Cool Stage A Actuator Fault
type: Class
subclass of: Function Point
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
    intersection of: Restriction
      has value: operationalStateFaulty
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1

Dim Send Style
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.13.i0.0
includes key value pair: Cyclically = 1
label: Dim Send Style

target position is reached = 1
type: NamedIndividual
value API: targetPositionIsReached
value KNX: 1

Solid
type: PhenomenonType
type: NamedIndividual
description: Substance with definite shape and volume

Channel Activation 24
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 30.1010: Channel Activation 24
subject: Channel Activation 24
subject: 30.1010
dpt bit size max: 24
dpt major number: 30
datapoint type minor number: 1010
is assembled with: type.dpt.field.30.1010.i8.ActivationStateOfChannel9
is assembled with: type.dpt.field.30.1010.i2.ActivationStateOfChannel3
is assembled with: type.dpt.field.30.1010.i12.ActivationStateOfChannel13
is assembled with: type.dpt.field.30.1010.i9.ActivationStateOfChannel10
is assembled with: type.dpt.field.30.1010.i13.ActivationStateOfChannel14
is assembled with: type.dpt.field.30.1010.i23.ActivationStateOfChannel24
is assembled with: type.dpt.field.30.1010.i6.ActivationStateOfChannel7
is assembled with: type.dpt.field.30.1010.i1.ActivationStateOfChannel2
is assembled with: type.dpt.field.30.1010.i19.ActivationStateOfChannel20
is assembled with: type.dpt.field.30.1010.i16.ActivationStateOfChannel17
is assembled with: type.dpt.field.30.1010.i10.ActivationStateOfChannel11
is assembled with: type.dpt.field.30.1010.i7.ActivationStateOfChannel8
is assembled with: type.dpt.field.30.1010.i21.ActivationStateOfChannel22
is assembled with: type.dpt.field.30.1010.i11.ActivationStateOfChannel12
is assembled with: type.dpt.field.30.1010.i4.ActivationStateOfChannel5
is assembled with: type.dpt.field.30.1010.i14.ActivationStateOfChannel15
is assembled with: type.dpt.field.30.1010.i5.ActivationStateOfChannel6
is assembled with: type.dpt.field.30.1010.i15.ActivationStateOfChannel16
is assembled with: type.dpt.field.30.1010.i0.ActivationStateOfChannel1
is assembled with: type.dpt.field.30.1010.i20.ActivationStateOfChannel21
is assembled with: type.dpt.field.30.1010.i18.ActivationStateOfChannel19
is assembled with: type.dpt.field.30.1010.i17.ActivationStateOfChannel18
is assembled with: type.dpt.field.30.1010.i22.ActivationStateOfChannel23
is assembled with: type.dpt.field.30.1010.i3.ActivationStateOfChannel4
label: Channel Activation 24
has communication mode: S

Value Thermal Capacity
type: NamedIndividual
type: Datapoint Type
description: DPT 14.071: Value of thermal capacity
subject: 14.71
subject: 14.071
subject: Value Thermal Capacity
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 71
is assembled with: type.dpt.field.14.71.i0
label: Value Thermal Capacity
has communication mode: S

volume flow, 0,001 ml/s = 72
type: NamedIndividual
value API: volumeFlow,0,001Mls
value KNX: 72

Speed
type: NamedIndividual
type: Quantity Kind
description: Speed is the magnitude of velocity, where velocity is seen as a vector (i.e., it includes a directional component). In contrast to velocity, speed is a scalar value.

CD
type: NamedIndividual
type: Unit
symbol: cd

sequence not interruptible
type: NamedIndividual
description: Sequence is not interruptible
value API: seqni
value KNX: 0

type.dpt.field.522.500.i1.si.AC
type: NamedIndividual
type: Datapoint Type Field
description: instruction is related to abnormal condition
field index: 1
field name: AC
field size: 1
field type: B
includes key value pair: type.kvpair.AbnormalCondition
includes key value pair: No abnormal condition

FanManual
type: Class
subject: 399.76
subject: FanManual
subject: 76
interface object type annotation: 399
label: FanManual
property identifier annotation: 76
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 76
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  has value: Enable
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Override Mode Manual
      on property: hasStateType
    intersection of: Restriction
      has value: overrideModeAutomatic
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo

LegioProtect = 1
type: NamedIndividual
value API: legioProtect
value KNX: 1

has quantity kind
type: FunctionalProperty
type: ObjectProperty
inverse of: is quality kind of
comment: A child OP relationship to a list that describes a quantity/countable characteristic “dimension” how an observation or actuation is made.
domain: Quality Kind
range: Quantity Kind
sub property of: has tag

The visual effect of channel 12 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel12IsActive
value KNX: 1

PA
type: Unit
type: NamedIndividual
symbol: Pa

Fire Alarming
type: Class
comment: Application functions to monitor a 'fire alarm'.
subclass of: monitoring

type.dpt.field.20.804.i0
type: NamedIndividual
type: Datapoint Type Field
description: BlindsControlMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.804.i0.0
includes key value pair: Manual Control = 1

type.dpt.field.525.500.i9.fv.Expected
type: NamedIndividual
type: Datapoint Type Field
description: Expected value
field index: 9
field name: Expected
field size: 16
includes DPT: Power

202.x
type: NamedIndividual
type: Datapoint Type
subject: 202.x
subject: 202.major
dpt bit size max: 16
dpt major number: 202
is assembled with: type.dpt.field.202.x.i0
label: 202.x
has communication mode: LTE

SwitchCool
type: Class
subject: 399.60
subject: SwitchCool
subject: 60
interface object type annotation: 399
label: SwitchCool
property identifier annotation: 60
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 60
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Enabled State
      on property: hasStateType
    intersection of: Restriction
      has value: Disabled State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  has value: Enable
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

invalid Group Object number (ASAP) = 17
type: NamedIndividual
value API: invalidGroupObjectNumber(ASAP)
value KNX: 17

Heat and cool = 13
type: NamedIndividual
value API: heatAndCool
value KNX: 13

type.dpt.field.23.102.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 2
field type: N
includes key value pair: type.kvpair.23.102.i0.3
includes key value pair: type.kvpair.23.102.i0.1
includes key value pair: Economy/Nothing = 2
includes key value pair: type.kvpair.23.102.i0.0

two PBs/binary inputs mode = 2
type: NamedIndividual
value API: twoPBsbinaryInputsMode
value KNX: 2

Meeting Room
type: NamedIndividual
type: Location Usages
description: A meeting room, conference room, or conference hall is a room provided for singular events such as business conferences and meetings. Preferably used with an Room.

type.dpt.field.241.800.i6.WeatherAlarm
type: NamedIndividual
type: Datapoint Type Field
description: At least one of the inputs Wind-/Rain-/Frost-Alarm is ‘in alarm’
field index: 6
field name: WeatherAlarm
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.17.1.i1.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 1
field name: Reserved
field size: 2
field type: r
includes reserved bit(s): type.bit.reserved

Leisure
type: NamedIndividual
type: Location Usages
description: A leisure centre facility or building may include a swimming pool, large sports hall, squash courts, cafeteria, licensed bar, fitness suite, aerobics studios, outdoor grass and/or artificial pitches for football (soccer), hockey etc., a solarium, sauna and/or steam room. Preferably used with a Building.

Switch Control
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 2.001: Switch Control
subject: Switch Control
subject: 2.001
subject: 2.1
dpt bit size max: 2
dpt major number: 2
datapoint type minor number: 1
is assembled with: type.dpt.field.2.1.i0.switch
is assembled with: type.dpt.field.2.x.i1.c
label: Switch Control
has communication mode: S

DateTime Period
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 256.001: DateTime Period
subject: 256.001
subject: 256.1
subject: DateTime Period
dpt bit size max: 128
dpt major number: 256
datapoint type minor number: 1
is assembled with: type.dpt.field.256.1.i1.StartDateTime
is assembled with: type.dpt.field.256.1.i0.StopDateTime
label: DateTime Period
has communication mode: S

Type of Temperature Setpoint Alternative
type: StateType
type: NamedIndividual
description: This state type expresses that an alternative room temperature setpoint (internal to the room setpoint manager) is used for temperature control in a room.

type.dpt.field.frbc.om.i3.CQ
type: NamedIndividual
type: Datapoint Type Field
field index: 3
field name: CQ
field size: 3
field type: U
includes key value pair: Natural Gas Flow Rate
includes key value pair: Electric Power L3
includes key value pair: type.kvpair.cqOilFlowRate
includes key value pair: Electric Power L2
includes key value pair: Electric Power L1
includes key value pair: Hydrogen Flow Rate
includes key value pair: type.kvpair.cqHeatThermalPower
includes key value pair: Heat Flow Rate

TempRoomSetpHeatEffNext
type: Class
subject: 52
subject: 101.52
subject: TempRoomSetpHeatEffNext
interface object type annotation: 101
label: TempRoomSetpHeatEffNext
property identifier annotation: 52
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: qk ph temporal delay
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 101
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: temphvacAbsNext
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph temporal delay
      on property: refersTo
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType

type.dpt.field.20.602.i0
type: NamedIndividual
type: Datapoint Type Field
description: FadeTime
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.602.i0.13
includes key value pair: 22,6 s = 11
includes key value pair: type.kvpair.20.602.i0.14
includes key value pair: type.kvpair.20.602.i0.8
includes key value pair: 1,4 s = 3
includes key value pair: type.kvpair.20.602.i0.9
includes key value pair: 5,7 s = 7
includes key value pair: type.kvpair.20.602.i0.2
includes key value pair: 4,0 s = 6
includes key value pair: 0,7 s = 1
includes key value pair: type.kvpair.20.602.i0.5
includes key value pair: 90,5 s = 15
includes key value pair: 32,0 s = 12
includes key value pair: type.kvpair.20.602.i0.0
includes key value pair: type.kvpair.20.602.i0.4
includes key value pair: type.kvpair.20.602.i0.10

type.dpt.field.psc.i3.Reserved
type: NamedIndividual
type: Datapoint Type Field
description: Reserved Bits
field index: 3
field name: RESERVED
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

datapoint type
type: DatatypeProperty
comment: A parent data property, used to express any kind of generic data that relates to a datapoint type.
domain: Datapoint Type

UElCurrentmA
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 7.012: UElCurrentmA
subject: 7.12
subject: UElCurrentmA
subject: 7.012
dpt bit size max: 16
dpt major number: 7
datapoint type minor number: 12
is assembled with: type.dpt.field.7.12.i0
label: UElCurrentmA
has communication mode: S

Button
type: NamedIndividual
type: EquipmentType
description: A device used to operate functions and equipment in a room by pushing. Examples are push buttons used to switch light, indicate presence and similar use cases.

type.dpt.field.203.100.i1.HVACAirQual
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: HVACAirQual
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: PPM

type.dpt.field.6.20.i0.f
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: f
field size: 3
field type: N
includes key value pair: type.kvpair.6.20.i0.4
includes key value pair: mode 0 is active = 1
includes key value pair: type.kvpair.6.20.i0.2

StatusRCC
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 21.105: StatusRCC
subject: 21.105
subject: StatusRCC
dpt bit size max: 8
dpt major number: 21
datapoint type minor number: 105
is assembled with: type.dpt.field.21.105.i0.Fault
is assembled with: type.dpt.field.21.105.i1.Reserved
label: StatusRCC
has communication mode: LTE

type.dpt.field.205.101.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

Emergency Heat = 8
type: NamedIndividual
value API: emergencyHeat
value KNX: 8

Current Colour RGB
type: Class
subject: CC_RGB
subject: 81
subject: Current Colour RGB
subject: 423.81
interface object type annotation: 423
label: Current Colour RGB
property identifier annotation: 81
subclass of: Restriction
  has value: Colour RGB
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Red
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Green
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 81
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: chromaticityBlue
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind

Generation Control
type: Class
comment: A specific Application Function that controls energy production. The Application Function represents a process of generating energy to the consumer according to energy demand keeping losses in distribution and generation to an absolute minimum.
subclass of: energyCtrl

ok = 0
type: NamedIndividual
value API: ok
value KNX: 0

HVACModeNext
type: Class
subject: 104.52
subject: HVACModeNext
subject: 52
interface object type annotation: 104
label: HVACModeNext
property identifier annotation: 52
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph temporal delay
      on property: refersTo
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: qk ph temporal delay
  on property: hasQualityKind
subclass of: Restriction
  has value: hvacModeNext
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 104
    on property: interface object type

ATES
type: NamedIndividual
type: EquipmentType
description: Aquifer thermal energy storage (ATES) is the storage and recovery of thermal energy in the subsurface. ATES is applied to provide heating and cooling to buildings. Storage and recovery of thermal energy is achieved by extraction and injection of groundwater from aquifers using groundwater wells.

open on overvoltage = 2
type: NamedIndividual
value API: openOnOvervoltage
value KNX: 2

TempRoomSetpSetCoolEff
type: Class
subject: 399.55
subject: 55
subject: TempRoomSetpSetCoolEff
interface object type annotation: 399
label: TempRoomSetpSetCoolEff
property identifier annotation: 55
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 55
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeProtection
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: tempRoomSetpSetF16 a4a
  on property: datapointType

Demand Driven Based Control
type: Class
comment: Application functions for "demand driven based control" is an approach to dynamically manage energy output based on the demand for energy that arises within the smart grid.
subclass of: Smart Grid Control

Hardwired switch is on = 0
type: NamedIndividual
value API: hardwiredSwitchIsOn
value KNX: 0

type.dpt.field.22.103.i2.DewPointStatus
type: Datapoint Type Field
type: NamedIndividual
description: Dew Point Status
field index: 2
field name: DewPointStatus
field size: 1
field type: B
includes key value pair: type.kvpair.22.103.i2.1
includes key value pair: no alarm = 0

HVAC absolute Temperature
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 205.100: TempHVACAbs_Z
subject: HVAC absolute Temperature
subject: 205.100
dpt bit size max: 24
dpt major number: 205
datapoint type minor number: 100
is assembled with: type.dpt.field.205.100.i1.Temp
is assembled with: type.dpt.field.205.100.i0.StatusCommand
label: HVAC absolute Temperature
has communication mode: LTE

Installation Hints
type: DatatypeProperty
type: FunctionalProperty
comment: From MaC assigend installation hints as part of the project.
range: string
sub property of: deviceData

type.dpt.field.245.600.i8.LTRD
type: NamedIndividual
type: Datapoint Type Field
description: LTRD
field index: 8
field name: LTRD
field size: 4
field type: N
includes key value pair: Unknown = 0
includes key value pair: type.kvpair.testResultFailedInTime
includes key value pair: Passed max delay exceeded = 2
includes key value pair: type.kvpair.testResultStopped
includes key value pair: type.kvpair.testResultFailedExceeded
includes key value pair: type.kvpair.testResultPassedInTime

type.dpt.field.252.600.i15.cR
type: NamedIndividual
type: Datapoint Type Field
description: Shall specify whether the colour component red shall be increased or decreased.
field index: 15
field name: cR
field size: 1
field type: B
includes key value pair: type.kvpair.increase
includes key value pair: type.kvpair.decrease

type.dpt.field.522.500.i6.si.IT
type: NamedIndividual
type: Datapoint Type Field
description: instruction type
field index: 6
field name: IT
field size: 4
field type: N
includes key value pair: type.kvpair.seqInstrStartInterrupt
includes key value pair: select sequence
includes key value pair: type.kvpair.seqInstrSchedule
includes key value pair: stop sequence interruption

DHW Control
type: Class
comment: The Domestic Hot Water Control Application Function represents a process of providing domestic hot water (DHW) for the kitchen and bathroom sinks, tubs and other appliances.
subclass of: energyCtrl
subclass of: Restriction
  has value: domesticHotWater
  on property: operatesForTrade

DALI Diagnostics
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 238.600: DALI Diagnostics
subject: DALI Diagnostics
subject: 238.600
dpt bit size max: 8
dpt major number: 238
datapoint type minor number: 600
is assembled with: type.dpt.field.238.600.i1.LampFailure
is assembled with: type.dpt.field.238.600.i0.DeviceAddress
is assembled with: type.dpt.field.238.600.i2.BallastFailure
label: DALI Diagnostics
has communication mode: S

Return Air Temperature Sensor
type: Class
subject: RNATS
subject: Return Air Temperature Sensor
subject: 323
interface object type annotation: 323
label: Return Air Temperature Sensor
is incomplete: true
subclass of: Restriction
  on class: Class
    intersection of: TempReturnAir
    intersection of: Restriction
      has value: TempReturnAir
      on property: point name
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  on class: TempReturnAir
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 323
    on property: interface object type

209.x
type: NamedIndividual
type: Datapoint Type
subject: 209.major
subject: 209.x
dpt bit size max: 24
dpt major number: 209
is assembled with: type.dpt.field.209.x.i0
label: 209.x
has communication mode: LTE

AHU Control
type: Class
comment: An Air Handling Unit (AHU) is an Application Function that controls equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system. An AHU Application Function has usually subfunctions such as fanCtrl, pumpCtrl etc.
subclass of: equipmentCtrl

Refrigerator
type: EquipmentType
type: NamedIndividual
description: A refrigerator, colloquially fridge, is a commercial and home appliance (EN50523) consisting of a thermally insulated compartment and a heat pump (mechanical, electronic or chemical) that transfers heat from its inside to its external environment so that its inside is cooled to a temperature below the room temperature.

non KNX mapping address
type: DatatypeProperty
comment: Used to map a foreign protocol address to a KNX address identifier that is mapped to a specific datapoint. Due to the large number of protocols the data property is not explicitly modeled per (foreign) protocol; it is defined as a generic (bitwise unlimited) integer. Hence this the actual address identifier can be expressed as a large – but unstructured – bit field.
range: integer

type.dpt.field.14.42.i0
type: NamedIndividual
type: Datapoint Type Field
description: luminous flux
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: LM

Scaling
type: NamedIndividual
type: Datapoint Type Field
description: Represents a percentage value between 0 and 100%.
field index: 0
field resolution: 0.3921566
field size: 8
field type: U
includes digit: type.digit.u8
label: Scaling
unit: PERCENT

242.x
type: NamedIndividual
type: Datapoint Type
subject: 242.major
subject: 242.x
dpt bit size max: 48
dpt major number: 242
is assembled with: type.dpt.field.242.x.i0
label: 242.x
has communication mode: S

type.dpt.field.26.1.i0.SceneNumber
type: Datapoint Type Field
type: NamedIndividual
description: SceneNumber
field index: 0
field name: SceneNumber
field resolution: 1.0
field size: 6
field type: U
includes digit: type.digit.u6
unit: NUM

has communication mode
type: DatatypeProperty
comment: Used to indicate that a KNX concept implements the KNX communication mode (S-Mode, LTE-Mode). Most likely, this can be assigned to KNX Datapoint Types and to KNX DPAs (i.e. those which are not present in S-Mode implementations of FBs)
range: Datatype
  one of: LTE
  one of: S

16.x
type: Datapoint Type
type: NamedIndividual
subject: 16.x
subject: 16.major
dpt bit size max: 112
dpt major number: 16
is assembled with: type.dpt.field.16.x.i0
label: 16.x
has communication mode: S

select sequence
type: NamedIndividual
description: select sequence
value API: seqInstrSeqSel
value KNX: 3

Opening Movement
type: StateType
type: NamedIndividual
description: This state type expresses that an equipment has a movement direction that can be interpreted as 'opening'. Usually, this is associated with equipments that can be moved by a drive in an horizontal axis or on a hinge, such as valves, windows, or doors.

field resolution
type: FunctionalProperty
type: DatatypeProperty
comment: Field resolution, a factor for the value range of a KNX data field as part of an entire datapoint type.
range: float
sub property of: datapointTypeDataField

garbage = 41
type: NamedIndividual
value API: garbage
value KNX: 41

off = 0
type: NamedIndividual
value API: off
value KNX: 0

No failure detected = 1
type: NamedIndividual
value API: noFailureDetected
value KNX: 1

Rest mode active = 4
type: NamedIndividual
value API: restModeActive
value KNX: 4

Manual Control = 1
type: NamedIndividual
value API: manualControl
value KNX: 1

type.dpt.field.14.12.i0
type: NamedIndividual
type: Datapoint Type Field
description: charge density (surface)
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: C-PER-M2

Day of week field valid = 0
type: NamedIndividual
value API: dayOfWeekFieldValid
value KNX: 0

type.dpt.field.242.600.i2.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 2
field name: Reserved
field size: 6
field type: r
includes reserved bit(s): type.bit.reserved

Heating-Cooling Stages Both
type: NamedIndividual
type: StateType
description: This state type relates to both primary and secondary stages of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.

EmergPurge = 3
type: NamedIndividual
value API: emergPurge
value KNX: 3

Meter
type: NamedIndividual
type: EquipmentType
description: EquipmentType to meter a substance or phenomenon

TempRoomSetpUserAbs
type: Class
subject: 83
subject: 397.83
subject: TempRoomSetpUserAbs
interface object type annotation: 397
label: TempRoomSetpUserAbs
property identifier annotation: 83
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 83
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind

HVAC VAC = 14
type: NamedIndividual
value API: hVACVAC
value KNX: 14

275.x
type: NamedIndividual
type: Datapoint Type
subject: 275.major
subject: 275.x
dpt bit size max: 64
dpt major number: 275
is assembled with: type.dpt.field.275.x.i0
label: 275.x
has communication mode: S

type.dpt.field.22.1010.i3.ActivationStateOfChannel4
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 4
field index: 3
field name: ActivationStateOfChannel4
field size: 1
field type: B
includes key value pair: The visual effect of channel 4 is active = 1
includes key value pair: The visual effect of channel 4 is inactive = 0

type.bit.reserved
type: NamedIndividual
value KNX: 0

type.dpt.field.230.1000.i1.Version
type: NamedIndividual
type: Datapoint Type Field
description: Version
field index: 1
field name: Version
field size: 8
field type: U
includes digit: type.digit.u8

no error = 0
type: NamedIndividual
value API: noError
value KNX: 0

No alarm = 0
type: NamedIndividual
value API: noAlarm
value KNX: 0

type.dpt.field.14.61.i0
type: Datapoint Type Field
type: NamedIndividual
description: resistivity
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: OHM-M

TempRoomSetpUserAbsEff
type: Class
subject: TempRoomSetpUserAbsEff
subject: 398.84
subject: 84
interface object type annotation: 398
label: TempRoomSetpUserAbsEff
property identifier annotation: 84
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 84
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type
subclass of: Restriction
  has value: Value Temp
  on property: datapointType

LED, trailing = 8
type: NamedIndividual
value API: lED,Trailing
value KNX: 8

type.dpt.field.523.500.i4.sms.PID
type: NamedIndividual
type: Datapoint Type Field
description: identifier of previous operation mode that was active before the state machine switched to the current one. CT=0 no previous operation mode declared
field index: 4
field name: PID
field size: 4
field type: U
includes digit: type.digit.u4

type.dpt.field.21.2.i0.UserStopped
type: NamedIndividual
type: Datapoint Type Field
description: The user application is stopped
field index: 0
field name: UserStopped
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

Car
type: EquipmentType
type: NamedIndividual
description: A car (or automobile) is a wheeled motor vehicle that is used for transportation.

type.dpt.field.246.600.i4.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 4
field name: Reserved
field size: 5
field type: r
includes reserved bit(s): type.bit.reserved

Shading
type: Trade
type: NamedIndividual
description: Protection of buildings, rooms, objects or persons against unwanted effects of solar radiation.

type.dpt.field.516.500.i0.pr.LV
type: Datapoint Type Field
type: NamedIndividual
description: lower value
field index: 0
field name: LV
field size: 16
field type: F
includes digit: type.digit.f16

type.digit.u6 0 59
type: NamedIndividual
range max: 59
range min: 0

10 s = 5
type: NamedIndividual
value API: 10S
value KNX: 5

Luminaire
type: NamedIndividual
type: EquipmentType
description: Light fixture using electricity to provide illumination.

Data Link Layer Raw Frames = 2
type: NamedIndividual
value API: dataLinkLayerRawFrames
value KNX: 2

type.dpt.field.ombc.om.i4.PR
type: NamedIndividual
type: Datapoint Type Field
description: list of power ranges
field index: 4
field name: PR
field type: D<n>
includes counter: type.dpt.field.ombc.om.i2.PR CNT
includes DPT: emPowerRange

Value Torque
type: NamedIndividual
type: Datapoint Type
description: DPT 14.075: Value of torque
subject: 14.075
subject: Value Torque
subject: 14.75
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 75
is assembled with: type.dpt.field.14.75.i0
label: Value Torque
has communication mode: S

M3-PER-HR
type: NamedIndividual
type: Unit
symbol: m³/hr

type.dpt.field.ddbc.ome.i0.SRR
type: NamedIndividual
type: Datapoint Type Field
description: supply rate range
field index: 0
field name: SRR
field size: 32
includes DPT: emPowerRange

type.dpt.field.9.24.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: KiloW

type.dpt.field.209.100.i6.TempFlowProdSegmH
type: Datapoint Type Field
type: NamedIndividual
description: common flow temperature of ProdSegmH
field index: 6
field name: TempFlowProdSegmH
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C

type.dpt.field.22.1010.i13.ActivationStateOfChannel14
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 14
field index: 13
field name: ActivationStateOfChannel14
field size: 1
field type: B
includes key value pair: type.kvpair.22.1010.i13.0
includes key value pair: type.kvpair.22.1010.i13.1

type.dpt.field.7.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 2-byte unsigned value
field index: 0
field size: 16
field type: U
includes digit: type.digit.u16

has address
type: FunctionalProperty
type: ObjectProperty
comment: Hosts 0...n vcard compatible addresses, usually fro a location. A domain definition is not defined. This allows to merge it with other ontologies, defined domains would result in an domain intersection (which is not the intended behavior).
range: External Address

type.dpt.field.14.63.i0
type: NamedIndividual
type: Datapoint Type Field
description: solid angle
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: SR

type.dpt.field.9.20.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: MilliV

cooling = 0
type: NamedIndividual
value API: cooling
value KNX: 0

Heat cost allocator = 8
type: NamedIndividual
value API: heatCostAllocator
value KNX: 8

volume flow, 1000 l/h = 62
type: NamedIndividual
value API: volumeFlow,1000Lh
value KNX: 62

N-PER-M
type: NamedIndividual
type: Unit
symbol: N/m

Value AngleRad
type: NamedIndividual
type: Datapoint Type
description: DPT 14.006: Value of an angle (in radiant)
subject: Value AngleRad
subject: 14.006
subject: 14.6
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 6
is assembled with: type.dpt.field.14.6.i0
label: Value AngleRad
has communication mode: S

emLeakageBehaviour
type: Datapoint Type
type: NamedIndividual
dpt bit size max: 1792
dpt major number: 512
datapoint type minor number: 509
is assembled with: type.dpt.field.512.509.i0.lb.LBE CNT
is assembled with: type.dpt.field.512.509.i1.lb.LBE

Core Thing
type: Class
dictionary version: 20
mac version: 6
comment: Root node to host all core related concepts.
subclass of: Restriction
  all values from: Literal
  on property: title (name)
subclass of: Restriction
  all values from: Literal
  on property: description

Value 1 U Count
type: NamedIndividual
type: Datapoint Type Field
description: Represents values for counting from 0 to 255 counter pulses.
field index: 0
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8
label: Value 1 U Count
unit: NUM

ScalingSpeed
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 225.001: ScalingSpeed
subject: 225.001
subject: ScalingSpeed
subject: 225.1
dpt bit size max: 24
dpt major number: 225
datapoint type minor number: 1
is assembled with: type.dpt.field.225.1.i0.Percent
is assembled with: type.dpt.field.225.1.i1.TimePeriod
label: ScalingSpeed
has communication mode: S

The visual effect of channel 4 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel4IsActive
value KNX: 1

type.dpt.field.20.1003.i0
type: NamedIndividual
type: Datapoint Type Field
description: RF_FilterSelect
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.1003.i0.1
includes key value pair: filtering by Domain Address and by Serial number table = 3
includes key value pair: filtering by KNX Serial Number table = 2
includes key value pair: no filtering, all supported received frames shall be passed to the cEMI client using L_Data.ind = 0

is referenced by
type: ObjectProperty
type: TransitiveProperty
inverse of: refersTo
comment: To define a general relation between different concepts. With the child properties a relation with a specific semantic meaning can be expressed (such as between locations, datapoints or function points). Due to the usage from several concepts the domain and range is not specified for this OP.

type.dpt.field.22.1000.i4.RF
type: NamedIndividual
type: Datapoint Type Field
description: RF
field index: 4
field name: RF
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

type.dpt.field.20.111.i0
type: NamedIndividual
type: Datapoint Type Field
description: FanMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.111.i0.0
includes key value pair: running in intervals = 2
includes key value pair: permanently running = 1

No alarm = 0
type: NamedIndividual
value API: noAlarm
value KNX: 0

leading edge (inductive load) = 1
type: NamedIndividual
value API: leadingEdge(inductiveLoad)
value KNX: 1

master = 2
type: NamedIndividual
value API: master
value KNX: 2

PER-SEC
type: Unit
type: NamedIndividual
symbol: /s

Combined Status HVA
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 22.102: Combined Status HVA
subject: 22.102
subject: Combined Status HVA
dpt bit size max: 16
dpt major number: 22
datapoint type minor number: 102
is assembled with: type.dpt.field.22.102.i6.ForcedPosition
is assembled with: type.dpt.field.22.102.i0.CurrentValvePosition
is assembled with: type.dpt.field.22.102.i4.ServiceMode
is assembled with: type.dpt.field.22.102.i7.LockedPosition
is assembled with: type.dpt.field.22.102.i9.Reserved
is assembled with: type.dpt.field.22.102.i1.ShortCircuit
is assembled with: type.dpt.field.22.102.i2.Overload
is assembled with: type.dpt.field.22.102.i3.ValveKick
is assembled with: type.dpt.field.22.102.i5.ManualOperation
is assembled with: type.dpt.field.22.102.i8.CalibrationMode
label: Combined Status HVA
has communication mode: S

invalid connection number (TSAP) = 16
type: NamedIndividual
value API: invalidConnectionNumber(TSAP)
value KNX: 16

SceneNumber
type: Class
subject: 72
subject: 418.72
subject: SceneNumber
interface object type annotation: 418
label: SceneNumber
property identifier annotation: 72
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Scene Recall
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: SceneNumber
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 72
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type

Level 3 = 3
type: NamedIndividual
value API: level3
value KNX: 3

type.dpt.field.275.101.i2.TempSetpShiftStdby
type: Datapoint Type Field
type: NamedIndividual
description: room temperature setpoint shift standby
field index: 2
field name: TempSetpShiftStdby
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: http://qudt.org/vocab/unit/K

Engine
type: EquipmentType
type: NamedIndividual
description: An engine or motor is a machine designed to convert one or more forms of energy into mechanical energy.

Geographical Location
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 255.001: Geographical Location
subject: 255.1
subject: 255.001
subject: Geographical Location
dpt bit size max: 64
dpt major number: 255
datapoint type minor number: 1
is assembled with: type.dpt.field.255.1.i0.Latitude
is assembled with: type.dpt.field.255.1.i1.Longitude
label: Geographical Location
has communication mode: S

type.dpt.field.209.101.i2.ShiftLoadPriority
type: NamedIndividual
type: Datapoint Type Field
description: shift load priority
field index: 2
field name: ShiftLoadPriority
field size: 1
includes DPT: Bool

Switch On Off Red
type: Class
subject: Switch On Off Red
subject: SOO_R
subject: 56
subject: 423.56
interface object type annotation: 423
label: Switch On Off Red
property identifier annotation: 56
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Red
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 56
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  has value: Switch
  on property: datapointType

Value Electromotive Force
type: NamedIndividual
type: Datapoint Type
description: DPT 14.030: Value of electromotive force
subject: 14.30
subject: 14.030
subject: Value Electromotive Force
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 30
is assembled with: type.dpt.field.14.30.i0
label: Value Electromotive Force
has communication mode: S

type.dpt.field.201.108.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

Conduits
type: Location Usages
type: NamedIndividual
description: Preferably used with an Space.

The visual effect of channel 15 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel15IsInactiv
value KNX: 0

type.dpt.field.21.1000.i1.BiBatMaster
type: NamedIndividual
type: Datapoint Type Field
description: BiBat Master
field index: 1
field name: BiBatMaster
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

type.dpt.field.22.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 16-bit set
field index: 0
field size: 16
field string schema: raw
field type: A[n]

Asset
type: Class
comment: A container for objects in an installation which have a sort of economic value and is owned and managed by an entity, e.g. a service organization.
subclass of: Core Thing
subclass of: Restriction
  all values from: Asset
  on property: contains asset

last actual value = 0
type: NamedIndividual
value API: lastActualValue
value KNX: 0

RainAlarm
type: Class
subject: 51
subject: RainAlarm
subject: 803.51
interface object type annotation: 803
label: RainAlarm
property identifier annotation: 51
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 803
    on property: interface object type
subclass of: Restriction
  has value: alarm
  on property: datapointType
subclass of: Restriction
  has value: qk ph rain volume outside
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: rainfall
      on property: hasStateType
    intersection of: Restriction
      has value: noRainfall
      on property: hasStateType
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph rain volume outside
      on property: refersTo

Cyclically = 1
type: NamedIndividual
value API: cyclically
value KNX: 1

RAD
type: Unit
type: NamedIndividual
symbol: rad

type.dpt.field.525.500.i2.fv.Reserved
type: NamedIndividual
type: Datapoint Type Field
description: Reserved bits
field index: 2
field name: RESERVED
field size: 6
field type: r
includes reserved bit(s): type.bit.reserved

value before locking = 6
type: NamedIndividual
value API: valueBeforeLocking
value KNX: 6

LUX
type: NamedIndividual
type: Unit
symbol: lx

Tariff
type: NamedIndividual
type: Datapoint Type Field
description: Used for reading and setting tariff information from 1 to 254. However, the mapping between tariffs and the DPT values is not standardized. The value 0 equals 'no tariff available'. The value 255 is reserved.
field index: 0
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8 0 254
label: Tariff
unit: UNITLESS

Normal = 2
type: NamedIndividual
value API: normal
value KNX: 2

value according additional parameter = 3
type: NamedIndividual
value API: valueAccordingAdditionalParameter
value KNX: 3

Off/FrostProtection = 4
type: NamedIndividual
value API: offFrostProtection
value KNX: 4

emPowerEnvelope
type: Datapoint Type
type: NamedIndividual
dpt bit size max: 1792
dpt major number: 512
datapoint type minor number: 502
is assembled with: type.dpt.field.512.502.i0.pe.ID
is assembled with: type.dpt.field.512.502.i1.pe.Reserved
is assembled with: type.dpt.field.512.502.i3.pe.LR CNT
is assembled with: type.dpt.field.512.502.i2.pe.CQ
is assembled with: type.dpt.field.512.502.i4.pe.LR

Software
type: Class
comment: A software represents a collection of data or instructions that are installed (hosted) on a Device or Computer and tell it how to work. Software is a generic term used to refer to applications, scripts and programs that run on a Device.
subclass of: Asset

The visual effect of channel 5 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel5IsActive
value KNX: 1

The visual effect of channel 20 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel20IsInactiv
value KNX: 0

oil = 1
type: NamedIndividual
value API: oil
value KNX: 1

BuildingMode
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.002: BuildingMode
subject: BuildingMode
subject: 20.2
subject: 20.002
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 2
is assembled with: type.dpt.field.20.2.i0
label: BuildingMode
has communication mode: S

Standard single-phase = 3
type: NamedIndividual
value API: standardSingle-phase
value KNX: 3

HVAC User Mode active (means DP ‘HVACModeUser’ is different from ‘Auto’) = 1
type: NamedIndividual
value API: hVACUserModeActive(meansDP‘HVACMode
value KNX: 1

type.dpt.field.4.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: character
field index: 0
field size: 8
field string schema: raw
field type: A

type.dpt.field.513.500.i1.rol.C1
type: NamedIndividual
type: Datapoint Type Field
description: roles for commodity GAS
field index: 1
field name: C1
field size: 2
field type: U
includes key value pair: type.kvpair.rolProducer
includes key value pair: type.kvpair.rolConsumerAndProducer
includes key value pair: type.kvpair.rolConsumer
includes key value pair: no role

type.dpt.field.td.i1.ID
type: NamedIndividual
type: Datapoint Type Field
description: identifier of the timer, has to start with 1
field index: 1
field name: ID
field size: 4
field type: U
includes digit: type.digit.u4 1 15

type.dpt.field.psc.i0.SC ID
type: NamedIndividual
type: Datapoint Type Field
description: Identifier of power sequence container
field index: 0
field name: SC_ID
field size: 4
field type: U
includes digit: type.digit.u4

hardware fault = 4
type: NamedIndividual
value API: hardwareFault
value KNX: 4

ComfortProlongEff
type: Class
subject: 100.60
subject: ComfortProlongEff
subject: 60
interface object type annotation: 100
label: ComfortProlongEff
property identifier annotation: 60
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 60
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type
subclass of: Restriction
  has value: State
  on property: datapointType

energy, 100 kJ = 13
type: NamedIndividual
value API: energy,100KJ
value KNX: 13

Type of Temperature Setpoint Protection Mode
type: StateType
type: NamedIndividual
description: This state type expresses that the buildin protection room temperature setpoint is used for temperature control in a room.

type.dpt.field.249.600.i5.AbsoluteColorTemperature
type: NamedIndividual
type: Datapoint Type Field
field index: 5
field name: AbsoluteColorTemperature
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: http://qudt.org/vocab/unit/K

PE2 in progress = 2
type: NamedIndividual
value API: pE2InProgress
value KNX: 2

VarString 8859-1
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 24.001: VarString 8859-1
subject: 24.1
subject: VarString 8859-1
subject: 24.001
dpt bit size max: 312
dpt major number: 24
datapoint type minor number: 1
is assembled with: type.dpt.field.24.1.i0
label: VarString 8859-1
has communication mode: S

Outside Temperature Sensor
type: Class
subject: Outside Temperature Sensor
subject: OTS
subject: 320
interface object type annotation: 320
label: Outside Temperature Sensor
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.320.52
    intersection of: Restriction
      has value: StatusGO
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  all values from: roomTemperatureControl
  on property: is applicable functionality of
subclass of: Restriction
  on class: Class
    intersection of: dpa.320.51
    intersection of: Restriction
      has value: TempOutside
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 320
    on property: interface object type
subclass of: Restriction
  on class: dpa.320.51
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.320.52
  on property: isComposedByOutput

Euridis Communication Interface Status
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.1204: Euridis Communication Interface Status
subject: 20.1204
subject: Euridis Communication Interface Status
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1204
is assembled with: type.dpt.field.20.1204.i0
label: Euridis Communication Interface Status
has communication mode: S

Value Wsp
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 9.005: Value Wsp
subject: 9.5
subject: 9.005
subject: Value Wsp
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 5
is assembled with: type.dpt.field.9.5.i0
label: Value Wsp
has communication mode: S

Room Setpoint Manager HVAC-Mode Driven
type: Class
subject: 100
subject: RSMHD
subject: Room Setpoint Manager HVAC-Mode Driven
interface object type annotation: 100
label: Room Setpoint Manager HVAC-Mode Driven
is incomplete: true
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpCoolEff
    intersection of: Restriction
      has value: TempRoomSetpCoolEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.384.54
    intersection of: Restriction
      has value: ComfortPushbutton
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.100.54
    intersection of: Restriction
      has value: TempRoomSetpSetCoolEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpSetHeatEff
    intersection of: Restriction
      has value: TempRoomSetpSetHeatEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Class
      union of: EnableComfort
      union of: dpa.110.53
    intersection of: Restriction
      has value: EnableComfort
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpUserOffsetEff
    intersection of: Restriction
      has value: TempRoomSetpUserOffsetEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: HVACModeUser
    intersection of: Restriction
      has value: HVACModeUser
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: ComfortProlongEff
    intersection of: Restriction
      has value: ComfortProlongEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: HVACModeUserEff
    intersection of: Restriction
      has value: HVACModeUserEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.384.51
    intersection of: Restriction
      has value: TempRoomSetpUserAbs
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: HVACModeEff
    intersection of: Restriction
      has value: HVACModeEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.121.52
    intersection of: Restriction
      has value: TempRoomSetpLoadShedShift
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.100.52
    intersection of: Restriction
      has value: HVACModeEffNext
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.343.51
    intersection of: Restriction
      has value: WindowStatus
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.115.63
    intersection of: Restriction
      has value: TempRoomSetpSetCoolShift
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpSetHeatShift
    intersection of: Restriction
      has value: TempRoomSetpSetHeatShift
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Class
      union of: HVACMode
    intersection of: Restriction
      has value: HVACMode
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpUserAbsEff
    intersection of: Restriction
      has value: TempRoomSetpUserAbsEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpUserOffset
    intersection of: Restriction
      has value: TempRoomSetpUserOffset
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpHeatEff
    intersection of: Restriction
      has value: TempRoomSetpHeatEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Class
      union of: PresenceStatus
      union of: dpa.391.51
    intersection of: Restriction
      has value: PresenceStatus
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.121.51
    intersection of: Restriction
      has value: TempRoomSetpTariffShift
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Class
      union of: HVACModeNext
      union of: dpa.110.52
    intersection of: Restriction
      has value: HVACModeNext
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.384.53
    intersection of: Restriction
  on property: is composed by input
subclass of: Class

Unlocked State
type: StateType
type: NamedIndividual
description: This state type expresses that an equipment is in an unlocked state. Typically, this means that the equipment reacts to new input commands as intended. This state type is the inverse of the 'locked' state type.

type.dpt.field.20.605.i0
type: NamedIndividual
type: Datapoint Type Field
description: SwitchPBModel
field index: 0
field size: 8
field type: N
includes key value pair: two PBs/binary inputs mode = 2
includes key value pair: type.kvpair.20.605.i0.1

The visual effect of channel 3 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel3IsInactive
value KNX: 0

type.dpt.field.30.1010.i8.ActivationStateOfChannel9
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 9
field index: 8
field name: ActivationStateOfChannel9
field size: 1
field type: B
includes key value pair: The visual effect of channel 9 is active = 1
includes key value pair: type.kvpair.30.1010.i8.0

type.dpt.field.253.600.i12.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 12
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.22.102.i6.ForcedPosition
type: NamedIndividual
type: Datapoint Type Field
description: Forced Position
field index: 6
field name: ForcedPosition
field size: 1
field type: B
includes key value pair: not forced = 0
includes key value pair: forced = 1

The visual effect of channel 4 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel4IsInactive
value KNX: 0

type.dpt.field.512.510.i2.smddb.TRAN CNT
type: NamedIndividual
type: Datapoint Type Field
description: number of transitions
field index: 2
field name: TRAN_CNT
field size: 4
field type: U
includes digit: type.digit.u4

type.dpt.field.12.1200.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: U
includes digit: type.digit.u32
unit: http://qudt.org/vocab/unit/L

type.dpt.field.253.600.i8.cC
type: Datapoint Type Field
type: NamedIndividual
description: Shall specify whether the colour shall be increased or decreased.
field index: 8
field name: cC
field size: 1
field type: B
includes key value pair: type.kvpair.decrease
includes key value pair: type.kvpair.increase

Relative Set Value Control White
type: Class
subject: 66
subject: Relative Set Value Control White
subject: 423.66
subject: RSC_W
interface object type annotation: 423
label: Relative Set Value Control White
property identifier annotation: 66
subclass of: Restriction
  has value: controlDimming
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 66
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity White
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

is change of value of
type: ObjectProperty
comment: The value of the target point is sent as an update notification (triggered). The trigger is defined by the metadata source datapoint value.
sub property of: isMetaDataOf

volume flow, 1 ml/s = 75
type: NamedIndividual
value API: volumeFlow,1Mls
value KNX: 75

Up Down
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.008: Up Down
subject: 1.8
subject: Up Down
subject: 1.008
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 8
is assembled with: Up / Down
label: Up Down
has communication mode: S

application program data
type: DatatypeProperty
comment: A parent data property, used to express any kind of generic data that relates to an application program.
domain: ApplicationProgram

type.dpt.field.14.65.i0
type: Datapoint Type Field
type: NamedIndividual
description: speed
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: M-PER-SEC

SwitchOnOff
type: Class
subject: SOO
subject: 52
subject: 417.52
subject: SwitchOnOff
interface object type annotation: 417
label: SwitchOnOff
property identifier annotation: 52
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 417
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind

Heat/Cool Z
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 200.100: Heat/Cool Z
subject: Heat/Cool Z
subject: 200.100
dpt bit size max: 16
dpt major number: 200
datapoint type minor number: 100
is assembled with: type.dpt.field.200.100.i1.HeatCool
is assembled with: type.dpt.field.200.100.i0.StatusCommand
label: Heat/Cool Z
has communication mode: LTE

Actual Dimming Value Red
type: Class
subject: 423.83
subject: Actual Dimming Value Red
subject: 83
subject: ASV_R
interface object type annotation: 423
label: Actual Dimming Value Red
property identifier annotation: 83
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 83
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Red
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: Scaling
  on property: datapointType

Value Phase AngleDeg
type: NamedIndividual
type: Datapoint Type
description: DPT 14.055: Value of phase angle (in degrees)
subject: 14.55
subject: 14.055
subject: Value Phase AngleDeg
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 55
is assembled with: type.dpt.field.14.55.i0
label: Value Phase AngleDeg
has communication mode: S

type.dpt.field.21.106.i3.Cool
type: NamedIndividual
type: Datapoint Type Field
description: Cool
field index: 3
field name: Cool
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

Moving Walkway
type: EquipmentType
type: NamedIndividual
description: Conveyor to move people across a horizontal or inclined plane. A moving walkway, also known as an autowalk, moving pavement, moving sidewalk, people-mover, travolator, or travelator, is a slow-moving conveyor mechanism that transports people across a horizontal or inclined plane over a short to medium distance.

Backup Value = 0
type: NamedIndividual
value API: backupValue
value KNX: 0

type.dpt.field.14.30.i0
type: NamedIndividual
type: Datapoint Type Field
description: electromotive force
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/V

HVACMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.102: HVACMode
subject: HVACMode
subject: 20.102
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 102
is assembled with: type.dpt.field.20.102.i0
label: HVACMode
has communication mode: S

Date Available
type: AnnotationProperty
comment: Date that the resource became or will become available.

