "Cooling", "Off", "Night Purge" etc.
Control Mode Pre-Cool
"Width" is the middle of three dimensions: length, width, thickness.
Width
a point representing DPT 8.011: Rotation Angle
Rotation Angle
Stations or other buildings used for public transport such as train stations, bus stations or metro stations. Preferably used with a Building.
Transportation
Switch On Off Green
true = actuator is in state DIMMING. false = actuator is not in state DIMMING. Not applicable for switching actuator LSAB.
a point representing DPT 20.120: ADAType