HVACMode
type: Class
subject: 104.51
subject: 51
subject: HVACMode
interface object type annotation: 104
label: HVACMode
property identifier annotation: 51
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 104
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation

type.dpt.field.20.108.i0
type: NamedIndividual
type: Datapoint Type Field
description: ValveMode
field index: 0
field size: 8
field type: N
includes key value pair: Cool stage B for cooling with two stages (A + B) = 4
includes key value pair: type.kvpair.20.108.i0.1
includes key value pair: type.kvpair.20.108.i0.3
includes key value pair: Heat stage B for heating with two stages (A + B) = 2
includes key value pair: type.kvpair.20.108.i0.5

type.dpt.field.20.611.i0
type: NamedIndividual
type: Datapoint Type Field
description: LoadTypeDetected
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.611.i0.1
includes key value pair: type.kvpair.20.611.i0.2
includes key value pair: type.kvpair.20.611.i0.5
includes key value pair: type.kvpair.20.611.i0.3
includes key value pair: type.kvpair.20.611.i0.4
includes key value pair: type.kvpair.20.611.i0.6

Order Number
type: DatatypeProperty
type: FunctionalProperty
comment: An identifier to specify the (string based) order number of a vendor product. The order number scheme is vendor specific.
range: string
sub property of: productData

is status of
type: IrreflexiveProperty
type: ObjectProperty
type: AsymmetricProperty
comment: An OP relationship to express the control/status relation, separated in KNX by using different function points (GAs) for each. A function point relates to another function point, with the specific meaning of FP x represents the status value of the (setpoint/comand value) of FP y.
domain: Function Point
range: Function Point
sub property of: is referenced by

type.dpt.field.250.600.i5.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 5
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.22.101.i13.FrostAlarm
type: Datapoint Type Field
type: NamedIndividual
description: FrostAlarm
field index: 13
field name: FrostAlarm
field size: 1
field type: B
includes key value pair: No alarm = 0
includes key value pair: alarm = 1

type.dpt.field.30.1010.i11.ActivationStateOfChannel12
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 12
field index: 11
field name: ActivationStateOfChannel12
field size: 1
field type: B
includes key value pair: type.kvpair.30.1010.i11.0
includes key value pair: type.kvpair.30.1010.i11.1

SwitchOnOffControlCmd
type: Class
subject: 60
subject: 417.60
subject: SwitchOnOffControlCmd
interface object type annotation: 417
label: SwitchOnOffControlCmd
property identifier annotation: 60
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 60
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 417
    on property: interface object type
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo

EnOcean
type: NamedIndividual
type: Protocol

type.dpt.field.525.500.i3.fv.Lower 95PPR
type: NamedIndividual
type: Datapoint Type Field
description: The lower boundary of the range with 95 % certainty the power value is in it
field index: 3
field name: Lower_95PPR
field size: 16
includes DPT: Power

Heat Stage A Actuator Current Position
type: Class
subclass of: Function Point
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Scaling
  on property: datapointType

Value Charge DensitySurface
type: NamedIndividual
type: Datapoint Type
description: DPT 14.012: Value of surface charge density
subject: 14.12
subject: 14.012
subject: Value Charge DensitySurface
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 12
is assembled with: type.dpt.field.14.12.i0
label: Value Charge DensitySurface
has communication mode: S

type.dpt.field.240.800.i4.HeightPosition
type: NamedIndividual
type: Datapoint Type Field
description: Height Position
field index: 4
field name: HeightPosition
field resolution: 0.3921566
field size: 8
field type: U
includes digit: type.digit.u8
unit: PERCENT

type.dpt.field.512.508.i3.fltp.PE
type: NamedIndividual
type: Datapoint Type Field
description: list of fill level target profile element
field index: 3
field name: PE
field type: D<n>
includes counter: type.dpt.field.512.508.i2.fltp.PE CNT
includes datapoint field: type.dpt.field.fltp.pe

has channel
type: ObjectProperty
type: InverseFunctionalProperty
inverse of: isChannelOf
comment: To express a relation of a channel, implemented in a device.
domain: Device
range: Channel

Air Supply Control
type: Class
comment: The air supply control Application Function connects and coordinates air and energy flow between air treatment (e.g. air handling unit) and energy consumer (emission control).
subclass of: Restriction
  has value: ventilation
  on property: operatesForTrade
subclass of: airCtrl
subclass of: Distribution Control
subclass of: Restriction
  has value: qk ph air volumeflowrate
  on property: hasQualityKind

error = 1
type: NamedIndividual
value API: error
value KNX: 1

SwitchPBModel
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.605: SwitchPBModel
subject: 20.605
subject: SwitchPBModel
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 605
is assembled with: type.dpt.field.20.605.i0
label: SwitchPBModel
has communication mode: S

Emergency mode active = 5
type: NamedIndividual
value API: emergencyModeActive
value KNX: 5

undefined load command received = 14
type: NamedIndividual
value API: undefinedLoadCommandReceived
value KNX: 14

type.dpt.field.ec.i0
type: NamedIndividual
type: Datapoint Type Field
description: energy constraint
field index: 0
field type: D<n>
includes datapoint field: type.dpt.field.ec.i5.Reserved
includes datapoint field: type.dpt.field.ec.i3.FROM
includes datapoint field: type.dpt.field.ec.i1.AVR
includes datapoint field: type.dpt.field.ec.i0.CQ
includes datapoint field: type.dpt.field.ec.i2.UNTIL
includes datapoint field: type.dpt.field.ec.i4.ID

power, 1 kJ/h = 51
type: NamedIndividual
value API: power,1KJh
value KNX: 51

contains asset
type: ObjectProperty
type: IrreflexiveProperty
type: AsymmetricProperty
inverse of: isAssetOf
comment: To define an asset included in other assets such as several equipment’s/ installations as part of an asset.
domain: Asset
range: Asset

type.dpt.field.21.107.i5.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 5
field name: Reserved
field size: 3
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.207.104.i4.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 4
field name: Reserved
field size: 4
includes reserved bit(s): type.bit.reserved

2.x
type: NamedIndividual
type: Datapoint Type
subject: 2.x
subject: 2.major
dpt bit size max: 2
dpt major number: 2
is assembled with: type.dpt.field.2.x.i0
label: 2.x
has communication mode: S

Steam meter = 5
type: NamedIndividual
value API: steamMeter
value KNX: 5

NUM
type: NamedIndividual
type: Unit
symbol: #

Smart Grid Control
type: Class
comment: Specific Application Function for "Smart Grid control". A Smart grid is a network of transmission lines, substations, transformers that delivers electricity from points of generation to points of consumption with two-way communication to ensure efficient and reliable energy flow.
subclass of: energyCtrl
subclass of: Restriction
  has value: Electrical
  on property: operatesForTrade

Enable
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.003: Enable
subject: Enable
subject: 1.3
subject: 1.003
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 3
is assembled with: Enable
label: Enable
has communication mode: S

HVAC Air Flow Relative Value
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 205.102: HVACAirFlowRel_Z
subject: 205.102
subject: HVAC Air Flow Relative Value
dpt bit size max: 24
dpt major number: 205
datapoint type minor number: 102
is assembled with: type.dpt.field.205.102.i1.HVACAirFlow
is assembled with: type.dpt.field.205.102.i0.StatusCommand
label: HVAC Air Flow Relative Value
has communication mode: LTE

ErrorClass HVAC
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.012: ErrorClass HVAC
subject: 20.012
subject: ErrorClass HVAC
subject: 20.12
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 12
is assembled with: type.dpt.field.20.12.i0
label: ErrorClass HVAC
has communication mode: S

type.dpt.field.265.1.i2.DateAndTime
type: NamedIndividual
type: Datapoint Type Field
description: Date and Time
field index: 2
field name: DateAndTime
field size: 64
includes DPT: DateTime

field name
type: FunctionalProperty
type: DatatypeProperty
comment: Field name, used to define a (user readable) name of a KNX data field as part of an entire datapoint type.
range: string
sub property of: datapointTypeDataField

Door Lock
type: NamedIndividual
type: EquipmentType
description: A door lock is a way to secure a door. A lock is a mechanical or electronic fastening device that is released by a physical object such as a key, keycard, fingerprint, RFID card, security token or coin.

Other Commercial
type: Location Usages
type: NamedIndividual
description: Preferably used with a Building.

type.dpt.field.uf.i0.FC VAL
type: NamedIndividual
type: Datapoint Type Field
description: forecast value
field index: 0
field name: FC_VAL
includes DPT: emForecastValue

Value Electric FieldStrength
type: NamedIndividual
type: Datapoint Type
description: DPT 14.023: Value of electric field strength
subject: Value Electric FieldStrength
subject: 14.023
subject: 14.23
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 23
is assembled with: type.dpt.field.14.23.i0
label: Value Electric FieldStrength
has communication mode: S

Water Temperature Control
type: Class
comment: Application Functions that controls the quantity 'water temperature'.
subclass of: waterCtrl

automatic light control = 0
type: NamedIndividual
value API: automaticLightControl
value KNX: 0

User Presence Switch
type: Class
subject: UPS
subject: 391
subject: User Presence Switch
interface object type annotation: 391
label: User Presence Switch
subclass of: Restriction
  on class: Class
    intersection of: dpa.391.51
    intersection of: Restriction
      has value: PresenceStatus
      on property: point name
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 391
    on property: interface object type
subclass of: Restriction
  on class: dpa.391.51
  on property: isComposedByOutput
  qualified cardinality: 1

The visual effect of channel 7 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel7IsActive
value KNX: 1

Bank Holiday (No working day) = 0
type: NamedIndividual
value API: bankHoliday(NoWorkingDay)
value KNX: 0

type.dpt.field.14.31.i0
type: Datapoint Type Field
type: NamedIndividual
description: energy
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/J

Re-Light / Reset Inhibit = 3
type: NamedIndividual
value API: re-LightResetInhibit
value KNX: 3

Value Magnetization
type: Datapoint Type
type: NamedIndividual
description: DPT 14.049: Value of magnetization
subject: Value Magnetization
subject: 14.49
subject: 14.049
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 49
is assembled with: type.dpt.field.14.49.i0
label: Value Magnetization
has communication mode: S

type.dpt.field.207.100.i0.PrelBurnerValid
type: NamedIndividual
type: Datapoint Type Field
description: validity of PrelBurnerField
field index: 0
field name: PrelBurnerValid
field size: 1
includes DPT: Bool

ControllerConnection = 2
type: NamedIndividual
value API: controllerConnection
value KNX: 2

last modified
type: DatatypeProperty
type: FunctionalProperty
comment: Last modified time stamp, usually generated by Mac. May be used from other concepts, therefore no domain is defined.
range: dateTime

type.dpt.field.7.12.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: MilliA

power, 0,001 kJ/h = 48
type: NamedIndividual
value API: power,0,001KJh
value KNX: 48

type.dpt.field.521.500.i4.ts.Reserved
type: Datapoint Type Field
type: NamedIndividual
description: reserved bits
field index: 4
field name: RESERVED
field size: 3
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.21.105.i0.Fault
type: NamedIndividual
type: Datapoint Type Field
description: Fault
field index: 0
field name: Fault
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

no error = 0
type: NamedIndividual
value API: noError
value KNX: 0

output state is not valid = 0
type: NamedIndividual
value API: outputStateIsNotValid
value KNX: 0

type.dpt.field.207.600.i0.ValidActualValue
type: NamedIndividual
type: Datapoint Type Field
description: Validity of field ActualValue
field index: 0
field name: ValidActualValue
field size: 1
includes DPT: Bool

type.dpt.field.225.3.i1.DelayTime
type: NamedIndividual
type: Datapoint Type Field
description: Delay time until next change of tariff
field index: 1
field name: DelayTime
field size: 16
includes DPT: TimePeriodMin

type.dpt.field.9.5.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16 0 670433
unit: M-PER-SEC

The visual effect of channel 7 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel7IsActive
value KNX: 1

Value Angular Momentum
type: Datapoint Type
type: NamedIndividual
description: DPT 14.008: Value of angular momentum
subject: Value Angular Momentum
subject: 14.8
subject: 14.008
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 8
is assembled with: type.dpt.field.14.8.i0
label: Value Angular Momentum
has communication mode: S

Heating
type: NamedIndividual
type: Trade
description: The transfer of energy to a space or to the air by the existence of a temperature gradient between the source and the space or air. This process may take different forms, e.g. conduction, convection or radiation.

CombinedStatus_HVA_CoolB
type: Class
subject: CombinedStatus_HVA_CoolB
subject: 73
subject: 399.73
interface object type annotation: 399
label: CombinedStatus_HVA_CoolB
property identifier annotation: 73
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: forced
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  has value: Combined Status HVA
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: Override Mode Manual
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Defect Short Circuit
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: opened
      on property: hasStateType
    intersection of: Restriction
      has value: closed
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 73
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateCalibration
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateDefectOverload
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType

HVACModeAct
type: Class
subject: 53
subject: HVACModeAct
subject: 397.53
interface object type annotation: 397
label: HVACModeAct
property identifier annotation: 53
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: HVACMode
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

TempRoomSetpUserOffsetEff
type: Class
subject: 100.58
subject: 58
subject: TempRoomSetpUserOffsetEff
interface object type annotation: 100
label: TempRoomSetpUserOffsetEff
property identifier annotation: 58
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 58
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: HVAC relative Temperature
  on property: datapointType

Air
type: PhenomenonType
type: NamedIndividual
description: The atmosphere of Earth or air is the layer of gases retained by Earth's gravity that surrounds the planet and forms its planetary atmosphere.

The visual effect of channel 20 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel20IsActive
value KNX: 1

The visual effect of channel 1 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel1IsActive
value KNX: 1

Building protection = 2
type: NamedIndividual
value API: buildingProtection
value KNX: 2

Switch On Off White
type: Class
subject: SOO_W
subject: 65
subject: 423.65
subject: Switch On Off White
interface object type annotation: 423
label: Switch On Off White
property identifier annotation: 65
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 65
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity White
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind

TempRoomSetpCoolEff
type: Class
subject: 100.56
subject: TempRoomSetpCoolEff
subject: 56
interface object type annotation: 100
label: TempRoomSetpCoolEff
property identifier annotation: 56
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 56
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type

Lower Limit
type: NamedIndividual
value API: LowerLimit
value KNX: 1

type.dpt.field.20.6.i0
type: NamedIndividual
type: Datapoint Type Field
description: ApplicationArea
field index: 0
field size: 8
field type: N
includes key value pair: Lighting = 20
includes key value pair: HVAC general FBs = 10
includes key value pair: type.kvpair.20.6.i0.30
includes key value pair: type.kvpair.20.6.i0.14
includes key value pair: type.kvpair.20.6.i0.0
includes key value pair: type.kvpair.20.6.i0.50
includes key value pair: HVAC Hot Water Heating = 11
includes key value pair: type.kvpair.20.6.i0.12
includes key value pair: type.kvpair.20.6.i0.40
includes key value pair: system and functions of common interest = 1
includes key value pair: HVAC Terminal Units = 13

type.dpt.field.229.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: 4-1-1 byte combined information
field index: 0
field size: 48
field string schema: raw
field type: A[n]

type.dpt.field.518.500.i3.rmd.RID
type: NamedIndividual
type: Datapoint Type Field
description: identifier of the resource manager. Must be unique within a single KNX system
field index: 3
field name: RID
field size: 16
field type: U
includes digit: type.digit.u16

TimePeriodHrs
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 7.007: TimePeriodHrs
subject: 7.007
subject: TimePeriodHrs
subject: 7.7
dpt bit size max: 16
dpt major number: 7
datapoint type minor number: 7
is assembled with: type.dpt.field.7.7.i0
label: TimePeriodHrs
has communication mode: S

Room Relative Humidity Sensor
type: Class
subject: RRHS
subject: 337
subject: Room Relative Humidity Sensor
interface object type annotation: 337
label: Room Relative Humidity Sensor
is incomplete: true
subclass of: Restriction
  on class: Class
    intersection of: dpa.337.51
    intersection of: Restriction
      has value: HumRelRoom
      on property: point name
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  on class: dpa.337.51
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 337
    on property: interface object type

type.dpt.field.30.1010.i17.ActivationStateOfChannel18
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 18
field index: 17
field name: ActivationStateOfChannel18
field size: 1
field type: B
includes key value pair: type.kvpair.30.1010.i17.1
includes key value pair: The visual effect of channel 18 is inactive = 0

SceneNumber
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 17.001: SceneNumber
subject: SceneNumber
subject: 17.1
subject: 17.001
dpt bit size max: 8
dpt major number: 17
datapoint type minor number: 1
is assembled with: type.dpt.field.17.1.i0.SceneNumber
is assembled with: type.dpt.field.17.1.i1.Reserved
label: SceneNumber
has communication mode: S

Wind
type: PhenomenonType
type: NamedIndividual
description: Wind is the natural movement of air or other gases relative to a planet's surface. Winds are commonly classified by their spatial scale, their speed and direction, the forces that cause them, the regions in which they occur, and their effect.

Roof
type: Locality
type: NamedIndividual
description: A roof is the top covering of a building, including all materials and constructions necessary to support it on the walls of the building or on uprights, providing protection against rain, snow, sunlight, extremes of temperature, and wind.

building protection setpoint = 2
type: NamedIndividual
value API: buildingProtectionSetpoint
value KNX: 2

Free Cool = 10
type: NamedIndividual
value API: freeCool
value KNX: 10

The visual effect of channel 21 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel21IsInactiv
value KNX: 0

20.x
type: NamedIndividual
type: Datapoint Type
subject: 20.major
subject: 20.x
dpt bit size max: 8
dpt major number: 20
is assembled with: type.dpt.field.20.x.i0
label: 20.x
has communication mode: S

TempRoomSetpCoolEff
type: Class
subject: TempRoomSetpCoolEff
subject: 53
subject: 101.53
interface object type annotation: 101
label: TempRoomSetpCoolEff
property identifier annotation: 53
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 101
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType

type.dpt.field.12.1.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: U
includes digit: type.digit.u32
unit: NUM

HVAC Mode Comfort
type: StateType
type: NamedIndividual
description: This state type expresses that the highest level named 'Comfort' is chosen for the HVAC mode. Usually, the 'Comfort' level is associated with an occupied room. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.

State
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.011: State
subject: 1.011
subject: 1.11
subject: State
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 11
is assembled with: State
label: State
has communication mode: S

Video
type: NamedIndividual
type: Trade
description: Video refers to the part of multimedia, which is dealing with visuals. The trade video contains applications for producing and capturing visual signals, such as images or movie clips.

CFL, leading = 5
type: NamedIndividual
value API: cFL,Leading
value KNX: 5

RAD-PER-SEC2
type: NamedIndividual
type: Unit
symbol: rad/s²

Hand Dryer
type: NamedIndividual
type: EquipmentType
description: A hand dryer is an electrical appliance that has the primary function of drying hands.

power, 10000 W = 47
type: NamedIndividual
value API: power,10000W
value KNX: 47

type.dpt.field.ddbc.om.i3.CQ
type: NamedIndividual
type: Datapoint Type Field
description: commodity quantity
field index: 3
field name: CQ
field size: 3
field type: U
includes key value pair: Electric Power L3
includes key value pair: Electric Power L1
includes key value pair: Hydrogen Flow Rate
includes key value pair: type.kvpair.cqHeatThermalPower
includes key value pair: Heat Flow Rate
includes key value pair: Natural Gas Flow Rate
includes key value pair: type.kvpair.cqOilFlowRate
includes key value pair: Electric Power L2

type.dpt.field.25.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 2-nibble set
field index: 0
field size: 8
field string schema: raw
field type: A[n]

Cabinet
type: Location Usages
type: NamedIndividual
description: Room or space used for electrical equipment such as switch cabinets, a fuese box etc. Preferably used with an Space.

Angle
type: NamedIndividual
type: Quantity Kind
description: The abstract notion of angle. Narrow concepts include plane angle and solid angle. While both plane angle and solid angle are dimensionless, they are actually length/length and area/area respectively.

Economy = 3
type: NamedIndividual
is applicable datapoint enum of: hvacModeEconomy
value API: economy
value KNX: 3

readable
type: DatatypeProperty
type: FunctionalProperty
comment: Defines the ability to read a datapoint. The r/w limits set with boolean values true (default) or false. It may be used to limit the access from a 3rd party interface or similar, set by a MaC.
range: boolean

type.digit.u4 0 7
type: NamedIndividual
range max: 7
range min: 0

SwitchOnOffControlCmd
type: Class
subject: SwitchOnOffControlCmd
subject: 60
subject: 418.60
interface object type annotation: 418
label: SwitchOnOffControlCmd
property identifier annotation: 60
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 60
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type

type.dpt.field.ombc.om.i1.AC
type: NamedIndividual
type: Datapoint Type Field
description: abnormal condition
field index: 1
field name: B
field size: 1
field type: B
includes key value pair: type.kvpair.AbnormalCondition
includes key value pair: No abnormal condition

type.dpt.field.27.1.i0.IOO1
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 1
field index: 0
field name: IOO1
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOn
includes key value pair: type.kvpair.outputStateOff

Peak Event Notice
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.1206: Peak Event Notice
subject: Peak Event Notice
subject: 20.1206
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1206
is assembled with: type.dpt.field.20.1206.i0
label: Peak Event Notice
has communication mode: S

J-SEC
type: Unit
type: NamedIndividual
symbol: J⋅s

type.dpt.field.20.610.i0
type: NamedIndividual
type: Datapoint Type Field
description: LoadTypeDetected
field index: 0
field size: 8
field type: N
includes key value pair: CFL, leading = 5
includes key value pair: type.kvpair.20.610.i0.6
includes key value pair: leading edge (inductive load) = 1
includes key value pair: calibration pending, waiting on trigger = 4
includes key value pair: type.kvpair.20.610.i0.0
includes key value pair: type.kvpair.20.610.i0.2
includes key value pair: type.kvpair.20.610.i0.8
includes key value pair: type.kvpair.20.610.i0.7
includes key value pair: detection not possible or error = 3

type.dpt.field.230.1000.i2.IdentNumber
type: Datapoint Type Field
type: NamedIndividual
description: IdentNumber
field index: 2
field name: IdentNumber
field size: 32
field type: U
includes digit: type.digit.u32

no error = 0
type: NamedIndividual
value API: noError
value KNX: 0

type.dpt.field.20.1205.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.1205.i0.1
includes key value pair: Registered (S-FSK) - reserved (G3-PLC) = 2
includes key value pair: type.kvpair.20.1205.i0.0

type.dpt.field.8.1.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 16
field type: V
includes digit: type.digit.s16
unit: NUM

Succeeded
type: NamedIndividual
value API: Succeeded
value KNX: 4

type.dpt.field.202.2.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

type.dpt.field.13.1201.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 32
field type: V
includes digit: type.digit.s32
unit: M3

Breaker Status
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.1203: Breaker Status
subject: Breaker Status
subject: 20.1203
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1203
is assembled with: type.dpt.field.20.1203.i0
label: Breaker Status
has communication mode: S

Fan Control
type: Class
comment: A specific Application Function that controls, for example, the speed of a fan.
subclass of: equipmentCtrl

volume flow, 0,1 l/min = 67
type: NamedIndividual
value API: volumeFlow,0,1Lmin
value KNX: 67

TempReturnAir
type: Class
subject: 51
subject: 323.51
subject: TempReturnAir
interface object type annotation: 323
label: TempReturnAir
property identifier annotation: 51
subclass of: Restriction
  has value: qk ph air temperature returnsection
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature returnsection
      on property: refersTo
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 323
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.lb.lbe.i1.FLR
type: Datapoint Type Field
type: NamedIndividual
description: the range of the fill level the leakage rate (LR) realtes to
field index: 0
field name: FLR
includes DPT: emFillLevelRange

type.dpt.field.27.1.i30.MaskBitIOO15
type: NamedIndividual
type: Datapoint Type Field
description: Mask Bit Info On Off Output 15
field index: 30
field name: MaskBitIOO15
field size: 1
field type: B
includes key value pair: output state is not valid = 0
includes key value pair: output state is valid = 1

type.dpt.field.512.505.i3.ps.I
type: NamedIndividual
type: Datapoint Type Field
description: Indicator whether sequence is interruptible or not
field index: 3
field name: I
field size: 1
field type: B
includes key value pair: sequence interruptible
includes key value pair: sequence not interruptible

Diagnostic Point
type: PointInterface
type: NamedIndividual
description: The tag represents information for a logical point, a diagnostic point that serves for monitoring.

cooling = 0
type: NamedIndividual
value API: cooling
value KNX: 0

type.dpt.field.265.11.i2.DateAndTime
type: NamedIndividual
type: Datapoint Type Field
description: Date and Time
field index: 2
field name: DateAndTime
field size: 64
includes DPT: DateTime

Scene AB
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.022: Scene AB
subject: 1.22
subject: 1.022
subject: Scene AB
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 22
is assembled with: Scene AB
label: Scene AB
has communication mode: S

Liquid
type: PhenomenonType
type: NamedIndividual
description: Substance with definite volume but takes the shape of its container

Light Dimming Sensor Basic
type: Class
subject: LDSB
subject: 420
subject: Light Dimming Sensor Basic
interface object type annotation: 420
label: Light Dimming Sensor Basic
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: ActualDimming-Value
    intersection of: Restriction
      has value: ActualDimming-Value
      on property: point name
  on property: is composed by input
subclass of: Restriction
  all values from: Class
    union of: User Light Switching
    union of: dimLight
  on property: is applicable functionality of
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TimedStartStop
    intersection of: Restriction
      has value: TimedStartStop
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  on class: Class
    intersection of: dpa.420.61
    intersection of: Restriction
      has value: SwitchOnOff
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.420.63
    intersection of: Restriction
      has value: AbsSetvalueControl
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.420.53
    intersection of: Restriction
      has value: InfoOnOff
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.420.62
    intersection of: Restriction
      has value: RelSetvalueControl
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: ControlModeUser
    intersection of: Restriction
      has value: ControlModeUser
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.420.54
    intersection of: Restriction
      has value: ControlModeEff
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: ControlModeUser
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: TimedStartStop
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.420.63
  on property: isComposedByOutput
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 420
    on property: interface object type
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.420.62
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.420.54
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: ActualDimming-Value
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.420.53
  on property: is composed by input
subclass of: Restriction
  on class: dpa.420.61
  on property: isComposedByOutput
  qualified cardinality: 1

type.dpt.field.22.102.i8.CalibrationMode
type: NamedIndividual
type: Datapoint Type Field
description: Calibration Mode
field index: 8
field name: CalibrationMode
field size: 1
field type: B
includes key value pair: type.kvpair.active
includes key value pair: Not active = 0

SwitchOn message sent = 2
type: NamedIndividual
value API: switchOnMessageSent
value KNX: 2

type.dpt.field.22.101.i6.StatusStopOptim
type: NamedIndividual
type: Datapoint Type Field
description: StatusStopOptim
field index: 6
field name: StatusStopOptim
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.201.109.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

type.dpt.field.225.2.i0.Percent
type: NamedIndividual
type: Datapoint Type Field
description: percent
field index: 0
field name: Percent
field size: 8
includes DPT: Scaling

Off = 6
type: NamedIndividual
value API: off
value KNX: 6

ActuatorConnectType
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.020: ActuatorConnectType
subject: 20.20
subject: 20.020
subject: ActuatorConnectType
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 20
is assembled with: type.dpt.field.20.20.i0
label: ActuatorConnectType
has communication mode: S

V-PER-M
type: NamedIndividual
type: Unit
symbol: V/m

Light Current Status
type: Class
disjoint with: LightSwitchRequest
subclass of: Restriction
  has value: qk ph light illuminance
  on property: observesPhenomenonQualityKind
subclass of: Restriction
  all values from: LightSwitchRequest
  on property: is status of
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: On State
      on property: hasStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: measuresEquipmentQualityKind
subclass of: Restriction
  has value: lighting
  on property: operatesForTrade

type.dpt.field.21.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 8-bit set
field index: 0
field size: 8
field string schema: raw
field type: A[n]

has tag
type: ObjectProperty
inverse of: isTagOf
comment: A parent OP relationship to express a general relation to a tag. The relationship specifies the OWL range class :Tag, allowing to express any relation to one of the individuals as part of the sub classes of :Tag. As it is also just a generic top OP of specialized (sub) OP relationship predicates, only the latter SHOULD be used.
range: Tag

control = 1
type: NamedIndividual
value API: control
value KNX: 1

type.dpt.field.ddbc.om.i4.OME
type: NamedIndividual
type: Datapoint Type Field
description: list of operation mode elements
field index: 4
field name: OME
field type: D<n>
includes counter: type.dpt.field.ddbc.om.i2.OME CNT
includes datapoint field: type.dpt.field.ddbc.ome

KiloW
type: NamedIndividual
type: Unit
symbol: kW

type.dpt.field.30.1010.i9.ActivationStateOfChannel10
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 10
field index: 9
field name: ActivationStateOfChannel10
field size: 1
field type: B
includes key value pair: The visual effect of channel 10 is active = 1
includes key value pair: type.kvpair.30.1010.i9.0

Valve (gas or water) = 33
type: NamedIndividual
value API: valve(gasOrWater)
value KNX: 33

false = 0
type: NamedIndividual
value API: false
value KNX: 0

Office
type: Location Usages
type: NamedIndividual
description: An office is a space where an organization's employees perform administrative work in order to support and realize objects and goals of the organization. Preferably used with a Building or Room.

type.dpt.field.265.11.i1.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: Reserved
field size: 7
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.217.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: datapoint type version
field index: 0
field size: 16
field string schema: raw
field type: A[n]

HeatCoolModeAct
type: Class
subject: HeatCoolModeAct
subject: 399.109
subject: 109
interface object type annotation: 399
label: HeatCoolModeAct
property identifier annotation: 109
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 109
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: heatpCool
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: controlModeHeating
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation

TempRoom
type: Class
subject: TempRoom
subject: 321.51
subject: 51
interface object type annotation: 321
label: TempRoom
property identifier annotation: 51
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 321
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.21.102.i3.TempReturnLimit
type: NamedIndividual
type: Datapoint Type Field
description: TempReturnLimit
field index: 3
field name: TempReturnLimit
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

Active State
type: StateType
type: NamedIndividual
description: This state type expresses that an equipment, an alarm or a certain situation is active. An active equipment is fulfilling its intended functionality, whereas an active alarm means that the alarm state was triggered. An active situation means that a certain state has been reached. The tag 'Active State' is often used for situations that feature an enumeration of possible states (e.g. operational states, control modes, HVAC modes, ...) to make a boolean statement about one of these states. The state type 'Active State' is the inverse of the 'Inactive State' state type.

Phase L3
type: Locality
type: NamedIndividual
description: Refers to the third phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.

Absolute Set Value Control White
type: Class
subject: 423.67
subject: 67
subject: ASV_W
subject: Absolute Set Value Control White
interface object type annotation: 423
label: Absolute Set Value Control White
property identifier annotation: 67
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 67
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity White
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

Storage Tank
type: EquipmentType
type: NamedIndividual
description: Tank used to store a substance for temporary holding. For example, a fuel tank (also called a petrol tank or gas tank) is a safe container for flammable fluids.

HVACModeEffNext
type: Class
subject: 82
subject: 398.82
subject: HVACModeEffNext
interface object type annotation: 398
label: HVACModeEffNext
property identifier annotation: 82
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: qk ph temporal delay
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 82
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type
subclass of: Restriction
  has value: hvacModeNext
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph temporal delay
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

Duration
type: NamedIndividual
type: Quantity Kind
description: 'Duration' is the length of a time interval, i.e. the amount of time that passes between two distinct points in time.

15 s = 6
type: NamedIndividual
value API: 15S
value KNX: 6

Lighting = 20
type: NamedIndividual
value API: lighting
value KNX: 20

18.x
type: NamedIndividual
type: Datapoint Type
subject: 18.major
subject: 18.x
dpt bit size max: 8
dpt major number: 18
is assembled with: type.dpt.field.18.x.i0
label: 18.x
has communication mode: S

type.dpt.field.11.1.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 3
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.241.800.i13.ValidSlatsPos
type: NamedIndividual
type: Datapoint Type Field
description: Validity slats pos.
field index: 13
field name: ValidSlatsPos
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

CalibrationMode
type: Class
subject: 400.72
subject: CalibrationMode
subject: 72
interface object type annotation: 400
label: CalibrationMode
property identifier annotation: 72
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 72
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 400
    on property: interface object type
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateCalibration
      on property: relatesToStateType

type.dpt.field.26.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 8-bit set
field index: 0
field size: 8
field string schema: raw
field type: A[n]

Cool = 3
type: NamedIndividual
value API: cool
value KNX: 3

Other
type: Location Usages
type: NamedIndividual
description: Used with any location type.

type.dpt.field.27.1.i15.IOO16
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 16
field index: 15
field name: IOO16
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOff
includes key value pair: type.kvpair.outputStateOn

configuration fault = 3
type: NamedIndividual
value API: configurationFault
value KNX: 3

has space
type: ObjectProperty
inverse of: isSpaceOf
comment: A strong OP relationship to express a relation to a space contained in a location.
domain: Class
  union of: Building
  union of: Floor
  union of: Space
range: Space
sub property of: has location

has location
type: AsymmetricProperty
type: InverseFunctionalProperty
type: IrreflexiveProperty
type: ObjectProperty
inverse of: is location of
comment: A relation to a subclass of a location, e.g. a room as spatial sub-location of a floor.
domain: Location
range: Location
sub property of: refersTo

Binary Value Control
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 2.006: Binary Value Control
subject: 2.6
subject: Binary Value Control
subject: 2.006
dpt bit size max: 2
dpt major number: 2
datapoint type minor number: 6
is assembled with: type.dpt.field.2.x.i1.c
is assembled with: Binary Value
label: Binary Value Control
has communication mode: S

Current Time
type: Class
subclass of: Restriction
  has value: qk ph temporal time site
  on property: acts on phenomenon quality kind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk ph temporal time site
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Function Point
subclass of: Restriction
  has value: TimeOfDay
  on property: datapointType

Operational State Defect Short Circuit
type: NamedIndividual
type: StateType
description: This state type is a special type of a defect state. It expresses that the actual device hosting the datapoint is not working properly due to a short circuit. Thus, no valid value is available at the datapoint.

PowerDensity
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 9.022: PowerDensity
subject: 9.022
subject: PowerDensity
subject: 9.22
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 22
is assembled with: type.dpt.field.9.22.i0
label: PowerDensity
has communication mode: S

stop = 4
type: NamedIndividual
value API: stop
value KNX: 4

Electric Power L1
type: NamedIndividual
value API: ElectricPowerL1
value KNX: 0

emStateMachineFRBC
type: NamedIndividual
type: Datapoint Type
dpt bit size max: 1792
dpt major number: 512
datapoint type minor number: 507
is assembled with: type.dpt.field.512.507.i4.smfrbc.OM
is assembled with: type.dpt.field.512.507.i0.smfrbc.COM
is assembled with: type.dpt.field.512.507.i1.smfrbc.OM CNT
is assembled with: type.dpt.field.512.507.i2.smfrbc.TRAN CNT
is assembled with: type.dpt.field.512.507.i3.smfrbc.Reserved
is assembled with: type.dpt.field.512.507.i5.smfrbc.TRAN

type.dpt.field.19.1.i6.ND
type: NamedIndividual
type: Datapoint Type Field
description: No Date
field default: 0
field index: 6
field name: ND
field size: 1
field type: B
includes key value pair: Month and Day of Month fields valid = 0
includes key value pair: type.kvpair.19.1.i6.1

Air Quality Control
type: Class
comment: Application functions that controls the quantity 'air quality'.
subclass of: airCtrl

type.dpt.field.16.0.i0.stringascii
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: stringascii
field size: 112
field string schema: us-ascii
field type: A
includes DPT: charascii
unit: UNITLESS

type.dpt.field.22.1010.i6.ActivationStateOfChannel7
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 7
field index: 6
field name: ActivationStateOfChannel7
field size: 1
field type: B
includes key value pair: type.kvpair.22.1010.i6.1
includes key value pair: type.kvpair.22.1010.i6.0

Room Temperature Setpoint Manager
type: Class
subject: RTSM
subject: 398
subject: Room Temperature Setpoint Manager
interface object type annotation: 398
label: Room Temperature Setpoint Manager
subclass of: Restriction
  on class: Class
    intersection of: HVACModeUser
    intersection of: Restriction
      has value: HVACModeUser
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.54
    intersection of: Restriction
      has value: ComfortProlongUser
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.92
    intersection of: Restriction
      has value: CombinedStatus_RTSM
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.86
    intersection of: Restriction
      has value: TempRoomSetpUserOffsetEff
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: WindowStatusEff
    intersection of: Restriction
      has value: WindowStatusEff
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.60
    intersection of: Restriction
      has value: TempRoomSetpSetHeatShift
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: ComfortProlongEff
    intersection of: Restriction
      has value: ComfortProlongEff
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: HVACModeUserEff
    intersection of: Restriction
      has value: HVACModeUserEff
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.87
    intersection of: Restriction
      has value: TempRoomSetpCoolEff
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  on class: Class
    intersection of: dpa.398.57
    intersection of: Restriction
      has value: TempRoomSetpUserOffset
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.59
    intersection of: Restriction
      has value: TempRoomSetpSetCool
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.58
    intersection of: Restriction
      has value: TempRoomSetpSetHeat
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: TempRoomSetpSetCoolShift
    intersection of: Restriction
      has value: TempRoomSetpSetCoolShift
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: HVACModeEffNext
    intersection of: Restriction
      has value: HVACModeEffNext
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: WindowStatus
    intersection of: Restriction
      has value: WindowStatus
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.63
    intersection of: Restriction
      has value: PresenceStatus
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.85
    intersection of: Restriction
      has value: TempRoomSetpHeatEff
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.398.65
    intersection of: Restriction
      has value: CombinedStatus_RTC
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Class

autonomous = 0
type: NamedIndividual
value API: autonomous
value KNX: 0

acts on phenomenon quality kind
type: ObjectProperty
inverse of: isPhenomenonQualityKindActedOnBy
comment: A Quality Kind with an actuatable quantity property that addresses a 'phenomenon', and the quantity property can only be indirectly influenced.
range: Phenomenon Quality Kind
sub property of: hasQualityKind

HVACModeUserEff
type: Class
subject: HVACModeUserEff
subject: 81
subject: 398.81
interface object type annotation: 398
label: HVACModeUserEff
property identifier annotation: 81
subclass of: Restriction
  has value: HVACMode
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 81
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type

type.dpt.field.241.800.i11.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 11
field name: Reserved
field size: 3
field type: r
includes reserved bit(s): type.bit.reserved

Switch Current Status
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: On State
      on property: hasStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Function Point

StatusSDHWC
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 21.103: StatusSDHWC
subject: 21.103
subject: StatusSDHWC
dpt bit size max: 8
dpt major number: 21
datapoint type minor number: 103
is assembled with: type.dpt.field.21.103.i2.SolarLoadSufficient
is assembled with: type.dpt.field.21.103.i3.Reserved
is assembled with: type.dpt.field.21.103.i1.SDHWLoadActive
is assembled with: type.dpt.field.21.103.i0.Fault
label: StatusSDHWC
has communication mode: LTE

Open Close
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.009: Open Close
subject: 1.009
subject: Open Close
subject: 1.9
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 9
is assembled with: type.dpt.field.1.9.i0
label: Open Close
has communication mode: S

Distribution Control
type: Class
comment: A specific Application Function that represents a process to provide a supply media to the consumer according to energy demand keeping losses in distribution and generation to an absolute minimum. distrCtrl functions control usually energy flow via water or air in pipes or ducts from energy generation to energy consumer in rooms (emission control).
subclass of: energyCtrl

Enable = 1
type: NamedIndividual
is applicable datapoint enum of: Enabled State
value API: enable
value KNX: 1

type.dpt.field.23.3.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field size: 2
field type: N
includes key value pair: type.kvpair.23.3.i0.0
includes key value pair: type.kvpair.23.3.i0.1
includes key value pair: DownUp = 3
includes key value pair: type.kvpair.23.3.i0.2

Auto = 0
type: NamedIndividual
is applicable datapoint enum of: hvacModeAuto
value API: auto
value KNX: 0

TempRoomSetpSetCoolShift
type: Class
subject: TempRoomSetpSetCoolShift
subject: 61
subject: 398.61
interface object type annotation: 398
label: TempRoomSetpSetCoolShift
property identifier annotation: 61
subclass of: Restriction
  has value: tempRoomSetpSetShiftF16 a4a
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 61
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeProtection
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind

BiBat information = 7
type: NamedIndividual
value API: biBatInformation
value KNX: 7

TempRoomSetpAct
type: Class
subject: TempRoomSetpAct
subject: 153
subject: 261.153
interface object type annotation: 261
label: TempRoomSetpAct
property identifier annotation: 153
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 153
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 261
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind

type.dpt.field.512.510.i4.smddb.OM
type: Datapoint Type Field
type: NamedIndividual
description: list of operation mode elements
field index: 4
field type: D<n>
includes counter: type.dpt.field.512.510.i1.smddbc.OM CNT
includes datapoint field: type.dpt.field.ddbc.om

value KNX
type: DatatypeProperty
comment: Specifies for enumeration DPTs a numerical value, that is used from the KNX system at runtime.
range: integer

ShutterBlinds Mode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.023: ShutterBlinds Mode
subject: ShutterBlinds Mode
subject: 1.23
subject: 1.023
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 23
is assembled with: Shutter and Blinds Mode
label: ShutterBlinds Mode
has communication mode: S

DHWModeNext
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 206.102: DHWModeNext
subject: 206.102
subject: DHWModeNext
dpt bit size max: 24
dpt major number: 206
datapoint type minor number: 102
is assembled with: type.dpt.field.206.102.i1.Time
is assembled with: type.dpt.field.206.102.i0.DHWmode
label: DHWModeNext
has communication mode: LTE

type.dpt.field.8.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: 2-byte signed value
field index: 0
field size: 16
field type: V
includes digit: type.digit.s16

The visual effect of channel 6 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel6IsInactive
value KNX: 0

notice PE3 in progress = 3
type: NamedIndividual
value API: noticePE3InProgress
value KNX: 3

Quality Kind
type: Class
comment: A quality kind (QK) describes a specific “type of interest” that is related to a value with a continuous, measurable physical quantity. The quantity can be figured out without any other context knowledge from any domain.
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    union of: EquipmentType
    union of: PhenomenonType
  on property: has tag
subclass of: TagSet
subclass of: Restriction
  max qualified cardinality: 1
  on class: Quantity Kind
  on property: has tag
subclass of: Restriction
  all values from: Class
    union of: EquipmentType
    union of: Locality
    union of: PhenomenonType
    union of: Quantity Kind
  on property: has tag

Boiler
type: EquipmentType
type: NamedIndividual
description: A boiler is a closed vessel in which fluid (generally water) is heated. Equipment to generate hot water or steam for heating.

236.x
type: Datapoint Type
type: NamedIndividual
subject: 236.major
subject: 236.x
dpt bit size max: 8
dpt major number: 236
is assembled with: type.dpt.field.236.x.i0
label: 236.x
has communication mode: S

Air Temperature Control
type: Class
comment: Application functions that controls the quantity 'air temperature'.
subclass of: airCtrl

type.dpt.field.207.105.i2.CalibrationMode
type: NamedIndividual
type: Datapoint Type Field
description: actuator is currently in calibration mode
field index: 2
field name: CalibrationMode
field size: 1
includes DPT: State

The visual effect of channel 9 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel9IsActive
value KNX: 1

installation data
type: DatatypeProperty
comment: A parent data property, used to express any kind of generic data that relates to an installation.
domain: Installation

type.dpt.field.521.500.i2.ts.ID
type: NamedIndividual
type: Datapoint Type Field
description: identifier of the timer, needs to be unique within the scope of the state machine
field index: 2
field name: ID
field size: 4
field type: U
includes digit: type.digit.u4

type.digit.u8 0 44
type: NamedIndividual
range max: 44
range min: 0

Undefined = 0
type: NamedIndividual
value API: undefined
value KNX: 0

Value 1 Count
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 6.010: Value 1 Count
subject: 6.10
subject: Value 1 Count
subject: 6.010
dpt bit size max: 8
dpt major number: 6
datapoint type minor number: 10
is assembled with: type.dpt.field.6.10.i0
label: Value 1 Count
has communication mode: S

type.dpt.field.19.1.i9.WD
type: NamedIndividual
type: Datapoint Type Field
description: Working Day
field default: 0
field index: 9
field name: WD
field size: 1
field type: B
includes key value pair: Bank Holiday (No working day) = 0
includes key value pair: type.kvpair.19.1.i9.1

notice PE2 in progress = 2
type: NamedIndividual
value API: noticePE2InProgress
value KNX: 2

type.dpt.field.8.7.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 16
field type: V
includes digit: type.digit.s16
unit: HR

on = 1
type: NamedIndividual
value API: on
value KNX: 1

Upper Limit
type: NamedIndividual
value API: UpperLimit
value KNX: 0

type.dpt.field.254.600.i5.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 5
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

SSSBMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.803: SSSBMode
subject: SSSBMode
subject: 20.803
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 803
is assembled with: type.dpt.field.20.803.i0
label: SSSBMode
has communication mode: S

type.dpt.field.psc.i1.SQ CNT
type: NamedIndividual
type: Datapoint Type Field
description: Number of power sequences in a power sequence container
field index: 1
field name: SQ_CNT
field size: 4
field type: U
includes digit: type.digit.u4

auto = 0
type: NamedIndividual
value API: auto
value KNX: 0

Inactive = 0
type: NamedIndividual
value API: inactive
value KNX: 0

stop sequence interruption
type: NamedIndividual
description: stop sequence interruption
value API: seqInstrStopInterrupt
value KNX: 2

DecimalFactor
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 5.005: DecimalFactor
subject: 5.5
subject: 5.005
subject: DecimalFactor
dpt bit size max: 8
dpt major number: 5
datapoint type minor number: 5
is assembled with: Decimal Factor
label: DecimalFactor
has communication mode: S

no fault = 0
type: NamedIndividual
value API: noFault
value KNX: 0

type.dpt.field.15.0.i3.P
type: NamedIndividual
type: Datapoint Type Field
description: Permission (informs about the access decision made by the controlling device)
field index: 3
field name: P
field size: 1
field type: B
includes key value pair: type.kvpair.15.0.i3.0
includes key value pair: type.kvpair.15.0.i3.1

1,4 s = 3
type: NamedIndividual
value API: 1,4S
value KNX: 3

type.dpt.field.22.103.i7.HeatingModeEnabled
type: NamedIndividual
type: Datapoint Type Field
description: Heating Mode Enabled
field index: 7
field name: HeatingModeEnabled
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

Units for HCA = 110
type: NamedIndividual
value API: unitsForHCA
value KNX: 110

HMI
type: EquipmentType
type: NamedIndividual
description: User interfaces are composed of one or more layers, including a human-machine interface (HMI) that interfaces machines with physical input hardware such as keyboards, mice, or game pads, and output hardware such as computer monitors, speakers, and printers.

Gas
type: PhenomenonType
type: NamedIndividual
description: Substance with neither definite volume nor shape

type.dpt.field.14.53.i0
type: NamedIndividual
type: Datapoint Type Field
description: momentum
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: N-SEC

Bedroom
type: NamedIndividual
type: Location Usages
description: A bedroom or bedchamber is a room situated within a residential or accommodation unit characterised by its usage for sleeping. Preferably used with a Room.

void device type = 255
type: NamedIndividual
value API: voidDeviceType
value KNX: 255

permanently running = 1
type: NamedIndividual
value API: permanentlyRunning
value KNX: 1

ActTargetPosHeatStageA
type: Class
subject: 399.102
subject: ActTargetPosHeatStageA
subject: 102
interface object type annotation: 399
label: ActTargetPosHeatStageA
property identifier annotation: 102
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 102
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind

type.dpt.pe.i0.LR
type: NamedIndividual
type: Datapoint Type Field
description: limit range defining upper and lower power values
field index: 0
field name: LR
field size: 32
includes DPT: emPowerRange

type.dpt.field.9.28.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16 0 670433
unit: KiloM-PER-HR

composes
type: ObjectProperty
inverse of: is composed by
comment: An OP relationship to express a relation from a functional block to datapoints as part of a FB. Such datapoints includes per definition additional semantic information, with this a FB can be composed with its mandatory/optional datapoints.
range: Functional Block
sub property of: isDatapointOf

type.dpt.field.207.600.i4.StaircaseLightingFunction
type: Datapoint Type Field
type: NamedIndividual
description: true = staircase lighting function is active, e.g. via input TimedStartStop.
field index: 4
field name: StaircaseLightingFunction
field size: 1
includes DPT: Bool

type.dpt.field.6.20.i2.d
type: NamedIndividual
type: Datapoint Type Field
description: Status D
field index: 2
field name: d
field size: 1
field type: B
includes key value pair: type.kvpair.set
includes key value pair: clear = 0

power, 0,01 W = 41
type: NamedIndividual
value API: power,0,01W
value KNX: 41

emUsageForecast
type: NamedIndividual
type: Datapoint Type
description: the usage forecast allow the resource manager to communicate planned usage of a storage for a certain period of time in the future
dpt bit size max: 1792
dpt major number: 512
datapoint type minor number: 512
is assembled with: type.dpt.field.512.512.i1.uf.FE CNT
is assembled with: type.dpt.field.512.512.i2.uf.FE
is assembled with: type.dpt.field.512.512.i0.uf.START

type.dpt.field.12.102.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: U
includes digit: type.digit.u32
unit: HR

UNITLESS
type: NamedIndividual
type: Unit
symbol: 一

type.dpt.field.244.600.i7.CM
type: NamedIndividual
type: Datapoint Type Field
description: Converter Mode according to the DALI converter state machine
field index: 7
field name: CM
field size: 4
field type: N
includes key value pair: Hardwired inhibit mode active = 3
includes key value pair: type.kvpair.244.600.i7.0
includes key value pair: type.kvpair.244.600.i7.2
includes key value pair: Extended emergency mode active = 6
includes key value pair: Normal mode active, all OK = 1
includes key value pair: Rest mode active = 4
includes key value pair: PDT in progress = 9
includes key value pair: DT in progress = 8
includes key value pair: Emergency mode active = 5
includes key value pair: type.kvpair.244.600.i7.7

type.dpt.field.21.100.i6.RoomHConf
type: NamedIndividual
type: Datapoint Type Field
description: RoomHConf
field index: 6
field name: RoomHConf
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

power, 100 W = 45
type: NamedIndividual
value API: power,100W
value KNX: 45

Enable
type: Class
subject: EN
subject: Enable
subject: 414.61
subject: 61
interface object type annotation: 414
label: Enable
property identifier annotation: 61
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Enabled State
      on property: hasStateType
    intersection of: Restriction
      has value: Disabled State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 61
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 414
    on property: interface object type
subclass of: Restriction
  has value: Enable
  on property: datapointType

comfort prolongation User not active = 0
type: NamedIndividual
value API: comfortProlongationUserNotActive
value KNX: 0

The visual effect of channel 14 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel14IsActive
value KNX: 1

mass flow, 100 kg/h = 85
type: NamedIndividual
value API: massFlow,100Kgh
value KNX: 85

ActualDimming-Value
type: Class
subject: ActualDimming-Value
subject: 55
subject: 420.55
interface object type annotation: 420
label: ActualDimming-Value
property identifier annotation: 55
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 55
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 420
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

HVAC Mode Z
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 201.100: HVAC Mode Z
subject: HVAC Mode Z
subject: 201.100
dpt bit size max: 16
dpt major number: 201
datapoint type minor number: 100
is assembled with: type.dpt.field.201.100.i0.StatusCommand
is assembled with: type.dpt.field.201.100.i1.HVACMode
label: HVAC Mode Z
has communication mode: LTE

last (value before bus power down) = 4
type: NamedIndividual
value API: last(valueBeforeBusPowerDown)
value KNX: 4

type.dpt.field.14.19.i0
type: Datapoint Type Field
type: NamedIndividual
description: electric current
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/A

TempRoomSetpAct
type: Class
subject: TempRoomSetpAct
subject: 153
subject: 257.153
interface object type annotation: 257
label: TempRoomSetpAct
property identifier annotation: 153
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 153
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 257
    on property: interface object type
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo

type.dpt.field.512.507.i2.smfrbc.TRAN CNT
type: NamedIndividual
type: Datapoint Type Field
description: number of transtions
field index: 2
field name: TRAN_CNT
field size: 4
field type: U
includes digit: type.digit.u4

ActPosDemAbs
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 207.104: ActPosDemAbs
subject: 207.104
subject: ActPosDemAbs
dpt bit size max: 16
dpt major number: 207
datapoint type minor number: 104
is assembled with: type.dpt.field.207.104.i0.PrelBurnerValid
is assembled with: type.dpt.field.207.104.i3.EmergDem
is assembled with: type.dpt.field.207.104.i4.Reserved
is assembled with: type.dpt.field.207.104.i1.AbsLoadPriority
is assembled with: type.dpt.field.207.104.i5.ActPosDemAbs
is assembled with: type.dpt.field.207.104.i2.ShiftLoadPriority
label: ActPosDemAbs
has communication mode: LTE

left to right = 0
type: NamedIndividual
value API: leftToRight
value KNX: 0

Sky obstructed from view = 9
type: NamedIndividual
value API: skyObstructedFromView
value KNX: 9

type.dpt.field.256.x.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 128
field string schema: raw
field type: A[n]

type.dpt.field.20.1200.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.1200.i0.3
includes key value pair: Breaker/Valve is released = 2
includes key value pair: type.kvpair.20.1200.i0.1
includes key value pair: Breaker/Valve is closed = 0

Value Heat Capacity
type: Datapoint Type
type: NamedIndividual
description: DPT 14.035: Value of heat capacity
subject: 14.035
subject: Value Heat Capacity
subject: 14.35
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 35
is assembled with: type.dpt.field.14.35.i0
label: Value Heat Capacity
has communication mode: S

Scene AB
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.22.i0.0
includes key value pair: scene B = 1
label: Scene AB

type.dpt.field.241.800.i8.Locked
type: NamedIndividual
type: Datapoint Type Field
description: Movement is locked, e.g. by DeviceLocked input
field index: 8
field name: Locked
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

has site segment
type: ObjectProperty
inverse of: isSiteSegmentOf
comment: A strong OP relationship to express a relation to a site segment contained in a site.
domain: Class
  union of: Site
  union of: SiteSegment
range: SiteSegment
sub property of: has location

Value Force
type: Datapoint Type
type: NamedIndividual
description: DPT 14.032: Value of force
subject: Value Force
subject: 14.32
subject: 14.032
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 32
is assembled with: type.dpt.field.14.32.i0
label: Value Force
has communication mode: S

not forced = 0
type: NamedIndividual
value API: notForced
value KNX: 0

type.dpt.field.21.102.i2.TempFlowLimit
type: NamedIndividual
type: Datapoint Type Field
description: TempFlowLimit
field index: 2
field name: TempFlowLimit
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

OverloadDetection
type: Class
subject: 57
subject: OverloadDetection
subject: 418.57
interface object type annotation: 418
label: OverloadDetection
property identifier annotation: 57
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: operationalStateDefectOverload
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 57
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  has value: alarm
  on property: datapointType

Locality
type: Class
comment: The tag category contains individuals that describe the location related oriented context for a measurement/adustment of an equipment or an observation/actuation of a phenomenon. It expresses a relation to a space (as a place of action or where an equipment is installed.
subclass of: Tag

MO
type: Unit
type: NamedIndividual
symbol: mo

type.dpt.field.21.1010.i2.ActivationStateOfChannel3
type: Datapoint Type Field
type: NamedIndividual
description: Activation state of channel 3
field index: 2
field name: ActivationStateOfChannel3
field size: 1
field type: B
includes key value pair: type.kvpair.21.1010.i2.1
includes key value pair: The visual effect of channel 3 is inactive = 0

Passed max delay exceeded = 2
type: NamedIndividual
value API: passedMaxDelayExceeded
value KNX: 2

type.dpt.field.7.10.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 16
field type: U
includes digit: type.digit.u16
unit: UNITLESS

general device fault (e.g. RAM, EEPROM, UI, watchdog, ...) = 1
type: NamedIndividual
value API: generalDeviceFault(e.g.RAM,EEPROM,U
value KNX: 1

type.dpt.field.203.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 16-Bit Unsigned Value with Status/Command
field index: 0
field size: 24
field string schema: raw
field type: A[n]

The visual effect of channel 15 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel15IsInactiv
value KNX: 0

FadeToControlCmd
type: Class
subject: 66
subject: FadeToControlCmd
subject: 418.66
interface object type annotation: 418
label: FadeToControlCmd
property identifier annotation: 66
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: qk ph temporal duration
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph temporal duration
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 66
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  has value: ScalingSpeed
  on property: datapointType

Fume Hood
type: NamedIndividual
type: EquipmentType
description: Ventilation equipment to limit exposure to hazardous fumes. A fume hood (sometimes called a fume cupboard or fume closet) is a type of local ventilation device that is designed to limit exposure to hazardous or toxic fumes, vapors or dusts.

type.dpt.field.ombc.om.i0.ID
type: Datapoint Type Field
type: NamedIndividual
description: identifier of the operation mode
field index: 0
field name: ID
field size: 4
field type: U
includes digit: type.digit.u4 1 15

Step Code
type: NamedIndividual
type: Datapoint Type Field
description: The number of intervals into which the range of 0 % … 100 % is subdivided, or the break indication.
field default: 4
field index: 0
field name: StepCode
field size: 3
field type: N
includes key value pair: type.kvpair.stepcode.5
includes key value pair: type.kvpair.stepcode.1
includes key value pair: 28% = 2
includes key value pair: 100% = 7
includes key value pair: type.kvpair.stepcode.3
includes key value pair: 84% = 6
includes key value pair: Break = 0
includes key value pair: type.kvpair.stepcode.4
label: Step Code

type.dpt.field.222.101.i1.TempSetpShiftStdby
type: NamedIndividual
type: Datapoint Type Field
description: TempSetpShiftStdby
field index: 1
field name: TempSetpShiftStdby
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: http://qudt.org/vocab/unit/K

Value Capacitance
type: Datapoint Type
type: NamedIndividual
description: DPT 14.011: Value of capacitance
subject: 14.011
subject: 14.11
subject: Value Capacitance
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 11
is assembled with: type.dpt.field.14.11.i0
label: Value Capacitance
has communication mode: S

Delta Volume Cubic Metre
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 13.1201: Delta Volume Cubic Metre
subject: Delta Volume Cubic Metre
subject: 13.1201
dpt bit size max: 32
dpt major number: 13
datapoint type minor number: 1201
is assembled with: type.dpt.field.13.1201.i0
label: Delta Volume Cubic Metre
has communication mode: S

Equipment
type: Class
comment: An equipment is often refered to as "Fixed Asset". Via an object property realationship an equipment has a relation to an element in the location, in most cases inside a building, for example, a whiteboard, a chair, a table, a fan or a motor, which one can assign a product category and/or product type.
subclass of: Restriction
  all values from: Location
  on property: is equipment of
subclass of: Class
  intersection of: Restriction
    all values from: Product
    on property: has product
  intersection of: Restriction
    max qualified cardinality: 1
    on class: Product
    on property: has product
subclass of: Asset
subclass of: Restriction
  all values from: Equipment
  on property: hasPart
subclass of: Restriction
  all values from: Quality Kind
  on property: hasQualityKind

CombinedStatus_HVA_HeatB
type: Class
subject: 399.71
subject: CombinedStatus_HVA_HeatB
subject: 71
interface object type annotation: 399
label: CombinedStatus_HVA_HeatB
property identifier annotation: 71
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateCalibration
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 71
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Locked State
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: Override Mode Manual
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateDefectOverload
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: forced
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  has value: Combined Status HVA
  on property: datapointType

Value MagnetomotiveForce
type: NamedIndividual
type: Datapoint Type
description: DPT 14.050: Value of magneto motive force
subject: 14.050
subject: Value MagnetomotiveForce
subject: 14.50
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 50
is assembled with: type.dpt.field.14.50.i0
label: Value MagnetomotiveForce
has communication mode: S

TempRoomSetpAct
type: Class
subject: 167.53
subject: TempRoomSetpAct
subject: 53
interface object type annotation: 167
label: TempRoomSetpAct
property identifier annotation: 53
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 167
    on property: interface object type
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo

yes = 1
type: NamedIndividual
value API: yes
value KNX: 1

Building Protection = 4
type: NamedIndividual
is applicable datapoint enum of: hvacModeProtection
value API: buildingProtection
value KNX: 4

is quality kind of
type: ObjectProperty
domain: Quantity Kind
range: Quality Kind
sub property of: isTagOf

volume flow, 0,0001 l/min = 64
type: NamedIndividual
value API: volumeFlow,0,0001Lmin
value KNX: 64

237.x
type: NamedIndividual
type: Datapoint Type
subject: 237.major
subject: 237.x
dpt bit size max: 16
dpt major number: 237
is assembled with: type.dpt.field.237.x.i0
label: 237.x
has communication mode: S

Cooling Load meter (inlet) = 10
type: NamedIndividual
value API: coolingLoadMeter(inlet)
value KNX: 10

FanMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.111: FanMode
subject: FanMode
subject: 20.111
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 111
is assembled with: type.dpt.field.20.111.i0
label: FanMode
has communication mode: S

Video
type: Class
comment: Video data and camera management function.
subclass of: monitoring

Normal (no fault) = 0
type: NamedIndividual
value API: normal(noFault)
value KNX: 0

Origin
type: Class
comment: The tag category contains individuals that describe a specific application data source of a point, used in cases where the input of an point is affected from a superordinated application control (instead of the common control loop).
subclass of: Tag

None = 0
type: NamedIndividual
value API: none
value KNX: 0

Shift load priority = 1
type: NamedIndividual
value API: shiftLoadPriority
value KNX: 1

all windows closed = 0
type: NamedIndividual
value API: allWindowsClosed
value KNX: 0

type.dpt.field.254.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: Relative Control RGB
field index: 0
field size: 24
field string schema: raw
field type: A[n]

type.dpt.field.30.1010.i4.ActivationStateOfChannel5
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 5
field index: 4
field name: ActivationStateOfChannel5
field size: 1
field type: B
includes key value pair: type.kvpair.30.1010.i4.0
includes key value pair: The visual effect of channel 5 is active = 1

power, 1000 kJ/h = 54
type: NamedIndividual
value API: power,1000KJh
value KNX: 54

type.dpt.field.249.600.i2.validityOfTimePeriod
type: NamedIndividual
type: Datapoint Type Field
description: validity of the Time Period
field index: 2
field name: validityOfTimePeriod
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

type.dpt.field.7.11.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: MilliM

Security = 30
type: NamedIndividual
value API: security
value KNX: 30

Air Volume Control
type: Class
comment: Application functions that controls the quantity 'air volume'.
subclass of: airCtrl

Ceiling
type: NamedIndividual
type: Locality
description: A ceiling is an overhead interior surface that covers the upper limits of a room.

Version
type: FunctionalProperty
type: DatatypeProperty
comment: An identifier to specify the (numerical) version of an application program.
range: positiveInteger
sub property of: application program data

FuelTypeSet
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 21.104: FuelTypeSet
subject: FuelTypeSet
subject: 21.104
dpt bit size max: 8
dpt major number: 21
datapoint type minor number: 104
is assembled with: type.dpt.field.21.104.i2.SolidState
is assembled with: type.dpt.field.21.104.i1.Gas
is assembled with: type.dpt.field.21.104.i3.Reserved
is assembled with: type.dpt.field.21.104.i0.Oil
label: FuelTypeSet
has communication mode: LTE

type.dpt.field.29.12.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 64
field type: V
includes digit: type.digit.s64
unit: V-A Reactive-HR

MBus BreakerValve State
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.1200: MBus BreakerValve State
subject: MBus BreakerValve State
subject: 20.1200
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1200
is assembled with: type.dpt.field.20.1200.i0
label: MBus BreakerValve State
has communication mode: S

emInstructionStatus
type: Datapoint Type
type: NamedIndividual
dpt bit size max: 24
dpt major number: 515
datapoint type minor number: 500
is assembled with: type.dpt.field.515.500.i0.is.STAT
is assembled with: type.dpt.field.515.500.i1.is.INSTR ID

KiloV-A Reactive-HR
type: NamedIndividual
type: Unit
symbol: kV⋅A{Reactive}⋅hr

VAV
type: NamedIndividual
type: EquipmentType
description: Variable air volume terminal unit. Variable air volume (VAV) is a type of heating, ventilating, and/or air-conditioning (HVAC) system. Unlike constant air volume (CAV) systems, which supply a constant airflow at a variable temperature, VAV systems vary the airflow at a constant temperature.

type.dpt.field.202.1.i0.StatusCommand
type: Datapoint Type Field
type: NamedIndividual
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

inactive = 0
type: NamedIndividual
value API: inactive
value KNX: 0

output state is valid = 1
type: NamedIndividual
value API: outputStateIsValid
value KNX: 1

type.dpt.field.9.11.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: MilliSEC

has proxy
type: AsymmetricProperty
type: ObjectProperty
type: IrreflexiveProperty
inverse of: isProxyFor
property disjoint with: isProxyFor
comment: To define a representative entry point for datapoints with a gateway. With this datapoints in an installation can be exposed for different purposes, such as all datapoints on a 3rd Party API (gateway).
domain: Device
range: Gateway

FanStepUser
type: Class
subject: 75
subject: FanStepUser
subject: 399.75
interface object type annotation: 399
label: FanStepUser
property identifier annotation: 75
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 75
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: fanStage
  on property: datapointType

Slats Actuator
type: EquipmentType
type: NamedIndividual
description: Slats are vertical or horizontal pieces of a window blind. Slats actuator is used to control an actuator equipment to regulate the light incidence (slats position/angle). Don't care if the slats position/angle is internally operated from the actuator by a motor or other means.

Warm water meter = 6
type: NamedIndividual
value API: warmWaterMeter
value KNX: 6

type.dpt.field.9.25.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: L-PER-HR

CoolingOnly = 1
type: NamedIndividual
value API: coolingOnly
value KNX: 1

Value Reactance
type: Datapoint Type
type: NamedIndividual
description: DPT 14.059: Value of reactance
subject: Value Reactance
subject: 14.59
subject: 14.059
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 59
is assembled with: type.dpt.field.14.59.i0
label: Value Reactance
has communication mode: S

type.digit.f16 0 670433
type: NamedIndividual
range max: 670433.0
range min: 0.0

Building in use = 0
type: NamedIndividual
value API: buildingInUse
value KNX: 0

type.dpt.field.229.1.i2.CountVal
type: NamedIndividual
type: Datapoint Type Field
description: CountVal
field index: 2
field name: CountVal
field resolution: 1.0
field size: 32
field type: V
includes digit: type.digit.s32
unit: NUM

Point Function
type: Class
comment: The tag category contains individuals that describe the role of a Point in the control loop of an application function.
subclass of: Tag

POP3
type: Protocol
type: NamedIndividual

disabled (PSU/DPSU fixed off) = 0
type: NamedIndividual
value API: disabled(PSUDPSUFixedOff)
value KNX: 0

Energy Storage Control
type: Class
comment: A specific Application Function to optimize different energy storages.
subclass of: energyCtrl

206.x
type: NamedIndividual
type: Datapoint Type
subject: 206.x
subject: 206.major
dpt bit size max: 24
dpt major number: 206
is assembled with: type.dpt.field.206.x.i0
label: 206.x
has communication mode: LTE

Room Temperature
type: Class
subclass of: Function Point
subclass of: Restriction
  has value: qk ph air temperature room
  on property: observesPhenomenonQualityKind
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1

StatusAct
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 207.105: StatusAct
subject: StatusAct
subject: 207.105
dpt bit size max: 16
dpt major number: 207
datapoint type minor number: 105
is assembled with: type.dpt.field.207.105.i6.ActPos
is assembled with: type.dpt.field.207.105.i2.CalibrationMode
is assembled with: type.dpt.field.207.105.i5.Reserved
is assembled with: type.dpt.field.207.105.i1.ManualOverride
is assembled with: type.dpt.field.207.105.i3.ValveKick
is assembled with: type.dpt.field.207.105.i4.SynchronizationMode
is assembled with: type.dpt.field.207.105.i0.Failure
label: StatusAct
has communication mode: LTE

The visual effect of channel 3 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel3IsInactive
value KNX: 0

Underfloor Heating
type: EquipmentType
type: NamedIndividual
description: Heats a space using pipes or cables embedded beneath floor. The most common kind of radiant heating is underfloor heating. There are three types of underfloor heating: hot air systems, hot water systems and electric systems.

Building
type: Class
disjoint with: Outside
comment: A building represents a whole building that hosts several other elements such as stacked floors or spaces or rooms. The concept can be mapped to a IfcBuilding.
label: Gebäude @de
subclass of: Restriction
  all values from: Room
  on property: hasRoom
subclass of: Location
subclass of: Restriction
  all values from: Space
  on property: has space
subclass of: Restriction
  all values from: Floor
  on property: has floor

type.dpt.field.523.500.i1.sms.ET
type: NamedIndividual
type: Datapoint Type Field
description: timestamp when last transition was executed
field index: 1
field name: ET
field size: 64
includes DPT: DateTime

no error = 0
type: NamedIndividual
value API: noError
value KNX: 0

The visual effect of channel 2 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel2IsActive
value KNX: 1

Value Heat Quantity
type: NamedIndividual
type: Datapoint Type
description: DPT 14.037: Value of heat quantity
subject: Value Heat Quantity
subject: 14.37
subject: 14.037
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 37
is assembled with: type.dpt.field.14.37.i0
label: Value Heat Quantity
has communication mode: S

drive is moving = 0
type: NamedIndividual
value API: driveIsMoving
value KNX: 0

Brightness
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 7.013: Brightness
subject: 7.13
subject: Brightness
subject: 7.013
dpt bit size max: 16
dpt major number: 7
datapoint type minor number: 13
is assembled with: type.dpt.field.7.13.i0
label: Brightness
has communication mode: S

type.dpt.field.253.600.i9.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 9
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

disabled = 0
type: NamedIndividual
value API: disabled
value KNX: 0

Length
type: NamedIndividual
type: Quantity Kind
description: In geometric measurements, length most commonly refers to the estimated dimension of an object. In some contexts, the term "length" is reserved for a certain dimension of an object along which the length is measured.

Scene Recall
type: StateType
type: NamedIndividual
description: This state type expresses that a scene is activated in scene-controlled instrumentations by restoring a previously learnt value. This covers both activating a scene based on a scene number (e.g. 0-63) or by choosing between two scenes (e.g. Scene A or Scene B).

type.dpt.pe.i0
type: NamedIndividual
type: Datapoint Type Field
description: power envelop element
field index: 0
field type: D<n>
includes datapoint field: type.dpt.pe.i1.DUR
includes datapoint field: type.dpt.pe.i0.LR

type.dpt.field.224.100.i0.HVACEmergMode
type: Datapoint Type Field
type: NamedIndividual
description: Actual HVAC Emergency Mode
field index: 0
field name: HVACEmergMode
field size: 8
includes DPT: HVACEmergMode

type.dpt.field.22.100.i2.LegioProtActive
type: Datapoint Type Field
type: NamedIndividual
description: LegioProtActive
field index: 2
field name: LegioProtActive
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

Building not used = 1
type: NamedIndividual
value API: buildingNotUsed
value KNX: 1

1 s = 1
type: NamedIndividual
value API: 1S
value KNX: 1

241.x
type: NamedIndividual
type: Datapoint Type
subject: 241.major
subject: 241.x
dpt bit size max: 32
dpt major number: 241
is assembled with: type.dpt.field.241.x.i0
label: 241.x
has communication mode: S

asynchronous = 0
type: NamedIndividual
value API: asynchronous
value KNX: 0

Historical single-phase = 1
type: NamedIndividual
value API: historicalSingle-phase
value KNX: 1

type.dpt.field.20.106.i0
type: NamedIndividual
type: Datapoint Type Field
description: HVACEmergMode
field index: 0
field size: 8
field type: N
includes key value pair: Normal = 0
includes key value pair: EmergPurge = 3
includes key value pair: type.kvpair.20.106.i0.1
includes key value pair: type.kvpair.20.106.i0.4
includes key value pair: EmergDepressure = 2
includes key value pair: type.kvpair.20.106.i0.5

property identifier annotation
type: AnnotationProperty
comment: In KNX used (numerical) identifier to address a specific property as part of an interface object. The range xsd:unsignedByte supports exactly the KNX value range from 0 to 255. As a note, this is a mirror property to the data property "knx:propertyIdentifier" and must ONLY be used on annotated datapoint (dpa.x) classes, not on the actual individuals!
range: unsignedByte

NumberedSceneControl
type: Class
subject: 417.73
subject: 73
subject: NSC
subject: NumberedSceneControl
interface object type annotation: 417
label: NumberedSceneControl
property identifier annotation: 73
subclass of: Restriction
  has value: sceneControl
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 73
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 417
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Scene Recall
      on property: hasStateType
    intersection of: Restriction
      has value: sceneSave
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation

Time Synchronization
type: Class
comment: Time synchronization coordinates independent clocks on different devices.
subclass of: Plant Management Control

Light colour xyY
type: NamedIndividual
type: Quantity Kind
description: Relates to the light colour value, measured in the xyY colour system. The coordinates x and y define the chromaticity of the colour, whereas the coordinate Y defines the luminance of the color.

Relative Set Value Control Blue
type: Class
subject: RSC_B
subject: Relative Set Value Control Blue
subject: 423.63
subject: 63
interface object type annotation: 423
label: Relative Set Value Control Blue
property identifier annotation: 63
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: chromaticityBlue
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: controlDimming
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 63
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type

Current Date
type: Class
subclass of: Restriction
  has value: date
  on property: datapointType
subclass of: Function Point
subclass of: Restriction
  has value: qk ph temporal datevalue site
  on property: acts on phenomenon quality kind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk ph temporal datevalue site
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1

inactive (no message sent) = 0
type: NamedIndividual
value API: inactive(noMessageSent)
value KNX: 0

energy, 0,1 Wh = 2
type: NamedIndividual
value API: energy,0,1Wh
value KNX: 2

Cool Stage A Actuator Valve Kick
type: Class
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Bool
  on property: datapointType

type.dpt.field.13.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: 4-byte signed value
field index: 0
field size: 32
field type: V
includes digit: type.digit.s32

is equipment type of
type: ObjectProperty
domain: EquipmentType
range: Quality Kind
sub property of: isTagOf

KNX
type: NamedIndividual
type: Protocol

Cloudless = 0
type: NamedIndividual
value API: cloudless
value KNX: 0

type.dpt.field.251.600.i6.W
type: NamedIndividual
type: Datapoint Type Field
description: Colour Level White
field index: 6
field name: W
field resolution: 0.3921566
field size: 8
field type: U
includes digit: type.digit.u8
unit: PERCENT

Occupied = 0
type: NamedIndividual
value API: occupied
value KNX: 0

RF Control Octet and Serial Number or DoA = 2
type: NamedIndividual
value API: rFControlOctetAndSerialNumberOrDoA
value KNX: 2

type.dpt.field.240.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: positions
field index: 0
field size: 24
field string schema: raw
field type: A[n]

Fire Safety
type: NamedIndividual
type: Trade
description: Fire safety deals with preventive actions against fire events (incidents, accidents, and other unwanted conditions) caused by unintentional, human error and/or technical deficiencies, and with the limitation or control of such incidents.

ChangeOverStatus
type: Class
subject: 399.64
subject: 64
subject: ChangeOverStatus
interface object type annotation: 399
label: ChangeOverStatus
property identifier annotation: 64
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: controlModeHeating
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph water temperature pipesection supplysection
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: heatpCool
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 64
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: qk ph water temperature pipesection supplysection
  on property: hasQualityKind

type.dpt.field.uf.i1.DUR
type: Datapoint Type Field
type: NamedIndividual
description: duration
field index: 1
field name: DUR
field size: 16
includes DPT: TimePeriodSec

mass flow, 10000 kg/h = 87
type: NamedIndividual
value API: massFlow,10000Kgh
value KNX: 87

Value Work
type: NamedIndividual
type: Datapoint Type
description: DPT 14.079: Value of work
subject: 14.079
subject: 14.79
subject: Value Work
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 79
is assembled with: type.dpt.field.14.79.i0
label: Value Work
has communication mode: S

type.dpt.field.217.1.i2.MagicNumber
type: NamedIndividual
type: Datapoint Type Field
description: Magic Number
field index: 2
field name: MagicNumber
field resolution: 1.0
field size: 5
field type: U
includes digit: type.digit.u5
unit: NUM

100% = 7
type: NamedIndividual
value API: 100%
value KNX: 7

type.dpt.field.14.1201.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: L-PER-SEC

type.dpt.field.200.100.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

SW fault = 5
type: NamedIndividual
value API: sWFault
value KNX: 5

Value Magnetic Flux
type: Datapoint Type
type: NamedIndividual
description: DPT 14.045: Value of magnetic flux
subject: 14.045
subject: Value Magnetic Flux
subject: 14.45
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 45
is assembled with: type.dpt.field.14.45.i0
label: Value Magnetic Flux
has communication mode: S

power, 10 W = 44
type: NamedIndividual
value API: power,10W
value KNX: 44

simple alarm = 1
type: NamedIndividual
value API: simpleAlarm
value KNX: 1

Year field not valid = 1
type: NamedIndividual
value API: yearFieldNotValid
value KNX: 1

HVAC relative Temperature
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 205.101: TempHVACRel_Z
subject: HVAC relative Temperature
subject: 205.101
dpt bit size max: 24
dpt major number: 205
datapoint type minor number: 101
is assembled with: type.dpt.field.205.101.i1.Temp
is assembled with: type.dpt.field.205.101.i0.StatusCommand
label: HVAC relative Temperature
has communication mode: LTE

5,7 s = 7
type: NamedIndividual
value API: 5,7S
value KNX: 7

type.dpt.field.20.22.i0
type: NamedIndividual
type: Datapoint Type Field
description: power return mode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.22.i0.1
includes key value pair: type.kvpair.20.22.i0.2
includes key value pair: type.kvpair.20.22.i0.0

Rotation Angle
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 8.011: Rotation Angle
subject: 8.11
subject: Rotation Angle
subject: 8.011
dpt bit size max: 16
dpt major number: 8
datapoint type minor number: 11
is assembled with: type.dpt.field.8.11.i0
label: Rotation Angle
has communication mode: S

type.dpt.field.19.1.i17.DayOfMonth
type: Datapoint Type Field
type: NamedIndividual
description: DayOfMonth
field index: 17
field name: DayOfMonth
field resolution: 1.0
field size: 5
field type: U
includes digit: type.digit.u5 1 31
unit: DAY

The visual effect of channel 17 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel17IsInactiv
value KNX: 0

type.dpt.field.pc.i3.LR CNT
type: Datapoint Type Field
type: NamedIndividual
description: number of limit ranges
field index: 3
field name: LR_CNT
field size: 8
field type: U
includes digit: type.digit.u8

TempRoomSetpAct
type: Class
subject: 397.55
subject: 55
subject: TempRoomSetpAct
interface object type annotation: 397
label: TempRoomSetpAct
property identifier annotation: 55
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 55
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind

Hour of day, Minutes and Seconds field valid = 0
type: NamedIndividual
value API: hourOfDay,MinutesAndSecondsFieldVal
value KNX: 0

type.dpt.field.22.1010.i2.ActivationStateOfChannel3
type: Datapoint Type Field
type: NamedIndividual
description: Activation state of channel 3
field index: 2
field name: ActivationStateOfChannel3
field size: 1
field type: B
includes key value pair: type.kvpair.22.1010.i2.1
includes key value pair: type.kvpair.22.1010.i2.0

last downloaded
type: DatatypeProperty
type: FunctionalProperty
comment: Last download time stamp, usually generated by Mac. May be used from other concepts, therefore no domain is defined.
range: dateTime

HVAC User Mode not active = 0
type: NamedIndividual
value API: hVACUserModeNotActive
value KNX: 0

type.dpt.field.255.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: F32F32
field index: 0
field size: 64
field string schema: raw
field type: A[n]

9.x
type: Datapoint Type
type: NamedIndividual
subject: 9.x
subject: 9.major
dpt bit size max: 16
dpt major number: 9
is assembled with: type.dpt.field.9.x.i0
label: 9.x
has communication mode: S

type.dpt.field.219.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: alarm info
field index: 0
field size: 48
field string schema: raw
field type: A[n]

move Up/Down + StepStop mode (blind) = 1
type: NamedIndividual
value API: moveUpDown+StepStopMode(blind)
value KNX: 1

scene B = 1
type: NamedIndividual
value API: sceneB
value KNX: 1

The visual effect of channel 4 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel4IsActive
value KNX: 1

Converter Info Fix
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 250.600: Converter Info Fix
subject: Converter Info Fix
subject: 250.600
dpt bit size max: 24
dpt major number: 250
datapoint type minor number: 600
is assembled with: type.dpt.field.250.600.i7.cCT
is assembled with: type.dpt.field.250.600.i0.BrightnessStepValidity
is assembled with: type.dpt.field.250.600.i3.StepCodeBrightness
is assembled with: type.dpt.field.250.600.i2.Reserved
is assembled with: type.dpt.field.250.600.i8.Reserved
is assembled with: type.dpt.field.250.600.i5.Reserved
is assembled with: type.dpt.field.250.600.i6.StepCodeColourTemperature
is assembled with: type.dpt.field.250.600.i1.ColourStepValidity
is assembled with: type.dpt.field.250.600.i4.cB
label: Converter Info Fix
has communication mode: S

Chromaticity White
type: StateType
type: NamedIndividual
description: This state type expresses that the white part of RGBW light color is referred to. It is mostly used in lighting applications that use the RGBW color model.

Alarming
type: Class
comment: Alarming is the automated alarm management in the event of alarms or faults in plants, subsystems or devices. The application function may contain a list of activ alarms, past alarms, alarm prioritization or sends a notification to recipients (e.g. email).
subclass of: Plant Management Control

type.dpt.field.14.34.i0
type: NamedIndividual
type: Datapoint Type Field
description: frequency, angular (pulsatance)
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: RAD-PER-SEC

Fresh air, e.g. for fancoils = 1
type: NamedIndividual
value API: freshAir,E.g.ForFancoils
value KNX: 1

The visual effect of channel 16 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel16IsInactiv
value KNX: 0

identifier
type: AnnotationProperty
comment: Used to represents an URN.

is room segment of
type: ObjectProperty
domain: RoomSegment
range: Class
  union of: Room
  union of: RoomSegment
sub property of: isSpaceOf

GM-PER-M3
type: NamedIndividual
type: Unit
symbol: g/m³

type.dpt.field.231.1.i1.Language
type: Datapoint Type Field
type: NamedIndividual
description: Language as in DPT_Language-CodeAlpha2_ASCII (234.001) this is ISO 639-1 alpha-2
field index: 1
field name: Language
field size: 16
includes DPT: languageCodeAlpha2ascii

Classroom
type: Location Usages
type: NamedIndividual
description: A classroom or schoolroom is a learning space in which both children and adults learn. Preferably used with a Room.

WindowStatusEff
type: Class
subject: WindowStatusEff
subject: 398.91
subject: 91
interface object type annotation: 398
label: WindowStatusEff
property identifier annotation: 91
subclass of: Restriction
  has value: windowDoor
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 91
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type
subclass of: Restriction
  has value: qk eq window positionvector room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: opened
      on property: hasStateType
    intersection of: Restriction
      has value: closed
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: totalizedValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq window positionvector room
      on property: refersTo

The visual effect of channel 1 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel1IsInactive
value KNX: 0

type.digit.u3
type: NamedIndividual
range max: 7
range min: 0

Cool Stage B Actuator Current Position
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Function Point
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: adjustsEquipmentQualityKind

State
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: Inactive = 0
includes key value pair: type.kvpair.active
label: State

type.dpt.field.21.601.i3.Underload
type: NamedIndividual
type: Datapoint Type Field
description: Underload
field index: 3
field name: Underload
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.209.102.i1.Fault
type: Datapoint Type Field
type: NamedIndividual
description: some failure in the chiller
field index: 1
field name: Fault
field size: 1
includes DPT: Bool

KiloGM
type: NamedIndividual
type: Unit
symbol: kg

type.dpt.field.26.1.i2.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 2
field name: Reserved
field size: 1
field type: r
includes reserved bit(s): type.bit.reserved

Power Envelope Based Control
type: Class
comment: Power Envelope is the aggregated measure of the extreme values of the power output over a period of time. Power Envelope Based Control allows you to set limits to these power envelopes for certain periods of time.
subclass of: Smart Grid Control

Step Control
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 2.007: Step Control
subject: 2.7
subject: 2.007
subject: Step Control
dpt bit size max: 2
dpt major number: 2
datapoint type minor number: 7
is assembled with: type.dpt.field.2.x.i1.c
is assembled with: Step
label: Step Control
has communication mode: S

type.dpt.field.200.100.i1.HeatCool
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: Heat Cool
field size: 8
includes DPT: heatpCool

Colour RGB
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 232.600: Colour RGB
subject: 232.600
subject: Colour RGB
dpt bit size max: 24
dpt major number: 232
datapoint type minor number: 600
is assembled with: type.dpt.field.232.600.i2.R
is assembled with: type.dpt.field.232.600.i0.B
is assembled with: type.dpt.field.232.600.i1.G
label: Colour RGB
has communication mode: S

LockDevice
type: Class
subject: 418.69
subject: LockDevice
subject: 69
interface object type annotation: 418
label: LockDevice
property identifier annotation: 69
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 69
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  has value: Enable
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Locked State
      on property: hasStateType
    intersection of: Restriction
      has value: Unlocked State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind

Wind Sensor
type: Class
subject: WS
subject: Wind Sensor
subject: 802
interface object type annotation: 802
label: Wind Sensor
subclass of: Restriction
  all values from: Class
    union of: User Shutter Control
    union of: User Blinds Control
  on property: is applicable functionality of
subclass of: Restriction
  on class: Class
    intersection of: dpa.802.51
    intersection of: Restriction
      has value: WindAlarm
      on property: point name
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  on class: dpa.802.51
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 802
    on property: interface object type

type.digit.s8
type: NamedIndividual
range max: 127
range min: -128

DownUp = 3
type: NamedIndividual
value API: downUp
value KNX: 3

N-M
type: Unit
type: NamedIndividual
symbol: N⋅m

type.dpt.field.232.600.i2.R
type: NamedIndividual
type: Datapoint Type Field
description: R
field index: 2
field name: R
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8
unit: NUM

one push button/binary input, MoveUp / StepUp message sent = 2
type: NamedIndividual
value API: onePushButtonbinaryInput,MoveUpStep
value KNX: 2

type.dpt.field.21.1010.i7.ActivationStateOfChannel8
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 8
field index: 7
field name: ActivationStateOfChannel8
field size: 1
field type: B
includes key value pair: type.kvpair.21.1010.i7.1
includes key value pair: type.kvpair.21.1010.i7.0

type.dpt.field.27.1.i5.IOO6
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 6
field index: 5
field name: IOO6
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOff
includes key value pair: type.kvpair.outputStateOn

energy, 10000 kJ = 15
type: NamedIndividual
value API: energy,10000KJ
value KNX: 15

Relative Control RGB
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 254.600: Relative Control RGB
subject: Relative Control RGB
subject: 254.600
dpt bit size max: 24
dpt major number: 254
datapoint type minor number: 600
is assembled with: type.dpt.field.254.600.i4.cG
is assembled with: type.dpt.field.254.600.i2.Reserved
is assembled with: type.dpt.field.254.600.i8.Reserved
is assembled with: type.dpt.field.254.600.i3.StepCodeColourGreen
is assembled with: type.dpt.field.254.600.i5.Reserved
is assembled with: type.dpt.field.254.600.i6.StepCodeColourRed
is assembled with: type.dpt.field.254.600.i0.StepCodeColourBlue
is assembled with: type.dpt.field.254.600.i1.cB
is assembled with: type.dpt.field.254.600.i7.cR
label: Relative Control RGB
has communication mode: S

Command
type: NamedIndividual
type: Point Function
description: A command is classified as a direct adjustment, such as a Point used from manage functionalities to send imperative commands to control actuators.

Type TIC Channel
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.1209: Type TIC Channel
subject: 20.1209
subject: Type TIC Channel
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1209
is assembled with: type.dpt.field.20.1209.i0
label: Type TIC Channel
has communication mode: S

Breaker/Valve is closed = 0
type: NamedIndividual
value API: breakerValveIsClosed
value KNX: 0

type.dpt.field.22.1010.i9.ActivationStateOfChannel10
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 10
field index: 9
field name: ActivationStateOfChannel10
field size: 1
field type: B
includes key value pair: The visual effect of channel 10 is inactive = 0
includes key value pair: type.kvpair.22.1010.i9.1

Combined Status RTSM
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 21.107: Combined Status RTSM
subject: 21.107
subject: Combined Status RTSM
dpt bit size max: 8
dpt major number: 21
datapoint type minor number: 107
is assembled with: type.dpt.field.21.107.i1.PresenceStatusEffective
is assembled with: type.dpt.field.21.107.i2.ComfortPushButtonEffective
is assembled with: type.dpt.field.21.107.i0.WindowStatusEffective
is assembled with: type.dpt.field.21.107.i3.ComfortProlongationUserStatus
is assembled with: type.dpt.field.21.107.i5.Reserved
is assembled with: type.dpt.field.21.107.i4.HVACModeUserModeStatus
label: Combined Status RTSM
has communication mode: S

is floor of
type: ObjectProperty
domain: Floor
range: Class
  union of: Building
  union of: Space
sub property of: is location of

scene is inactive = 1
type: NamedIndividual
value API: sceneIsInactive
value KNX: 1

Value ThermoelectricPower
type: NamedIndividual
type: Datapoint Type
description: DPT 14.073: Value of thermoelectric power
subject: Value ThermoelectricPower
subject: 14.073
subject: 14.73
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 73
is assembled with: type.dpt.field.14.73.i0
label: Value ThermoelectricPower
has communication mode: S

type.dpt.field.265.12.i2.DateAndTime
type: NamedIndividual
type: Datapoint Type Field
description: Date and Time
field index: 2
field name: DateAndTime
field size: 64
includes DPT: DateTime

type.dpt.field.235.1.i0.T
type: NamedIndividual
type: Datapoint Type Field
description: validity of the Tariff data
field index: 0
field name: T
field size: 1
field type: B
includes key value pair: type.kvpair.235.1.i0.1
includes key value pair: type.kvpair.235.1.i0.0

type.dpt.field.275.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: F16F16F16F16
field index: 0
field size: 64
field string schema: raw
field type: A[n]

LightApplicationMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.005: LightApplicationMode
subject: 20.005
subject: 20.5
subject: LightApplicationMode
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 5
is assembled with: type.dpt.field.20.5.i0
label: LightApplicationMode
has communication mode: S

HVACMode
type: Class
subject: 110.51
subject: 51
subject: HVACMode
interface object type annotation: 110
label: HVACMode
property identifier annotation: 51
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 110
    on property: interface object type
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType

Relation to GMT
type: Class
subclass of: Function Point
subclass of: Restriction
  has value: qk ph temporal time site
  on property: acts on phenomenon quality kind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk ph temporal time site
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: deltaTimeMin
  on property: datapointType

Wall
type: EquipmentType
type: NamedIndividual
description: A wall is a building element that physically separates two or more neighbouring locations (typically rooms).

has application function
type: ObjectProperty
inverse of: isApplicationFunctionOf
domain: Location
range: ApplicationFunction

type.dpt.field.241.800.i7.Forced
type: NamedIndividual
type: Datapoint Type Field
description: Up/down position is forced by MoveUpDownForced input
field index: 7
field name: Forced
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

energy, 1000 kJ = 14
type: NamedIndividual
value API: energy,1000KJ
value KNX: 14

Priority
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.004: Priority
subject: 20.004
subject: 20.4
subject: Priority
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 4
is assembled with: type.dpt.field.20.4.i0
label: Priority
has communication mode: S

HVACModeAct
type: Class
subject: 54
subject: 167.54
subject: HVACModeAct
interface object type annotation: 167
label: HVACModeAct
property identifier annotation: 54
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 54
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 167
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.243.600.i0.B
type: NamedIndividual
type: Datapoint Type Field
description: This field shall indicate whether the Brightness information in the field Brightness is valid or not.
field index: 0
field name: B
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

type.dpt.field.15.0.i0.Index
type: NamedIndividual
type: Datapoint Type Field
description: Index of access identification code
field index: 0
field name: Index
field resolution: 1.0
field size: 4
field type: U
includes digit: type.digit.u4

occupied = 0
type: NamedIndividual
value API: occupied
value KNX: 0

type.dpt.field.517.500.i2.lr.LT
type: NamedIndividual
type: Datapoint Type Field
description: limit type
field index: 2
field name: LT
field size: 4
field type: N
includes key value pair: Lower Limit
includes key value pair: Upper Limit

Value SolidAngle
type: NamedIndividual
type: Datapoint Type
description: DPT 14.063: Value of solid angle
subject: 14.63
subject: 14.063
subject: Value SolidAngle
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 63
is assembled with: type.dpt.field.14.63.i0
label: Value SolidAngle
has communication mode: S

type.dpt.field.238.600.i1.LampFailure
type: NamedIndividual
type: Datapoint Type Field
description: Lamp Failure
field index: 1
field name: LampFailure
field size: 1
field type: B
includes key value pair: type.kvpair.238.600.i1.1
includes key value pair: no error = 0

running in intervals = 2
type: NamedIndividual
value API: runningInIntervals
value KNX: 2

HVAC Terminal Units = 13
type: NamedIndividual
value API: hVACTerminalUnits
value KNX: 13

type.dpt.field.265.9.i0.BinaryInformation
type: NamedIndividual
type: Datapoint Type Field
description: Binary Information
field index: 0
field name: BinaryInformation
field size: 1
includes DPT: Open Close

Value Electric Charge
type: NamedIndividual
type: Datapoint Type
description: DPT 14.018: Value of electric charge
subject: 14.18
subject: 14.018
subject: Value Electric Charge
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 18
is assembled with: type.dpt.field.14.18.i0
label: Value Electric Charge
has communication mode: S

DamperMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.109: DamperMode
subject: DamperMode
subject: 20.109
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 109
is assembled with: type.dpt.field.20.109.i0
label: DamperMode
has communication mode: S

Dimmer
type: NamedIndividual
type: EquipmentType
description: A dimmer is a device connected to a light fixture and used to lower the brightness of the light.

Override Mode Manual
type: NamedIndividual
type: StateType
description: This state type expresses that an equipment is controlled manually, rather than being controlled automatically. The equipment's value / position is the result of an input command with high priority, such as a manual control command. Other input commands of normal priority (e.g. automatic commands from a controller) are ignored, i.e. they were overridden by the high-priority command. This state type is the inverse of the 'Override Mode Automatic' state type.

Operational State In Alarm
type: NamedIndividual
type: StateType
description: This state type expresses that some alarm condition for a datapoint occurred. No assumption about the validity of the datapoint’s value can be made.

no fault = 0
type: NamedIndividual
value API: noFault
value KNX: 0

Setpoint Manager Relative Humidity
type: Class
subject: Setpoint Manager Relative Humidity
subject: 103
subject: SMRH
interface object type annotation: 103
label: Setpoint Manager Relative Humidity
is incomplete: true
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: HumRelSetpHumEff
    intersection of: Restriction
      has value: HumRelSetpHumEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.103.52
    intersection of: Restriction
      has value: HumRelSetpDehumEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: HumRelSetpUserEff
    intersection of: Restriction
      has value: HumRelSetpUserEff
      on property: point name
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.388.51
    intersection of: Restriction
      has value: HumRelSetpUser
      on property: point name
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.103.54
    intersection of: Restriction
      has value: HumDehumMode
      on property: point name
  on property: isComposedByOutput
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 103
    on property: interface object type
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.388.51
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: HumRelSetpUserEff
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.103.52
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.103.54
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: HumRelSetpHumEff
  on property: isComposedByOutput

Concentration
type: NamedIndividual
type: Quantity Kind
description: Generic concentration without a specific type. In chemistry, concentration is defined as the abundance of a constituent divided by the total volume of a mixture. The term concentration can be applied to any kind of chemical mixture, but most frequently it refers to solutes in solutions.

clear = 0
type: NamedIndividual
value API: clear
value KNX: 0

HVACModeUser
type: Class
subject: 80
subject: HVACModeUser
subject: 397.80
interface object type annotation: 397
label: HVACModeUser
property identifier annotation: 80
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 80
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVACMode
  on property: datapointType

0,7 s = 1
type: NamedIndividual
value API: 0,7S
value KNX: 1

type.dpt.field.205.103.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

No Layer = 255
type: NamedIndividual
value API: noLayer
value KNX: 255

type.dpt.field.203.101.i1.WindSpeed
type: NamedIndividual
type: Datapoint Type Field
description: wind speed absolute value m/s
field index: 1
field name: WindSpeed
field resolution: 0.01
field size: 16
field type: U
includes digit: type.digit.u16 0 20000
unit: M-PER-SEC

type.dpt.field.519.500.i3.tran.TO
type: NamedIndividual
type: Datapoint Type Field
description: operation mode id the transition points to
field index: 3
field name: TO
field size: 4
field type: U
includes digit: type.digit.u4 1 15

type.dpt.field.515.500.i1.is.INSTR ID
type: Datapoint Type Field
type: NamedIndividual
description: identifier of the instruction
field index: 1
field name: INSTR_ID
field size: 16
field type: U
includes digit: type.digit.u16

22.x
type: Datapoint Type
type: NamedIndividual
subject: 22.x
subject: 22.major
dpt bit size max: 16
dpt major number: 22
is assembled with: type.dpt.field.22.x.i0
label: 22.x
has communication mode: S

type.dpt.field.27.1.i10.IOO11
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 11
field index: 10
field name: IOO11
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOn
includes key value pair: type.kvpair.outputStateOff

232.x
type: Datapoint Type
type: NamedIndividual
subject: 232.major
subject: 232.x
dpt bit size max: 24
dpt major number: 232
is assembled with: type.dpt.field.232.x.i0
label: 232.x
has communication mode: S

type.dpt.field.512.502.i0.pe.ID
type: NamedIndividual
type: Datapoint Type Field
description: power envelope identifier
field index: 0
field name: ID
field size: 4
field type: U
includes digit: type.digit.u4

operates on protocol
type: ObjectProperty
comment: An OP relationship to a list that describes the primary protocol that a datapoint uses to send its data.
domain: Class
  union of: Function Point
  union of: Datapoint
range: Protocol
sub property of: has tag

CAV
type: EquipmentType
type: NamedIndividual
description: Constant air volume terminal unit. Constant air volume (CAV) is a type of heating, ventilating, and air-conditioning (HVAC) system. In a simple CAV system, the supply air flow rate is constant, but the supply air temperature is varied to meet the thermal loads of a space.

type.dpt.field.22.101.i15.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 15
field name: Reserved
field size: 1
field type: r
includes reserved bit(s): type.bit.reserved

inactive = 0
type: NamedIndividual
value API: inactive
value KNX: 0

enable = 0
type: NamedIndividual
value API: enable
value KNX: 0

type.dpt.field.242.600.i5.xaxis
type: NamedIndividual
type: Datapoint Type Field
description: x-coordinate of the colour information
field index: 5
field name: xaxis
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: NUM

Down = 1
type: NamedIndividual
is applicable datapoint enum of: downwards
value API: down
value KNX: 1

type.dpt.field.14.4.i0
type: Datapoint Type Field
type: NamedIndividual
description: amount of substance
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: MOL

ActCurrPos
type: Class
subject: 60
subject: ActCurrPos
subject: 400.60
interface object type annotation: 400
label: ActCurrPos
property identifier annotation: 60
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 60
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 400
    on property: interface object type
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Scaling
  on property: datapointType

type.dpt.field.516.500.i1.pr.UV
type: NamedIndividual
type: Datapoint Type Field
description: upper value
field index: 1
field name: UV
field size: 16
field type: F
includes digit: type.digit.f16

Low-voltage Power Distribution
type: Class
comment: A specific Application Function that controls the electical power network (e.g. fuses, circuit breakers etc.) from distribution transformer to consumers. The voltage level of a low-voltage distribution system is typically equal to the mains voltage of electrical appliances.
subclass of: Distribution Control
subclass of: Restriction
  has value: Electrical
  on property: operatesForTrade

FanManualEff
type: Class
subject: 67
subject: 397.67
subject: FanManualEff
interface object type annotation: 397
label: FanManualEff
property identifier annotation: 67
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Override Mode Manual
      on property: hasStateType
    intersection of: Restriction
      has value: overrideModeAutomatic
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 67
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: Enable
  on property: datapointType

type.dpt.field.232.600.i1.G
type: Datapoint Type Field
type: NamedIndividual
description: G
field index: 1
field name: G
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8
unit: NUM

HR
type: NamedIndividual
type: Unit
symbol: hr

Level 15 = 15
type: NamedIndividual
value API: level15
value KNX: 15

Converter Control
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.612: Converter Control
subject: 20.612
subject: Converter Control
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 612
is assembled with: type.dpt.field.20.612.i0
label: Converter Control
has communication mode: S

type.dpt.field.512.506.i0.smombc.COM
type: NamedIndividual
type: Datapoint Type Field
description: supported commodities (b0 = electricity, b1 = gas, b2 = oil, b3 = 0/reserved)
field index: 0
field name: COM
field size: 4
field type: U
includes digit: type.digit.u4

type.dpt.field.20.1207.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.1207.i0.0
includes key value pair: type.kvpair.20.1207.i0.3
includes key value pair: PE2 in progress = 2
includes key value pair: type.kvpair.20.1207.i0.1

2 s = 2
type: NamedIndividual
value API: 2S
value KNX: 2

Request Converter PDT Info = 6
type: NamedIndividual
value API: requestConverterPDTInfo
value KNX: 6

two PBs/binary inputs mode = 4
type: NamedIndividual
value API: twoPBsbinaryInputsMode
value KNX: 4

mass, 1 kg = 27
type: NamedIndividual
value API: mass,1Kg
value KNX: 27

ApplicationArea
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.006: ApplicationArea
subject: 20.006
subject: ApplicationArea
subject: 20.6
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 6
is assembled with: type.dpt.field.20.6.i0
label: ApplicationArea
has communication mode: S

type.dpt.field.242.600.i4.yaxis
type: NamedIndividual
type: Datapoint Type Field
description: y-coordinate of the colour information
field index: 4
field name: yaxis
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: NUM

type.dpt.field.232.600.i0.B
type: Datapoint Type Field
type: NamedIndividual
description: B
field index: 0
field name: B
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8
unit: NUM

The visual effect of channel 11 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel11IsActive
value KNX: 1

Converter Test Control
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.611: Converter Test Control
subject: 20.611
subject: Converter Test Control
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 611
is assembled with: type.dpt.field.20.611.i0
label: Converter Test Control
has communication mode: S

ADAType
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.120: ADAType
subject: ADAType
subject: 20.120
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 120
is assembled with: type.dpt.field.20.120.i0
label: ADAType
has communication mode: S

is point function type of
type: ObjectProperty
domain: Point Function
range: OperationKind
sub property of: isTagOf

type.dpt.field.20.607.i0
type: NamedIndividual
type: Datapoint Type Field
description: LDSBMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.607.i0.3
includes key value pair: one PB/binary input; SwitchOnOff inverts on each transmission = 1
includes key value pair: type.kvpair.20.607.i0.2
includes key value pair: two PBs/binary inputs mode = 4

has point interface
type: ObjectProperty
inverse of: is point interface of
comment: An OP relationship to a list that describes the runtime interworking interface type of a datapoint. A datapoint usually reflects a logical or physical (input/output) point, combinations with other (parameter/diagnostic) tags are possible.
domain: Datapoint
range: PointInterface
sub property of: has tag

Humidification Mode Inactive
type: StateType
type: NamedIndividual
description: This state type expresses that the ventilation system is inactive, i.e. performing neither humidification nor dehumidification tasks.

The visual effect of channel 1 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel1IsInactive
value KNX: 0

type.dpt.field.22.1010.i14.ActivationStateOfChannel15
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 15
field index: 14
field name: ActivationStateOfChannel15
field size: 1
field type: B
includes key value pair: The visual effect of channel 15 is active = 1
includes key value pair: The visual effect of channel 15 is inactive = 0

TempRoomSetpAbs
type: Class
subject: TempRoomSetpAbs
subject: 385.51
subject: 51
interface object type annotation: 385
label: TempRoomSetpAbs
property identifier annotation: 51
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 385
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType

gentle brezze = 3
type: NamedIndividual
value API: gentleBrezze
value KNX: 3

type.dpt.field.235.1.i4.ActiveElectricalEnergy
type: NamedIndividual
type: Datapoint Type Field
description: ActiveElectricalEnergy
field index: 4
field name: ActiveElectricalEnergy
field size: 32
includes DPT: activeEnergy

Fan Speed Current
type: Class
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Function Point

Transportation
type: Location Usages
type: NamedIndividual
description: Stations or other buildings used for public transport such as train stations, bus stations or metro stations. Preferably used with a Building.

The visual effect of channel 13 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel13IsInactiv
value KNX: 0

Value Phase AngleRad
type: NamedIndividual
type: Datapoint Type
description: DPT 14.054: Value of phase angle (in radiant)
subject: 14.54
subject: Value Phase AngleRad
subject: 14.054
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 54
is assembled with: type.dpt.field.14.54.i0
label: Value Phase AngleRad
has communication mode: S

type.dpt.field.244.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: Converter Status
field index: 0
field size: 16
field string schema: raw
field type: A[n]

type.dpt.field.252.600.i16.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 16
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.21.101.i0.ForceRequest
type: NamedIndividual
type: Datapoint Type Field
description: ForceRequest
field index: 0
field name: ForceRequest
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

TempRoomSetpAct
type: Class
subject: 153
subject: 256.153
subject: TempRoomSetpAct
interface object type annotation: 256
label: TempRoomSetpAct
property identifier annotation: 153
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 153
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 256
    on property: interface object type

Value Density
type: Datapoint Type
type: NamedIndividual
description: DPT 14.017: Value of density
subject: 14.17
subject: Value Density
subject: 14.017
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 17
is assembled with: type.dpt.field.14.17.i0
label: Value Density
has communication mode: S

HVACModeEff
type: Class
subject: 399.50
subject: 50
subject: HVACModeEff
interface object type annotation: 399
label: HVACModeEff
property identifier annotation: 50
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: HVACMode
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 50
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type

not locked = 0
type: NamedIndividual
value API: notLocked
value KNX: 0

222.x
type: NamedIndividual
type: Datapoint Type
subject: 222.major
subject: 222.x
dpt bit size max: 48
dpt major number: 222
is assembled with: type.dpt.field.222.x.i0
label: 222.x
has communication mode: S

has lower floor
type: FunctionalProperty
type: InverseFunctionalProperty
type: ObjectProperty
inverse of: hasUpperFloor
comment: A relation from one floor to the next floor.
domain: Floor
range: Floor
sub property of: refersTo

activate the scene corresponding to the field Scene Number = 0
type: NamedIndividual
value API: activateTheSceneCorrespondingToTheF
value KNX: 0

Absolute Set Value Control Red
type: Class
subject: ASV_R
subject: Absolute Set Value Control Red
subject: 58
subject: 423.58
interface object type annotation: 423
label: Absolute Set Value Control Red
property identifier annotation: 58
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Red
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 58
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type

volume, 0,001 l = 16
type: NamedIndividual
value API: volume,0,001L
value KNX: 16

Blinds Stop Step
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq slatsactuator positionvector
      on property: refersTo
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: downwards
      on property: hasStateType
    intersection of: Restriction
      has value: Stopped Movement
      on property: hasStateType
    intersection of: Restriction
      has value: upwards
      on property: hasStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: qk eq slatsactuator positionvector
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  has value: qk eq blindsactuator positionvector
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  has value: qk ph light illuminance room
  on property: acts on phenomenon quality kind
subclass of: Restriction
  has value: step
  on property: datapointType
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq blindsactuator positionvector
      on property: refersTo
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: downwards
      on property: hasStateType
    intersection of: Restriction
      has value: Stopped Movement
      on property: hasStateType
    intersection of: Restriction
      has value: upwards
      on property: hasStateType
  on property: hasOperationKind
  qualified cardinality: 1

OnOff Action
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 23.001: OnOff Action
subject: OnOff Action
subject: 23.001
subject: 23.1
dpt bit size max: 2
dpt major number: 23
datapoint type minor number: 1
is assembled with: type.dpt.field.23.1.i0
label: OnOff Action
has communication mode: S

State
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: state
field size: 1
includes DPT: State
label: State

type.dpt.field.275.100.i1.TempSetpEco
type: Datapoint Type Field
type: NamedIndividual
description: room temperature setpoint economy
field index: 1
field name: TempSetpEco
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16 neg27300 65534
unit: DEG C

Window/ Door Opening
type: NamedIndividual
type: Trade
description: Refers to a trade that is concerned with windows and doors and their positions / openings.

Heat Flow Rate
type: NamedIndividual
value API: HeatFlowRate
value KNX: 7

type.dpt.field.30.1010.i23.ActivationStateOfChannel24
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 24
field index: 23
field name: ActivationStateOfChannel24
field size: 1
field type: B
includes key value pair: The visual effect of channel 24 is inactive = 0
includes key value pair: The visual effect of channel 24 is active = 1

Switch On Off Blue
type: Class
subject: Switch On Off Blue
subject: 423.62
subject: 62
subject: SOO_B
interface object type annotation: 423
label: Switch On Off Blue
property identifier annotation: 62
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: chromaticityBlue
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 62
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind

Night Purge = 4
type: NamedIndividual
value API: nightPurge
value KNX: 4

Up = 0
type: NamedIndividual
is applicable datapoint enum of: upwards
value API: up
value KNX: 0

title (name)
type: DatatypeProperty
comment: A human friendly title (short text), used to define user specific data for an individual. Edited in a MaC or from predefined product data or dictionary content. No limitation of the actual amaount, external entites may add additional language depended text. The 'Range' is not limited to a string, allowing to express also text in several languages (note W3C does not define a range).
range: Literal

Level 2 = 2
type: NamedIndividual
value API: level2
value KNX: 2

Laundry Room
type: NamedIndividual
type: Location Usages
description: Laundry refers to the washing of clothing and other textiles, and, more broadly, their drying and ironing as well. Preferably used with an Room.

Level 3 = 3
type: NamedIndividual
value API: level3
value KNX: 3

Prioritised Mode Control
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 236.001: Prioritised Mode Control
subject: 236.001
subject: Prioritised Mode Control
subject: 236.1
dpt bit size max: 8
dpt major number: 236
datapoint type minor number: 1
is assembled with: type.dpt.field.236.1.i2.d
is assembled with: type.dpt.field.236.1.i0.m
is assembled with: type.dpt.field.236.1.i1.p
label: Prioritised Mode Control
has communication mode: S

is point priority of
type: InverseFunctionalProperty
type: ObjectProperty
domain: Origin
range: OperationKind
sub property of: isTagOf

Point Operation
type: Class
comment: The tag category contains individuals allowing to express how a point value has to be interpreted (mathematically or logically) in order to affect the behavior of the system.
subclass of: Tag

type.dpt.field.19.1.i20.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 20
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

HVACEmergMode
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.106: HVACEmergMode
subject: HVACEmergMode
subject: 20.106
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 106
is assembled with: type.dpt.field.20.106.i0
label: HVACEmergMode
has communication mode: S

TimePeriodMsec
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 7.002: TimePeriodMsec
subject: TimePeriodMsec
subject: 7.2
subject: 7.002
dpt bit size max: 16
dpt major number: 7
datapoint type minor number: 2
is assembled with: type.dpt.field.7.2.i0
label: TimePeriodMsec
has communication mode: S

The visual effect of channel 22 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel22IsActive
value KNX: 1

Audio Control
type: Class
comment: A specific Application Function category that controls the audio system. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: ApplicationFunction
subclass of: Restriction
  has value: audio
  on property: operatesForTrade

WindowSwitch
type: Class
subject: WindowSwitch
subject: 52
subject: 343.52
interface object type annotation: 343
label: WindowSwitch
property identifier annotation: 52
subclass of: Restriction
  has value: qk eq window positionvector room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 343
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: opened
      on property: hasStateType
    intersection of: Restriction
      has value: closed
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq window positionvector room
      on property: refersTo
subclass of: Restriction
  has value: windowDoor
  on property: datapointType

Current Date and Time
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk ph temporal time site
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: qk ph temporal time site
  on property: acts on phenomenon quality kind
subclass of: Restriction
  has value: DateTime
  on property: datapointType
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk ph temporal datevalue site
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: qk ph temporal datevalue site
  on property: acts on phenomenon quality kind

Value Pressure
type: NamedIndividual
type: Datapoint Type
description: DPT 14.058: Value of pressure
subject: Value Pressure
subject: 14.058
subject: 14.58
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 58
is assembled with: type.dpt.field.14.58.i0
label: Value Pressure
has communication mode: S

219.x
type: Datapoint Type
type: NamedIndividual
subject: 219.major
subject: 219.x
dpt bit size max: 48
dpt major number: 219
is assembled with: type.dpt.field.219.x.i0
label: 219.x
has communication mode: S

type.dpt.field.27.1.i23.MaskBitIOO8
type: NamedIndividual
type: Datapoint Type Field
description: Mask Bit Info On Off Output 8
field index: 23
field name: MaskBitIOO8
field size: 1
field type: B
includes key value pair: output state is valid = 1
includes key value pair: output state is not valid = 0

type.dpt.field.512.503.i2.pei.IT
type: Datapoint Type Field
type: NamedIndividual
description: instruction type
field index: 2
field name: IT
field size: 4
field type: N
includes digit: type.digit.u4 0 7

TempRoomSetpSetShift[3]
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 212.100: TempRoomSetpSetShift[3]
subject: 212.100
subject: TempRoomSetpSetShift[3]
dpt bit size max: 48
dpt major number: 212
datapoint type minor number: 100
is assembled with: type.dpt.field.212.100.i2.TempSetpShiftComf
is assembled with: type.dpt.field.212.100.i1.TempSetpShiftStdby
is assembled with: type.dpt.field.212.100.i0.TempSetpShiftEco
label: TempRoomSetpSetShift[3]
has communication mode: LTE

type.dpt.field.27.1.i16.MaskBitIOO1
type: NamedIndividual
type: Datapoint Type Field
description: Mask Bit Info On Off Output 1
field index: 16
field name: MaskBitIOO1
field size: 1
field type: B
includes key value pair: output state is valid = 1
includes key value pair: output state is not valid = 0

Electricity
type: PhenomenonType
type: NamedIndividual
description: Associated with electricity or with electrical force, power, or energy.

type.dpt.field.13.12.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 32
field type: V
includes digit: type.digit.s32
unit: V-A Reactive-HR

Value Length
type: Datapoint Type
type: NamedIndividual
description: DPT 14.039: Value of length
subject: 14.39
subject: 14.039
subject: Value Length
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 39
is assembled with: type.dpt.field.14.39.i0
label: Value Length
has communication mode: S

is composed by
type: ObjectProperty
domain: Functional Block
sub property of: hasDatapoint

28% = 2
type: NamedIndividual
value API: 28%
value KNX: 2

Other device type = 0
type: NamedIndividual
value API: otherDeviceType
value KNX: 0

type.dpt.field.psc.i0
type: NamedIndividual
type: Datapoint Type Field
description: Power sequence container
field index: 0
field type: D<n>
includes datapoint field: type.dpt.field.psc.i2.SQ SEL
includes datapoint field: type.dpt.field.psc.i4.SQ
includes datapoint field: type.dpt.field.psc.i1.SQ CNT
includes datapoint field: type.dpt.field.psc.i0.SC ID
includes reserved bit(s): type.dpt.field.psc.i3.Reserved

type.dpt.field.21.103.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 3
field name: Reserved
field size: 5
field type: r
includes reserved bit(s): type.bit.reserved

has phenomenon type
type: ObjectProperty
type: FunctionalProperty
inverse of: isPhenomenonTypeOf
comment: A child OP relationship to a list that describes the interest characteristic “type of interest” on what an observation or actuation is made.
domain: Quality Kind
range: PhenomenonType
sub property of: has tag

Tariff ActiveEnergy
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 235.001: Tariff ActiveEnergy
subject: 235.001
subject: 235.1
subject: Tariff ActiveEnergy
dpt bit size max: 48
dpt major number: 235
datapoint type minor number: 1
is assembled with: type.dpt.field.235.1.i3.Tariff
is assembled with: type.dpt.field.235.1.i4.ActiveElectricalEnergy
is assembled with: type.dpt.field.235.1.i1.E
is assembled with: type.dpt.field.235.1.i2.Reserved
is assembled with: type.dpt.field.235.1.i0.T
label: Tariff ActiveEnergy
has communication mode: S

type.dpt.field.10.1.i4.Hour
type: NamedIndividual
type: Datapoint Type Field
description: Hour
field index: 4
field name: Hour
field resolution: 1.0
field size: 5
field type: U
includes digit: type.digit.u5 0 23
unit: HR

type.dpt.field.520.500.i3.ss.CID
type: Datapoint Type Field
type: NamedIndividual
description: sequence container ID
field index: 3
field name: CID
field size: 4
field type: U
includes digit: type.digit.u4

Function Point
type: Class
disjoint with: ApplicationFunction
comment: A function point groups typically more than one point needed to express the communication link between all the points. The points provide the input/output data interfaces of the devices in an installation. A function point is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: Restriction
  on data range: string
  on property: securityMode
  qualified cardinality: 1
subclass of: Class
  intersection of: Restriction
    all values from: boolean
    on property: writable
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: boolean
    on property: writable
subclass of: Restriction
  max qualified cardinality: 1
  on data range: string
  on property: ipv6Multicast
subclass of: Class
  intersection of: Restriction
    all values from: boolean
    on property: readable
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: boolean
    on property: readable
subclass of: Restriction
  all values from: Trade
  on property: operatesForTrade
subclass of: Restriction
  all values from: Function Point
  on property: is status of
subclass of: Restriction
  all values from: integer
  on property: non KNX mapping address
subclass of: Class
  intersection of: Restriction
    all values from: Datapoint Type
    on property: datapointType
  intersection of: Restriction
    max qualified cardinality: 1
    on class: Datapoint Type
    on property: datapointType
subclass of: Restriction
  all values from: string
  on property: comment
subclass of: Aspect
subclass of: Class
  intersection of: Restriction
    all values from: Protocol
    on property: operates on protocol
  intersection of: Restriction
    max qualified cardinality: 1
    on class: Protocol
    on property: operates on protocol
subclass of: Restriction
  all values from: Class
    union of: OperationKind
    union of: Quality Kind
  on property: has tag set
subclass of: Class
  intersection of: Restriction
    all values from: positiveInteger
    on property: groupAddress
  intersection of: Restriction
    on data range: positiveInteger
    on property: groupAddress
    qualified cardinality: 1

type.dpt.field.6.20.i1.e
type: NamedIndividual
type: Datapoint Type Field
description: Status E
field index: 1
field name: e
field size: 1
field type: B
includes key value pair: clear = 0
includes key value pair: type.kvpair.set

type.dpt.field.20.1002.i0
type: NamedIndividual
type: Datapoint Type Field
description: ModeSelect
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.1002.i0.1
includes key value pair: type.kvpair.20.1002.i0.2
includes key value pair: asynchronous = 0

type.dpt.field.14.24.i0
type: NamedIndividual
type: Datapoint Type Field
description: electric flux
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/C

Cooling load meter (outlet) = 10
type: NamedIndividual
value API: coolingLoadMeter(outlet)
value KNX: 10

is heartbeat of
type: ObjectProperty
comment: The value of the target datapoint is sent at the latest after a certain duration. The duration is defined by the metadata datapoint's value.
sub property of: isMetaDataOf

type.dpt.field.lb.lbe
type: NamedIndividual
type: Datapoint Type Field
description: leakage behaviour element
field index: 0
field type: D<n>
includes datapoint field: type.dpt.field.lb.lbe.i1.FLR
includes datapoint field: type.dpt.field.lb.lbe.i0.LR

type.dpt.field.205.100.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

standby = 1
type: NamedIndividual
value API: standby
value KNX: 1

insufficient non volatile memory = 6
type: NamedIndividual
value API: insufficientNonVolatileMemory
value KNX: 6

Invert
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: invert
field size: 1
includes DPT: invert
label: Invert

3 min = 15
type: NamedIndividual
value API: 3Min
value KNX: 15

The visual effect of channel 8 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel8IsInactive
value KNX: 0

is trade operated by
type: ObjectProperty
inverse of: operatesForTrade
domain: Trade
range: Class
  union of: Aspect
  union of: Datapoint
sub property of: isTagOf

type.dpt.field.240.800.i1.ValidHeightPos
type: NamedIndividual
type: Datapoint Type Field
description: Validity Height Position
field index: 1
field name: ValidHeightPos
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

no alarm is used = 0
type: NamedIndividual
value API: noAlarmIsUsed
value KNX: 0

type.dpt.field.209.100.i0.TempFlowValid
type: NamedIndividual
type: Datapoint Type Field
description: validity of TempFlowProdSegmH field
field index: 0
field name: TempFlowValid
field size: 1
includes DPT: Bool

type.dpt.field.14.79.i0
type: Datapoint Type Field
type: NamedIndividual
description: work
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/J

The visual effect of channel 8 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel8IsActive
value KNX: 1

V-PER-K
type: NamedIndividual
type: Unit
symbol: V/K

HVAC Mode Standby
type: StateType
type: NamedIndividual
description: This state type expresses that the second-highest level named 'Standby' (or 'Pre-Comfort') is chosen for the HVAC mode. Usually, the 'Standby' level is associated with an unoccupied room that needs to be able to reach the 'Comfort' level in a short period of time. In general, the HVAC mode is also known as comfort level and is used for computations in HVAC systems, such as the computation of currently active temperature setpoints.

comprises
type: ObjectProperty
inverse of: isComprisedBy
comment: To define the existence of KNX standardized functionality block, implemented in a channel. Since a FB is specified with a certain set of mandatory and optional datapoints a channel needs to define at least the mandatory datapoints.
domain: Channel
range: Functional Block

Reception
type: NamedIndividual
type: Location Usages
description: The term reception or front desk is used in many hotels for an administrative department where a receptionist's duties also may include room reservations and assignment, guest registration, cashier work, credit checks, key control, and mail and message service.

volume flow, 0,1 ml/s = 74
type: NamedIndividual
value API: volumeFlow,0,1Mls
value KNX: 74

type.dpt.field.222.100.i0.TempSetpEco
type: Datapoint Type Field
type: NamedIndividual
description: TempSetpEco
field index: 0
field name: TempSetpEco
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16 neg27300 670433
unit: DEG C

Logical Output Point
type: NamedIndividual
type: PointInterface
description: The tag represents information for a logical point, a communication interworking (logical) output Point, it sends data.

type.dpt.field.22.1010.i10.ActivationStateOfChannel11
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 11
field index: 10
field name: ActivationStateOfChannel11
field size: 1
field type: B
includes key value pair: type.kvpair.22.1010.i10.0
includes key value pair: type.kvpair.22.1010.i10.1

Displacement
type: NamedIndividual
type: Quantity Kind
description: "Displacement" is the shortest distance from the initial to the final position of a point P.

Emergency Steam Mode = 17
type: NamedIndividual
value API: emergencySteamMode
value KNX: 17

type.dpt.field.27.1.i26.MaskBitIOO11
type: Datapoint Type Field
type: NamedIndividual
description: Mask Bit Info On Off Output 11
field index: 26
field name: MaskBitIOO11
field size: 1
field type: B
includes key value pair: output state is not valid = 0
includes key value pair: output state is valid = 1

Blinds Actuator
type: EquipmentType
type: NamedIndividual
description: Used to control an actuator equipment to regulate the light incidence (blinds or shutter position). Don't care if the blinds position is internally operated from the actuator by a motor or other means.

Building protected = 2
type: NamedIndividual
value API: buildingProtected
value KNX: 2

Day = 0
type: NamedIndividual
value API: day
value KNX: 0

type.dpt.field.246.600.i0.BatteryChargeLevel
type: NamedIndividual
type: Datapoint Type Field
description: Battery Charge Level
field index: 0
field name: BatteryChargeLevel
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8

Heat Pump
type: EquipmentType
type: NamedIndividual
description: A heat pump is a device that can heat a building (or part of a building) by transferring thermal energy from the outside using the refrigeration cycle. Many heat pumps can also operate in the opposite direction, cooling the building by removing heat from the enclosed space and ejecting it outside. Units that only provide cooling are called air conditioners.

type.dpt.field.20.608.i0
type: NamedIndividual
type: Datapoint Type Field
description: SwitchOnMode
field index: 0
field size: 8
field type: N
includes key value pair: last actual value = 0
includes key value pair: last received absolute setvalue = 2
includes key value pair: type.kvpair.20.608.i0.1

type.dpt.field.249.600.i0.validityOfAbsoluteBrightness
type: NamedIndividual
type: Datapoint Type Field
description: validity of the absolute brightness
field index: 0
field name: validityOfAbsoluteBrightness
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

Enable
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: enable
field size: 1
includes DPT: Enable
label: Enable

HVAC Hot Water Heating = 11
type: NamedIndividual
value API: hVACHotWaterHeating
value KNX: 11

type.dpt.field.7.4.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 100.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: MilliSEC

type.dpt.field.7.600.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: http://qudt.org/vocab/unit/K

Heat = 1
type: NamedIndividual
value API: heat
value KNX: 1

HVACModeUserEff
type: Class
subject: 57
subject: 100.57
subject: HVACModeUserEff
interface object type annotation: 100
label: HVACModeUserEff
property identifier annotation: 57
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 57
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type

Kitchen
type: Location Usages
type: NamedIndividual
description: A kitchen is a room or part of a room used for cooking and food preparation in a dwelling or in a commercial establishment. Preferably used with an Room.

type.dpt.field.ec.i3.FROM
type: NamedIndividual
type: Datapoint Type Field
description: timestamp when this constraint will be valid
field index: 3
field name: FROM
field size: 64
includes DPT: DateTime

type.dpt.field.8.4.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 100.0
field size: 16
field type: V
includes digit: type.digit.s16
unit: MilliSEC

HVACModeAct
type: Class
subject: 54
subject: 224.54
subject: HVACModeAct
interface object type annotation: 224
label: HVACModeAct
property identifier annotation: 54
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 54
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 224
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

229.x
type: Datapoint Type
type: NamedIndividual
subject: 229.major
subject: 229.x
dpt bit size max: 48
dpt major number: 229
is assembled with: type.dpt.field.229.x.i0
label: 229.x
has communication mode: S

includes datapoint field
type: ObjectProperty
range: Datapoint Type Field
sub property of: includes

mass, 0,1 kg = 26
type: NamedIndividual
value API: mass,0,1Kg
value KNX: 26

Printer
type: EquipmentType
type: NamedIndividual
description: A machine that has the primary function of printing a stream of characters onto paper or other media.

Converter Data Request
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.613: Converter Data Request
subject: Converter Data Request
subject: 20.613
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 613
is assembled with: type.dpt.field.20.613.i0
label: Converter Data Request
has communication mode: S

Power Supply
type: NamedIndividual
type: EquipmentType
description: A power supply is an electrical device that supplies electric power to an electrical load. The main purpose of a power supply is to convert electric current from a source to the correct voltage, current, and frequency to power the load.

detection not possible or error = 3
type: NamedIndividual
value API: detectionNotPossibleOrError
value KNX: 3

ActualDimmingValue
type: Class
subject: ActualDimmingValue
subject: 418.52
subject: 52
interface object type annotation: 418
label: ActualDimmingValue
property identifier annotation: 52
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo

type.dpt.field.22.1010.i15.ActivationStateOfChannel16
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 16
field index: 15
field name: ActivationStateOfChannel16
field size: 1
field type: B
includes key value pair: type.kvpair.22.1010.i15.1
includes key value pair: The visual effect of channel 16 is inactive = 0

No ramp = 0
type: NamedIndividual
value API: noRamp
value KNX: 0

type.dpt.field.237.600.i3.LampFailure
type: Datapoint Type Field
type: NamedIndividual
description: Lamp Failure
field index: 3
field name: LampFailure
field size: 1
field type: B
includes key value pair: no error = 0
includes key value pair: error = 1

SABExceptBehaviour
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.801: SABExceptBehaviour
subject: 20.801
subject: SABExceptBehaviour
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 801
is assembled with: type.dpt.field.20.801.i0
label: SABExceptBehaviour
has communication mode: S

Value Wsp kmh
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 9.028: Value Wsp kmh
subject: 9.28
subject: 9.028
subject: Value Wsp kmh
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 28
is assembled with: type.dpt.field.9.28.i0
label: Value Wsp kmh
has communication mode: S

205.x
type: NamedIndividual
type: Datapoint Type
subject: 205.major
subject: 205.x
dpt bit size max: 24
dpt major number: 205
is assembled with: type.dpt.field.205.x.i0
label: 205.x
has communication mode: LTE

manual light control = 1
type: NamedIndividual
value API: manualLightControl
value KNX: 1

Datapoint Type
type: Class
comment: A generic concept of a KNX datapoint type (DPT). Each present individual represents a corresponding DPT of KNX. The chosen individual name follows a defined structure. A datapoint type is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: Restriction
  all values from: Datatype
    one of: LTE
    one of: S
  on property: has communication mode
subclass of: Class
  intersection of: Restriction
    all values from: nonNegativeInteger
    on property: datapoint type minor number
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: nonNegativeInteger
    on property: datapoint type minor number
subclass of: Class
  intersection of: Restriction
    all values from: positiveInteger
    on property: dptMajorNumber
  intersection of: Restriction
    on data range: positiveInteger
    on property: dptMajorNumber
    qualified cardinality: 1
subclass of: Core Thing
subclass of: Class
  intersection of: Restriction
    all values from: Datapoint Type Field
    on property: is assembled with
  intersection of: Restriction
    min qualified cardinality: 1
    on class: Datapoint Type Field
    on property: is assembled with
subclass of: Class
  intersection of: Restriction
    all values from: positiveInteger
    on property: dptBitSizeMax
  intersection of: Restriction
    on data range: positiveInteger
    on property: dptBitSizeMax
    qualified cardinality: 1

type.dpt.field.27.1.i1.IOO2
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 2
field index: 1
field name: IOO2
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOn
includes key value pair: type.kvpair.outputStateOff

type.dpt.field.14.39.i0
type: NamedIndividual
type: Datapoint Type Field
description: length
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/M

Dishwasher
type: EquipmentType
type: NamedIndividual
description: A dishwasher is a home appliance machine (EN 50523) that is used to clean dishware, cookware, and cutlery automatically.

type.dpt.field.20.122.i0
type: NamedIndividual
type: Datapoint Type Field
description: StartSynchronization
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.122.i0.2
includes key value pair: Single close = 1
includes key value pair: Position unchanged = 0

power, 0,1 W = 42
type: NamedIndividual
value API: power,0,1W
value KNX: 42

type.dpt.field.217.1.i0.RevisionNumber
type: NamedIndividual
type: Datapoint Type Field
description: Revision Number
field index: 0
field name: RevisionNumber
field resolution: 1.0
field size: 6
field type: U
includes digit: type.digit.u6
unit: NUM

type.dpt.field.209.102.i2.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 4
field name: Reserved
field size: 4
includes reserved bit(s): type.bit.reserved

type.dpt.field.238.1.i0.SceneNumber
type: NamedIndividual
type: Datapoint Type Field
description: This shall be the number of the scene for which the DPT-value contains the configuration information.
field index: 0
field name: SceneNumber
field resolution: 1.0
field size: 6
field type: U
includes digit: type.digit.u6
unit: NUM

type.dpt.field.207.104.i5.ActPosDemAbs
type: NamedIndividual
type: Datapoint Type Field
description: Absolute actuator position demand (setpoint, valve linearized)
field index: 5
field name: ActPosDemAbs
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8 0 100
unit: PERCENT

volume flow, 10 ml/s = 76
type: NamedIndividual
value API: volumeFlow,10Mls
value KNX: 76

type.dpt.field.9.6.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16 0 670433
unit: PA

The visual effect of channel 5 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel5IsActive
value KNX: 1

type.dpt.field.237.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: configuration/ diagnostics
field index: 0
field size: 16
field string schema: raw
field type: A[n]

type.dpt.field.265.12.i0.BinaryInformation
type: Datapoint Type Field
type: NamedIndividual
description: Binary Information
field index: 0
field name: BinaryInformation
field size: 1
includes DPT: invert

Operational State Defect
type: NamedIndividual
type: StateType
description: This state type expresses that the actual device hosting the datapoint is not working properly due to a failure. Thus, no valid value is available at the datapoint. The cause of the device failure cannot be specified any further.

has outside
type: ObjectProperty
inverse of: isOutsideOf
comment: A general OP relationship to express a relation of location individuals to individuals which are outside of a particular building. The location to be outside (as the domain) MUST fulfil the boundary conditions to be allowed outside. Example is a relation to an outdoor location which does not directly belong to a building (e.g. garden).
range: Outside
sub property of: has location

V-A Reactive-HR
type: NamedIndividual
type: Unit
symbol: V⋅A{reactive}⋅hr

Bus/System = 14
type: NamedIndividual
value API: busSystem
value KNX: 14

type.dpt.field.275.101.i3.TempSetpShiftComf
type: NamedIndividual
type: Datapoint Type Field
description: room temperature setpoint shift comfort
field index: 3
field name: TempSetpShiftComf
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: http://qudt.org/vocab/unit/K

type.dpt.field.14.47.i0
type: NamedIndividual
type: Datapoint Type Field
description: magnetic moment
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: A-M2

LM
type: Unit
type: NamedIndividual
symbol: lm

VAV = 2
type: NamedIndividual
value API: vAV
value KNX: 2

WD field valid = 0
type: NamedIndividual
value API: wDFieldValid
value KNX: 0

1,25 min = 11
type: NamedIndividual
value API: 1,25Min
value KNX: 11

type.dpt.field.250.600.i8.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 8
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.20.112.i0
type: NamedIndividual
type: Datapoint Type Field
description: MasterSlaveMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.112.i0.2
includes key value pair: autonomous = 0
includes key value pair: type.kvpair.20.112.i0.1

None = 0
type: NamedIndividual
value API: none
value KNX: 0

type.dpt.field.525.500.i8.fv.Lower Limit
type: NamedIndividual
type: Datapoint Type Field
description: The lower boundary of the range with 100 % certainty the power value is in it
field index: 8
field name: Lower_Limit
field size: 16
includes DPT: Power

type.dpt.field.512.512.i1.uf.FE CNT
type: NamedIndividual
type: Datapoint Type Field
description: number of usage forecast elements
field index: 1
field name: FE_CNT
field size: 8
field type: U
includes digit: type.digit.u8 0 12

Wind Speed Z
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 203.101: Wind Speed Z
subject: 203.101
subject: Wind Speed Z
dpt bit size max: 24
dpt major number: 203
datapoint type minor number: 101
is assembled with: type.dpt.field.203.101.i1.WindSpeed
is assembled with: type.dpt.field.203.101.i0.StatusCommand
label: Wind Speed Z
has communication mode: LTE

Enable HC Stage
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.116: Enable HC Stage
subject: Enable HC Stage
subject: 20.116
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 116
is assembled with: type.dpt.field.20.116.i0
label: Enable HC Stage
has communication mode: S

type.dpt.field.512.507.i1.smfrbc.OM CNT
type: NamedIndividual
type: Datapoint Type Field
description: number of FRBC operation modes
field index: 1
field name: OM_CNT
field size: 4
field type: U
includes digit: type.digit.u4 1 15

type.dpt.field.pc.i0.ID
type: NamedIndividual
type: Datapoint Type Field
description: ID of the power constraint
field index: 0
field name: ID
field size: 4
field type: U
includes digit: type.digit.u4

Operational State Maintenance
type: StateType
type: NamedIndividual
description: This state type expresses that a device is currently in maintenance mode, i.e. it cannot be expected to fulfill its usual functionality until it is fully operational once again. Specific examples include ‘service mode’ or the ‘valve kick’ of valve actuators.

Location
type: Class
comment: A location is a physical named geographical place that is used to identify a point, an area or room, inside or outside of a building. This generic location root node simplifies the replacement of the entire location model.
subclass of: Core Thing

Ack
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.16.i0.0
includes key value pair: type.kvpair.1.16.i0.1
label: Ack

type.dpt.field.250.600.i2.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 2
field name: Reserved
field size: 6
field type: r
includes reserved bit(s): type.bit.reserved

Hallway
type: Location Usages
type: NamedIndividual
description: A hallway or corridor is an interior space in a building that is used to connect other rooms. Preferably used with an Room.

TempRoomDemAbs
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 209.101: TempRoomDemAbs
subject: TempRoomDemAbs
subject: 209.101
dpt bit size max: 24
dpt major number: 209
datapoint type minor number: 101
is assembled with: type.dpt.field.209.101.i4.Reserved
is assembled with: type.dpt.field.209.101.i3.EmergDem
is assembled with: type.dpt.field.209.101.i1.AbsLoadPriority
is assembled with: type.dpt.field.209.101.i0.DemValid
is assembled with: type.dpt.field.209.101.i5.TempRoomDem
is assembled with: type.dpt.field.209.101.i2.ShiftLoadPriority
label: TempRoomDemAbs
has communication mode: LTE

type.dpt.field.21.601.i1.Undervoltage
type: NamedIndividual
type: Datapoint Type Field
description: Undervoltage
field index: 1
field name: Undervoltage
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

Value Temp
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 9.001: Value Temp
subject: Value Temp
subject: 9.001
subject: 9.1
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 1
is assembled with: type.dpt.field.9.1.i0
label: Value Temp
has communication mode: S

Decimal Factor
type: NamedIndividual
type: Datapoint Type Field
description: Represents a ratio.
field index: 0
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8
label: Decimal Factor
unit: UNITLESS

no change = 2
type: NamedIndividual
value API: noChange
value KNX: 2

Frost Alarm
type: Class
subclass of: Restriction
  has value: qk ph air temperature outside
  on property: observesPhenomenonQualityKind
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk ph air temperature outside
      on property: refersTo
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: frost
      on property: hasStateType
    intersection of: Restriction
      has value: No Frost
      on property: hasStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: alarm
  on property: datapointType

Scene Control
type: Class
comment: A specific Application Function category that controls a customized setting of different trades for an activity or situation. Scene controllers are intelligent pre-configured settings that orchestrate multiple devices and settings with a single touch of a button or a simple voice command. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: ApplicationFunction

type.dpt.field.207.105.i6.ActPos
type: NamedIndividual
type: Datapoint Type Field
description: actual actuator position
field index: 6
field name: ActPos
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8 0 100
unit: PERCENT

type.dpt.field.250.600.i4.cB
type: NamedIndividual
type: Datapoint Type Field
description: Increase or decrease the brightness.
field index: 4
field name: cB
field size: 1
field type: B
includes key value pair: type.kvpair.increase
includes key value pair: type.kvpair.decrease

Cool stage B for cooling with two stages (A + B) = 4
type: NamedIndividual
value API: coolStageBForCoolingWithTwoStages(A
value KNX: 4

type.dpt.field.219.1.i12.LogNumber
type: NamedIndividual
type: Datapoint Type Field
description: Log Number
field index: 12
field name: LogNumber
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8
unit: NUM

EnableHeat
type: Class
subject: 399.61
subject: 61
subject: EnableHeat
interface object type annotation: 399
label: EnableHeat
property identifier annotation: 61
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 61
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Heating-Cooling Stages None
      on property: hasStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: hasStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: hasStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Both
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Enable HC Stage
  on property: datapointType

filtering by Domain Address and by Serial number table = 3
type: NamedIndividual
value API: filteringByDomainAddressAndBySerial
value KNX: 3

Stopped Movement
type: StateType
type: NamedIndividual
description: This state type expresses that the movement of an equipment has stopped. Usually, this is associated with equipments that can be moved by a drive, such as valves, blinds, slats, windows, or doors.

type.dpt.field.19.1.i15.HourOfDay
type: Datapoint Type Field
type: NamedIndividual
description: HourOfDay
field index: 15
field name: HourOfDay
field resolution: 1.0
field size: 5
field type: U
includes digit: type.digit.u5 0 24
unit: HR

type.dpt.field.265.9.i1.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: Reserved
field size: 7
field type: r
includes reserved bit(s): type.bit.reserved

3.x
type: Datapoint Type
type: NamedIndividual
subject: 3.x
subject: 3.major
dpt bit size max: 4
dpt major number: 3
is assembled with: type.dpt.field.3.x.i0
label: 3.x
has communication mode: S

Value Curr
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 9.021: Value Curr
subject: 9.021
subject: Value Curr
subject: 9.21
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 21
is assembled with: type.dpt.field.9.21.i0
label: Value Curr
has communication mode: S

type.dpt.field.21.100.i0.ForceRequest
type: NamedIndividual
type: Datapoint Type Field
description: ForceRequest
field index: 0
field name: ForceRequest
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

HVAC general FBs = 10
type: NamedIndividual
value API: hVACGeneralFBs
value KNX: 10

Fault = 1
type: NamedIndividual
value API: fault
value KNX: 1

External Address
type: Class
comment: An address is represented by an external ontology object, which has data properties such as country-name, locality (city), street-address.

24 h = 25
type: NamedIndividual
value API: 24H
value KNX: 25

Value Weight
type: Datapoint Type
type: NamedIndividual
description: DPT 14.078: Value of weight
subject: 14.78
subject: Value Weight
subject: 14.078
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 78
is assembled with: type.dpt.field.14.78.i0
label: Value Weight
has communication mode: S

type.dpt.field.13.16.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: V
includes digit: type.digit.s32
unit: MegaW-HR

type.dpt.field.8.12.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 16
field type: V
includes digit: type.digit.s16
unit: http://qudt.org/vocab/unit/M

type.dpt.field.11.1.i1.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: Reserved
field size: 1
field type: r
includes reserved bit(s): type.bit.reserved

point name
type: DatatypeProperty
comment: Point name, used to indicate the name of a point. This is used in assigning names to the (input/output) points of functional blocks
domain: Point
range: string

Registered (S-FSK) - reserved (G3-PLC) = 2
type: NamedIndividual
value API: registered(S-FSK)-Reserved(G3-PLC)
value KNX: 2

Colour_Relative Control_RGB
type: Class
subject: Colour_Relative Control_RGB
subject: 53
subject: RC_RGB
subject: 423.53
interface object type annotation: 423
label: Colour_Relative Control_RGB
property identifier annotation: 53
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Red
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Green
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: Relative Control RGB
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: chromaticityBlue
      on property: relatesToStateType

type.dpt.field.234.2.i1.Character1
type: Datapoint Type Field
type: NamedIndividual
description: first character of RegionCode, ASCII-coded
field index: 1
field name: Character1
field size: 8
includes DPT: charascii

TimeOfDay
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 10.001: TimeOfDay
subject: 10.1
subject: TimeOfDay
subject: 10.001
dpt bit size max: 24
dpt major number: 10
datapoint type minor number: 1
is assembled with: type.dpt.field.10.1.i2.Minutes
is assembled with: type.dpt.field.10.1.i0.Seconds
is assembled with: type.dpt.field.10.1.i3.Reserved
is assembled with: type.dpt.field.10.1.i1.Reserved
is assembled with: type.dpt.field.10.1.i4.Hour
is assembled with: type.dpt.field.10.1.i5.Day
label: TimeOfDay
has communication mode: S

type.dpt.field.201.100.i1.HVACMode
type: NamedIndividual
type: Datapoint Type Field
description: HVAC operating mode
field index: 1
field name: HVACMode
field size: 8
includes DPT: HVACMode

Precool = 5
type: NamedIndividual
value API: precool
value KNX: 5

type.dpt.field.255.1.i1.Longitude
type: NamedIndividual
type: Datapoint Type Field
description: Longitude information
field index: 1
field name: Longitude
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: DEG

HeatCoolMode
type: Class
subject: 151
subject: 257.151
subject: HeatCoolMode
interface object type annotation: 257
label: HeatCoolMode
property identifier annotation: 151
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: controlModeHeating
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: heatpCool
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 151
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 257
    on property: interface object type

type.dpt.field.22.100.i3.DHWPushActive
type: NamedIndividual
type: Datapoint Type Field
description: DHWPushActive
field index: 3
field name: DHWPushActive
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

Rejected
type: NamedIndividual
value API: Rejected
value KNX: 1

SABBehaviour Lock Unlock
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.802: SABBehaviour Lock Unlock
subject: 20.802
subject: SABBehaviour Lock Unlock
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 802
is assembled with: type.dpt.field.20.802.i0
label: SABBehaviour Lock Unlock
has communication mode: S

type.dpt.field.241.800.i4.TargetHPosRestrict
type: Datapoint Type Field
type: NamedIndividual
description: Restriction of target height pos., pos. can not be reached
field index: 4
field name: TargetHPosRestrict
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

KelvinPerPercent
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 9.023: KelvinPerPercent
subject: 9.23
subject: 9.023
subject: KelvinPerPercent
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 23
is assembled with: type.dpt.field.9.23.i0
label: KelvinPerPercent
has communication mode: S

W-PER-M2
type: Unit
type: NamedIndividual
symbol: W/m²

is applicable functionality of
type: ObjectProperty
comment: This OP defines what predefined application function can be preferably used with a collection of datapoints. The collection may be expressed with a common functionality or more detailed with a functional block or channel (subclasses of functionality).
domain: Functionality
range: ApplicationFunction

type.dpt.field.21.1010.i1.ActivationStateOfChannel2
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 2
field index: 1
field name: ActivationStateOfChannel2
field size: 1
field type: B
includes key value pair: type.kvpair.21.1010.i1.1
includes key value pair: type.kvpair.21.1010.i1.0

Facade
type: Locality
type: NamedIndividual
description: A façade is generally the front part or exterior of a building. Mainly used as a building facade.

type.dpt.field.520.500.i2.ss.SID
type: NamedIndividual
type: Datapoint Type Field
description: sequence ID
field index: 2
field name: SID
field size: 4
field type: U
includes digit: type.digit.u4

User Light Switching
type: Class
subject: LSAB
subject: LSSB
comment: A user operated light switch request including an explicit switch status.
subclass of: Restriction
  has value: qk ph light illuminance
  on property: hasQualityKind
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on class: LightSwitchRequest
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: Light Current Status
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Lighting Control

type.dpt.field.202.1.i1.RelValue
type: NamedIndividual
type: Datapoint Type Field
description: Unsigned relative value
field index: 1
field name: RelValue
field size: 8
includes DPT: percentU8

CombinedStatus_RTC
type: Class
subject: 399.110
subject: CombinedStatus_RTC
subject: 110
interface object type annotation: 399
label: CombinedStatus_RTC
property identifier annotation: 110
subclass of: Restriction
  has value: qk ph air dewpointtemperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air dewpointtemperature room
      on property: refersTo
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: controlModeHeating
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 110
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: inactive
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeEmergencyHeat
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Enabled State
      on property: hasStateType
    intersection of: Restriction
      has value: Disabled State
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  has value: Combined Status RTC
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeEmergencyCool
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Enabled State
      on property: hasStateType
    intersection of: Restriction
      has value: Disabled State
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Defect
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType

Value Luminous Flux
type: Datapoint Type
type: NamedIndividual
description: DPT 14.042: Value of luminous flux
subject: 14.42
subject: Value Luminous Flux
subject: 14.042
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 42
is assembled with: type.dpt.field.14.42.i0
label: Value Luminous Flux
has communication mode: S

communication fault = 2
type: NamedIndividual
value API: communicationFault
value KNX: 2

Gym
type: NamedIndividual
type: Location Usages
description: A gym (also known as a fitness club, fitness center, health spa, and health club) is a place that houses exercise equipment for the purpose of physical exercise.

deactivated = 0
type: NamedIndividual
value API: deactivated
value KNX: 0

type.dpt.field.22.100.i1.DHWLoadActive
type: NamedIndividual
type: Datapoint Type Field
description: DHWLoadActive
field index: 1
field name: DHWLoadActive
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

Level 11 = 11
type: NamedIndividual
value API: level11
value KNX: 11

Heating-Cooling Stages Secondary
type: NamedIndividual
type: StateType
description: This state type relates to the secondary stage of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.

Value Frequency
type: NamedIndividual
type: Datapoint Type
description: DPT 14.033: Value of frequency
subject: 14.033
subject: 14.33
subject: Value Frequency
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 33
is assembled with: type.dpt.field.14.33.i0
label: Value Frequency
has communication mode: S

PresenceStatus
type: Class
subject: 51
subject: PresenceStatus
subject: 345.51
interface object type annotation: 345
label: PresenceStatus
property identifier annotation: 51
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: presenceOccupied
      on property: hasStateType
    intersection of: Restriction
      has value: Presence Unoccupied
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph person positionvector room
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 345
    on property: interface object type
subclass of: Restriction
  has value: occupancy
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph person positionvector room
  on property: hasQualityKind

type.digit.f16 neg27300 65534
type: NamedIndividual
range max: 65534.0
range min: -27300.0

HeatCoolModeAct
type: Class
subject: 397.63
subject: 63
subject: HeatCoolModeAct
interface object type annotation: 397
label: HeatCoolModeAct
property identifier annotation: 63
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 63
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: heatpCool
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: controlModeHeating
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.251.600.i8.G
type: NamedIndividual
type: Datapoint Type Field
description: Colour Level Green
field index: 8
field name: G
field resolution: 0.3921566
field size: 8
field type: U
includes digit: type.digit.u8
unit: PERCENT

type.dpt.field.207.100.i1.Fault
type: NamedIndividual
type: Datapoint Type Field
description: burner failure
field index: 1
field name: Fault
field size: 1
includes DPT: Bool

HumDehumMode
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.115: HumDehumMode
subject: 20.115
subject: HumDehumMode
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 115
is assembled with: type.dpt.field.20.115.i0
label: HumDehumMode
has communication mode: S

type.dpt.field.512.500.i1.pc.CE
type: Datapoint Type Field
type: NamedIndividual
description: Power Constraint Element
field index: 1
field type: D<n>
includes counter: type.dpt.field.512.500.i0.pc.CE CNT
includes datapoint field: type.dpt.field.pc.i0

Busmonitor Error Flags = 3
type: NamedIndividual
value API: busmonitorErrorFlags
value KNX: 3

Standby = 2
type: NamedIndividual
is applicable datapoint enum of: HVAC Mode Standby
value API: standby
value KNX: 2

Discharge air, e.g. for VAV = 3
type: NamedIndividual
value API: dischargeAir,E.g.ForVAV
value KNX: 3

type.dpt.field.250.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: status
field index: 0
field size: 24
field string schema: raw
field type: A[n]

type.dpt.field.244.600.i0.CF
type: NamedIndividual
type: Datapoint Type Field
description: Converter Failure
field index: 0
field name: CF
field size: 2
field type: N
includes key value pair: Failure detected = 2
includes key value pair: type.kvpair.244.600.i0.0
includes key value pair: No failure detected = 1

humidification = 1
type: NamedIndividual
value API: humidification
value KNX: 1

type.dpt.field.512.503.i4.pei.ET
type: NamedIndividual
type: Datapoint Type Field
description: timestamp when the instruction has to be executed
field index: 4
field name: ET
field size: 64
includes DPT: DateTime

Trigger
type: NamedIndividual
type: Point Operation
description: The value does not carry data to calculate with, only the access to it can already be interpreted.

type.dpt.field.251.600.i9.R
type: Datapoint Type Field
type: NamedIndividual
description: Colour Level Red
field index: 9
field name: R
field resolution: 0.3921566
field size: 8
field type: U
includes digit: type.digit.u8
unit: PERCENT

type.dpt.field.242.600.i1.C
type: NamedIndividual
type: Datapoint Type Field
description: This field shall indicate whether the colour infor-mation in the fields x-axis and y-axis is valid or not.
field index: 1
field name: C
field size: 1
field type: B
includes key value pair: type.kvpair.valid
includes key value pair: type.kvpair.invalid

TempRoomSetpSetHeatEff
type: Class
subject: 399.54
subject: TempRoomSetpSetHeatEff
subject: 54
interface object type annotation: 399
label: TempRoomSetpSetHeatEff
property identifier annotation: 54
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: tempRoomSetpSetF16 a4a
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeProtection
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 54
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType

number
type: DatatypeProperty
comment: Used to define the current number of an entity, such as the building number. May be used from other concepets, therefore no domain is defined.
range: string
sub property of: topDataProperty

The visual effect of channel 6 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel6IsActive
value KNX: 1

Dim Send Style
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.013: Dim Send Style
subject: 1.013
subject: 1.13
subject: Dim Send Style
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 13
is assembled with: Dim Send Style
label: Dim Send Style
has communication mode: S

Ice
type: PhenomenonType
type: NamedIndividual
description: Water in its solid form

type.dpt.field.230.1000.i0.Medium
type: NamedIndividual
type: Datapoint Type Field
description: Medium
field index: 0
field name: Medium
field size: 8
field type: N
includes key value pair: type.kvpair.230.1000.i0.5
includes key value pair: Cooling Load meter (inlet) = 10
includes key value pair: Breaker (electricity) = 32
includes key value pair: type.kvpair.230.1000.i0.55
includes key value pair: type.kvpair.230.1000.i0.12
includes key value pair: type.kvpair.230.1000.i0.7
includes key value pair: Other = 0
includes key value pair: type.kvpair.230.1000.i0.6
includes key value pair: Waste water meter = 40
includes key value pair: Bus/System = 14
includes key value pair: Compressed Air = 9
includes key value pair: Valve (gas or water) = 33
includes key value pair: type.kvpair.230.1000.i0.13
includes key value pair: type.kvpair.230.1000.i0.2
includes key value pair: type.kvpair.230.1000.i0.1
includes key value pair: type.kvpair.230.1000.i0.3
includes key value pair: Garbage = 41
includes key value pair: type.kvpair.230.1000.i0.11
includes key value pair: type.kvpair.230.1000.i0.4
includes key value pair: Heat cost allocator = 8
includes key value pair: type.kvpair.230.1000.i0.15

volume flow, 0,01 l/min = 66
type: NamedIndividual
value API: volumeFlow,0,01Lmin
value KNX: 66

Blinds Status
type: Class
subclass of: Restriction
  has value: Up Down
  on property: datapointType
subclass of: Restriction
  has value: qk ph light illuminance room
  on property: observesPhenomenonQualityKind
subclass of: Restriction
  has value: qk eq blindsactuator positionvector
  on property: measuresEquipmentQualityKind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq blindsactuator positionvector
      on property: refersTo
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: downwards
      on property: hasStateType
    intersection of: Restriction
      has value: upwards
      on property: hasStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Function Point

ReactiveEnergy
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 13.012: ReactiveEnergy
subject: 13.12
subject: ReactiveEnergy
subject: 13.012
dpt bit size max: 32
dpt major number: 13
datapoint type minor number: 12
is assembled with: type.dpt.field.13.12.i0
label: ReactiveEnergy
has communication mode: S

The visual effect of channel 10 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel10IsInactiv
value KNX: 0

Level 12 = 12
type: NamedIndividual
value API: level12
value KNX: 12

at base condition = 2
type: NamedIndividual
value API: atBaseCondition
value KNX: 2

type.dpt.field.20.801.i0
type: NamedIndividual
type: Datapoint Type Field
description: SABExceptBehaviour
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.801.i0.2
includes key value pair: type.kvpair.20.801.i0.0
includes key value pair: type.kvpair.20.801.i0.3
includes key value pair: type.kvpair.20.801.i0.1
includes key value pair: stop = 4

Value Light Quantity
type: Datapoint Type
type: NamedIndividual
description: DPT 14.040: Value of light quantity
subject: 14.040
subject: Value Light Quantity
subject: 14.40
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 40
is assembled with: type.dpt.field.14.40.i0
label: Value Light Quantity
has communication mode: S

DeltaTime100MSec
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 8.004: DeltaTime100MSec
subject: 8.004
subject: DeltaTime100MSec
subject: 8.4
dpt bit size max: 16
dpt major number: 8
datapoint type minor number: 4
is assembled with: type.dpt.field.8.4.i0
label: DeltaTime100MSec
has communication mode: S

Length mm
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 7.011: Length mm
subject: 7.11
subject: 7.011
subject: Length mm
dpt bit size max: 16
dpt major number: 7
datapoint type minor number: 11
is assembled with: type.dpt.field.7.11.i0
label: Length mm
has communication mode: S

Hardwired inhibit mode active = 3
type: NamedIndividual
value API: hardwiredInhibitModeActive
value KNX: 3

Group Object Type exceeds (PID_MAX_APDU_LENGTH - 2) = 18
type: NamedIndividual
value API: groupObjectTypeExceeds(PID_MAX_APDU
value KNX: 18

Value Thermal Conductivity
type: Datapoint Type
type: NamedIndividual
description: DPT 14.072: Value of thermal conductivity
subject: 14.72
subject: Value Thermal Conductivity
subject: 14.072
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 72
is assembled with: type.dpt.field.14.72.i0
label: Value Thermal Conductivity
has communication mode: S

is room of
type: ObjectProperty
domain: Room
range: Class
  union of: Building
  union of: Floor
  union of: Room
  union of: Space
sub property of: isSpaceOf

FanStep
type: Class
subject: 56
subject: 372.56
subject: FanStep
interface object type annotation: 372
label: FanStep
property identifier annotation: 56
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 56
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 372
    on property: interface object type
subclass of: Restriction
  has value: uCountValue8Z
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.digit.u8 0 10
type: NamedIndividual
range max: 10
range min: 0

type.dpt.field.1.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: 1-bit
field index: 0
field size: 1
field string schema: raw
field type: A[n]

type.dpt.field.517.500.i3.lr.AC
type: NamedIndividual
type: Datapoint Type Field
description: limit range is related to abnormal condition
field index: 3
field size: 1
field type: B
includes key value pair: type.kvpair.AbnormalCondition
includes key value pair: No abnormal condition

emPowerRange
type: NamedIndividual
type: Datapoint Type
description: Power Range
dpt bit size max: 32
dpt major number: 516
datapoint type minor number: 500
is assembled with: type.dpt.field.516.500.i1.pr.UV
is assembled with: type.dpt.field.516.500.i0.pr.LV

History values
type: NamedIndividual
type: Point Function
description: A Point representing history/ trend data with a log of timestamp/value pairs. Only this tag value is allowed to be used together with other tags from this category, such as to define a Datapoint expressing a history log of process values.

Heat Stage B Actuator Calibration Mode
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
    intersection of: Restriction
      has value: operationalStateCalibration
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Function Point

Haystack
type: Protocol
type: NamedIndividual

ActTargetPosCoolStageB
type: Class
subject: 105
subject: 399.105
subject: ActTargetPosCoolStageB
interface object type annotation: 399
label: ActTargetPosCoolStageB
property identifier annotation: 105
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 105
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind

Unknown = 0
type: NamedIndividual
value API: unknown
value KNX: 0

type.dpt.field.218.2.i1.FlowRate
type: NamedIndividual
type: Datapoint Type Field
description: Flow Rate in m³/h with high resolution
field index: 1
field name: FlowRate
field resolution: 0.0001
field size: 32
field type: V
includes digit: type.digit.s32
unit: M3-PER-HR

3 h = 22
type: NamedIndividual
value API: 3H
value KNX: 22

type.dpt.field.21.1010.i4.ActivationStateOfChannel5
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 5
field index: 4
field name: ActivationStateOfChannel5
field size: 1
field type: B
includes key value pair: type.kvpair.21.1010.i4.0
includes key value pair: type.kvpair.21.1010.i4.1

type.dpt.field.22.103.i3.FrostAlarm
type: NamedIndividual
type: Datapoint Type Field
description: Frost Alarm
field index: 3
field name: FrostAlarm
field size: 1
field type: B
includes key value pair: No alarm = 0
includes key value pair: alarm = 1

The visual effect of channel 6 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel6IsActive
value KNX: 1

type.dpt.field.12.101.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 32
field type: U
includes digit: type.digit.u32
unit: MIN

The visual effect of channel 6 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel6IsInactive
value KNX: 0

type.dpt.field.205.103.i1.HVACAirQuality
type: NamedIndividual
type: Datapoint Type Field
description: Relative air quality value
field index: 1
field name: HVACAirQuality
field resolution: 1.0
field size: 16
field type: V
includes digit: type.digit.s16
unit: PPM

type.dpt.field.20.105.i0
type: NamedIndividual
type: Datapoint Type Field
description: HVACContrMode
field index: 0
field size: 8
field type: N
includes key value pair: Emergency Steam Mode = 17
includes key value pair: type.kvpair.20.105.i0.0
includes key value pair: Dehumidification = 14
includes key value pair: Maximum Heating Mode = 12
includes key value pair: Off = 6
includes key value pair: type.kvpair.20.105.i0.4
includes key value pair: type.kvpair.20.105.i0.15
includes key value pair: type.kvpair.20.105.i0.8
includes key value pair: type.kvpair.20.105.i0.13
includes key value pair: type.kvpair.20.105.i0.7
includes key value pair: type.kvpair.20.105.i0.10
includes key value pair: type.kvpair.20.105.i0.5
includes key value pair: type.kvpair.20.105.i0.9
includes key value pair: type.kvpair.20.105.i0.11
includes key value pair: type.kvpair.20.105.i0.20
includes key value pair: type.kvpair.20.105.i0.16
includes key value pair: type.kvpair.20.105.i0.1
includes key value pair: Cool = 3
includes key value pair: type.kvpair.20.105.i0.2

type.dpt.field.8.10.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field size: 16
field type: V
includes digit: type.digit.s16
unit: PERCENT

Value Energy
type: Datapoint Type
type: NamedIndividual
description: DPT 14.031: Value of energy
subject: 14.031
subject: Value Energy
subject: 14.31
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 31
is assembled with: type.dpt.field.14.31.i0
label: Value Energy
has communication mode: S

TempRoomSetpHeatEff
type: Class
subject: TempRoomSetpHeatEff
subject: 58
subject: 397.58
interface object type annotation: 397
label: TempRoomSetpHeatEff
property identifier annotation: 58
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 58
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType

type.dpt.field.207.101.i0.LockRequest
type: NamedIndividual
type: Datapoint Type Field
description: indicates if power reduction is necessary (validity of PwrReduction)
field index: 0
field name: LockRequest
field size: 1
includes DPT: Bool

Enable
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.3.i0.0
includes key value pair: Enable = 1
label: Enable

auto (PSU/DPSU automatic on/off) = 2
type: NamedIndividual
value API: auto(PSUDPSUAutomaticOnoff)
value KNX: 2

Steam
type: PhenomenonType
type: NamedIndividual
description: Water in its gas form

type.dpt.field.14.27.i0
type: NamedIndividual
type: Datapoint Type Field
description: electric potential
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/V

reliable synchronisation source (radio, Internet) = 1
type: NamedIndividual
value API: reliableSynchronisationSource(radio
value KNX: 1

type.dpt.field.21.102.i7.SummerMode
type: Datapoint Type Field
type: NamedIndividual
description: SummerMode
field index: 7
field name: SummerMode
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

Window Door
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.19.i0.1
includes key value pair: type.kvpair.1.19.i0.0
label: Window Door

type.dpt.field.ombc.om.i2.PR CNT
type: NamedIndividual
type: Datapoint Type Field
description: number of power ranges
field index: 2
field name: PR_CNT
field size: 3
field type: U
includes digit: type.digit.u3

Converter Status
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 244.600: Converter Status
subject: 244.600
subject: Converter Status
dpt bit size max: 16
dpt major number: 244
datapoint type minor number: 600
is assembled with: type.dpt.field.244.600.i0.CF
is assembled with: type.dpt.field.244.600.i2.DP
is assembled with: type.dpt.field.244.600.i1.PP
is assembled with: type.dpt.field.244.600.i5.HSswitch
is assembled with: type.dpt.field.244.600.i4.HSinhibit
is assembled with: type.dpt.field.244.600.i3.FP
is assembled with: type.dpt.field.244.600.i6.Reserved
is assembled with: type.dpt.field.244.600.i7.CM
label: Converter Status
has communication mode: S

type.dpt.field.275.101.i0.TempSetpShiftBProt
type: NamedIndividual
type: Datapoint Type Field
description: room temperature setpoint shift building protection
field index: 0
field name: TempSetpShiftBProt
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: http://qudt.org/vocab/unit/K

The visual effect of channel 24 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel24IsActive
value KNX: 1

type.dpt.field.22.1010.i1.ActivationStateOfChannel2
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 2
field index: 1
field name: ActivationStateOfChannel2
field size: 1
field type: B
includes key value pair: type.kvpair.22.1010.i1.1
includes key value pair: The visual effect of channel 2 is inactive = 0

Concentration, VOC
type: NamedIndividual
type: Quantity Kind
description: Refers to the concentration of volatile organic compounds (TVOC) in the air, measured in ppm. This is a specialization of quantitykind:Concentration.

Heating-Cooling Stages Primary
type: NamedIndividual
type: StateType
description: This state type relates to the primary stage of the HVAC system. In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.

LockDevice
type: Class
subject: LD
subject: 417.69
subject: LockDevice
subject: 69
interface object type annotation: 417
label: LockDevice
property identifier annotation: 69
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Locked State
      on property: hasStateType
    intersection of: Restriction
      has value: Unlocked State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: Enable
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 69
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 417
    on property: interface object type

Extended Relative Timestamp = 6
type: NamedIndividual
value API: extendedRelativeTimestamp
value KNX: 6

ComfortProlongEff
type: Class
subject: 83
subject: ComfortProlongEff
subject: 398.83
interface object type annotation: 398
label: ComfortProlongEff
property identifier annotation: 83
subclass of: Restriction
  has value: State
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 83
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type

alarm position is DOWN = 2
type: NamedIndividual
value API: alarmPositionIsDOWN
value KNX: 2

type.dpt.field.256.1.i0.StopDateTime
type: NamedIndividual
type: Datapoint Type Field
description: Stop Date Time
field index: 0
field name: StopDateTime
field size: 64
includes DPT: DateTime

DetectedLoadType
type: Class
subject: 56
subject: 418.56
subject: DetectedLoadType
interface object type annotation: 418
label: DetectedLoadType
property identifier annotation: 56
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 56
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: loadTypeDetected
  on property: datapointType

failure = 1
type: NamedIndividual
value API: failure
value KNX: 1

Luminance
type: Quantity Kind
type: NamedIndividual
description: Illuminance is the total luminous flux incident on a surface, per unit area. It is a measure of the intensity of the incident light, wavelength-weighted by the luminosity function to correlate with human brightness perception. As a note, focus is the light source, which is mostly NOT the interest in the building control domain.

DEG
type: NamedIndividual
type: Unit
symbol: °

value according additional parameter = 3
type: NamedIndividual
value API: valueAccordingAdditionalParameter
value KNX: 3

type.digit.u5 0 24
type: NamedIndividual
range max: 24
range min: 0

ControlModeUser
type: Class
subject: 64
subject: ControlModeUser
subject: 420.64
interface object type annotation: 420
label: ControlModeUser
property identifier annotation: 64
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Override Mode Manual
      on property: hasStateType
    intersection of: Restriction
      has value: overrideModeAutomatic
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: lightControlMode
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 64
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 420
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.236.1.i1.p
type: NamedIndividual
type: Datapoint Type Field
description: priority level
field index: 1
field name: p
field size: 3
field type: N
includes key value pair: Level 2 = 2
includes key value pair: type.kvpair.236.1.i1.5
includes key value pair: type.kvpair.236.1.i1.1
includes key value pair: Level 3 = 3
includes key value pair: Level 0 = 0
includes key value pair: type.kvpair.236.1.i1.7
includes key value pair: type.kvpair.236.1.i1.6
includes key value pair: type.kvpair.236.1.i1.4

type.dpt.field.252.600.i1.MaskCB
type: NamedIndividual
type: Datapoint Type Field
description: validity of the fields CB and Step Code Colour Blue.
field index: 1
field name: MaskCB
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

Percent V16 Z
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 205.017: Percent_V16_Z
subject: Percent V16 Z
subject: 205.017
subject: 205.17
dpt bit size max: 24
dpt major number: 205
datapoint type minor number: 17
is assembled with: type.dpt.field.205.17.i0.StatusCommand
is assembled with: type.dpt.field.205.17.i1.RelSignedValue
label: Percent V16 Z
has communication mode: LTE

manufacturer
type: FunctionalProperty
type: DatatypeProperty
comment: The manufacturer of an application program or product (as a note, a device is part of a product).
domain: Class
  union of: ApplicationProgram
  union of: Product
range: string

CombinedStatus_RTSM
type: Class
subject: 64
subject: 397.64
subject: CombinedStatus_RTSM
interface object type annotation: 397
label: CombinedStatus_RTSM
property identifier annotation: 64
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: hvacModeAuto
      on property: relatesToStateType
subclass of: Restriction
  has value: qk ph person positionvector room
  on property: hasQualityKind
subclass of: Restriction
  has value: Combined Status RTSM
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: Trigger
      on property: hasPointOperation
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: presenceOccupied
      on property: hasStateType
    intersection of: Restriction
      has value: Presence Unoccupied
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: totalizedValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph person positionvector room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: opened
      on property: hasStateType
    intersection of: Restriction
      has value: closed
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: totalizedValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq window positionvector room
      on property: refersTo
subclass of: Restriction
  has value: qk eq window positionvector room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 64
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type

Reduced = 3
type: NamedIndividual
value API: reduced
value KNX: 3

type.dpt.field.522.500.i0.si.ET
type: NamedIndividual
type: Datapoint Type Field
description: timestamp when instruction shall be executed. In case the instruction type is SCHEDULE, ET will be the start time of the addressed sequence.
field index: 0
field name: ET
field size: 64
includes DPT: DateTime

Sun
type: PhenomenonType
type: NamedIndividual
description: Relating to energy from the sun.

Direction 1
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: direction1
field size: 1
includes DPT: Up Down
label: Direction 1

type.dpt.field.14.78.i0
type: Datapoint Type Field
type: NamedIndividual
description: weight
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/N

uncritical = 0
type: NamedIndividual
value API: uncritical
value KNX: 0

Public Building
type: Location Usages
type: NamedIndividual
description: Preferably used with a Building.

ActCurrPosCoolStageB
type: Class
subject: 69
subject: 399.69
subject: ActCurrPosCoolStageB
interface object type annotation: 399
label: ActCurrPosCoolStageB
property identifier annotation: 69
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 69
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

PPM
type: NamedIndividual
type: Unit
symbol: PPM

datapoint type minor number
type: DatatypeProperty
type: FunctionalProperty
comment: The trailing number of the minor datapoint type (DPT) in bits, specified in KNX with a numerical scheme. The minor type must be present for sub types but not for a major type. The range is used to include 0 (the KNX DPT numbering scheme starts at 0).
range: nonNegativeInteger
sub property of: datapoint type

type.dpt.field.11.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: date
field index: 0
field size: 24
field string schema: raw
field type: A[n]

is equipment of
type: ObjectProperty
domain: Equipment
range: Location

type.dpt.field.14.41.i0
type: NamedIndividual
type: Datapoint Type Field
description: luminance
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: CD-PER-M2

is equipment quality kind adjusted by
type: ObjectProperty
domain: Restriction
  all values from: Class
    union of: EquipmentType
    union of: Locality
    union of: Quantity Kind
  on property: isTagOf
sub property of: isQualityKindOf

type.dpt.field.12.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 4-byte unsigned value
field index: 0
field size: 32
field type: U
includes digit: type.digit.u32

MaC floor
type: Class
equivalent class: Class
  intersection of: Floor
  intersection of: Restriction
    all values from: Class
      one of: elevatorShaft
      one of: Entrance
      one of: Hallway
      one of: staircase
    on property: has location usage
comment: By a MaC (ETS) allowed location usages for a floor.

Bool Control
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 2.002: Bool Control
subject: 2.002
subject: Bool Control
subject: 2.2
dpt bit size max: 2
dpt major number: 2
datapoint type minor number: 2
is assembled with: type.dpt.field.2.2.i0.bool
is assembled with: type.dpt.field.2.x.i1.c
label: Bool Control
has communication mode: S

type.dpt.field.psc.i2.SQ SEL
type: NamedIndividual
type: Datapoint Type Field
description: Selected power sequence container
field index: 2
field name: SQ_SEL
field size: 4
field type: U
includes digit: type.digit.u4

reset command (trigger) = 1
type: NamedIndividual
value API: resetCommand(trigger)
value KNX: 1

StatusGen
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 21.001: StatusGen
subject: 21.1
subject: StatusGen
subject: 21.001
dpt bit size max: 8
dpt major number: 21
datapoint type minor number: 1
is assembled with: type.dpt.field.21.1.i5.Reserved
is assembled with: type.dpt.field.21.1.i2.Overridden
is assembled with: type.dpt.field.21.1.i3.InAlarm
is assembled with: type.dpt.field.21.1.i1.Fault
is assembled with: type.dpt.field.21.1.i4.AlarmUnAck
is assembled with: type.dpt.field.21.1.i0.OutOfService
label: StatusGen
has communication mode: S

TempRoomSetpCoolEffNext
type: Class
subject: 54
subject: 101.54
subject: TempRoomSetpCoolEffNext
interface object type annotation: 101
label: TempRoomSetpCoolEffNext
property identifier annotation: 54
subclass of: Restriction
  has value: qk ph temporal delay
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 54
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 101
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph temporal delay
      on property: refersTo
subclass of: Restriction
  has value: temphvacAbsNext
  on property: datapointType

Electric Power 3 Phase Symmetric
type: NamedIndividual
value API: ElectricPower3PhaseSymmetric
value KNX: 4

type.dpt.field.21.1001.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 3
field name: Reserved
field size: 5
field type: r
includes reserved bit(s): type.bit.reserved

N-SEC
type: Unit
type: NamedIndividual
symbol: N⋅s

Ice = 11
type: NamedIndividual
value API: ice
value KNX: 11

Natural Gas Flow Rate
type: NamedIndividual
value API: NaturalGasFlowRate
value KNX: 5

HeatCoolMode
type: Class
subject: 151
subject: HeatCoolMode
subject: 258.151
interface object type annotation: 258
label: HeatCoolMode
property identifier annotation: 151
subclass of: Restriction
  has value: heatpCool
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 151
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 258
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: controlModeHeating
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

Single close = 1
type: NamedIndividual
value API: singleClose
value KNX: 1

type.digit.s16 neg13650 32767
type: NamedIndividual
range max: 32767
range min: -13650

Month and Day of Month fields valid = 0
type: NamedIndividual
value API: monthAndDayOfMonthFieldsValid
value KNX: 0

type.dpt.field.512.502.i4.pe.LR
type: NamedIndividual
type: Datapoint Type Field
description: list of power envelope elements
field index: 4
field name: LR
field type: D<n>
includes datapoint field: type.dpt.pe.i0

Enabled State
type: StateType
type: NamedIndividual
description: This state type expresses that an equipment or a functionality is enabled. An enabled equipment may become active and fulfill its intended functionality. Being in 'Enabled State' makes no assumption on whether the equipment is currently active or inactive, but it merely expresses the state that the equipment is allowed to be active. Similarly, an enabled functionality is available to the system, i.e. it may contribute to the system's overall functionality. Usually, the equipment or functionality is enabled by management functionality, such as a building management system. This state type is the inverse of the 'Disabled State' state type.

Normal = 0
type: NamedIndividual
value API: normal
value KNX: 0

Alert
type: NamedIndividual
type: Point Function
description: A point contains a warning that draws attention to something that usually does not need immediate attention.

Maximum Heating Mode = 12
type: NamedIndividual
value API: maximumHeatingMode
value KNX: 12

type.dpt.field.225.3.i0.Tariff
type: Datapoint Type Field
type: NamedIndividual
description: The next active Tariff after expiration of the delay time
field index: 0
field name: Tariff
field size: 8
includes DPT: tariff

A-M2
type: NamedIndividual
type: Unit
symbol: A⋅m²

emPowerEnvelopeInstruction
type: NamedIndividual
type: Datapoint Type
dpt bit size max: 1792
dpt major number: 512
datapoint type minor number: 503
is assembled with: type.dpt.field.512.503.i4.pei.ET
is assembled with: type.dpt.field.512.503.i2.pei.IT
is assembled with: type.dpt.field.512.503.i8.pei.PWR ENV
is assembled with: type.dpt.field.512.503.i5.pei.PC ID
is assembled with: type.dpt.field.512.503.i1.pei.AC
is assembled with: type.dpt.field.512.503.i0.pei.ID
is assembled with: type.dpt.field.512.503.i7.pei.PE CNT
is assembled with: type.dpt.field.512.503.pei.Reserved
is assembled with: type.dpt.field.512.503.i3.pei.Reserved

type.dpt.field.209.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 16-Bit Signed Value & 8-Bit Set
field index: 0
field size: 24
field string schema: raw
field type: A[n]

serial number
type: FunctionalProperty
type: DatatypeProperty
comment: An identifier to specify the (string based) erial number of a device.
range: string
sub property of: deviceData

Invert
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.12.i0.0
includes key value pair: Inverted = 1
label: Invert

Shutter and Blinds Mode
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.23.i0.0
includes key value pair: move Up/Down + StepStop mode (blind) = 1
label: Shutter and Blinds Mode

HVAC Air Quality Relative Value
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 205.103: HVACAirQualRel_Z
subject: HVAC Air Quality Relative Value
subject: 205.103
dpt bit size max: 24
dpt major number: 205
datapoint type minor number: 103
is assembled with: type.dpt.field.205.103.i1.HVACAirQuality
is assembled with: type.dpt.field.205.103.i0.StatusCommand
label: HVAC Air Quality Relative Value
has communication mode: LTE

Converter Test Result
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 245.600: Converter Test Result
subject: Converter Test Result
subject: 245.600
dpt bit size max: 48
dpt major number: 245
datapoint type minor number: 600
is assembled with: type.dpt.field.245.600.i4.SD
is assembled with: type.dpt.field.245.600.i0.LPDTR
is assembled with: type.dpt.field.245.600.i5.SF
is assembled with: type.dpt.field.245.600.i7.LTRP
is assembled with: type.dpt.field.245.600.i6.Reserved
is assembled with: type.dpt.field.245.600.i9.LTRF
is assembled with: type.dpt.field.245.600.i8.LTRD
is assembled with: type.dpt.field.245.600.i2.Reserved
is assembled with: type.dpt.field.245.600.i3.SP
is assembled with: type.dpt.field.245.600.i1.LDTR
label: Converter Test Result
has communication mode: S

Store Room
type: Location Usages
type: NamedIndividual
description: A store room is a room within a house where equipment not used in day-to-day activities is kept.

dehumidification = 2
type: NamedIndividual
value API: dehumidification
value KNX: 2

type.dpt.field.20.1.i0
type: Datapoint Type Field
type: NamedIndividual
description: SCLOMode
field index: 0
field size: 8
field type: N
includes key value pair: master = 2
includes key value pair: slave = 1
includes key value pair: type.kvpair.20.1.i0.0

The visual effect of channel 4 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel4IsInactive
value KNX: 0

EnableHCStage Z
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 201.105: EnableHCStage Z
subject: EnableHCStage Z
subject: 201.105
dpt bit size max: 16
dpt major number: 201
datapoint type minor number: 105
is assembled with: type.dpt.field.201.105.i1.EnableHCStage
is assembled with: type.dpt.field.201.105.i0.StatusCommand
label: EnableHCStage Z
has communication mode: LTE

Electrical
type: Trade
type: NamedIndividual
description: An electrical installation is a group of items of electrical equipment that are permanently electrically connected together and can be supplied with electricity from the works of an electricity entity or from a generating source. An electrical installation contains the electrical wiring of buildings, transmission lines, stationary machines, fuses, and related equipment.

Programmable Controller
type: EquipmentType
type: NamedIndividual
description: A programmable logic controller (PLC) or programmable controller is an industrial computer that has been ruggedized and adapted for the control of manufacturing processes, such as assembly lines, machines, robotic devices, or any activity that requires high reliability, ease of programming, and process fault diagnosis.

Quantity Kind
type: Class
comment: The tag category contains individuals that describe the numerical quantity of the measurement/adjustment (equipment) or observation/actuation (phenomenon).
subclass of: Tag

at least one comfort push button is pressed = 1
type: NamedIndividual
value API: atLeastOneComfortPushButtonIsPresse
value KNX: 1

no filtering, all supported received frames shall be passed to the cEMI client using L_Data.ind = 0
type: NamedIndividual
value API: noFiltering,AllSupportedReceivedFra
value KNX: 0

Value Electric Displacement
type: Datapoint Type
type: NamedIndividual
description: DPT 14.022: Value of electric displacement
subject: Value Electric Displacement
subject: 14.22
subject: 14.022
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 22
is assembled with: type.dpt.field.14.22.i0
label: Value Electric Displacement
has communication mode: S

mass flow, 0,1 kg/h = 82
type: NamedIndividual
value API: massFlow,0,1Kgh
value KNX: 82

type.dpt.field.522.500.i2.si.Reserved
type: NamedIndividual
type: Datapoint Type Field
description: reserved bits
field index: 2
field name: RESERVED
field size: 7
field type: r
includes reserved bit(s): type.bit.reserved

type.digit.u8 0 15
type: NamedIndividual
range max: 15
range min: 0

type.dpt.field.21.2.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 3
field name: Reserved
field size: 5
field type: r
includes reserved bit(s): type.bit.reserved

90,5 s = 15
type: NamedIndividual
value API: 90,5S
value KNX: 15

type.dpt.field.512.507.i5.smfrbc.TRAN
type: Datapoint Type Field
type: NamedIndividual
description: list of transitions
field index: 5
field name: TRAN
field type: D<n>
includes counter: type.dpt.field.512.507.i2.smfrbc.TRAN CNT
includes DPT: emTransition

Return Section
type: Locality
type: NamedIndividual
description: Refers to distribution systems used to transport substances (and phenomena) such as water, air, or heat back to the specific centralized plants in a building. The distribution systems interface with the individual rooms at the start of the return part of the distribution system.

type.dpt.field.212.100.i2.TempSetpShiftComf
type: NamedIndividual
type: Datapoint Type Field
description: room temperature setpoint shift comfort (delta value)
field index: 2
field name: TempSetpShiftComf
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16
unit: http://qudt.org/vocab/unit/K

Intrusion Alarming
type: Class
comment: Application functions to monitor an 'intrusion alarm'.
subclass of: monitoring

Media Type
type: DatatypeProperty
comment: An identifier to specify the (string based) media where this product can be used. Usually, IP, RF, TP.
range: string
sub property of: productData

configuration fault = 3
type: NamedIndividual
value API: configurationFault
value KNX: 3

ActTargetFanSpeedEff
type: Class
subject: 397.66
subject: 66
subject: ActTargetFanSpeedEff
interface object type annotation: 397
label: ActTargetFanSpeedEff
property identifier annotation: 66
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 66
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  has value: Scaling
  on property: datapointType

type.dpt.field.21.103.i2.SolarLoadSufficient
type: NamedIndividual
type: Datapoint Type Field
description: SolarLoadSufficient
field index: 2
field name: SolarLoadSufficient
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

off = 0
type: NamedIndividual
value API: off
value KNX: 0

emStateMachineDDBC
type: NamedIndividual
type: Datapoint Type
dpt bit size max: 1792
dpt major number: 512
datapoint type minor number: 510
is assembled with: type.dpt.field.512.510.i0.smddbc.COM
is assembled with: type.dpt.field.512.510.i1.smddbc.OM CNT
is assembled with: type.dpt.field.512.510.i4.smddb.OM
is assembled with: type.dpt.field.512.510.i5.smddb.TRAN
is assembled with: type.dpt.field.512.510.i3.smddb.Reserved
is assembled with: type.dpt.field.512.510.i2.smddb.TRAN CNT

Reset Lamp Time = 4
type: NamedIndividual
value API: resetLampTime
value KNX: 4

Breaker (electricity) = 32
type: NamedIndividual
value API: breaker(electricity)
value KNX: 32

The visual effect of channel 18 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel18IsInactiv
value KNX: 0

OHM
type: NamedIndividual
type: Unit
symbol: Ω

User Shutter Control
type: Class
subject: SSSB
subject: SAB
comment: Application function for 'shutter control'.
subclass of: shadingCtrl
subclass of: Restriction
  on class: WindAlarm
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: ShutterPositionLength
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  has value: qk eq blindsactuator positionvector
  on property: hasQualityKind
subclass of: Restriction
  has value: qk ph light illuminance room
  on property: hasQualityKind
subclass of: Restriction
  on class: Shutter Stop Step
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: ShutterMoveUpDown
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: ShutterStopTrigger
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: Shutter Position Percentage
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: Frost Alarm
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: RainAlarm
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: ShutterStatus
  on property: hasFunctionPoint
  qualified cardinality: 1

type.dpt.field.14.37.i0
type: Datapoint Type Field
type: NamedIndividual
description: heat, quantity of
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/J

unknown = 0
type: NamedIndividual
value API: unknown
value KNX: 0

type.dpt.field.219.1.i4.Ack Sup
type: Datapoint Type Field
type: NamedIndividual
description: Ack_Sup
field index: 4
field name: Ack_Sup
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

ReactiveEnergy kVARh
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 13.015: ReactiveEnergy kVARh
subject: 13.15
subject: 13.015
subject: ReactiveEnergy kVARh
dpt bit size max: 32
dpt major number: 13
datapoint type minor number: 15
is assembled with: type.dpt.field.13.15.i0
label: ReactiveEnergy kVARh
has communication mode: S

Time = UT+X+1 = 1
type: NamedIndividual
value API: time=UT+X+1
value KNX: 1

TempOutside
type: Class
subject: 399.57
subject: TempOutside
subject: 57
interface object type annotation: 399
label: TempOutside
property identifier annotation: 57
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature outside
      on property: refersTo
subclass of: Restriction
  has value: qk ph air temperature outside
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 57
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type

Datapoint Type Field
type: Class
comment: A generic concept to describe the individual parts of a KNX datapoint type. A datapoint type field is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: Class
  intersection of: Restriction
    all values from: nonNegativeInteger
    on property: fieldIndex
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: nonNegativeInteger
    on property: fieldIndex
subclass of: Class
  intersection of: Restriction
    all values from: Literal
    on property: fieldDefault
  intersection of: Restriction
    max cardinality: 1
    on property: fieldDefault
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: fieldStringSchema
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: fieldStringSchema
subclass of: Class
  intersection of: Restriction
    all values from: positiveInteger
    on property: fieldSize
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: positiveInteger
    on property: fieldSize
subclass of: Class
  intersection of: Restriction
    all values from: float
    on property: field resolution
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: float
    on property: field resolution
subclass of: Class
  intersection of: Restriction
    on property: includes
    some values from: Thing
  intersection of: Restriction
    all values from: Thing
    on property: includes
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: field name
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: field name
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: fieldType
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: fieldType
subclass of: Class
  intersection of: Restriction
    all values from: Unit
    on property: unit
  intersection of: Restriction
    max qualified cardinality: 1
    on class: Unit
    on property: unit
subclass of: Core Thing

2,5 min = 14
type: NamedIndividual
value API: 2,5Min
value KNX: 14

The visual effect of channel 15 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel15IsActive
value KNX: 1

type.dpt.field.20.604.i0
type: NamedIndividual
type: Datapoint Type Field
description: LightControlMode
field index: 0
field size: 8
field type: N
includes key value pair: automatic light control = 0
includes key value pair: manual light control = 1

TempOutside
type: Class
subject: 398.64
subject: TempOutside
subject: 64
interface object type annotation: 398
label: TempOutside
property identifier annotation: 64
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature outside
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature outside
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 64
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type

one PB/binary input; SwitchOnOff inverts on each transmission = 1
type: NamedIndividual
value API: onePBbinaryInput
value KNX: 1

Value Magnetic Moment
type: NamedIndividual
type: Datapoint Type
description: DPT 14.047: Value of magnetic moment
subject: Value Magnetic Moment
subject: 14.047
subject: 14.47
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 47
is assembled with: type.dpt.field.14.47.i0
label: Value Magnetic Moment
has communication mode: S

type.dpt.field.14.3.i0
type: Datapoint Type Field
type: NamedIndividual
description: activity (radioactivity)
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: PER-SEC

No abnormal condition
type: NamedIndividual
description: No abnormal condition
value API: nac
value KNX: 0

type.dpt.field.253.600.i1.MaskCC
type: NamedIndividual
type: Datapoint Type Field
description: validity of the fields CC and Step Code Colour.
field index: 1
field name: MaskCC
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

type.dpt.field.15.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: entrance access
field index: 0
field size: 32
field string schema: raw
field type: A[n]

27.x
type: NamedIndividual
type: Datapoint Type
subject: 27.major
subject: 27.x
dpt bit size max: 32
dpt major number: 27
is assembled with: type.dpt.field.27.x.i0
label: 27.x
has communication mode: S

type.dpt.field.512.505.i1.ps.SLT CNT
type: NamedIndividual
type: Datapoint Type Field
description: Number of power sequence slots
field index: 1
field name: SLT_CNT
field size: 4
field type: U
includes digit: type.digit.u4 1 15

DateTime State
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 265.011: DateTime State
subject: 265.011
subject: 265.11
subject: DateTime State
dpt bit size max: 72
dpt major number: 265
datapoint type minor number: 11
is assembled with: type.dpt.field.265.11.i2.DateAndTime
is assembled with: type.dpt.field.265.11.i0.BinaryInformation
is assembled with: type.dpt.field.265.11.i1.Reserved
label: DateTime State
has communication mode: S

sequence interruptible
type: NamedIndividual
description: Sequence is interruptible
value API: seqi
value KNX: 1

type.dpt.field.pc.i4.LR
type: NamedIndividual
type: Datapoint Type Field
description: list of limit ranges
field index: 4
field name: LR
field type: D<n>
includes counter: type.dpt.field.pc.i3.LR CNT
includes DPT: emLimitRange

Supply Section
type: Locality
type: NamedIndividual
description: Refers to distribution systems used to supply a room with e.g. heat, water, or air. Usually, those substances (and the energy they carry) originate in specific plants, which are mostly centralized for each building. From there, the distribution systems transport substances to the individual rooms.

Off State
type: NamedIndividual
type: StateType
description: This state type expresses that an equipment, such as a luminaire, is switched off. This state type is the inverse of the 'On State' state type.

fresh breeze = 5
type: NamedIndividual
value API: freshBreeze
value KNX: 5

Trend
type: Class
comment: A trend application function monitors live and historical, time-indexed, quantitative etc. data, for example, for visuaization.
subclass of: monitoring

type.dpt.field.237.600.i5.ConvertorError
type: NamedIndividual
type: Datapoint Type Field
description: Convertor error
field index: 5
field name: ConvertorError
field size: 1
field type: B
includes key value pair: type.kvpair.237.600.i5.1
includes key value pair: no error = 0

type.dpt.field.14.0.i0
type: NamedIndividual
type: Datapoint Type Field
description: acceleration
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: M-PER-SEC

power, 1000 W = 46
type: NamedIndividual
value API: power,1000W
value KNX: 46

Distance
type: NamedIndividual
type: Quantity Kind
description: "Distance" is a numerical description of how far apart objects are.

type.dpt.field.20.803.i0
type: Datapoint Type Field
type: NamedIndividual
description: SSSBMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.803.i0.3
includes key value pair: type.kvpair.20.803.i0.1
includes key value pair: one push button/binary input, MoveUp / StepUp message sent = 2
includes key value pair: two push buttons/binary inputs mode = 4

has building
type: ObjectProperty
inverse of: is building of
comment: A strong OP relationship to express a relation to building contained in a site.
domain: Class
  union of: Site
  union of: SiteSegment
range: Building
sub property of: has location

has actionpoint
type: ObjectProperty
inverse of: isActionpointOf
range: Actionpoint
sub property of: hasPoint

HVAC Air Qual Z
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 203.100: HVAC Air Qual Z
subject: HVAC Air Qual Z
subject: 203.100
dpt bit size max: 24
dpt major number: 203
datapoint type minor number: 100
is assembled with: type.dpt.field.203.100.i0.StatusCommand
is assembled with: type.dpt.field.203.100.i1.HVACAirQual
label: HVAC Air Qual Z
has communication mode: LTE

SceneInfo
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 26.001: SceneInfo
subject: SceneInfo
subject: 26.001
subject: 26.1
dpt bit size max: 8
dpt major number: 26
datapoint type minor number: 1
is assembled with: type.dpt.field.26.1.i0.SceneNumber
is assembled with: type.dpt.field.26.1.i1.B
is assembled with: type.dpt.field.26.1.i2.Reserved
label: SceneInfo
has communication mode: S

Entertainment
type: Location Usages
type: NamedIndividual
description: Entertainment buildings or places host a form of activity that holds the attention and interest of an audience or gives pleasure and delight. Examples are cinemas, operas, theatres, museum etc. Preferably used with a Building.

Dressing Room
type: Location Usages
type: NamedIndividual
description: A dressing room is a room to get dressed. Preferably used with a Room.

HVAC Contr Mode Z
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 201.104: HVAC Contr Mode Z
subject: HVAC Contr Mode Z
subject: 201.104
dpt bit size max: 16
dpt major number: 201
datapoint type minor number: 104
is assembled with: type.dpt.field.201.104.i0.StatusCommand
is assembled with: type.dpt.field.201.104.i1.HVACContrMode
label: HVAC Contr Mode Z
has communication mode: LTE

Extended emergency mode active = 6
type: NamedIndividual
value API: extendedEmergencyModeActive
value KNX: 6

BurnerType
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.101: BurnerType
subject: 20.101
subject: BurnerType
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 101
is assembled with: type.dpt.field.20.101.i0
label: BurnerType
has communication mode: S

DT in progress = 8
type: NamedIndividual
value API: dTInProgress
value KNX: 8

type.dpt.field.20.1204.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 8
field type: N
includes key value pair: deactivated = 0
includes key value pair: type.kvpair.20.1204.i0.2
includes key value pair: activated without security = 1

mode 0 is active = 1
type: NamedIndividual
value API: mode0IsActive
value KNX: 1

240.x
type: Datapoint Type
type: NamedIndividual
subject: 240.x
subject: 240.major
dpt bit size max: 24
dpt major number: 240
is assembled with: type.dpt.field.240.x.i0
label: 240.x
has communication mode: S

Start
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.10.i0.0
includes key value pair: type.kvpair.1.10.i0.1
label: Start

type.dpt.field.238.1.i2.StorageFunction
type: NamedIndividual
type: Datapoint Type Field
description: The field Storage function shall indicate whether the set value(s) for the scene number SN can be modified at runtime through DPT_SceneControl or not.
field index: 2
field name: StorageFunction
field size: 1
field type: B
includes key value pair: enable = 0
includes key value pair: type.kvpair.238.1.i2.1

12 h = 24
type: NamedIndividual
value API: 12H
value KNX: 24

volume flow, 10000 ml/s = 79
type: NamedIndividual
value API: volumeFlow,10000Mls
value KNX: 79

energy, 0,001 kJ = 8
type: NamedIndividual
value API: energy,0,001KJ
value KNX: 8

Value Humidity
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 9.007: Value Humidity
subject: 9.7
subject: 9.007
subject: Value Humidity
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 7
is assembled with: type.dpt.field.9.7.i0
label: Value Humidity
has communication mode: S

emTransitionInstruction
type: NamedIndividual
type: Datapoint Type
description: Instruction to force the state machine switching from one operation mode to another or just set a new new value of the operation mode factor
dpt bit size max: 104
dpt major number: 524
datapoint type minor number: 500
is assembled with: type.dpt.field.524.500.i1.ti.Reserved
is assembled with: type.dpt.field.524.500.i4.ti.ID
is assembled with: type.dpt.field.524.500.i2.ti.OMF
is assembled with: type.dpt.field.524.500.i0.ti.AC
is assembled with: type.dpt.field.524.500.i3.ti.ET

type.dpt.field.201.102.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

type.dpt.field.21.1000.i0.Asynchronous
type: NamedIndividual
type: Datapoint Type Field
description: Asynchronous
field index: 0
field name: Asynchronous
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

has location usage
type: ObjectProperty
inverse of: is location usage of
domain: Location
range: Location Usages
sub property of: has tag

BlinkingDisabled = 0
type: NamedIndividual
value API: blinkingDisabled
value KNX: 0

error = 1
type: NamedIndividual
value API: error
value KNX: 1

Logical Function
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 1.021: Logical Function
subject: 1.021
subject: Logical Function
subject: 1.21
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 21
is assembled with: Logical Function
label: Logical Function
has communication mode: S

type.dpt.field.512.503.i7.pei.PE CNT
type: Datapoint Type Field
type: NamedIndividual
description: number of poer envelopes
field index: 7
field name: PE_CNT
field size: 8
field type: U
includes digit: type.digit.u8 0 15

Cool Stage B Actuator Fault
type: Class
subclass of: Function Point
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
    intersection of: Restriction
      has value: operationalStateFaulty
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1

Energy Management
type: NamedIndividual
type: Trade
description: Metering and monitoring are used, for example, for efficient energy management.

type.digit.u4 1 15
type: NamedIndividual
range max: 15
range min: 1

Value Speed
type: Datapoint Type
type: NamedIndividual
description: DPT 14.065: Value of speed
subject: 14.065
subject: Value Speed
subject: 14.65
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 65
is assembled with: type.dpt.field.14.65.i0
label: Value Speed
has communication mode: S

valve (gas or water) = 33
type: NamedIndividual
value API: valve(gasOrWater)
value KNX: 33

type.dpt.field.20.2.i0
type: NamedIndividual
type: Datapoint Type Field
description: BuildingMode
field index: 0
field size: 8
field type: N
includes key value pair: Building not used = 1
includes key value pair: Building protection = 2
includes key value pair: Building in use = 0

Level 8 = 8
type: NamedIndividual
value API: level8
value KNX: 8

224.x
type: NamedIndividual
type: Datapoint Type
subject: 224.x
subject: 224.major
dpt bit size max: 48
dpt major number: 224
is assembled with: type.dpt.field.224.x.i0
label: 224.x
has communication mode: LTE

TempRoomSetpHeatEff
type: Class
subject: TempRoomSetpHeatEff
subject: 399.52
subject: 52
interface object type annotation: 399
label: TempRoomSetpHeatEff
property identifier annotation: 52
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType

Heat (inlet) = 12
type: NamedIndividual
value API: heat(inlet)
value KNX: 12

type.dpt.field.20.120.i0
type: NamedIndividual
type: Datapoint Type Field
description: ADAType
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.120.i0.1
includes key value pair: VAV = 2

SwitchOnOffForced
type: Class
subject: 418.61
subject: 61
subject: SwitchOnOffForced
interface object type annotation: 418
label: SwitchOnOffForced
property identifier annotation: 61
subclass of: Restriction
  has value: Switch Control
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 61
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.21.103.i1.SDHWLoadActive
type: NamedIndividual
type: Datapoint Type Field
description: SDHWLoadActive
field index: 1
field name: SDHWLoadActive
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.213.102.i1.TempSetpShiftEco
type: Datapoint Type Field
type: NamedIndividual
description: room temperature setpoint shift economy (delta value)
field index: 1
field name: TempSetpShiftEco
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16
unit: http://qudt.org/vocab/unit/K

Water
type: PhenomenonType
type: NamedIndividual
description: Water (chemical formula H2O) is an inorganic, transparent, tasteless, odorless, and nearly colorless chemical substance, which is the main constituent of Earth's hydrosphere and the fluids of all known living organisms.

230.x
type: NamedIndividual
type: Datapoint Type
subject: 230.x
subject: 230.major
dpt bit size max: 64
dpt major number: 230
is assembled with: type.dpt.field.230.x.i0
label: 230.x
has communication mode: S

type.dpt.field.20.104.i0
type: NamedIndividual
type: Datapoint Type Field
description: LoadPriority
field index: 0
field size: 8
field type: N
includes key value pair: None = 0
includes key value pair: Shift load priority = 1
includes key value pair: type.kvpair.20.104.i0.2

Dining Room
type: Location Usages
type: NamedIndividual
description: A dining room is a room for consuming food. Preferably used with an Room.

type.dpt.field.13.10.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: V
includes digit: type.digit.s32
unit: W-HR

SwitchOnOff
type: Class
subject: 418.62
subject: SwitchOnOff
subject: 62
interface object type annotation: 418
label: SwitchOnOff
property identifier annotation: 62
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 62
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type

Unknown = 0
type: NamedIndividual
value API: unknown
value KNX: 0

Historical = 0
type: NamedIndividual
value API: historical
value KNX: 0

type.dpt.field.14.52.i0
type: NamedIndividual
type: Datapoint Type Field
description: mass flux
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: KiloGM-PER-SEC

type.dpt.field.21.1.i0.OutOfService
type: Datapoint Type Field
type: NamedIndividual
description: corresponding Datapoint value is out of service
field index: 0
field name: OutOfService
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

type.dpt.field.20.102.i0
type: Datapoint Type Field
type: NamedIndividual
description: HVACMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.102.i0.2
includes key value pair: Auto = 0
includes key value pair: type.kvpair.20.102.i0.1
includes key value pair: Economy = 3
includes key value pair: Building Protection = 4

Garden
type: NamedIndividual
type: Location Usages
description: A garden is a planned space, usually outdoors, set aside for the cultivation, display, and enjoyment of plants and other forms of nature. Preferably used with an outside Location or Space.

6.x
type: NamedIndividual
type: Datapoint Type
subject: 6.major
subject: 6.x
dpt bit size max: 8
dpt major number: 6
is assembled with: type.dpt.field.6.x.i0
label: 6.x
has communication mode: S

HumRelSetpHumEff
type: Class
subject: 51
subject: HumRelSetpHumEff
subject: 103.51
interface object type annotation: 103
label: HumRelSetpHumEff
property identifier annotation: 51
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 103
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air relativehumidity room
      on property: refersTo
    intersection of: Restriction
      has value: humidificationMode
      on property: relatesToStateType
subclass of: Restriction
  has value: relValueZ
  on property: datapointType
subclass of: Restriction
  has value: qk ph air relativehumidity room
  on property: hasQualityKind

type.dpt.field.13.13.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: V
includes digit: type.digit.s32
unit: KiloW-HR

type.dpt.field.222.101.i2.TempSetpShiftComf
type: NamedIndividual
type: Datapoint Type Field
description: TempSetpShiftComf
field index: 2
field name: TempSetpShiftComf
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: http://qudt.org/vocab/unit/K

Width
type: NamedIndividual
type: Quantity Kind
description: "Width" is the middle of three dimensions: length, width, thickness.

Refrigerator
type: EquipmentType
type: NamedIndividual
description: A washing machine (laundry machine, clothes washer, washer, or simply wash) is a home appliance (EN 50523) used to wash laundry.

last received absolute setvalue = 2
type: NamedIndividual
value API: lastReceivedAbsoluteSetvalue
value KNX: 2

type.dpt.field.14.77.i0
type: Datapoint Type Field
type: NamedIndividual
description: volume flux
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: M3-PER-SEC

type.dpt.field.21.100.i7.RoomHMax
type: NamedIndividual
type: Datapoint Type Field
description: RoomHMax
field index: 7
field name: RoomHMax
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.250.600.i0.BrightnessStepValidity
type: NamedIndividual
type: Datapoint Type Field
description: CB and Step Code Brightness Validity
field index: 0
field name: BrightnessStepValidity
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

StatusWTC
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 209.103: StatusWTC
subject: 209.103
subject: StatusWTC
dpt bit size max: 24
dpt major number: 209
datapoint type minor number: 103
is assembled with: type.dpt.field.209.103.i2.CtrlStatus
is assembled with: type.dpt.field.209.103.i1.Fault
is assembled with: type.dpt.field.209.103.i4.TempWater
is assembled with: type.dpt.field.209.103.i0.TempWaterValid
is assembled with: type.dpt.field.209.103.i3.Reserved
label: StatusWTC
has communication mode: LTE

filtering by KNX Serial Number table = 2
type: NamedIndividual
value API: filteringByKNXSerialNumberTable
value KNX: 2

includes reserved bit(s)
type: ObjectProperty
sub property of: includes

Technical Room
type: NamedIndividual
type: Location Usages
description: A technical room is a space in a building that is used to host equipment. Preferably used with a Room.

29.x
type: NamedIndividual
type: Datapoint Type
subject: 29.major
subject: 29.x
dpt bit size max: 64
dpt major number: 29
is assembled with: type.dpt.field.29.x.i0
label: 29.x
has communication mode: S

type.dpt.field.lb.lbe.i0.LR
type: NamedIndividual
type: Datapoint Type Field
description: the leakage rate for the given FLR
field index: 0
field name: LR
field size: 16
includes DPT: emFillLevelLeakageRate

violent storm = 11
type: NamedIndividual
value API: violentStorm
value KNX: 11

type.dpt.field.20.20.i0
type: NamedIndividual
type: Datapoint Type Field
description: ActuatorConnectType
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.20.i0.1
includes key value pair: ControllerConnection = 2

type.dpt.field.518.500.i2.rmd.IPD
type: Datapoint Type Field
type: NamedIndividual
description: instruction processing delay
field index: 2
field name: IPD
field size: 16
includes DPT: TimePeriodSec

type.dpt.field.252.600.i2.MaskCG
type: NamedIndividual
type: Datapoint Type Field
description: validity of the fields CG and Step Code Colour Green.
field index: 2
field name: MaskCG
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

Time
type: NamedIndividual
type: Quantity Kind
description: Time is a basic component of the measuring system used to sequence events, to compare the durations of events and the intervals between them, and to quantify the motions of objects.

type.dpt.field.524.500.i4.ti.ID
type: Datapoint Type Field
type: NamedIndividual
description: identifier of this instruction. value shall be unique. Old IDs will be reused.
field index: 4
field name: ID
field size: 16
field type: U
includes digit: type.digit.u16

11.x
type: Datapoint Type
type: NamedIndividual
subject: 11.x
subject: 11.major
dpt bit size max: 24
dpt major number: 11
is assembled with: type.dpt.field.11.x.i0
label: 11.x
has communication mode: S

type.dpt.field.frbc.ome.i0.PR
type: NamedIndividual
type: Datapoint Type Field
description: power range
field index: 0
field name: PR
field size: 32
includes DPT: emPowerRange

Locked State
type: StateType
type: NamedIndividual
description: This state type expresses that an equipment is in a locked state, which usually indicates that the equipment will not react on new input commands until the locked state is lifted. This state type is the inverse of the 'unlocked' state type.

type.dpt.field.519.500.i1.tran.START TIMERS
type: Datapoint Type Field
type: NamedIndividual
description: defines wich timers will start when executing this transition . each of the 16 timers could be referenced by setting the bits 0-15 to 0 (not starting) or 1 (starting)
field index: 1
field name: START_TIMERS
field size: 16
field type: U
includes digit: type.digit.u16

Value Surface Tension
type: Datapoint Type
type: NamedIndividual
description: DPT 14.067: Value of surface tension
subject: 14.67
subject: Value Surface Tension
subject: 14.067
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 67
is assembled with: type.dpt.field.14.67.i0
label: Value Surface Tension
has communication mode: S

Pool
type: Location Usages
type: NamedIndividual
description: A swimming pool, swimming bath, wading pool, paddling pool, or simply pool, is a structure designed to hold water to enable swimming or other leisure activities. Preferably used with an Space.

type.dpt.field.236.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: Prioritised Mode Control
field index: 0
field size: 8
field string schema: raw
field type: A[n]

type.dpt.field.19.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: Date Time
field index: 0
field size: 64
field string schema: raw
field type: A[n]

DEG F
type: NamedIndividual
type: Unit
symbol: °F

Frost Sensor
type: Class
subject: FS
subject: 804
subject: Frost Sensor
interface object type annotation: 804
label: Frost Sensor
subclass of: Restriction
  on class: Class
    intersection of: dpa.804.51
    intersection of: Restriction
      has value: FrostAlarm
      on property: point name
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  all values from: Class
    union of: User Shutter Control
    union of: User Blinds Control
  on property: is applicable functionality of
subclass of: Restriction
  on class: dpa.804.51
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 804
    on property: interface object type

no fault = 0
type: NamedIndividual
value API: noFault
value KNX: 0

Power
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 9.024: Power
subject: Power
subject: 9.024
subject: 9.24
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 24
is assembled with: type.dpt.field.9.24.i0
label: Power
has communication mode: S

Value Angular Velocity
type: NamedIndividual
type: Datapoint Type
description: DPT 14.009: Value of angular velocity
subject: 14.9
subject: Value Angular Velocity
subject: 14.009
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 9
is assembled with: type.dpt.field.14.9.i0
label: Value Angular Velocity
has communication mode: S

Balcony
type: NamedIndividual
type: Location Usages
description: A balcony (from Italian: balcone, 'scaffold') is a platform projecting from the wall of a building, supported by columns or console brackets, and enclosed with a balustrade, usually above the ground floor. Preferably used with an Space.

Value 4 Ucount
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 12.001: Value 4 Ucount
subject: 12.1
subject: 12.001
subject: Value 4 Ucount
dpt bit size max: 32
dpt major number: 12
datapoint type minor number: 1
is assembled with: type.dpt.field.12.1.i0
label: Value 4 Ucount
has communication mode: S

Economy/Nothing = 2
type: NamedIndividual
value API: economyNothing
value KNX: 2

System & functions of common interest = 1
type: NamedIndividual
value API: system&FunctionsOfCommonInterest
value KNX: 1

Step
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: step
field size: 1
includes DPT: step
label: Step

calibration pending, waiting on trigger = 4
type: NamedIndividual
value API: calibrationPending,WaitingOnTrigger
value KNX: 4

DewPointStatus
type: Class
subject: DewPointStatus
subject: 399.63
subject: 63
interface object type annotation: 399
label: DewPointStatus
property identifier annotation: 63
subclass of: Restriction
  has value: alarm
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air dewpointtemperature room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph air dewpointtemperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 63
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type

Value MassFlux
type: NamedIndividual
type: Datapoint Type
description: DPT 14.052: Value of mass flux
subject: 14.52
subject: Value MassFlux
subject: 14.052
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 52
is assembled with: type.dpt.field.14.52.i0
label: Value MassFlux
has communication mode: S

type.dpt.field.22.101.i7.HeatingDisabled
type: NamedIndividual
type: Datapoint Type Field
description: HeatingDisabled
field index: 7
field name: HeatingDisabled
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

solid state fuel = 3
type: NamedIndividual
value API: solidStateFuel
value KNX: 3

trailing edge (resistive - or capacitive load) = 2
type: NamedIndividual
value API: trailingEdge(resistive-OrCapacitive
value KNX: 2

S-PER-M
type: NamedIndividual
type: Unit
symbol: S/m

Break = 0
type: NamedIndividual
value API: break
value KNX: 0

HVACModeAct
type: Class
subject: HVACModeAct
subject: 399.100
subject: 100
interface object type annotation: 399
label: HVACModeAct
property identifier annotation: 100
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 100
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVACMode
  on property: datapointType

Room AQ Sensor
type: Class
subject: RAQS
subject: 331
subject: Room AQ Sensor
interface object type annotation: 331
label: Room AQ Sensor
is incomplete: true
subclass of: Restriction
  on class: Class
    intersection of: AQRoom
    intersection of: Restriction
      has value: AQRoom
      on property: point name
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 331
    on property: interface object type
subclass of: Restriction
  on class: AQRoom
  on property: isComposedByOutput
  qualified cardinality: 1

type.dpt.field.14.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 4-byte float value
field index: 0
field size: 32
field type: F
includes digit: type.digit.f32

Disabled State
type: StateType
type: NamedIndividual
description: This state type expresses that an equipment or a functionality is disabled. A disabled equipment is inactive, cannot be activated and thus is not able to fulfill its intended functionality. Similarly, a disabled functionality is not available in the system. Usually, the equipment or functionality is disabled by management functionality, such as a building management system. This state type is the inverse of the 'Enabled State' state type.

whole gale / storm = 10
type: NamedIndividual
value API: wholeGaleStorm
value KNX: 10

MIN
type: NamedIndividual
type: Unit
symbol: min

HVAC Hot Water Heating = 11
type: NamedIndividual
value API: hVACHotWaterHeating
value KNX: 11

type.dpt.field.209.102.i0.OffPerm
type: Datapoint Type Field
type: NamedIndividual
description: permanently off (manual switch or failure)
field index: 2
field name: OffPerm
field size: 1
includes DPT: Bool

type.dpt.field.22.102.i1.ShortCircuit
type: NamedIndividual
type: Datapoint Type Field
description: Short Circuit
field index: 1
field name: ShortCircuit
field size: 1
field type: B
includes key value pair: No alarm = 0
includes key value pair: alarm = 1

value before locking = 6
type: NamedIndividual
value API: valueBeforeLocking
value KNX: 6

TempRoomSetpAct
type: Class
subject: TempRoomSetpAct
subject: 240.55
subject: 55
interface object type annotation: 240
label: TempRoomSetpAct
property identifier annotation: 55
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 55
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 240
    on property: interface object type

The visual effect of channel 12 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel12IsInactiv
value KNX: 0

type.dpt.field.245.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: Converter test result
field index: 0
field size: 48
field string schema: raw
field type: A[n]

Unknown = 0
type: NamedIndividual
value API: unknown
value KNX: 0

volume flow, 100 l/min = 70
type: NamedIndividual
value API: volumeFlow,100Lmin
value KNX: 70

Hydrogen Flow Rate
type: NamedIndividual
value API: HydrogenFlowRate
value KNX: 6

PDT in progress = 9
type: NamedIndividual
value API: pDTInProgress
value KNX: 9

Off/FrostProtect = 4
type: NamedIndividual
value API: offFrostProtect
value KNX: 4

type.dpt.field.22.101.i11.CoolingDisabled
type: NamedIndividual
type: Datapoint Type Field
description: CoolingDisabled
field index: 11
field name: CoolingDisabled
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

power, 0,1 kJ/h = 50
type: NamedIndividual
value API: power,0,1KJh
value KNX: 50

Concentration, CO2
type: NamedIndividual
type: Quantity Kind
description: Refers to the concentration of CO2 molecules in the air, measured in ppm. This is a specialization of quantitykind:Concentration.

type.dpt.field.519.500.i6.tran.Reserved
type: NamedIndividual
type: Datapoint Type Field
description: reserved bits
field index: 6
field name: RESERVED
field size: 3
field type: B
includes reserved bit(s): type.bit.reserved

type.dpt.field.512.500.i0.pc.CE CNT
type: NamedIndividual
type: Datapoint Type Field
description: Number of power contraint elements
field index: 0
field name: CE_CNT
field size: 8
field type: U
includes digit: type.digit.u8 0 15

HumRelSetpUserEff
type: Class
subject: 103.53
subject: 53
subject: HumRelSetpUserEff
interface object type annotation: 103
label: HumRelSetpUserEff
property identifier annotation: 53
subclass of: Restriction
  has value: relValueZ
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 103
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air relativehumidity room
      on property: refersTo
subclass of: Restriction
  has value: qk ph air relativehumidity room
  on property: hasQualityKind

The visual effect of channel 13 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel13IsActive
value KNX: 1

W-PER-M-K
type: NamedIndividual
type: Unit
symbol: W/(m⋅K)

Level 7 = 7
type: NamedIndividual
value API: level7
value KNX: 7

TimePeriodSec
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 7.005: TimePeriodSec
subject: 7.5
subject: 7.005
subject: TimePeriodSec
dpt bit size max: 16
dpt major number: 7
datapoint type minor number: 5
is assembled with: type.dpt.field.7.5.i0
label: TimePeriodSec
has communication mode: S

type.dpt.field.ec.i4.ID
type: NamedIndividual
type: Datapoint Type Field
description: id of the energy constraint
field index: 4
field name: ID
field size: 4
field type: U
includes digit: type.digit.u4

slave = 1
type: NamedIndividual
value API: slave
value KNX: 1

activated without security = 1
type: NamedIndividual
value API: activatedWithoutSecurity
value KNX: 1

Binary Value
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.006: Binary Value
subject: Binary Value
subject: 1.006
subject: 1.6
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 6
is assembled with: type.dpt.field.1.6.i0
label: Binary Value
has communication mode: S

type.dpt.field.525.500.i5.fv.Upper 68PPR
type: NamedIndividual
type: Datapoint Type Field
description: The upper boundary of the range with 68 % certainty the power value is in it
field index: 5
field name: Upper_68PPR
field size: 16
includes DPT: Power

learn the scene corresponding to the field Scene Number = 1
type: NamedIndividual
value API: learnTheSceneCorrespondingToTheFiel
value KNX: 1

type.dpt.field.207.100.i2.StatusStage1
type: NamedIndividual
type: Datapoint Type Field
description: stage 1 or base stage active
field index: 2
field name: StatusStage1
field size: 1
includes DPT: Switch

type.dpt.field.212.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: S16S16S16
field index: 0
field size: 48
field string schema: raw
field type: A[n]

The visual effect of channel 1 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel1IsActive
value KNX: 1

Inverted = 1
type: NamedIndividual
value API: inverted
value KNX: 1

Discharge Temperature Sensor
type: Class
subject: 328
subject: DATS
subject: Discharge Temperature Sensor
interface object type annotation: 328
label: Discharge Temperature Sensor
is incomplete: true
subclass of: Restriction
  on class: Class
    intersection of: dpa.328.51
    intersection of: Restriction
      has value: TempDischargeAir
      on property: point name
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 328
    on property: interface object type
subclass of: Restriction
  on class: dpa.328.51
  on property: isComposedByOutput
  qualified cardinality: 1

Blinds Position Percentage
type: Class
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: qk eq blindsactuator positionvector
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  has value: qk ph light illuminance room
  on property: acts on phenomenon quality kind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq blindsactuator positionvector
      on property: refersTo
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Function Point

type.dpt.field.203.104.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

V-A-HR
type: NamedIndividual
type: Unit
symbol: V⋅A⋅hr

type.dpt.field.27.1.i14.IOO15
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 15
field index: 14
field name: IOO15
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOff
includes key value pair: type.kvpair.outputStateOn

The visual effect of channel 13 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel13IsInactiv
value KNX: 0

Bluetooth
type: NamedIndividual
type: Protocol

The visual effect of channel 16 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel16IsActive
value KNX: 1

Colour Actuator RGB(W)
type: Class
subject: Colour Actuator RGB(W)
subject: 423
subject: CARGB
interface object type annotation: 423
label: Colour Actuator RGB(W)
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Actual Dimming Value Red
    intersection of: Restriction
      has value: Actual Dimming Value Red
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.423.82
    intersection of: Restriction
      has value: Current Colour RGBW
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.423.84
    intersection of: Restriction
      has value: Actual Dimming Value Green
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Switch On Off White
    intersection of: Restriction
      has value: Switch On Off White
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.423.86
    intersection of: Restriction
      has value: Actual Dimming Value White
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  on class: Class
    intersection of: dpa.423.57
    intersection of: Restriction
      has value: Relative Set Value Control Red
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  on class: Class
    intersection of: Switch On Off Red
    intersection of: Restriction
      has value: Switch On Off Red
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  on class: Class
    intersection of: dpa.423.52
    intersection of: Restriction
      has value: Colour Set RGB
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Current Colour RGB
    intersection of: Restriction
      has value: Current Colour RGB
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  on class: Class
    intersection of: Relative Set Value Control Blue
    intersection of: Restriction
      has value: Relative Set Value Control Blue
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  on class: Class
    intersection of: dpa.423.60
    intersection of: Restriction
      has value: Relative Set Value Control Green
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  on class: Class
    intersection of: Switch On Off Blue
    intersection of: Restriction
      has value: Switch On Off Blue
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Absolute Set Value Control White
    intersection of: Restriction
      has value: Absolute Set Value Control White
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.423.55
    intersection of: Restriction
      has value: Colour Relative Control RGBW
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  on class: Class
    intersection of: dpa.423.64
    intersection of: Restriction
      has value: Absolute Set Value Control Blue
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  on class: Class
    intersection of: dpa.423.80
    intersection of: Restriction
      has value: Combined Info On Off
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: Colour_Relative Control_RGB
    intersection of: Restriction
      has value: Colour_Relative Control_RGB
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  on class: Class
    intersection of: Absolute Set Value Control Red
    intersection of: Restriction
      has value: Absolute Set Value Control Red
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Class

inactive = 1
type: NamedIndividual
value API: inactive
value KNX: 1

type.dpt.field.23.1.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 2
field type: N
includes key value pair: type.kvpair.23.1.i0.3
includes key value pair: off = 0
includes key value pair: type.kvpair.23.1.i0.2
includes key value pair: on = 1

interface object type
type: FunctionalProperty
type: DatatypeProperty
comment: In KNX used (numerical) identifier to address a specific interface object type reflecting a KNX functional block id. The range xsd:unsignedShort supports exactly the KNX value range from 0 to 65535.
domain: Class
  union of: Datapoint
  union of: Functional Block
range: unsignedShort

no error = 0
type: NamedIndividual
value API: noError
value KNX: 0

Absolute Set Value Control Green
type: Class
subject: 423.61
subject: 61
subject: ASV_G
subject: Absolute Set Value Control Green
interface object type annotation: 423
label: Absolute Set Value Control Green
property identifier annotation: 61
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 61
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Green
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind

NightMode
type: Class
subject: 63
subject: NightMode
subject: 418.63
interface object type annotation: 418
label: NightMode
property identifier annotation: 63
subclass of: Restriction
  has value: Enable
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 63
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type

type.dpt.field.241.800.i9.LocalOverride
type: Datapoint Type Field
type: NamedIndividual
description: Actuator setvalue is locally overridden, e.g. via a local user interface
field index: 9
field name: LocalOverride
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

type.dpt.field.22.1000.i3.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 3
field name: Reserved
field size: 1
field type: r
includes reserved bit(s): type.bit.reserved

AddInfoTypes
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.1001: AddInfoTypes
subject: 20.1001
subject: AddInfoTypes
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1001
is assembled with: type.dpt.field.20.1001.i0
label: AddInfoTypes
has communication mode: S

type.dpt.field.219.1.i6.AlarmText Sup
type: NamedIndividual
type: Datapoint Type Field
description: AlarmText_Sup
field index: 6
field name: AlarmText_Sup
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

OccMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.003: OccMode
subject: 20.3
subject: 20.003
subject: OccMode
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 3
is assembled with: type.dpt.field.20.3.i0
label: OccMode
has communication mode: S

type.dpt.field.22.1000.i0.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: Reserved
field size: 1
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.19.1.i10.F
type: NamedIndividual
type: Datapoint Type Field
description: Fault
field default: 0
field index: 10
field name: F
field size: 1
field type: B
includes key value pair: Normal (no fault) = 0
includes key value pair: Fault = 1

User Blinds Control
type: Class
subject: SAB
subject: SSSB
comment: Application function for 'blinds control'.
subclass of: Restriction
  on class: BlindsPositionLength
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: BlindsStopTrigger
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: BlindsMoveUpDown
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  has value: qk ph light illuminance
  on property: hasQualityKind
subclass of: Restriction
  on class: Blinds Position Percentage
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  has value: qk eq blindsactuator positionvector
  on property: hasQualityKind
subclass of: Restriction
  on class: WindAlarm
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: Blinds Stop Step
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: BlindsSlatPositionPercentage
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  has value: qk eq slatsactuator positionvector
  on property: hasQualityKind
subclass of: Restriction
  on class: Frost Alarm
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: RainAlarm
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: BlindsSlatPositionDegrees
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  on class: Blinds Status
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: shadingCtrl

Heat Stage B Actuator Valve Kick
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Function Point
subclass of: Restriction
  has value: Bool
  on property: datapointType

M2-PER-N
type: NamedIndividual
type: Unit
symbol: m²/N

enable stage A = 1
type: NamedIndividual
value API: enableStageA
value KNX: 1

includes counter
type: ObjectProperty
range: Datapoint Type Field
sub property of: includes

The visual effect of channel 22 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel22IsInactiv
value KNX: 0

WindowStatus
type: Class
subject: WindowStatus
subject: 62
subject: 398.62
interface object type annotation: 398
label: WindowStatus
property identifier annotation: 62
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: opened
      on property: hasStateType
    intersection of: Restriction
      has value: closed
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: totalizedValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq window positionvector room
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 62
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type
subclass of: Restriction
  has value: qk eq window positionvector room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: windowDoor
  on property: datapointType

type.dpt.field.22.102.i4.ServiceMode
type: NamedIndividual
type: Datapoint Type Field
description: Service mode
field index: 4
field name: ServiceMode
field size: 1
field type: B
includes key value pair: type.kvpair.active
includes key value pair: Not active = 0

Waste water meter = 40
type: NamedIndividual
value API: wasteWaterMeter
value KNX: 40

type.dpt.field.27.1.i31.MaskBitIOO16
type: NamedIndividual
type: Datapoint Type Field
description: Mask Bit Info On Off Output 16
field index: 31
field name: MaskBitIOO16
field size: 1
field type: B
includes key value pair: output state is not valid = 0
includes key value pair: output state is valid = 1

231.x
type: Datapoint Type
type: NamedIndividual
subject: 231.x
subject: 231.major
dpt bit size max: 32
dpt major number: 231
is assembled with: type.dpt.field.231.x.i0
label: 231.x
has communication mode: S

type.dpt.field.21.104.i1.Gas
type: NamedIndividual
type: Datapoint Type Field
description: Gas
field index: 1
field name: Gas
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

Reset
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: no action (dummy) = 0
includes key value pair: reset command (trigger) = 1
label: Reset

HVACModeAct
type: Class
subject: 261.152
subject: 152
subject: HVACModeAct
interface object type annotation: 261
label: HVACModeAct
property identifier annotation: 152
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 152
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 261
    on property: interface object type

22,6 s = 11
type: NamedIndividual
value API: 22,6S
value KNX: 11

Alarm Reaction
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 23.002: Alarm Reaction
subject: 23.002
subject: 23.2
subject: Alarm Reaction
dpt bit size max: 2
dpt major number: 23
datapoint type minor number: 2
is assembled with: type.dpt.field.23.2.i0
label: Alarm Reaction
has communication mode: S

Timed StartStop
type: Class
subject: TSS
subject: 52
subject: Timed StartStop
subject: 414.52
interface object type annotation: 414
label: Timed StartStop
property identifier annotation: 52
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: Trigger
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 414
    on property: interface object type
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: start
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

15.x
type: NamedIndividual
type: Datapoint Type
subject: 15.x
subject: 15.major
dpt bit size max: 32
dpt major number: 15
is assembled with: type.dpt.field.15.x.i0
label: 15.x
has communication mode: S

Relative Control xyY
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 253.600: Relative Control xyY
subject: 253.600
subject: Relative Control xyY
dpt bit size max: 32
dpt major number: 253
datapoint type minor number: 600
is assembled with: type.dpt.field.253.600.i5.cB
is assembled with: type.dpt.field.253.600.i12.Reserved
is assembled with: type.dpt.field.253.600.i10.StepCodeSaturation
is assembled with: type.dpt.field.253.600.i3.Reserved
is assembled with: type.dpt.field.253.600.i6.Reserved
is assembled with: type.dpt.field.253.600.i2.MaskCS
is assembled with: type.dpt.field.253.600.i9.Reserved
is assembled with: type.dpt.field.253.600.i4.StepCodeBrightness
is assembled with: type.dpt.field.253.600.i7.StepCodeColour
is assembled with: type.dpt.field.253.600.i11.cS
is assembled with: type.dpt.field.253.600.i0.MaskCB
is assembled with: type.dpt.field.253.600.i8.cC
is assembled with: type.dpt.field.253.600.i1.MaskCC
label: Relative Control xyY
has communication mode: S

type.dpt.field.pc.i1.CT
type: NamedIndividual
type: Datapoint Type Field
description: consequence type of the power constraint
field index: 1
field name: CT
field size: 4
field type: U
includes digit: type.digit.u4

Bathroom
type: Location Usages
type: NamedIndividual
description: A bathroom or washroom is a room, typically in a home or other residential building, that contains either a bathtub or a shower (or both). Preferably used with an Room.

Lighting Control
type: Class
comment: A specific Application Function category that provides illumination and controls luminaries. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: Restriction
  has value: lighting
  on property: operatesForTrade
subclass of: ApplicationFunction

type.dpt.field.14.28.i0
type: NamedIndividual
type: Datapoint Type Field
description: electric potential difference
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/V

Request Converter Status = 1
type: NamedIndividual
value API: requestConverterStatus
value KNX: 1

TempRoomSetpHeatEff
type: Class
subject: TempRoomSetpHeatEff
subject: 55
subject: 100.55
interface object type annotation: 100
label: TempRoomSetpHeatEff
property identifier annotation: 55
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 55
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type

no action (dummy) = 0
type: NamedIndividual
value API: noAction(dummy)
value KNX: 0

Start Control
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 2.010: Start Control
subject: 2.10
subject: 2.010
subject: Start Control
dpt bit size max: 2
dpt major number: 2
datapoint type minor number: 10
is assembled with: type.dpt.field.2.x.i1.c
is assembled with: type.dpt.field.2.10.i0.start
label: Start Control
has communication mode: S

type.dpt.field.21.2.i1.OwnIA
type: NamedIndividual
type: Datapoint Type Field
description: A datagram with the own Individual Address as Source Address has been received
field index: 1
field name: OwnIA
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.236.1.i2.d
type: NamedIndividual
type: Datapoint Type Field
description: deactivation of priority
field index: 2
field name: d
field size: 1
field type: B
includes key value pair: type.kvpair.236.1.i2.0
includes key value pair: type.kvpair.236.1.i2.1

Concentration µg/m3
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 9.030: Concentration µg/m3
subject: 9.030
subject: 9.30
subject: Concentration µg/m3
dpt bit size max: 16
dpt major number: 9
datapoint type minor number: 30
is assembled with: type.dpt.field.9.30.i0
label: Concentration µg/m3
has communication mode: S

Request Converter FT Info = 4
type: NamedIndividual
value API: requestConverterFTInfo
value KNX: 4

Health Care
type: Location Usages
type: NamedIndividual
description: A health facility is, in general, any location where healthcare is provided. Health facilities are clinics and doctor's offices or urgent care centers with elaborate emergency rooms. Preferably used with a Building or a Site/Space.

RAD-PER-SEC
type: NamedIndividual
type: Unit
symbol: rad/s

14.x
type: NamedIndividual
type: Datapoint Type
subject: 14.major
subject: 14.x
dpt bit size max: 32
dpt major number: 14
is assembled with: type.dpt.field.14.x.i0
label: 14.x
has communication mode: S

type.dpt.field.21.103.i0.Fault
type: NamedIndividual
type: Datapoint Type Field
description: Fault
field index: 0
field name: Fault
field size: 1
field type: B
includes key value pair: type.kvpair.21.103.i0.1
includes key value pair: ok = 0

Location Usages
type: Class
comment: The tag category contains individuals that describe for which purpose a location is used for.
subclass of: Tag

KNX Information Ontology
type: Ontology
Date Available: 2024-02-23
license: Copyright 2023, KNX Association, Brussels-Diegem, Belgium. Permission is hereby granted, free of charge, to any person obtaining a copy of this software and associated documentation files (the “Software”), to deal in the Software without restriction, including without limitation the rights to use, copy, modify, merge, publish, distribute, sublicense, and/or sell copies of the Software, and to permit persons to whom the Software is furnished to do so, subject to the following conditions: The above copyright notice and this permission notice shall be included in all copies or substantial portions of the Software. THE SOFTWARE IS PROVIDED “AS IS”, WITHOUT WARRANTY OF ANY KIND, EXPRESS OR IMPLIED, INCLUDING BUT NOT LIMITED TO THE WARRANTIES OF MERCHANTABILITY, FITNESS FOR A PARTICULAR PURPOSE AND NONINFRINGEMENT. IN NO EVENT SHALL THE AUTHORS OR COPYRIGHT HOLDERS BE LIABLE FOR ANY CLAIM, DAMAGES OR OTHER LIABILITY, WHETHER IN AN ACTION OF CONTRACT, TORT OR OTHERWISE, ARISING FROM, OUT OF OR IN CONNECTION WITH THE SOFTWARE OR THE USE OR OTHER DEALINGS IN THE SOFTWARE.
replaces: v1
version IRI: v2
version info: v2
comment: Represents the combined KNX Information Model with its individual (core/knx/location/tag) models. The Core model represents the commonly known IoT and building control domain concepts of an installation. The KNX model represents the KNX System part of an installation. The Location model represents the spatial location structure of an installation. The Tag model represents a set of entities, each with a standardized semantical meaning that is independent from any actual installation. The date of the last update of the model - usually regarding the dictionary content - is shown in the DCTERMS property dcterms:available. See also the corresponding version identifier at class core:Thing.
comment: The terms of service can be found under https://www.knx.org/knx-en/privacy. The applied license agreement is a MIT License from https://opensource.org/licenses/MIT.

RF FilterSelect
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.1003: RF FilterSelect
subject: RF FilterSelect
subject: 20.1003
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1003
is assembled with: type.dpt.field.20.1003.i0
label: RF FilterSelect
has communication mode: S

Position Vector
type: NamedIndividual
type: Quantity Kind
description: Represents a (numerical, countable) position, such as %.

Electric Power L3
type: NamedIndividual
value API: ElectricPowerL3
value KNX: 2

type.dpt.field.14.26.i0
type: NamedIndividual
type: Datapoint Type Field
description: electric polarization
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: C-PER-M2

type.dpt.field.14.44.i0
type: NamedIndividual
type: Datapoint Type Field
description: magnetic field strength
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: A-PER-M

The visual effect of channel 23 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel23IsInactiv
value KNX: 0

power, 1 MW = 169
type: NamedIndividual
value API: power,1MW
value KNX: 169

type.dpt.field.205.102.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

DateTime
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 19.001: DateTime
subject: 19.001
subject: DateTime
subject: 19.1
dpt bit size max: 64
dpt major number: 19
datapoint type minor number: 1
is assembled with: type.dpt.field.19.1.i14.Reserved
is assembled with: type.dpt.field.19.1.i10.F
is assembled with: type.dpt.field.19.1.i2.CLQ
is assembled with: type.dpt.field.19.1.i1.SRC
is assembled with: type.dpt.field.19.1.i9.WD
is assembled with: type.dpt.field.19.1.i15.HourOfDay
is assembled with: type.dpt.field.19.1.i16.DayOfWeek
is assembled with: type.dpt.field.19.1.i17.DayOfMonth
is assembled with: type.dpt.field.19.1.i12.Reserved
is assembled with: type.dpt.field.19.1.i21.Year
is assembled with: type.dpt.field.19.1.i13.Minutes
is assembled with: type.dpt.field.19.1.i20.Reserved
is assembled with: type.dpt.field.19.1.i8.NWD
is assembled with: type.dpt.field.19.1.i7.NY
is assembled with: type.dpt.field.19.1.i3.SUTI
is assembled with: type.dpt.field.19.1.i11.Seconds
is assembled with: type.dpt.field.19.1.i19.Month
is assembled with: type.dpt.field.19.1.i18.Reserved
is assembled with: type.dpt.field.19.1.i4.NT
is assembled with: type.dpt.field.19.1.i5.NDOW
is assembled with: type.dpt.field.19.1.i6.ND
is assembled with: type.dpt.field.19.1.i0.Reserved
label: DateTime
has communication mode: S

Normal mode active, all OK = 1
type: NamedIndividual
value API: normalModeActive,AllOK
value KNX: 1

TariffNext
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 225.003: TariffNext
subject: TariffNext
subject: 225.3
subject: 225.003
dpt bit size max: 24
dpt major number: 225
datapoint type minor number: 3
is assembled with: type.dpt.field.225.3.i0.Tariff
is assembled with: type.dpt.field.225.3.i1.DelayTime
label: TariffNext
has communication mode: S

PowerReturnMode
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.022: PowerReturnMode
subject: 20.022
subject: 20.22
subject: PowerReturnMode
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 22
is assembled with: type.dpt.field.20.22.i0
label: PowerReturnMode
has communication mode: S

Not Forced State
type: StateType
type: NamedIndividual
description: This state type expresses that an equipment is not in a forced state, i.e. no command with very high priority influenced the equipment's current value / position. The equipment's normal processing of input commands is executed. This state type is the inverse of the 'Forced State' state type.

Switch
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.001: Switch
subject: Switch
subject: 1.1
subject: 1.001
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 1
is assembled with: type.dpt.field.1.1.i0
label: Switch
has communication mode: S

type.dpt.field.241.800.i2.LowerPredefPos
type: NamedIndividual
type: Datapoint Type Field
description: Lower predef. pos. reached, typ. height 100 %, slats-angle < 100 %
field index: 2
field name: LowerPredefPos
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

Request Converter Info Fix = 8
type: NamedIndividual
value API: requestConverterInfoFix
value KNX: 8

HVACModeUser
type: Class
subject: HVACModeUser
subject: 398.53
subject: 53
interface object type annotation: 398
label: HVACModeUser
property identifier annotation: 53
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: HVACMode
  on property: datapointType

Electric Power L2
type: NamedIndividual
value API: ElectricPowerL2
value KNX: 1

type.dpt.field.27.1.i29.MaskBitIOO14
type: Datapoint Type Field
type: NamedIndividual
description: Mask Bit Info On Off Output 14
field index: 29
field name: MaskBitIOO14
field size: 1
field type: B
includes key value pair: output state is not valid = 0
includes key value pair: output state is valid = 1

type.dpt.field.219.1.i5.TimeStamp Sup
type: NamedIndividual
type: Datapoint Type Field
description: TimeStamp_Sup
field index: 5
field name: TimeStamp_Sup
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.512.503.i5.pei.PC ID
type: NamedIndividual
type: Datapoint Type Field
description: identifier of power constraint
field index: 5
field name: PC_ID
field size: 4
field type: U
includes digit: type.digit.u4

type.dpt.field.209.101.i0.DemValid
type: Datapoint Type Field
type: NamedIndividual
description: Validity of TempRoomDem. ‘false’ means also ‘no demand’
field index: 0
field name: DemValid
field size: 1
includes DPT: Bool

Cool Stage B Actuator Valve Kick
type: Class
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Bool
  on property: datapointType

type.dpt.field.212.101.i2.TempSetpComf
type: NamedIndividual
type: Datapoint Type Field
description: room temperature setpoint comfort
field index: 2
field name: TempSetpComf
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C

type.dpt.field.252.600.i14.StepCodeColourRed
type: NamedIndividual
type: Datapoint Type Field
description: Shall specify the fading step size or to the code to stop the fading of the colour red
field index: 14
field name: StepCodeColourRed
field resolution: 1.0
field size: 3
field type: U
includes digit: type.digit.u3

AlarmClassType
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.007: AlarmClassType
subject: 20.007
subject: 20.7
subject: AlarmClassType
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 7
is assembled with: type.dpt.field.20.7.i0
label: AlarmClassType
has communication mode: S

normal = 0
type: NamedIndividual
value API: normal
value KNX: 0

Shutter Stop Step
type: Class
subclass of: Function Point
subclass of: Restriction
  has value: step
  on property: datapointType
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq blindsactuator positionvector
      on property: refersTo
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: downwards
      on property: hasStateType
    intersection of: Restriction
      has value: Stopped Movement
      on property: hasStateType
    intersection of: Restriction
      has value: upwards
      on property: hasStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: qk eq blindsactuator positionvector
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  has value: qk ph light illuminance room
  on property: acts on phenomenon quality kind

253.x
type: NamedIndividual
type: Datapoint Type
subject: 253.x
subject: 253.major
dpt bit size max: 32
dpt major number: 253
is assembled with: type.dpt.field.253.x.i0
label: 253.x
has communication mode: S

no = 0
type: NamedIndividual
value API: no
value KNX: 0

TempRoomSetpSetHeatEff
type: Class
subject: TempRoomSetpSetHeatEff
subject: 100.53
subject: 53
interface object type annotation: 100
label: TempRoomSetpSetHeatEff
property identifier annotation: 53
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeProtection
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  has value: tempRoomSetpSet a4a
  on property: datapointType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.241.800.i15.HeightPosition
type: Datapoint Type Field
type: NamedIndividual
description: Height Position
field index: 15
field name: HeightPosition
field resolution: 0.3921566
field size: 8
field type: U
includes digit: type.digit.u8
unit: PERCENT

type.digit.u16
type: NamedIndividual
range max: 65535
range min: 0

Speaker
type: EquipmentType
type: NamedIndividual
description: A loudspeaker (commonly referred to as a speaker or speaker driver) is one type of electroacoustic transducer, that is, a device that converts an electrical audio signal into a corresponding sound.

energy, 1 GJ = 137
type: NamedIndividual
value API: energy,1GJ
value KNX: 137

type.dpt.field.22.103.i9.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 9
field name: Reserved
field size: 7
field type: r
includes reserved bit(s): type.bit.reserved

Light Relative Dimming Request
type: Class
subclass of: Restriction
  has value: lighting
  on property: operatesForTrade
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  has value: qk ph light illuminance
  on property: acts on phenomenon quality kind
subclass of: Restriction
  has value: controlDimming
  on property: datapointType
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Function Point

KiloGM-PER-SEC
type: NamedIndividual
type: Unit
symbol: kg/s

The visual effect of channel 2 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel2IsInactive
value KNX: 0

Heat stage B for heating with two stages (A + B) = 2
type: NamedIndividual
value API: heatStageBForHeatingWithTwoStages(A
value KNX: 2

modulating = 3
type: NamedIndividual
value API: modulating
value KNX: 3

Heat
type: PhenomenonType
type: NamedIndividual
description: The phenomenon of high temperatures. This can relate to high ambient temperatures (e.g. as a weather phenomenon or in buildings) or to high temperatures in devices (e.g. when in the danger of overheating).

type.dpt.field.20.109.i0
type: NamedIndividual
type: Datapoint Type Field
description: DamperMode
field index: 0
field size: 8
field type: N
includes key value pair: Fresh air, e.g. for fancoils = 1
includes key value pair: Discharge air, e.g. for VAV = 3
includes key value pair: type.kvpair.20.109.i0.4
includes key value pair: type.kvpair.20.109.i0.2

fresh gale = 8
type: NamedIndividual
value API: freshGale
value KNX: 8

Wednesday = 3
type: NamedIndividual
value API: wednesday
value KNX: 3

type.dpt.field.14.1200.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: M3-PER-HR

TempRoomSetpAct
type: Class
subject: TempRoomSetpAct
subject: 153
subject: 260.153
interface object type annotation: 260
label: TempRoomSetpAct
property identifier annotation: 153
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 153
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 260
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

Actuator
type: EquipmentType
type: NamedIndividual
description: Used to control a (generic) actuator equipment. Don't care if the (generic functionality) is internally operated from the actuator by a motor or other means.

RF ModeSelect
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.1002: RF ModeSelect
subject: RF ModeSelect
subject: 20.1002
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1002
is assembled with: type.dpt.field.20.1002.i0
label: RF ModeSelect
has communication mode: S

has product
type: ObjectProperty
type: FunctionalProperty
inverse of: isProductOf
comment: To define a relation to a product from an equipment.
domain: Equipment
range: Product

automatic (resistive, capacitive or inductive) = 0
type: NamedIndividual
value API: automatic(resistive,CapacitiveOrInd
value KNX: 0

type.dpt.field.9.4.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16 0 670433
unit: LUX

type.dpt.field.30.1010.i2.ActivationStateOfChannel3
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 3
field index: 2
field name: ActivationStateOfChannel3
field size: 1
field type: B
includes key value pair: The visual effect of channel 3 is inactive = 0
includes key value pair: type.kvpair.30.1010.i2.1

is application program of
type: ObjectProperty
type: FunctionalProperty
domain: ApplicationProgram
range: Device

type.dpt.field.252.600.i9.cB
type: Datapoint Type Field
type: NamedIndividual
description: Shall specify whether the colour component blue shall be increased or decreased.
field index: 9
field name: cB
field size: 1
field type: B
includes key value pair: type.kvpair.decrease
includes key value pair: type.kvpair.increase

Garbage = 41
type: NamedIndividual
value API: garbage
value KNX: 41

TempRoomSetpUserAbs
type: Class
subject: 398.56
subject: TempRoomSetpUserAbs
subject: 56
interface object type annotation: 398
label: TempRoomSetpUserAbs
property identifier annotation: 56
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 56
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo

type.dpt.field.203.101.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

type.dpt.field.21.1010.i5.ActivationStateOfChannel6
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 6
field index: 5
field name: ActivationStateOfChannel6
field size: 1
field type: B
includes key value pair: The visual effect of channel 6 is inactive = 0
includes key value pair: type.kvpair.21.1010.i5.1

No Frost
type: NamedIndividual
type: StateType
description: This state type expresses the state of no frost. Usually, this state is related to the protection of shading equipment such as blinds and slats. In case no frost has been detected, no frost protection is required and this equipment might be used as intended. This state type is the inverse of the 'Frost State' state type.

CFL, trailing = 6
type: NamedIndividual
value API: cFL,Trailing
value KNX: 6

The visual effect of channel 15 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel15IsActive
value KNX: 1

energy, 0,1 GJ = 136
type: NamedIndividual
value API: energy,0,1GJ
value KNX: 136

type.dpt.field.14.1.i0
type: NamedIndividual
type: Datapoint Type Field
description: acceleration, angular
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: RAD-PER-SEC2

Storm State
type: StateType
type: NamedIndividual
description: This state type expresses the state of storm. Usually, this state is related to the protection of shading equipment such as blinds and slats, which can be damaged due to high wind speeds. In case of storm, this equipment might be put into a protective position, which prevents it from being used for shading purposes. This state type is the inverse of the 'No Storm' state type.

Up / Down
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: Down = 1
includes key value pair: Up = 0
label: Up / Down

true = 1
type: NamedIndividual
value API: true
value KNX: 1

type.dpt.field.22.1000.i6.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 6
field name: Reserved
field size: 10
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.27.1.i7.IOO8
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 8
field index: 7
field name: IOO8
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOn
includes key value pair: type.kvpair.outputStateOff

type.dpt.field.27.1.i21.MaskBitIOO6
type: Datapoint Type Field
type: NamedIndividual
description: Mask Bit Info On Off Output 6
field index: 21
field name: MaskBitIOO6
field size: 1
field type: B
includes key value pair: output state is not valid = 0
includes key value pair: output state is valid = 1

ControlModeEff
type: Class
subject: 54
subject: 418.54
subject: ControlModeEff
interface object type annotation: 418
label: ControlModeEff
property identifier annotation: 54
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: lightControlMode
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 54
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Override Mode Manual
      on property: hasStateType
    intersection of: Restriction
      has value: overrideModeAutomatic
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo

type.dpt.field.230.1000.i3.ManufactID
type: NamedIndividual
type: Datapoint Type Field
description: ManufactID
field index: 3
field name: ManufactID
field size: 16
field type: U
includes digit: type.digit.u16

CombinedStatus_HVA_HeatA
type: Class
subject: 70
subject: CombinedStatus_HVA_HeatA
subject: 399.70
interface object type annotation: 399
label: CombinedStatus_HVA_HeatA
property identifier annotation: 70
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateDefectOverload
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Locked State
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 70
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: forced
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: Override Mode Manual
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateCalibration
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: opened
      on property: hasStateType
    intersection of: Restriction
      has value: closed
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
subclass of: Restriction
  has value: Combined Status HVA
  on property: datapointType
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class

Dehumidification = 14
type: NamedIndividual
value API: dehumidification
value KNX: 14

Colour Set RGBW
type: Class
subject: Colour Set RGBW
subject: CS_RGBW
subject: 423.54
subject: 54
interface object type annotation: 423
label: Colour Set RGBW
property identifier annotation: 54
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: chromaticityBlue
      on property: relatesToStateType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity White
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Green
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 54
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 423
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Chromaticity Red
      on property: relatesToStateType
subclass of: Restriction
  has value: converterInfo
  on property: datapointType

clock without ext. sync signal = 0
type: NamedIndividual
value API: clockWithoutExt.SyncSignal
value KNX: 0

type.dpt.field.213.101.i0.TempSetpOffFrostProtect
type: NamedIndividual
type: Datapoint Type Field
description: DHW temperature setpoint for Off/FrostProtect operating mode
field index: 0
field name: TempSetpOffFrostProtect
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C

Direction 1 Control
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 2.008: Direction 1 Control
subject: 2.008
subject: Direction 1 Control
subject: 2.8
dpt bit size max: 2
dpt major number: 2
datapoint type minor number: 8
is assembled with: type.dpt.field.2.x.i1.c
is assembled with: Direction 1
label: Direction 1 Control
has communication mode: S

type.dpt.field.20.107.i0
type: NamedIndividual
type: Datapoint Type Field
description: ChangeoverMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.107.i0.0
includes key value pair: CoolingOnly = 1
includes key value pair: type.kvpair.20.107.i0.2

type.dpt.field.27.1.i2.IOO3
type: NamedIndividual
type: Datapoint Type Field
description: Info On Off Output 3
field index: 2
field name: IOO3
field size: 1
field type: B
includes key value pair: type.kvpair.outputStateOn
includes key value pair: type.kvpair.outputStateOff

energy, 1 kJ = 11
type: NamedIndividual
value API: energy,1KJ
value KNX: 11

type.dpt.field.222.100.i2.TempSetpComf
type: NamedIndividual
type: Datapoint Type Field
description: TempSetpComf
field index: 2
field name: TempSetpComf
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16 neg27300 670433
unit: DEG C

Logical Function
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.21.i0.1
includes key value pair: logical function OR = 0
label: Logical Function

218.x
type: NamedIndividual
type: Datapoint Type
subject: 218.major
subject: 218.x
dpt bit size max: 40
dpt major number: 218
is assembled with: type.dpt.field.218.x.i0
label: 218.x
has communication mode: LTE

Not active = 0
type: NamedIndividual
value API: notActive
value KNX: 0

ControlModeUser
type: Class
subject: ControlModeUser
subject: 417.74
subject: 74
interface object type annotation: 417
label: ControlModeUser
property identifier annotation: 74
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Override Mode Manual
      on property: hasStateType
    intersection of: Restriction
      has value: overrideModeAutomatic
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: lightControlMode
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 74
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 417
    on property: interface object type

Sensor
type: EquipmentType
type: NamedIndividual
description: Sensor is a Peripheral that measures physical input from its environment and converts it into data that can be interpreted by either a human or a machine.

type.dpt.field.9.33.i0.fr.VAL
type: NamedIndividual
type: Datapoint Type Field
description: fill rate value
field index: 0
field name: VAL
field size: 16
field type: F
includes digit: type.digit.f16

type.dpt.field.6.1.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 8
field type: V
includes digit: type.digit.s8
unit: PERCENT

EmergDepressure = 2
type: NamedIndividual
value API: emergDepressure
value KNX: 2

BlinkingWithAcknowledge = 2
type: NamedIndividual
value API: blinkingWithAcknowledge
value KNX: 2

AQRoom
type: Class
subject: AQRoom
subject: 331.51
subject: 51
interface object type annotation: 331
label: AQRoom
property identifier annotation: 51
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air co2concentration room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 331
    on property: interface object type
subclass of: Restriction
  has value: HVAC Air Qual Z
  on property: datapointType
subclass of: Restriction
  has value: qk ph air co2concentration room
  on property: hasQualityKind

type.dpt.field.23.2.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 2
field type: N
includes key value pair: alarm position is DOWN = 2
includes key value pair: type.kvpair.23.2.i0.1
includes key value pair: no alarm is used = 0

A-PER-M
type: NamedIndividual
type: Unit
symbol: A/m

forced = 1
type: NamedIndividual
value API: forced
value KNX: 1

type.dpt.field.212.101.i0.TempSetpEco
type: NamedIndividual
type: Datapoint Type Field
description: room temperature setpoint economy
field index: 0
field name: TempSetpEco
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C

type.dpt.field.238.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: configuration/ diagnostics
field index: 0
field size: 8
field string schema: raw
field type: A[n]

30 min = 19
type: NamedIndividual
value API: 30Min
value KNX: 19

StatusBUC
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 207.100: StatusBUC
subject: StatusBUC
subject: 207.100
dpt bit size max: 16
dpt major number: 207
datapoint type minor number: 100
is assembled with: type.dpt.field.207.100.i4.Reserved
is assembled with: type.dpt.field.207.100.i5.PrelBurner
is assembled with: type.dpt.field.207.100.i1.Fault
is assembled with: type.dpt.field.207.100.i2.StatusStage1
is assembled with: type.dpt.field.207.100.i0.PrelBurnerValid
is assembled with: type.dpt.field.207.100.i3.StatusStage2
label: StatusBUC
has communication mode: LTE

scene is active = 0
type: NamedIndividual
value API: sceneIsActive
value KNX: 0

Alarm
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field name: alarm
field size: 1
includes DPT: alarm
label: Alarm

UTF-8
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 28.001: UTF-8
subject: 28.1
subject: UTF-8
subject: 28.001
dpt bit size max: 312
dpt major number: 28
datapoint type minor number: 1
is assembled with: type.dpt.field.28.1.i0
label: UTF-8
has communication mode: S

Fan Actuator
type: Class
subject: FA
comment: A fan actuator.
subclass of: Restriction
  on class: FanSpeedTarget
  on property: hasFunctionPoint
  qualified cardinality: 1
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity
  on property: hasQualityKind
subclass of: Fan Control
subclass of: Restriction
  on class: Fan Speed Current
  on property: hasFunctionPoint
  qualified cardinality: 1

Electricity meter = 2
type: NamedIndividual
value API: electricityMeter
value KNX: 2

Comfort = 1
type: NamedIndividual
is applicable datapoint enum of: HVAC Mode Comfort
value API: comfort
value KNX: 1

type.digit.u16 0 20000
type: NamedIndividual
range max: 20000
range min: 0

TempRoomSetpUserOffset
type: Class
subject: 52
subject: TempRoomSetpUserOffset
subject: 384.52
interface object type annotation: 384
label: TempRoomSetpUserOffset
property identifier annotation: 52
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 384
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: HVAC relative Temperature
  on property: datapointType

type.dpt.field.238.600.i2.BallastFailure
type: Datapoint Type Field
type: NamedIndividual
description: Ballast Failure
field index: 2
field name: BallastFailure
field size: 1
field type: B
includes key value pair: no error = 0
includes key value pair: type.kvpair.238.600.i2.1

type.digit.u8 0 54
type: NamedIndividual
range max: 54
range min: 0

Volume Flow Rate
type: NamedIndividual
type: Quantity Kind
description: Volumetric Flow Rate, (also known as volume flow rate, rate of fluid flow or volume velocity) is the volume of fluid which passes through a given surface per unit time.

type.dpt.field.265.9.i2.DateAndTime
type: NamedIndividual
type: Datapoint Type Field
description: Date and Time
field index: 2
field name: DateAndTime
field size: 64
includes DPT: DateTime

mass, 0,001 kg = 24
type: NamedIndividual
value API: mass,0,001Kg
value KNX: 24

type.dpt.field.22.102.i0.CurrentValvePosition
type: NamedIndividual
type: Datapoint Type Field
description: Current Valve position
field index: 0
field name: CurrentValvePosition
field size: 1
field type: B
includes key value pair: current position=0 = 0
includes key value pair: type.kvpair.22.102.i0.1

Economy = 3
type: NamedIndividual
is applicable datapoint enum of: hvacModeEconomy
value API: economy
value KNX: 3

FanManual
type: Class
subject: FanManual
subject: 397.89
subject: 89
interface object type annotation: 397
label: FanManual
property identifier annotation: 89
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 89
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  has value: Enable
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Override Mode Manual
      on property: hasStateType
    intersection of: Restriction
      has value: overrideModeAutomatic
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo

FARAD
type: NamedIndividual
type: Unit
symbol: F

mass flow, 0,01 kg/h = 81
type: NamedIndividual
value API: massFlow,0,01Kgh
value KNX: 81

type.dpt.field.22.1010.i8.ActivationStateOfChannel9
type: Datapoint Type Field
type: NamedIndividual
description: Activation state of channel 9
field index: 8
field name: ActivationStateOfChannel9
field size: 1
field type: B
includes key value pair: type.kvpair.22.1010.i8.0
includes key value pair: type.kvpair.22.1010.i8.1

type.dpt.field.21.104.i0.Oil
type: NamedIndividual
type: Datapoint Type Field
description: Oil
field index: 0
field name: Oil
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

TimedStartStop
type: Class
subject: TimedStartStop
subject: 420.65
subject: 65
interface object type annotation: 420
label: TimedStartStop
property identifier annotation: 65
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: Trigger
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: start
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 65
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 420
    on property: interface object type

Trigger
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 1
field type: B
includes key value pair: type.kvpair.1.17.i0.0
includes key value pair: type.kvpair.1.17.i0.1
label: Trigger

32,0 s = 12
type: NamedIndividual
value API: 32,0S
value KNX: 12

WindowStatusEff
type: Class
subject: WindowStatusEff
subject: 62
subject: 397.62
interface object type annotation: 397
label: WindowStatusEff
property identifier annotation: 62
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: opened
      on property: hasStateType
    intersection of: Restriction
      has value: closed
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: totalizedValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq window positionvector room
      on property: refersTo
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: windowDoor
  on property: datapointType
subclass of: Restriction
  has value: qk eq window positionvector room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 62
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 397
    on property: interface object type

HZ
type: NamedIndividual
type: Unit
symbol: Hz

volume, 10 l = 20
type: NamedIndividual
value API: volume,10L
value KNX: 20

TimedStartStop
type: Class
subject: TimedStartStop
subject: 417.71
subject: 71
subject: TSS
interface object type annotation: 417
label: TimedStartStop
property identifier annotation: 71
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: Trigger
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 71
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 417
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: start
  on property: datapointType

type.dpt.field.14.67.i0
type: NamedIndividual
type: Datapoint Type Field
description: surface tension
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: N-PER-M

type.dpt.field.209.101.i1.AbsLoadPriority
type: NamedIndividual
type: Datapoint Type Field
description: absolute load priority
field index: 1
field name: AbsLoadPriority
field size: 1
includes DPT: Bool

The visual effect of channel 24 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel24IsInactiv
value KNX: 0

TimedStartStop
type: Class
subject: 71
subject: 418.71
subject: TimedStartStop
interface object type annotation: 418
label: TimedStartStop
property identifier annotation: 71
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 71
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: Trigger
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: start
  on property: datapointType

type.dpt.field.252.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: Relative Control RGBW
field index: 0
field size: 40
field string schema: raw
field type: A[n]

type.dpt.field.30.1010.i14.ActivationStateOfChannel15
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 15
field index: 14
field name: ActivationStateOfChannel15
field size: 1
field type: B
includes key value pair: The visual effect of channel 15 is active = 1
includes key value pair: The visual effect of channel 15 is inactive = 0

type.dpt.field.252.600.i5.StepCodeColourWhite
type: Datapoint Type Field
type: NamedIndividual
description: Shall specify the fading step size or to the code to stop the fading of the colour white
field index: 5
field name: StepCodeColourWhite
field resolution: 1.0
field size: 3
field type: U
includes digit: type.digit.u3

Cool Stage B Actuator Target Position
type: Class
subclass of: Function Point
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1

The visual effect of channel 8 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel8IsActive
value KNX: 1

1 h = 20
type: NamedIndividual
value API: 1H
value KNX: 20

Normal = 2
type: NamedIndividual
value API: normal
value KNX: 2

type.dpt.field.245.600.i9.LTRF
type: NamedIndividual
type: Datapoint Type Field
description: LTRF
field index: 9
field name: LTRF
field size: 4
field type: N
includes key value pair: type.kvpair.testResultFailedExceeded
includes key value pair: type.kvpair.testResultPassedInTime
includes key value pair: Unknown = 0
includes key value pair: type.kvpair.testResultFailedInTime
includes key value pair: type.kvpair.testResultStopped
includes key value pair: Passed max delay exceeded = 2

The visual effect of channel 16 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel16IsInactiv
value KNX: 0

Percent V8
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 6.001: Percent V8
subject: Percent V8
subject: 6.1
subject: 6.001
dpt bit size max: 8
dpt major number: 6
datapoint type minor number: 1
is assembled with: type.dpt.field.6.1.i0
label: Percent V8
has communication mode: S

Data Link Layer Busmonitor = 1
type: NamedIndividual
value API: dataLinkLayerBusmonitor
value KNX: 1

power, 0,1 GJ/h = 176
type: NamedIndividual
value API: power,0,1GJh
value KNX: 176

type.dpt.field.253.600.i3.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 3
field name: Reserved
field size: 5
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.21.107.i2.ComfortPushButtonEffective
type: NamedIndividual
type: Datapoint Type Field
description: Effective value of the comfort push button
field index: 2
field name: ComfortPushButtonEffective
field size: 1
field type: B
includes key value pair: no comfort push button is pressed = 0
includes key value pair: at least one comfort push button is pressed = 1

type.dpt.field.19.1.i14.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 14
field name: Reserved
field size: 2
field type: r
includes reserved bit(s): type.bit.reserved

type.dpt.field.10.1.i3.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 3
field name: Reserved
field size: 2
field type: r
includes reserved bit(s): type.bit.reserved

alarm = 1
type: NamedIndividual
value API: alarm
value KNX: 1

TIC Type
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.1208: TIC Type
subject: TIC Type
subject: 20.1208
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1208
is assembled with: type.dpt.field.20.1208.i0
label: TIC Type
has communication mode: S

type.dpt.field.8.5.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 16
field type: V
includes digit: type.digit.s16
unit: SEC

HVAC Emerg Mode Z
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 201.109: HVAC Emerg Mode Z
subject: 201.109
subject: HVAC Emerg Mode Z
dpt bit size max: 16
dpt major number: 201
datapoint type minor number: 109
is assembled with: type.dpt.field.201.109.i1.HVACEmergMode
is assembled with: type.dpt.field.201.109.i0.StatusCommand
label: HVAC Emerg Mode Z
has communication mode: LTE

Building Protection = 4
type: NamedIndividual
is applicable datapoint enum of: hvacModeProtection
value API: buildingProtection
value KNX: 4

type.dpt.field.14.16.i0
type: Datapoint Type Field
type: NamedIndividual
description: conductivity, electrical
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: S-PER-M

Combined Status RTC
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 22.103: Combined Status RTC
subject: 22.103
subject: Combined Status RTC
dpt bit size max: 16
dpt major number: 22
datapoint type minor number: 103
is assembled with: type.dpt.field.22.103.i0.GeneralFailureInformation
is assembled with: type.dpt.field.22.103.i4.OverheatAlarm
is assembled with: type.dpt.field.22.103.i7.HeatingModeEnabled
is assembled with: type.dpt.field.22.103.i5.ControllerInactive
is assembled with: type.dpt.field.22.103.i8.CoolingModeEnabled
is assembled with: type.dpt.field.22.103.i2.DewPointStatus
is assembled with: type.dpt.field.22.103.i1.ActiveMode
is assembled with: type.dpt.field.22.103.i6.AdditionalHeatingCoolingStage
is assembled with: type.dpt.field.22.103.i9.Reserved
is assembled with: type.dpt.field.22.103.i3.FrostAlarm
label: Combined Status RTC
has communication mode: S

Heat Stage A Actuator Fault
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
    intersection of: Restriction
      has value: operationalStateFaulty
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Function Point

Chromaticity Red
type: NamedIndividual
type: StateType
description: This state type expresses that the red part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.

is composed by input
type: ObjectProperty
sub property of: is composed by

DAY
type: Unit
type: NamedIndividual
symbol: day

type.dpt.field.252.600.i13.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 13
field name: Reserved
field size: 4
field type: r
includes reserved bit(s): type.bit.reserved

type.digit.u6
type: NamedIndividual
range max: 63
range min: 0

energy, 1 Wh = 3
type: NamedIndividual
value API: energy,1Wh
value KNX: 3

Protocol
type: Class
comment: The tag category contains individuals allowing to express that a point value originates from another system with a specific/underlying communication protocol.
subclass of: Tag

Occ Mode Z
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 201.108: Occ Mode Z
subject: Occ Mode Z
subject: 201.108
dpt bit size max: 16
dpt major number: 201
datapoint type minor number: 108
is assembled with: type.dpt.field.201.108.i1.OccMode
is assembled with: type.dpt.field.201.108.i0.StatusCommand
label: Occ Mode Z
has communication mode: LTE

Value Electric Flux
type: Datapoint Type
type: NamedIndividual
description: DPT 14.024: Value of electric flux
subject: 14.24
subject: Value Electric Flux
subject: 14.024
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 24
is assembled with: type.dpt.field.14.24.i0
label: Value Electric Flux
has communication mode: S

KiloV-A-HR
type: NamedIndividual
type: Unit
symbol: kV⋅A/hr

type.dpt.field.30.1010.i7.ActivationStateOfChannel8
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 8
field index: 7
field name: ActivationStateOfChannel8
field size: 1
field type: B
includes key value pair: The visual effect of channel 8 is active = 1
includes key value pair: type.kvpair.30.1010.i7.0

Multimedia Room
type: NamedIndividual
type: Location Usages
description: A multimedia room is a space in a building that is used to contain multimedia gadgets such like consoles and entertainment. Preferably used with a Room.

type.dpt.field.201.100.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

type.dpt.field.246.600.i1.BatteryFailure
type: NamedIndividual
type: Datapoint Type Field
description: Battery Failure
field index: 1
field name: BatteryFailure
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

244.x
type: NamedIndividual
type: Datapoint Type
subject: 244.x
subject: 244.major
dpt bit size max: 16
dpt major number: 244
is assembled with: type.dpt.field.244.x.i0
label: 244.x
has communication mode: S

Channel Activation 8
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 21.1010: Channel Activation 8
subject: 21.1010
subject: Channel Activation 8
dpt bit size max: 8
dpt major number: 21
datapoint type minor number: 1010
is assembled with: type.dpt.field.21.1010.i1.ActivationStateOfChannel2
is assembled with: type.dpt.field.21.1010.i2.ActivationStateOfChannel3
is assembled with: type.dpt.field.21.1010.i0.ActivationStateOfChannel1
is assembled with: type.dpt.field.21.1010.i4.ActivationStateOfChannel5
is assembled with: type.dpt.field.21.1010.i3.ActivationStateOfChannel4
is assembled with: type.dpt.field.21.1010.i5.ActivationStateOfChannel6
is assembled with: type.dpt.field.21.1010.i6.ActivationStateOfChannel7
is assembled with: type.dpt.field.21.1010.i7.ActivationStateOfChannel8
label: Channel Activation 8
has communication mode: S

Consumer = 0
type: NamedIndividual
value API: consumer
value KNX: 0

Peak Event
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.1207: Peak Event
subject: 20.1207
subject: Peak Event
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1207
is assembled with: type.dpt.field.20.1207.i0
label: Peak Event
has communication mode: S

type.dpt.field.512.509.i1.lb.LBE
type: NamedIndividual
type: Datapoint Type Field
description: list of leakage behaviour elements
field index: 1
field name: LBE
field type: D<n>
includes counter: type.dpt.field.512.509.i0.lb.LBE CNT
includes datapoint field: type.dpt.field.lb.lbe

Unit
type: Class
comment: (SI) unit class for function points (FP) and datapoints.
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: symbol
  intersection of: Restriction
    min cardinality: 0
    on property: symbol

Functional Block
type: Class
comment: A functional block represents a software element that has internal storage and produces a computable result with output values when executed with a particular set of input values.
subclass of: Functionality
subclass of: Restriction
  on data range: unsignedShort
  on property: interface object type
  qualified cardinality: 1

no occupancy from presence detectors = 0
type: NamedIndividual
value API: noOccupancyFromPresenceDetectors
value KNX: 0

volume flow, 1 l/h = 59
type: NamedIndividual
value API: volumeFlow,1Lh
value KNX: 59

Standard three-phase = 4
type: NamedIndividual
value API: standardThree-phase
value KNX: 4

type.dpt.field.21.107.i1.PresenceStatusEffective
type: NamedIndividual
type: Datapoint Type Field
description: Effective value of the presence status
field index: 1
field name: PresenceStatusEffective
field size: 1
field type: B
includes key value pair: type.kvpair.21.107.i1.1
includes key value pair: no occupancy from presence detectors = 0

two push buttons/binary inputs mode = 4
type: NamedIndividual
value API: twoPushButtonsbinaryInputsMode
value KNX: 4

Invert Control
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 2.012: Invert Control
subject: Invert Control
subject: 2.012
subject: 2.12
dpt bit size max: 2
dpt major number: 2
datapoint type minor number: 12
is assembled with: type.dpt.field.2.x.i1.c
is assembled with: Invert
label: Invert Control
has communication mode: S

Power
type: NamedIndividual
type: Quantity Kind
description: Power is the rate at which work is performed or energy is transmitted, or the amount of energy required or expended for a given unit of time. As a rate of change of work done or the energy of a subsystem, power is work divided by time.

type.dpt.field.242.x.i0
type: Datapoint Type Field
type: NamedIndividual
description: status
field index: 0
field size: 48
field string schema: raw
field type: A[n]

type.dpt.field.27.1.i17.MaskBitIOO2
type: NamedIndividual
type: Datapoint Type Field
description: Mask Bit Info On Off Output 2
field index: 17
field name: MaskBitIOO2
field size: 1
field type: B
includes key value pair: output state is not valid = 0
includes key value pair: output state is valid = 1

5.x
type: NamedIndividual
type: Datapoint Type
subject: 5.major
subject: 5.x
dpt bit size max: 8
dpt major number: 5
is assembled with: type.dpt.field.5.x.i0
label: 5.x
has communication mode: S

1 min = 10
type: NamedIndividual
value API: 1Min
value KNX: 10

Electrical Panel
type: NamedIndividual
type: EquipmentType
description: Physical housing for electrical circuits, fuses, and breakers. A electric panel (also known as distribution board, panelboard, breaker panel, DB board or DB box) is a component of an electricity supply system that divides an electrical power feed into subsidiary circuits while providing a protective fuse or circuit breaker for each circuit in a common enclosure.

type.dpt.field.512.506.i2.smombc.TRAN CNT
type: NamedIndividual
type: Datapoint Type Field
description: number of transitions
field index: 2
field name: TRAN_CNT
field size: 4
field type: U
includes digit: type.digit.u4

2 stage = 2
type: NamedIndividual
value API: 2Stage
value KNX: 2

type.dpt.field.22.103.i1.ActiveMode
type: NamedIndividual
type: Datapoint Type Field
description: Active Mode
field index: 1
field name: ActiveMode
field size: 1
field type: B
includes key value pair: type.kvpair.22.103.i1.1
includes key value pair: type.kvpair.22.103.i1.0

type.dpt.field.244.600.i4.HSinhibit
type: NamedIndividual
type: Datapoint Type Field
description: HS - Hardwired inhibit
field index: 4
field name: HS inhibit
field size: 1
field type: B
includes key value pair: type.kvpair.244.600.i4.0
includes key value pair: type.kvpair.244.600.i4.1

StatusHPM
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 209.100: StatusHPM
subject: 209.100
subject: StatusHPM
dpt bit size max: 24
dpt major number: 209
datapoint type minor number: 100
is assembled with: type.dpt.field.209.100.i4.NoHeatAvailable
is assembled with: type.dpt.field.209.100.i5.Reserved
is assembled with: type.dpt.field.209.100.i2.SummerMode
is assembled with: type.dpt.field.209.100.i1.Fault
is assembled with: type.dpt.field.209.100.i3.OffPerm
is assembled with: type.dpt.field.209.100.i0.TempFlowValid
is assembled with: type.dpt.field.209.100.i6.TempFlowProdSegmH
label: StatusHPM
has communication mode: LTE

maximum
type: FunctionalProperty
type: DatatypeProperty
comment: Limits a numerical datapoint value in its applicative behavior to a maximum. Represents an external definition, hence it is also used from other concepts, therefore no domain is defined (merged ontologies -> intersection problems). The range xsd:decimal covers also numerical values with a fraction such as 12.34 or -13.56.
range: decimal

Phenomenon Quality Kind
type: Class
subclass of: Restriction
  on class: PhenomenonType
  on property: has tag
  qualified cardinality: 1
subclass of: Quality Kind

EnableComfort
type: Class
subject: EnableComfort
subject: 53
subject: 104.53
interface object type annotation: 104
label: EnableComfort
property identifier annotation: 53
subclass of: Restriction
  has value: Enable
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 53
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 104
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Enabled State
      on property: hasStateType
    intersection of: Restriction
      has value: Disabled State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType

Level 14 = 14
type: NamedIndividual
value API: level14
value KNX: 14

220.x
type: NamedIndividual
type: Datapoint Type
subject: 220.x
subject: 220.major
dpt bit size max: 32
dpt major number: 220
is assembled with: type.dpt.field.220.x.i0
label: 220.x
has communication mode: LTE

assigend trades
type: DatatypeProperty
comment: To a device assigned trade, whereas the trade definitions (names/structures) can be freely defined by the MaC user. The trade definitions MAY have a logical relation to the KIM trade tags. A device is assigned to one trade only.
range: string
sub property of: deviceData

type.dpt.field.15.0.i7.D3
type: Datapoint Type Field
type: NamedIndividual
description: digit 3 of access identification code. Only a card or key number should be used. System number, version number, country code, etc are not necessary. Ciphered access information code should be possible in principle. If 24 bits are not necessary, the most significant positions shall be set to zero.
field index: 7
field name: D3
field resolution: 1.0
field size: 4
field type: U
includes digit: type.digit.u4 0 9

has tag set
type: ObjectProperty
inverse of: isTagSetOf
comment: To define a generic set of tags with no limitation on the amount. The tag set may represent a quality kind or process kind.
domain: Class
  union of: Function Point
  union of: ApplicationFunction
  union of: Datapoint
  union of: Equipment
range: TagSet

Logical Input Point
type: NamedIndividual
type: PointInterface
description: The tag represents information for a logical point, a communication interworking (logical) input Point, it receives data.

has point function type
type: ObjectProperty
inverse of: is point function type of
comment: An OP relationship to a list that describes the position of a point in a control loop.
domain: OperationKind
range: Point Function
sub property of: has tag

Compressed Air = 9
type: NamedIndividual
value API: compressedAir
value KNX: 9

type.dpt.field.10.1.i5.Day
type: NamedIndividual
type: Datapoint Type Field
description: Day
field index: 5
field name: Day
field size: 3
field type: N
includes key value pair: type.kvpair.10.1.i5.2
includes key value pair: Monday = 1
includes key value pair: type.kvpair.10.1.i5.4
includes key value pair: type.kvpair.10.1.i5.0
includes key value pair: type.kvpair.10.1.i5.5
includes key value pair: type.kvpair.10.1.i5.7
includes key value pair: type.kvpair.10.1.i5.6
includes key value pair: Wednesday = 3

system and functions of common interest = 1
type: NamedIndividual
value API: systemAndFunctionsOfCommonInterest
value KNX: 1

type.dpt.field.213.102.i3.TempSetpShiftComf
type: NamedIndividual
type: Datapoint Type Field
description: room temperature setpoint shift comfort (delta value)
field index: 3
field name: TempSetpShiftComf
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16
unit: http://qudt.org/vocab/unit/K

type.dpt.field.218.2.i0.StatusCommand
type: NamedIndividual
type: Datapoint Type Field
description: standard Status/Command
field index: 0
field name: StatusCommand
field size: 8
field type: Z8
includes DPT: StatusGen

process fault / controller fault = 2
type: NamedIndividual
value API: processFaultControllerFault
value KNX: 2

power, 0,01 kJ/h = 49
type: NamedIndividual
value API: power,0,01KJh
value KNX: 49

LongTimePeriod Hrs
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 12.102: LongTimePeriod Hrs
subject: 12.102
subject: LongTimePeriod Hrs
dpt bit size max: 32
dpt major number: 12
datapoint type minor number: 102
is assembled with: type.dpt.field.12.102.i0
label: LongTimePeriod Hrs
has communication mode: S

emSequenceInstruction
type: NamedIndividual
type: Datapoint Type
description: sequence instruction
dpt bit size max: 104
dpt major number: 522
datapoint type minor number: 500
is assembled with: type.dpt.field.522.500.i1.si.AC
is assembled with: type.dpt.field.522.500.i5.si.PID
is assembled with: type.dpt.field.522.500.i0.si.ET
is assembled with: type.dpt.field.522.500.i6.si.IT
is assembled with: type.dpt.field.522.500.i4.si.CID
is assembled with: type.dpt.field.522.500.i3.si.SID
is assembled with: type.dpt.field.522.500.i7.si.ID
is assembled with: type.dpt.field.522.500.i2.si.Reserved

type.dpt.field.9.22.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 0.01
field size: 16
field type: F
includes digit: type.digit.f16
unit: W-PER-M2

type.dpt.field.512.510.i5.smddb.TRAN
type: Datapoint Type Field
type: NamedIndividual
description: list of transitions
field index: 5
field type: D<n>
includes counter: type.dpt.field.512.510.i2.smddb.TRAN CNT
includes DPT: emTransition

type.dpt.field.19.1.i12.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 12
field name: Reserved
field size: 2
field type: r
includes reserved bit(s): type.bit.reserved

Entrance
type: Location Usages
type: NamedIndividual
description: Entrance generally refers to the place of entering like a lobby, foyer, gate, door, or road or the permission to do so. Preferably used with an Room.

type.dpt.field.207.105.i0.Failure
type: NamedIndividual
type: Datapoint Type Field
description: actuator has a failure
field index: 0
field name: Failure
field size: 1
includes DPT: Bool

84% = 6
type: NamedIndividual
value API: 84%
value KNX: 6

type.dpt.field.13.100.i0
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field resolution: 1.0
field size: 32
field type: V
includes digit: type.digit.s32
unit: SEC

Location
type: Class
comment: To represent a location, used to express a spatial location structure. The defined location model class/subclass structure does not reflect the hierarchy of a real world spatial building, such as a site/building with floors, rooms and/or spaces.
label: Ort @de
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: state
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: state
subclass of: Restriction
  all values from: Location
  on property: hasAdjacentLocation
subclass of: Restriction
  all values from: Location
  on property: has location
subclass of: Restriction
  all values from: Location Usages
  on property: has location usage
subclass of: Restriction
  all values from: string
  on property: comment
subclass of: Restriction
  all values from: External Address
  on property: has address
subclass of: Restriction
  all values from: Equipment
  on property: containsEquipment
subclass of: Restriction
  all values from: ApplicationFunction
  on property: has application function
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: number
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: number
subclass of: Location
subclass of: Restriction
  all values from: Outside
  on property: has outside

30 s = 8
type: NamedIndividual
value API: 30S
value KNX: 8

SCLOMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.001: SCLOMode
subject: 20.1
subject: 20.001
subject: SCLOMode
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 1
is assembled with: type.dpt.field.20.1.i0
label: SCLOMode
has communication mode: S

Familiy House
type: Location Usages
type: NamedIndividual
description: A stand-alone house (also called a single-detached dwelling, detached residence or detached house) is a free-standing residential building. Preferably used with a Building or Site/Space.

LoadFailedDetection
type: Class
subject: 418.58
subject: LoadFailedDetection
subject: 58
interface object type annotation: 418
label: LoadFailedDetection
property identifier annotation: 58
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 58
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: alarm
  on property: datapointType
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
    intersection of: Restriction
      has value: Operational State Defect
      on property: relatesToStateType

type.dpt.field.21.1001.i1.KNXSN
type: NamedIndividual
type: Datapoint Type Field
description: KNX SN
field index: 1
field name: KNXSN
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

waste water meter = 40
type: NamedIndividual
value API: wasteWaterMeter
value KNX: 40

Shutter Position Percentage
type: Class
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: qk ph light illuminance room
  on property: acts on phenomenon quality kind
subclass of: Restriction
  has value: qk eq blindsactuator positionvector
  on property: adjustsEquipmentQualityKind
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq blindsactuator positionvector
      on property: refersTo
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Function Point

Time Delay
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.013: Time Delay
subject: Time Delay
subject: 20.013
subject: 20.13
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 13
is assembled with: type.dpt.field.20.13.i0
label: Time Delay
has communication mode: S

type.dpt.field.14.10.i0
type: NamedIndividual
type: Datapoint Type Field
description: area
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: M2

Fan Stage
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8
label: Fan Stage
unit: UNITLESS

type.dpt.field.7.13.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: LUX

FanSpeed
type: Class
subject: 372.55
subject: FanSpeed
subject: 55
interface object type annotation: 372
label: FanSpeed
property identifier annotation: 55
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq fanmotor angularvelocity room
      on property: refersTo
subclass of: Restriction
  has value: relValueZ
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 55
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 372
    on property: interface object type
subclass of: Restriction
  has value: qk eq fanmotor angularvelocity room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

type.dpt.field.21.100.i1.Protection
type: NamedIndividual
type: Datapoint Type Field
description: Protection
field index: 1
field name: Protection
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.26.1.i1.B
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: B
field size: 1
field type: B
includes key value pair: scene is active = 0
includes key value pair: scene is inactive = 1

25.x
type: NamedIndividual
type: Datapoint Type
subject: 25.x
subject: 25.major
dpt bit size max: 8
dpt major number: 25
is assembled with: type.dpt.field.25.x.i0
label: 25.x
has communication mode: S

includes key value pair
type: ObjectProperty
sub property of: includes

HVAC Valve Actuator
type: Class
subject: HVA
subject: HVAC Valve Actuator
subject: 400
interface object type annotation: 400
label: HVAC Valve Actuator
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.400.70
    intersection of: Restriction
      has value: Fault
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  all values from: roomTemperatureControl
  on property: is applicable functionality of
subclass of: Restriction
  on class: Class
    intersection of: dpa.400.50
    intersection of: Restriction
      has value: ActTargetPos
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.400.74
    intersection of: Restriction
      has value: CombinedStatus_HVA
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.400.52
    intersection of: Restriction
      has value: ForcedPositionEnable
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.400.73
    intersection of: Restriction
      has value: ValveKick
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: CalibrationMode
    intersection of: Restriction
      has value: CalibrationMode
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: ActCurrPos
    intersection of: Restriction
      has value: ActCurrPos
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.400.71
    intersection of: Restriction
      has value: Overridden
      on property: point name
    intersection of: Restriction
      has value: many
      on property: hasCardinality
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: Class
    intersection of: dpa.400.51
    intersection of: Restriction
      has value: ForcedPosition
      on property: point name
    intersection of: Restriction
      has value: one
      on property: hasCardinality
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: ActCurrPos
  on property: isComposedByOutput
subclass of: Restriction
  on class: dpa.400.50
  on property: is composed by input
  qualified cardinality: 1
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.400.70
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.400.73
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.400.71
  on property: isComposedByOutput
subclass of: Class
  intersection of: Functional Block
  intersection of: Restriction
    has value: 400
    on property: interface object type
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.400.51
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: CalibrationMode
  on property: isComposedByOutput
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.400.52
  on property: is composed by input
subclass of: Restriction
  max qualified cardinality: 1
  on class: dpa.400.74
  on property: isComposedByOutput

type.dpt.field.30.1010.i18.ActivationStateOfChannel19
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 19
field index: 18
field name: ActivationStateOfChannel19
field size: 1
field type: B
includes key value pair: type.kvpair.30.1010.i18.0
includes key value pair: type.kvpair.30.1010.i18.1

RelDimmingSpeed
type: Class
subject: 418.67
subject: RelDimmingSpeed
subject: 67
interface object type annotation: 418
label: RelDimmingSpeed
property identifier annotation: 67
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph temporal duration
      on property: refersTo
subclass of: Restriction
  has value: qk ph temporal duration
  on property: hasQualityKind
subclass of: Restriction
  has value: timePeriod100MSec
  on property: datapointType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 67
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

http://qudt.org/vocab/unit/W
type: NamedIndividual
type: Unit
symbol: W

Smoke
type: PhenomenonType
type: NamedIndividual
description: Smoke is a suspension of airborne particulates and gases emitted when a material undergoes combustion, together with the quantity of air that is entrained or otherwise mixed into the mass. It is commonly an unwanted by-product of fires.

TimePeriodMin
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 7.006: TimePeriodMin
subject: 7.006
subject: 7.6
subject: TimePeriodMin
dpt bit size max: 16
dpt major number: 7
datapoint type minor number: 6
is assembled with: type.dpt.field.7.6.i0
label: TimePeriodMin
has communication mode: S

type.dpt.field.22.100.i8.Reserved
type: NamedIndividual
type: Datapoint Type Field
field index: 8
field name: Reserved
field size: 8
field type: r
includes reserved bit(s): type.bit.reserved

extended alarm = 3
type: NamedIndividual
value API: extendedAlarm
value KNX: 3

logical function OR = 0
type: NamedIndividual
value API: logicalFunctionOR
value KNX: 0

Presence Unoccupied
type: StateType
type: NamedIndividual
description: This state type expresses that a room is unoccupied, i.e. no people are in the room. This state type is the inverse of the 'Presence Occupied' state type.

type.dpt.field.235.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: Signed value with classification and validity
field index: 0
field size: 48
field string schema: raw
field type: A[n]

no alarm = 0
type: NamedIndividual
value API: noAlarm
value KNX: 0

has locality
type: ObjectProperty
inverse of: isLocalityOf
comment: A child OP relationship to a list that describes the generic locality characteristic where an observation or actuation is made. It is a generic “place of action”, when e.g., assigned to a room this means “the action happens in a place that is a room” but not in which room exactly, this is a room instance of an installation.
domain: Quality Kind
range: Locality
sub property of: has tag

type.dpt.field.20.613.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field size: 8
field type: N
includes key value pair: Request Converter FT Info = 4
includes key value pair: Request Converter Status = 1
includes key value pair: Request Converter Info Fix = 8
includes key value pair: Request Converter PDT Info = 6
includes key value pair: type.kvpair.20.613.i0.2
includes key value pair: type.kvpair.20.613.i0.7
includes key value pair: type.kvpair.20.613.i0.3
includes key value pair: type.kvpair.20.613.i0.5

type.dpt.field.512.507.i4.smfrbc.OM
type: NamedIndividual
type: Datapoint Type Field
description: list of operation modes
field index: 4
field name: OM
field type: D<n>
includes counter: type.dpt.field.512.507.i1.smfrbc.OM CNT
includes datapoint field: type.dpt.field.frbc.om

Value Sound Intensity
type: Datapoint Type
type: NamedIndividual
description: DPT 14.064: Value of sound intensity
subject: 14.64
subject: 14.064
subject: Value Sound Intensity
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 64
is assembled with: type.dpt.field.14.64.i0
label: Value Sound Intensity
has communication mode: S

type.dpt.field.234.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: language code ISO 639-1
field index: 0
field size: 16
field string schema: raw
field type: A[n]

has room segment
type: ObjectProperty
inverse of: is room segment of
comment: A strong OP relationship to express a relation to a room segment contained in a room or room segment.
domain: Class
  union of: Room
  union of: RoomSegment
range: RoomSegment
sub property of: has space

type.dpt.field.207.600.i8.ActualValue
type: NamedIndividual
type: Datapoint Type Field
description: Current lighting level in %. In case of a switching actuator LSAB the range is limited to the discrete values 0 % and 100 %.
field index: 8
field name: ActualValue
field resolution: 1.0
field size: 8
field type: U
includes digit: type.digit.u8 0 100
unit: PERCENT

Colour xyY
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 242.600: Colour xyY
subject: 242.600
subject: Colour xyY
dpt bit size max: 48
dpt major number: 242
datapoint type minor number: 600
is assembled with: type.dpt.field.242.600.i3.Brightness
is assembled with: type.dpt.field.242.600.i2.Reserved
is assembled with: type.dpt.field.242.600.i1.C
is assembled with: type.dpt.field.242.600.i5.xaxis
is assembled with: type.dpt.field.242.600.i0.B
is assembled with: type.dpt.field.242.600.i4.yaxis
label: Colour xyY
has communication mode: S

symbol
type: DatatypeProperty
comment: The symbol is a glyph that is used to represent some concept, typically a unit or a quantity, in a compact form. For example, the symbol for an Ohm is a capital greek Omega. This contrasts with 'unit:abbreviation', which gives a short alphanumeric abbreviation for the unit, 'ohm' for Ohm.

type.dpt.field.20.11.i0
type: NamedIndividual
type: Datapoint Type Field
description: ErrorClass_System
field index: 0
field size: 8
field type: N
includes key value pair: invalid Group Object number (ASAP) = 17
includes key value pair: type.kvpair.20.11.i0.8
includes key value pair: hardware fault = 4
includes key value pair: type.kvpair.20.11.i0.10
includes key value pair: type.kvpair.20.11.i0.15
includes key value pair: type.kvpair.20.11.i0.9
includes key value pair: general device fault (e.g. RAM, EEPROM, UI, watchdog, ...) = 1
includes key value pair: type.kvpair.20.11.i0.7
includes key value pair: invalid connection number (TSAP) = 16
includes key value pair: undefined load command received = 14
includes key value pair: type.kvpair.20.11.i0.5
includes key value pair: insufficient non volatile memory = 6
includes key value pair: type.kvpair.20.11.i0.13
includes key value pair: type.kvpair.20.11.i0.2
includes key value pair: type.kvpair.20.11.i0.12
includes key value pair: type.kvpair.20.11.i0.11
includes key value pair: Group Object Type exceeds (PID_MAX_APDU_LENGTH - 2) = 18
includes key value pair: no fault = 0
includes key value pair: configuration fault = 3

composes input
type: ObjectProperty
inverse of: is composed by input
sub property of: composes

type.dpt.field.206.100.i1.Time
type: NamedIndividual
type: Datapoint Type Field
description: delay time (min)
field index: 1
field name: Time
field size: 16
includes DPT: TimePeriodMin

type.digit.u5 0 23
type: NamedIndividual
range max: 23
range min: 0

type.dpt.field.212.100.i1.TempSetpShiftStdby
type: NamedIndividual
type: Datapoint Type Field
description: room temperature setpoint shift standby (delta value)
field index: 1
field name: TempSetpShiftStdby
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16
unit: http://qudt.org/vocab/unit/K

volume flow, 1000 ml/s = 78
type: NamedIndividual
value API: volumeFlow,1000Mls
value KNX: 78

EnergyDirection
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.1201: EnergyDirection
subject: EnergyDirection
subject: 1.1201
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 1201
is assembled with: type.dpt.field.1.1201.i0
label: EnergyDirection
has communication mode: S

Heat Stage A Actuator Valve Kick
type: Class
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1

description
type: DatatypeProperty
comment: A human friendly description (longer text), used to define user specific data for an individual. Edited in a MaC or from predefined product data or dictionary content. No limitation of the actual amaount, external entites may add additional language depended text. The 'Range' is not limited to a string, allowing to express also text in several languages (note W3C does not define a range).
range: Literal

LoadTypeSet
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.609: LoadTypeSet
subject: LoadTypeSet
subject: 20.609
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 609
is assembled with: type.dpt.field.20.609.i0
label: LoadTypeSet
has communication mode: S

AbsSetvalueControl
type: Class
subject: 70
subject: 418.70
subject: AbsSetvalueControl
interface object type annotation: 418
label: AbsSetvalueControl
property identifier annotation: 70
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 70
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 418
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Command
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

HVACModeUser
type: Class
subject: 55
subject: HVACModeUser
subject: 384.55
interface object type annotation: 384
label: HVACModeUser
property identifier annotation: 55
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: user
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 55
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 384
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

Heating-Cooling Stages None
type: NamedIndividual
type: StateType
description: This state type expresses that an HVAC system has neither primary nor secondary stage (for its cooling or heating subsystem). In general, an HVAC system may consist of multiple stages, which might be independently defined for both heating and cooling subsystems. The number of stages might vary, but usually up to two stages are used. These are referred to as 'primary' and 'secondary' stages.

Status Lighting Actuator
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 207.600: Status Lighting Actuator
subject: Status Lighting Actuator
subject: 207.600
dpt bit size max: 16
dpt major number: 207
datapoint type minor number: 600
is assembled with: type.dpt.field.207.600.i3.NightModeActive
is assembled with: type.dpt.field.207.600.i5.Dimming
is assembled with: type.dpt.field.207.600.i4.StaircaseLightingFunction
is assembled with: type.dpt.field.207.600.i8.ActualValue
is assembled with: type.dpt.field.207.600.i7.Failure
is assembled with: type.dpt.field.207.600.i0.ValidActualValue
is assembled with: type.dpt.field.207.600.i1.Locked
is assembled with: type.dpt.field.207.600.i6.LocalOverride
is assembled with: type.dpt.field.207.600.i2.Forced
label: Status Lighting Actuator
has communication mode: S

256.x
type: NamedIndividual
type: Datapoint Type
subject: 256.x
subject: 256.major
dpt bit size max: 128
dpt major number: 256
is assembled with: type.dpt.field.256.x.i0
label: 256.x
has communication mode: S

type.dpt.field.14.60.i0
type: NamedIndividual
type: Datapoint Type Field
description: resistance
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: OHM

type.dpt.field.20.21.i0
type: NamedIndividual
type: Datapoint Type Field
description: CloudCover
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.21.i0.1
includes key value pair: type.kvpair.20.21.i0.6
includes key value pair: type.kvpair.20.21.i0.7
includes key value pair: type.kvpair.20.21.i0.3
includes key value pair: Sunshiny = 2
includes key value pair: Sky obstructed from view = 9
includes key value pair: type.kvpair.20.21.i0.5
includes key value pair: type.kvpair.20.21.i0.4
includes key value pair: Cloudless = 0
includes key value pair: type.kvpair.20.21.i0.8

type.dpt.field.20.103.i0
type: NamedIndividual
type: Datapoint Type Field
description: DHWMode
field index: 0
field size: 8
field type: N
includes key value pair: type.kvpair.20.103.i0.0
includes key value pair: type.kvpair.20.103.i0.3
includes key value pair: Off/FrostProtect = 4
includes key value pair: type.kvpair.20.103.i0.1
includes key value pair: Normal = 2

Scaling
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 5.001: Scaling
subject: 5.1
subject: Scaling
subject: 5.001
dpt bit size max: 8
dpt major number: 5
datapoint type minor number: 1
is assembled with: Scaling
label: Scaling
has communication mode: S

type.dpt.field.234.2.i0.Character2
type: NamedIndividual
type: Datapoint Type Field
description: second character of RegionCode, ASCII-coded
field index: 0
field name: Character2
field size: 8
includes DPT: charascii

type.dpt.field.22.101.i14.OverheatAlarm
type: NamedIndividual
type: Datapoint Type Field
description: OverheatAlarm
field index: 14
field name: OverheatAlarm
field size: 1
field type: B
includes key value pair: alarm = 1
includes key value pair: No alarm = 0

Bool
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 1.002: Bool
subject: 1.002
subject: 1.2
subject: Bool
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 2
is assembled with: type.dpt.field.1.2.i0
label: Bool
has communication mode: S

is location of
type: ObjectProperty
type: FunctionalProperty
type: IrreflexiveProperty
type: AsymmetricProperty
domain: Location
range: Location
sub property of: is referenced by

at least one window opened = 1
type: NamedIndividual
value API: atLeastOneWindowOpened
value KNX: 1

no fault = 0
type: NamedIndividual
value API: noFault
value KNX: 0

The visual effect of channel 7 is inactive = 0
type: NamedIndividual
value API: theVisualEffectOfChannel7IsInactive
value KNX: 0

type.dpt.field.30.1010.i1.ActivationStateOfChannel2
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 2
field index: 1
field name: ActivationStateOfChannel2
field size: 1
field type: B
includes key value pair: type.kvpair.30.1010.i1.0
includes key value pair: The visual effect of channel 2 is active = 1

type.dpt.field.513.500.i2.rol.C2
type: NamedIndividual
type: Datapoint Type Field
description: roles for commodity OIL
field index: 2
field name: C2
field size: 2
field type: U
includes key value pair: type.kvpair.rolConsumer
includes key value pair: no role
includes key value pair: type.kvpair.rolProducer
includes key value pair: type.kvpair.rolConsumerAndProducer

has status
type: ObjectProperty
comment: The target value represents a status of a corresponding source datapoint.
sub property of: influences

no role
type: NamedIndividual
value API: roleNone
value KNX: 0

Pump Control
type: Class
comment: A specific Application Function that controls, for example, the speed of a pump.
subclass of: equipmentCtrl

type.dpt.field.212.101.i1.TempSetpStdby
type: Datapoint Type Field
type: NamedIndividual
description: room temperature setpoint standby
field index: 1
field name: TempSetpStdby
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C

Villa
type: Location Usages
type: NamedIndividual
description: A villa is a upper class country house. Preferably used with a Building.

type.dpt.field.14.70.i0
type: NamedIndividual
type: Datapoint Type Field
description: temperature difference
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/K

Chromaticity Green
type: StateType
type: NamedIndividual
description: This state type expresses that the green part of RGB(W) light color is referred to. It is mostly used in lighting applications that use the RGB or RGBW color model.

current position=0 = 0
type: NamedIndividual
value API: currentPosition=0
value KNX: 0

VolumeLiquid Litre
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 12.1200: VolumeLiquid Litre
subject: 12.1200
subject: VolumeLiquid Litre
dpt bit size max: 32
dpt major number: 12
datapoint type minor number: 1200
is assembled with: type.dpt.field.12.1200.i0
label: VolumeLiquid Litre
has communication mode: S

Building not in use = 1
type: NamedIndividual
value API: buildingNotInUse
value KNX: 1

Other = 0
type: NamedIndividual
value API: other
value KNX: 0

Cool Stage A Actuator Current Position
type: Class
subclass of: Restriction
  has value: Scaling
  on property: datapointType
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: qk eq valveactuator positionvector pipesection supplysection
      on property: refersTo
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: controlModeCooling
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Function Point
subclass of: Restriction
  has value: qk eq valveactuator positionvector pipesection supplysection
  on property: adjustsEquipmentQualityKind

type.dpt.field.225.1.i0.Percent
type: NamedIndividual
type: Datapoint Type Field
description: percent
field index: 0
field name: Percent
field size: 8
includes DPT: Scaling

type.dpt.field.201.105.i1.EnableHCStage
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: EnableHCStage
field size: 8
includes DPT: Enable HC Stage

Device
type: Class
comment: A Device can be any electronic equipment with some computing ability that has a firmware, optionally with input and output terminals (I/O), an Application Program that provides as set of Points as the interface for the I/O operations, and parameter values controlling the behavior of the I/O operations at Runtime.
subclass of: Restriction
  max qualified cardinality: 1
  on data range: string
  on property: assigend trades
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: firmware
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: firmware
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: state
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: state
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: hardware
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: hardware
subclass of: Restriction
  all values from: Functional Block
  on property: supportsFunctionalBlock
subclass of: Restriction
  all values from: string
  on property: comment
subclass of: Equipment
subclass of: Restriction
  max qualified cardinality: 1
  on data range: dateTime
  on property: last downloaded
subclass of: Restriction
  max qualified cardinality: 1
  on data range: string
  on property: serial number
subclass of: Restriction
  all values from: Gateway
  on property: has proxy
subclass of: Restriction
  max qualified cardinality: 1
  on data range: dateTime
  on property: last modified
subclass of: Restriction
  all values from: ApplicationProgram
  on property: hosts
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: Installation Hints
  intersection of: Restriction
    max qualified cardinality: 1
    on data range: string
    on property: Installation Hints
subclass of: Restriction
  on data range: string
  on property: individualAddress
  qualified cardinality: 1
subclass of: Restriction
  all values from: Channel
  on property: has channel

type.dpt.field.244.600.i2.DP
type: Datapoint Type Field
type: NamedIndividual
description: Duration Test Pending
field index: 2
field name: DP
field size: 2
field type: N
includes key value pair: type.kvpair.testNotPending
includes key value pair: Unknown = 0
includes key value pair: type.kvpair.testPending

Calculated = 1
type: NamedIndividual
value API: calculated
value KNX: 1

Product
type: Class
comment: An item offered for sale; it can be assigned from any equipment. Manufacturers usually provide identifiers for each product they make. Identifier examples are type/model or version number or the order number.
subclass of: Core Thing
subclass of: Restriction
  max qualified cardinality: 1
  on data range: string
  on property: Order Number
subclass of: Class
  intersection of: Restriction
    on property: Media Type
    some values from: string
  intersection of: Restriction
    all values from: string
    on property: Media Type
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: manufacturer
  intersection of: Restriction
    on data range: string
    on property: manufacturer
    qualified cardinality: 1
subclass of: Class
  intersection of: Restriction
    all values from: string
    on property: certificationStatus
  intersection of: Restriction
    on data range: string
    on property: certificationStatus
    qualified cardinality: 1

Group Address = 1
type: NamedIndividual
value API: groupAddress
value KNX: 1

type.dpt.field.ec.i1.AVR
type: Datapoint Type Field
type: NamedIndividual
description: power range the device will operate for the given time period
field index: 1
field name: AVR
field size: 32
includes DPT: emPowerRange

type.dpt.field.21.100.i2.Oversupply
type: Datapoint Type Field
type: NamedIndividual
description: Oversupply
field index: 2
field name: Oversupply
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.207.100.i5.PrelBurner
type: Datapoint Type Field
type: NamedIndividual
description: Actual relative power %
field index: 5
field name: PrelBurner
field resolution: 1.0
field size: 8
includes digit: type.digit.u8 0 100
unit: PERCENT

Monday = 1
type: NamedIndividual
value API: monday
value KNX: 1

type.dpt.field.512.505.i4.ps.S
type: NamedIndividual
type: Datapoint Type Field
description: Indicator whether sequence is selected to be executed within the power sequence container
field index: 4
field name: S
field size: 1
field type: B
includes key value pair: type.kvpair.seqNotSelected
includes key value pair: type.kvpair.seqSelected

type.dpt.field.220.100.i0.Temp
type: NamedIndividual
type: Datapoint Type Field
description: absolute temperature value
field index: 0
field name: Temp
field resolution: 0.02
field size: 16
field type: V
includes digit: type.digit.s16 neg13650 32767
unit: DEG C

Value Absolute Temperature
type: NamedIndividual
type: Datapoint Type
description: DPT 14.069: Value of absolute temperature
subject: 14.69
subject: 14.069
subject: Value Absolute Temperature
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 69
is assembled with: type.dpt.field.14.69.i0
label: Value Absolute Temperature
has communication mode: S

type.dpt.field.14.68.i0
type: Datapoint Type Field
type: NamedIndividual
description: temperature, common
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: DEG C

critical = 1
type: NamedIndividual
value API: critical
value KNX: 1

Off = 6
type: NamedIndividual
value API: off
value KNX: 6

Value Power Factor
type: Datapoint Type
type: NamedIndividual
description: DPT 14.057: Value of power factor
subject: 14.057
subject: Value Power Factor
subject: 14.57
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 57
is assembled with: type.dpt.field.14.57.i0
label: Value Power Factor
has communication mode: S

217.x
type: NamedIndividual
type: Datapoint Type
subject: 217.major
subject: 217.x
dpt bit size max: 16
dpt major number: 217
is assembled with: type.dpt.field.217.x.i0
label: 217.x
has communication mode: S

TempRoomSetpUserAbsEff
type: Class
subject: TempRoomSetpUserAbsEff
subject: 100.59
subject: 59
interface object type annotation: 100
label: TempRoomSetpUserAbsEff
property identifier annotation: 59
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: HVAC absolute Temperature
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 59
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

Functionality
type: Class
comment: A functionality represents a concrete piece of software and a set of any type of interfaces (mainly Points) that is needed to accomplish a task for which a Device is designed for.
subclass of: Software
subclass of: Restriction
  all values from: Point
  on property: hasPoint
subclass of: Restriction
  all values from: ApplicationFunction
  on property: is applicable functionality of

type.dpt.field.22.103.i8.CoolingModeEnabled
type: NamedIndividual
type: Datapoint Type Field
description: Cooling Mode Enabled
field index: 8
field name: CoolingModeEnabled
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

Movement Trigger
type: Class
subject: 63
subject: Movement Trigger
subject: MT
subject: 414.63
interface object type annotation: 414
label: Movement Trigger
property identifier annotation: 63
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph person positionvector room
      on property: refersTo
subclass of: Restriction
  has value: start
  on property: datapointType
subclass of: Restriction
  has value: qk ph person positionvector room
  on property: hasQualityKind
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 63
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 414
    on property: interface object type

http://qudt.org/vocab/unit/M
type: NamedIndividual
type: Unit
symbol: m

volume flow, 0,001 l/h = 56
type: NamedIndividual
value API: volumeFlow,0,001Lh
value KNX: 56

TempRoom
type: Class
subject: 56
subject: 399.56
subject: TempRoom
interface object type annotation: 399
label: TempRoom
property identifier annotation: 56
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  has value: Value Temp
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: pv
      on property: has point function type
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 56
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type

type.dpt.field.519.500.i5.tran.AC
type: NamedIndividual
type: Datapoint Type Field
description: abnormal condition
field index: 5
field name: AC
field size: 1
field type: B
includes key value pair: type.kvpair.AbnormalCondition
includes key value pair: No abnormal condition

Position unchanged = 0
type: NamedIndividual
value API: positionUnchanged
value KNX: 0

type.dpt.field.7.1.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 16
field type: U
includes digit: type.digit.u16
unit: NUM

5 min = 16
type: NamedIndividual
value API: 5Min
value KNX: 16

Thread
type: Protocol
type: NamedIndividual

is point interface of
type: ObjectProperty
domain: PointInterface
range: Datapoint
sub property of: isTagOf

type.dpt.field.200.101.i1.BinaryValue
type: NamedIndividual
type: Datapoint Type Field
field index: 1
field name: BinaryValue
field size: 8
includes DPT: Binary Value

TempRoomSetpAct
type: Class
subject: 399.101
subject: TempRoomSetpAct
subject: 101
interface object type annotation: 399
label: TempRoomSetpAct
property identifier annotation: 101
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 101
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: automatic
      on property: hasOrigin
    intersection of: Restriction
      has value: absoluteValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
subclass of: Restriction
  has value: Value Temp
  on property: datapointType

Frequency
type: Quantity Kind
type: NamedIndividual
description: "Frequency" is the number of occurrences of a repeating event per unit time. The repetition of the events may be periodic (that is. the length of time between event repetitions is fixed) or aperiodic (i.e. the length of time between event repetitions varies). Therefore, we distinguish between periodic and aperiodic frequencies. In the SI system, periodic frequency is measured in hertz (Hz) or multiples of hertz, while aperiodic frequency is measured in becquerel (Bq). In spectroscopy, v is mostly used. Light passing through different media keeps its frequency, but not its wavelength or wavenumber.

Scaling Step Time
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 225.002: Scaling Step Time
subject: 225.002
subject: 225.2
subject: Scaling Step Time
dpt bit size max: 24
dpt major number: 225
datapoint type minor number: 2
is assembled with: type.dpt.field.225.2.i0.Percent
is assembled with: type.dpt.field.225.2.i1.TimePeriod
label: Scaling Step Time
has communication mode: S

HVACMode
type: Class
subject: 51
subject: 398.51
subject: HVACMode
interface object type annotation: 398
label: HVACMode
property identifier annotation: 51
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: HVACMode
  on property: datapointType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 398
    on property: interface object type

Outside
type: Class
disjoint with: Room
disjoint with: RoomSegment
comment: Expresses if an location is outside in perspective of a Building. A Space, Site or SiteSegment can be outside of a Building.
label: Außenbereich @de
subclass of: Location

On = 1
type: NamedIndividual
is applicable datapoint enum of: On State
value API: on
value KNX: 1

Switch OnOff
type: Class
subject: Switch OnOff
subject: SOO
subject: 414.51
subject: 51
interface object type annotation: 414
label: Switch OnOff
property identifier annotation: 51
subclass of: Restriction
  has value: qk eq luminaire dimmlevel
  on property: hasQualityKind
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 414
    on property: interface object type
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: Switch
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: On State
      on property: hasStateType
    intersection of: Restriction
      has value: Off State
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk eq luminaire dimmlevel
      on property: refersTo

203.x
type: NamedIndividual
type: Datapoint Type
subject: 203.major
subject: 203.x
dpt bit size max: 24
dpt major number: 203
is assembled with: type.dpt.field.203.x.i0
label: 203.x
has communication mode: LTE

type.dpt.field.21.102.i5.StatusStartOptim
type: NamedIndividual
type: Datapoint Type Field
description: StatusStartOptim
field index: 5
field name: StatusStartOptim
field size: 1
field type: B
includes key value pair: type.kvpair.true
includes key value pair: type.kvpair.false

On State
type: NamedIndividual
type: StateType
description: This state type expresses that an equipment, such as a luminaire, is switched on. This state type is the inverse of the 'Off State' state type.

Aspect
type: Class
comment: A generic referencing mechanism between one or more points that reflects a specific view of the installation.
subclass of: Restriction
  all values from: Point
  on property: groups
subclass of: Core Thing

Reset
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 1.015: Reset
subject: 1.15
subject: 1.015
subject: Reset
dpt bit size max: 1
dpt major number: 1
datapoint type minor number: 15
is assembled with: Reset
label: Reset
has communication mode: S

Heat Stage A Actuator Calibration Mode
type: Class
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Function Point
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Primary
      on property: relatesToStateType
    intersection of: Restriction
      has value: operationalStateCalibration
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1

type.dpt.field.3.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 3-bit controlled
field index: 0
field size: 4
field string schema: raw
field type: A[n]

type.dpt.field.249.600.i1.validityOfAbsoluteColourTemperature
type: NamedIndividual
type: Datapoint Type Field
description: validity of the Absolute Colour Temperature
field index: 1
field name: validityOfAbsoluteColourTemperature
field size: 1
field type: B
includes key value pair: type.kvpair.invalid
includes key value pair: type.kvpair.valid

type.dpt.field.209.101.i4.Reserved
type: Datapoint Type Field
type: NamedIndividual
field index: 4
field name: Reserved
field size: 4
includes reserved bit(s): type.bit.reserved

type.dpt.field.22.101.i12.DewPointStatus
type: NamedIndividual
type: Datapoint Type Field
description: DewPointStatus
field index: 12
field name: DewPointStatus
field size: 1
field type: B
includes key value pair: alarm = 1
includes key value pair: No alarm = 0

mass, 10 kg = 28
type: NamedIndividual
value API: mass,10Kg
value KNX: 28

is assembled with
type: IrreflexiveProperty
type: ObjectProperty
comment: At least one DPT field must be present for a datapoint type (DPT).
domain: Datapoint Type
range: Datapoint Type Field

ZWave
type: NamedIndividual
type: Protocol

Value Luminance
type: Datapoint Type
type: NamedIndividual
description: DPT 14.041: Value of luminance
subject: Value Luminance
subject: 14.041
subject: 14.41
dpt bit size max: 32
dpt major number: 14
datapoint type minor number: 41
is assembled with: type.dpt.field.14.41.i0
label: Value Luminance
has communication mode: S

Plant Management Control
type: Class
comment: A specific Application Function category for overall management functions of a plant or a part of a plant. For example, a Scheduler automatically schedules the systems, such as heating, ventilation, and lighting, to coordinate with facility usage. The category is derived from parent concepts that are specified as part of the EN 50090-6-2.
subclass of: ApplicationFunction

type.dpt.field.14.69.i0
type: NamedIndividual
type: Datapoint Type Field
description: temperature (absolute)
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: http://qudt.org/vocab/unit/K

Air Handling Unit
type: NamedIndividual
type: EquipmentType
description: An Air Handling Unit (AHU) is an equipment to regulate and circulate air as part of a heating, ventilating, and air-conditioning (HVAC) system.

emSupportedControlTypes
type: NamedIndividual
type: Datapoint Type
dpt bit size max: 8
dpt major number: 21
datapoint type minor number: 500
is assembled with: type.dpt.field.21.500.i0.sct.CT

Breaker/Valve is released = 2
type: NamedIndividual
value API: breakerValveIsReleased
value KNX: 2

no comfort push button is pressed = 0
type: NamedIndividual
value API: noComfortPushButtonIsPressed
value KNX: 0

no failure = 0
type: NamedIndividual
value API: noFailure
value KNX: 0

7.x
type: Datapoint Type
type: NamedIndividual
subject: 7.major
subject: 7.x
dpt bit size max: 16
dpt major number: 7
is assembled with: type.dpt.field.7.x.i0
label: 7.x
has communication mode: S

CombinedStatus_FA
type: Class
subject: 399.78
subject: CombinedStatus_FA
subject: 78
interface object type annotation: 399
label: CombinedStatus_FA
property identifier annotation: 78
subclass of: Restriction
  has value: StatusGen
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateOutOfService
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateFaulty
      on property: relatesToStateType
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 78
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 399
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateAlarmPending
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State In Alarm
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType

type.dpt.field.30.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 24 times channel activation
field index: 0
field size: 24
field string schema: raw
field type: A[n]

TempRoomSetpSetHeatShift
type: Class
subject: 62
subject: 115.62
subject: TempRoomSetpSetHeatShift
interface object type annotation: 115
label: TempRoomSetpSetHeatShift
property identifier annotation: 62
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 62
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 115
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  has value: qk ph air temperature room
  on property: hasQualityKind
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: sp
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: relativeValue
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph air temperature room
      on property: refersTo
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: relatesToStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
subclass of: Restriction
  has value: TempRoomSetpSetShift[3]
  on property: datapointType

LongDeltaTimeSec
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 13.100: LongDeltaTimeSec
subject: 13.100
subject: LongDeltaTimeSec
dpt bit size max: 32
dpt major number: 13
datapoint type minor number: 100
is assembled with: type.dpt.field.13.100.i0
label: LongDeltaTimeSec
has communication mode: S

2 min = 13
type: NamedIndividual
value API: 2Min
value KNX: 13

hosts
type: ObjectProperty
type: InverseFunctionalProperty
inverse of: is application program of
comment: To define the existence of an application program as part of a device, except it is a pure HW, such as a power supply or similar. Devices may support more than one application program, at runtime in an installation usually one.
domain: Device
range: ApplicationProgram

power, 0,1 MW = 168
type: NamedIndividual
value API: power,0,1MW
value KNX: 168

Heat Stage B Actuator Fault
type: Class
subclass of: Restriction
  on class: Class
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: relatesToStateType
    intersection of: Restriction
      has value: Heating-Cooling Stages Secondary
      on property: relatesToStateType
    intersection of: Restriction
      has value: operationalStateFaulty
      on property: relatesToStateType
  on property: hasOperationKind
  qualified cardinality: 1
subclass of: Restriction
  has value: Bool
  on property: datapointType
subclass of: Function Point

HVACModeEff
type: Class
subject: HVACModeEff
subject: 51
subject: 100.51
interface object type annotation: 100
label: HVACModeEff
property identifier annotation: 51
subclass of: Restriction
  has value: HVAC Mode Z
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: HVAC Mode Comfort
      on property: hasStateType
    intersection of: Restriction
      has value: HVAC Mode Standby
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeEconomy
      on property: hasStateType
    intersection of: Restriction
      has value: hvacModeProtection
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 100
    on property: interface object type

4,0 s = 6
type: NamedIndividual
value API: 4,0S
value KNX: 6

is building of
type: ObjectProperty
domain: Building
range: Class
  union of: Site
  union of: SiteSegment
sub property of: is location of

PSUMode
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.008: PSUMode
subject: PSUMode
subject: 20.008
subject: 20.8
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 8
is assembled with: type.dpt.field.20.8.i0
label: PSUMode
has communication mode: S

Binary Value
type: Datapoint Type Field
type: NamedIndividual
field index: 0
field name: binaryValue
field size: 1
includes DPT: Binary Value
label: Binary Value

Level 0 = 0
type: NamedIndividual
value API: level0
value KNX: 0

type.dpt.field.30.1010.i16.ActivationStateOfChannel17
type: NamedIndividual
type: Datapoint Type Field
description: Activation state of channel 17
field index: 16
field name: ActivationStateOfChannel17
field size: 1
field type: B
includes key value pair: type.kvpair.30.1010.i16.1
includes key value pair: The visual effect of channel 17 is inactive = 0

is location usage of
type: ObjectProperty
domain: Location Usages
range: Location
sub property of: isTagOf

Sunshiny = 2
type: NamedIndividual
value API: sunshiny
value KNX: 2

type.dpt.field.19.1.i5.NDOW
type: NamedIndividual
type: Datapoint Type Field
description: No Day of Week
field default: 1
field index: 5
field name: NDOW
field size: 1
field type: B
includes key value pair: type.kvpair.19.1.i5.1
includes key value pair: Day of week field valid = 0

type.dpt.field.27.1.i20.MaskBitIOO5
type: NamedIndividual
type: Datapoint Type Field
description: Mask Bit Info On Off Output 5
field index: 20
field name: MaskBitIOO5
field size: 1
field type: B
includes key value pair: output state is valid = 1
includes key value pair: output state is not valid = 0

type.dpt.field.512.505.i7.ps.SLT
type: NamedIndividual
type: Datapoint Type Field
description: List of power sequence slots
field index: 7
field name: SLT
field type: D<n>
includes counter: type.dpt.field.512.505.i1.ps.SLT CNT
includes DPT: emPowerSequenceSlot

TempRoomSetpSetShift[4]
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 213.102: TempRoomSetpSetShift[4]
subject: 213.102
subject: TempRoomSetpSetShift[4]
dpt bit size max: 64
dpt major number: 213
datapoint type minor number: 102
is assembled with: type.dpt.field.213.102.i0.TempSetpShiftBProt
is assembled with: type.dpt.field.213.102.i2.TempSetpShiftStdby
is assembled with: type.dpt.field.213.102.i1.TempSetpShiftEco
is assembled with: type.dpt.field.213.102.i3.TempSetpShiftComf
label: TempRoomSetpSetShift[4]
has communication mode: LTE

BlinkingMode
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 20.603: BlinkingMode
subject: BlinkingMode
subject: 20.603
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 603
is assembled with: type.dpt.field.20.603.i0
label: BlinkingMode
has communication mode: S

SR
type: NamedIndividual
type: Unit
symbol: sr

MicroGM-PER-M3
type: Unit
type: NamedIndividual
symbol: μg/m³

Illuminance
type: NamedIndividual
type: Quantity Kind
description: Illuminance is the total luminous flux incident on a surface, per unit area. It is a measure of the intensity of the incident light. As a note, focus is the light source, which is mostly the interest in the building control domain.

Failure detected = 2
type: NamedIndividual
value API: failureDetected
value KNX: 2

type.dpt.field.209.103.i0.TempWaterValid
type: NamedIndividual
type: Datapoint Type Field
description: validity of TempWater field
field index: 0
field name: TempWaterValid
field size: 1
includes DPT: Bool

The visual effect of channel 10 is active = 1
type: NamedIndividual
value API: theVisualEffectOfChannel10IsActive
value KNX: 1

type.dpt.field.21.106.i2.Heat
type: NamedIndividual
type: Datapoint Type Field
description: Heat
field index: 2
field name: Heat
field size: 1
field type: B
includes key value pair: type.kvpair.false
includes key value pair: type.kvpair.true

type.dpt.field.29.11.i0
type: NamedIndividual
type: Datapoint Type Field
field index: 0
field resolution: 1.0
field size: 64
field type: V
includes digit: type.digit.s64
unit: V-A-HR

type.dpt.field.254.600.i4.cG
type: NamedIndividual
type: Datapoint Type Field
description: Shall specify whether the colour component green shall be increased or decreased.
field index: 4
field name: cG
field size: 1
field type: B
includes key value pair: type.kvpair.decrease
includes key value pair: type.kvpair.increase

Channel Activation 16
type: Datapoint Type
type: NamedIndividual
description: a point representing DPT 22.1010: Channel Activation 16
subject: Channel Activation 16
subject: 22.1010
dpt bit size max: 16
dpt major number: 22
datapoint type minor number: 1010
is assembled with: type.dpt.field.22.1010.i2.ActivationStateOfChannel3
is assembled with: type.dpt.field.22.1010.i4.ActivationStateOfChannel5
is assembled with: type.dpt.field.22.1010.i7.ActivationStateOfChannel8
is assembled with: type.dpt.field.22.1010.i14.ActivationStateOfChannel15
is assembled with: type.dpt.field.22.1010.i0.ActivationStateOfChannel1
is assembled with: type.dpt.field.22.1010.i15.ActivationStateOfChannel16
is assembled with: type.dpt.field.22.1010.i13.ActivationStateOfChannel14
is assembled with: type.dpt.field.22.1010.i11.ActivationStateOfChannel12
is assembled with: type.dpt.field.22.1010.i10.ActivationStateOfChannel11
is assembled with: type.dpt.field.22.1010.i3.ActivationStateOfChannel4
is assembled with: type.dpt.field.22.1010.i6.ActivationStateOfChannel7
is assembled with: type.dpt.field.22.1010.i9.ActivationStateOfChannel10
is assembled with: type.dpt.field.22.1010.i1.ActivationStateOfChannel2
is assembled with: type.dpt.field.22.1010.i8.ActivationStateOfChannel9
is assembled with: type.dpt.field.22.1010.i5.ActivationStateOfChannel6
is assembled with: type.dpt.field.22.1010.i12.ActivationStateOfChannel13
label: Channel Activation 16
has communication mode: S

type.dpt.field.14.74.i0
type: NamedIndividual
type: Datapoint Type Field
description: time
field index: 0
field resolution: 1.0
field size: 32
field type: F
includes digit: type.digit.f32
unit: SEC

Level 2 = 2
type: NamedIndividual
value API: level2
value KNX: 2

type.dpt.field.523.500.i0.sms.STAT TMR
type: NamedIndividual
type: Datapoint Type Field
description: status of all timers wether they are running or not. each bit declares the status of the timer with the id of the bit position. bn = 0 means timer n is not running, bn = 1 means timer n is running
field index: 0
field name: STAT_TMR
field size: 16
includes DPT: emTimerStatus

StatusGO
type: Class
subject: 321.52
subject: 52
subject: StatusGO
interface object type annotation: 321
label: StatusGO
property identifier annotation: 52
comment: This DPA represents a generic Status (Z8), as described in KNX Vol 3/7/2, section 4.1.2. This includes bits (used as flags with the state types tag:active and tag:inactive) for the following information referring to the device: Bit 0) OutOfService (modeled by the state type tag:operationalStateOutOfService); Bit 1) Fault (modeled by the state type tag:operationalStateFaulty); Bit 2) Overridden (device being in maintenance mode, modeled by the state type tag:operationalStateMaintenance); Bit 3) InAlarm (modeled by the state type tag:operationalStateInAlarm); Bit 4) AlarmUnAck (modeled by the state type tag:operationalStateAlarmPending)
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 52
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 321
    on property: interface object type
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State Maintenance
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: alarm
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: Operational State In Alarm
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateOutOfService
      on property: relatesToStateType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateAlarmPending
      on property: relatesToStateType
subclass of: Restriction
  has value: StatusGen
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: Active State
      on property: hasStateType
    intersection of: Restriction
      has value: inactive
      on property: hasStateType
    intersection of: Restriction
      has value: situation
      on property: has point function type
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: operationalStateFaulty
      on property: relatesToStateType
subclass of: Restriction
  has value: KNX
  on property: operates on protocol

Time = UT+X = 0
type: NamedIndividual
value API: time=UT+X
value KNX: 0

Phase L1
type: Locality
type: NamedIndividual
description: Refers to the first phase of a three-phase electric power system, which is the most common method used by electrical grids to transfer power.

UserChangeOverMode
type: Class
subject: UserChangeOverMode
subject: 392.51
subject: 51
interface object type annotation: 392
label: UserChangeOverMode
property identifier annotation: 51
subclass of: Restriction
  has value: KNX
  on property: operates on protocol
subclass of: Restriction
  has value: qk ph water temperature pipesection supplysection
  on property: hasQualityKind
subclass of: Restriction
  has value: changeoverMode
  on property: datapointType
subclass of: Restriction
  on property: hasOperationKind
  some values from: Class
    intersection of: OperationKind
    intersection of: Restriction
      has value: controlModeAuto
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeHeating
      on property: hasStateType
    intersection of: Restriction
      has value: controlModeCooling
      on property: hasStateType
    intersection of: Restriction
      has value: activation
      on property: has point function type
    intersection of: Restriction
      has value: management
      on property: hasOrigin
    intersection of: Restriction
      has value: enumeration
      on property: hasPointOperation
    intersection of: Restriction
      has value: qk ph water temperature pipesection supplysection
      on property: refersTo
subclass of: Class
  intersection of: Datapoint
  intersection of: Restriction
    has value: 51
    on property: propertyIdentifier
  intersection of: Restriction
    has value: 392
    on property: interface object type

other fault = 4
type: NamedIndividual
value API: otherFault
value KNX: 4

type.dpt.field.6.x.i0
type: NamedIndividual
type: Datapoint Type Field
description: 8-bit signed value
field index: 0
field size: 8
field type: V
includes digit: type.digit.s8

has floor
type: ObjectProperty
inverse of: is floor of
comment: A strong OP relationship to express a relation to a floor contained in a location.
domain: Class
  union of: Building
  union of: Space
range: Floor
sub property of: has location

LoadPriority
type: NamedIndividual
type: Datapoint Type
description: a point representing DPT 20.104: LoadPriority
subject: 20.104
subject: LoadPriority
dpt bit size max: 8
dpt major number: 20
datapoint type minor number: 104
is assembled with: type.dpt.field.20.104.i0
label: LoadPriority
has communication mode: S

Access Control
type: NamedIndividual
type: Trade
description: The access trade is the selective access and control to resources (e.g. a place, information, etc.).

Cabinet
type: Class
disjoint with: Device
comment: A Cabinet is a physical enclosure for electrical or electronic equipment such as automatic switches, fuses, circuit breakers, control devices, timers and similar.
subclass of: Equipment
subclass of: Restriction
  all values from: string
  on property: comment

Restriction
has value: ComfortProlongUser
on property: point name

Restriction
max qualified cardinality: 1
on class: TempRoomSetpSetHeatEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: TempRoomSetpUserAbsEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: TempRoomSetpUserOffset
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.384.51
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.121.51
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: ComfortProlongEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: TempRoomSetpHeatEff
on property: isComposedByOutput

Class
intersection of: Functional Block
intersection of: Restriction
  has value: 100
  on property: interface object type

Restriction
max qualified cardinality: 1
on class: Class
  union of: HVACMode
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.121.52
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: TempRoomSetpSetHeatShift
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Class
  union of: PresenceStatus
  union of: dpa.391.51
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: TempRoomSetpCoolEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.100.52
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.100.54
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.343.51
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Class
  union of: HVACModeNext
  union of: dpa.110.52
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: TempRoomSetpUserOffsetEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.384.53
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Class
  union of: EnableComfort
  union of: dpa.110.53
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: HVACModeUserEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.115.63
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: HVACModeEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.384.54
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: HVACModeUser
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: TempOutside
  intersection of: Restriction
    has value: TempOutside
    on property: point name
  intersection of: Restriction
    has value: one
    on property: hasCardinality
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: dpa.398.89
  intersection of: Restriction
    has value: TempRoomSetpSetHeatEff
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: TempRoomSetpUserAbsEff
  intersection of: Restriction
    has value: TempRoomSetpUserAbsEff
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: isComposedByOutput

Restriction
on class: Class
  intersection of: dpa.398.80
  intersection of: Restriction
    has value: HVACModeEff
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: isComposedByOutput
qualified cardinality: 1

Restriction
on class: Class
  intersection of: HVACMode
  intersection of: Restriction
    has value: HVACMode
    on property: point name
  intersection of: Restriction
    has value: one
    on property: hasCardinality
on property: is composed by input
qualified cardinality: 1

Restriction
on class: Class
  intersection of: TempRoomSetpUserAbs
  intersection of: Restriction
    has value: TempRoomSetpUserAbs
    on property: point name
  intersection of: Restriction
    has value: one
    on property: hasCardinality
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: dpa.398.52
  intersection of: Restriction
    has value: HVACModeNext
    on property: point name
  intersection of: Restriction
    has value: one
    on property: hasCardinality
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: dpa.398.90
  intersection of: Restriction
    has value: TempRoomSetpSetCoolEff
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: dpa.398.55
  intersection of: Restriction
    has value: ComfortPushbutton
    on property: point name
  intersection of: Restriction
    has value: one
    on property: hasCardinality
on property: is composed by input

Restriction
on class: TempRoomSetpUserAbs
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: HVACModeUserEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: ComfortProlongEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.398.89
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.398.63
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.398.65
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.398.54
on property: is composed by input

Restriction
on class: dpa.398.80
on property: isComposedByOutput
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: TempRoomSetpSetCoolShift
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: HVACModeEffNext
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.398.90
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.398.58
on property: is composed by input

Restriction
on class: dpa.398.57
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: TempRoomSetpUserAbsEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.398.92
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: WindowStatusEff
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.398.87
on property: isComposedByOutput

Class
intersection of: Functional Block
intersection of: Restriction
  has value: 398
  on property: interface object type

Restriction
on class: HVACMode
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: dpa.398.55
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.398.85
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: TempOutside
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.398.86
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.398.60
on property: is composed by input

Restriction
on class: HVACModeUser
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: WindowStatus
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.398.52
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: dpa.398.59
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: Colour Set RGBW
  intersection of: Restriction
    has value: Colour Set RGBW
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: is composed by input

Restriction
on class: Class
  intersection of: dpa.423.59
  intersection of: Restriction
    has value: Switch On Off Green
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: is composed by input
qualified cardinality: 1

Restriction
on class: Class
  intersection of: Absolute Set Value Control Green
  intersection of: Restriction
    has value: Absolute Set Value Control Green
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: dpa.423.85
  intersection of: Restriction
    has value: Actual Dimming Value Blue
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: Class
  intersection of: Relative Set Value Control White
  intersection of: Restriction
    has value: Relative Set Value Control White
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: is composed by input

Restriction
on class: Class
  intersection of: dpa.423.51
  intersection of: Restriction
    has value: Combined Switch On Off
    on property: point name
  intersection of: Restriction
    has value: many
    on property: hasCardinality
on property: is composed by input
qualified cardinality: 1

Restriction
on class: Relative Set Value Control Blue
on property: is composed by input
qualified cardinality: 1

Restriction
on class: Absolute Set Value Control Red
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: dpa.423.85
on property: isComposedByOutput

Class
intersection of: Functional Block
intersection of: Restriction
  has value: 423
  on property: interface object type

Restriction
max qualified cardinality: 1
on class: dpa.423.82
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: Current Colour RGB
on property: isComposedByOutput

Restriction
on class: dpa.423.52
on property: is composed by input
qualified cardinality: 1

Restriction
on class: dpa.423.64
on property: is composed by input
qualified cardinality: 1

Restriction
on class: dpa.423.51
on property: is composed by input
qualified cardinality: 1

Restriction
on class: dpa.423.57
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: dpa.423.84
on property: isComposedByOutput

Restriction
on class: Switch On Off Red
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: Switch On Off White
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Colour_Relative Control_RGB
on property: is composed by input

Restriction
on class: dpa.423.60
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: Absolute Set Value Control White
on property: is composed by input

Restriction
on class: dpa.423.59
on property: is composed by input
qualified cardinality: 1

Restriction
on class: dpa.423.80
on property: isComposedByOutput
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: Colour Set RGBW
on property: is composed by input

Restriction
on class: Absolute Set Value Control Green
on property: is composed by input
qualified cardinality: 1

Restriction
max qualified cardinality: 1
on class: Relative Set Value Control White
on property: is composed by input

Restriction
max qualified cardinality: 1
on class: Actual Dimming Value Red
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.423.86
on property: isComposedByOutput

Restriction
max qualified cardinality: 1
on class: dpa.423.55
on property: is composed by input

Restriction
on class: Switch On Off Blue
on property: is composed by input
qualified cardinality: 1